Federal Pacific Electric Panel Tests Indicate Failures
FPE Stab-Lok® PANEL TEST EXAMPLE - CONTENTS: Results of independent testing on an individual FPE Stab-Lok® panel obtained from a homeowner. Subset of the entire UL 489 Standard, is intended to determine
proper electrical circuit breaker function in response to overcurrent. In the electrical industry, the failure rate for non-trip breakers is virtually zero.
InspectAPedia tolerates no conflicts of interest. We have no relationship with advertisers, products, or services discussed at this website.
Independent tests of FPE Equipment: October 15, 2000, Poughkeepsie, NY. Tests by an independent forensic engineer
confirmed failures of circuit breakers in a Federal Pacific Stab-Lok® residential
electric panel that was contributed by a homeowner.
Replacement FPE Stab-Lok® circuit breakers are unlikely to reduce the failure risk of this equipment. We recommend that residential FPE Stab-Lok® electrical panels be replaced entirely or the entire panel bus assembly be replaced, regardless of FPE model number or FPE year of manufacture. We do not sell circuit breakers nor any other products.
Federal Pacific Electric Test Performed on Homeowner's FPE Breaker Panel
The breakers in this Federal Pacific Stab-Lok® panel were tested according to the
Underwriters Laboratories UL Standard UL 489 calibration test.
This test, a
subset of the entire UL 489 Standard, is intended to determine
proper electrical circuit breaker function in response to overcurrent.
40-Amp breakers were tested at 135% of rated load and should
trip within an hour. 20-Amp and 15-Amp breakers were tested at 200% of
rated load and should trip within 2 minutes.
Federal Pacific Electric (FPE Panel) Test Results
The FPE panel tested contained 19 circuit breakers.
4 breakers (green tabs in various photos) performed properly: the breaker opened the circuit within the prescribed time and the toggle switch moved to the "tripped" position.
13 breakers (yellow tabs in various photos) did not work properly, demonstrating mechanical irregularities within the product: while all "opened" the circuit, some moved to the full-off position and others stayed in the full-on position.
2 breakers (red tabs in various photos), nominally "tripped" in that there was partial or full toggle movement. However, they failed to open the circuit on at least one pole.
10% (2 out of 19) of the Federal Pacific Electric Stab-Lok® breakers in the panel tested
failed to perform properly. In the electrical industry, the failure rate for non-trip breakers is virtually zero.
Photographs of Federal Pacific Electric Panel Tested
FPE PANEL after testing - oblique view - note variations in toggles after every breaker was subjected to overcurrent
Or see CIRCUIT BREAKER RELIABILITY TESTS gives test results and no-trip failures for both older and newer FEP, FPE & UBI-FPE Circuit Breakers showing high failure rates also for some Murray and Crouse Hinds circuit breakers.
Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Ask a Question or Search InspectApedia
Questions & answers or comments about tests on FPE Panels and Breakers.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Carson, Dunlop & Associates Ltd., 120 Carlton Street Suite 407, Toronto ON M5A 4K2. Tel: (416) 964-9415 1-800-268-7070 Email: firstname.lastname@example.org. The firm provides professional home inspection services & home inspection education & publications. Alan Carson is a past president of ASHI, the American Society of Home Inspectors. Thanks to Alan Carson and Bob Dunlop, for permission for InspectAPedia to use text excerpts from The Home Reference Book & illustrations from The Illustrated Home. Carson Dunlop Associates' provides extensive home inspection education and report writing material.
The Illustrated Home illustrates construction details and building components, a reference for owners & inspectors. Special Offer: For a 5% discount on any number of copies of the Illustrated Home purchased as a single order Enter INSPECTAILL in the order payment page "Promo/Redemption" space.
TECHNICAL REFERENCE GUIDE to manufacturer's model and serial number information for heating and cooling equipment, useful for determining the age of heating boilers, furnaces, water heaters is provided by Carson Dunlop, Associates, Toronto - Carson Dunlop Weldon & Associates Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on any number of copies of the Technical Reference Guide purchased as a single order. Just enter INSPECTATRG in the order payment page "Promo/Redemption" space.
The Home Reference Book - the Encyclopedia of Homes, Carson Dunlop & Associates, Toronto, Ontario, 25th Ed., 2012, is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. Field inspection worksheets are included at the back of the volume.
Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on these courses: Enter INSPECTAHITP in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Horizon Software System manages business operations,scheduling, & inspection report writing using Carson Dunlop's knowledge base & color images. The Horizon system runs on always-available cloud-based software for office computers, laptops, tablets, iPad, Android, & other smartphones