Find & Fix Air Conditioning or Heating Supply Air Duct Leaks or Obstructions
SUPPLY DUCT AIR LEAKS - CONTENTS: Checklist for Finding HVAC Supply Air Leaks & Obstructions. Heating & Cooling Ducts - Supply Registers & Zones. Air Conditioning (or Heating) Duct Defects. The D'Arcy-Weisbach equation for pressure and head loss applied to HVAC ducts.
InspectAPedia tolerates no conflicts of interest. We have no relationship with advertisers, products, or services discussed at this website.
Guide to heating & cooling duct work supply air flow adequacy, flow rate, temperature, and related problems.
This chapter of "How to Inspect the Central Air Conditioning or Cooling System" describes the
inspection of heating and air conditioning (HVAC) duct registers & zones for defects such as missing air conditioning cool air supply
or return air registers, undersized air conditioning duct openings, improper cooling duct routing, cooling (or heating) air duct corrosion, leaky air duct connections,
defective heating or cooling ductwork materials such as Goodman gray flex-duct, some Owens Corning Flex-duct, and asbestos-containing air conditioning or heating duct work.
The photograph above shows a 1930's heating and cooling air supply register still in active use, but with leakage around the register which transmitted odors and mold from the building basement.
HVAC Supply Air Duct Leaks & Obstructions - Theory & Practice
Blockages or crimps in HVAC ducts (photo at left) restrict air flow and in severe cases can cut it off entirely.
Leaks in HVAC cooling or heating air supply ducts mean that cooling or heating costs are increased, since the HVAC system needs to run longer to reach the desired indoor temperature and humidity.
[Click to enlarge any image]
Where more severe supply air duct leaks are occurring, some areas of the building or even the entire building may receive no heated or cooled air at all, even though the equipment is running.
List of Articles giving Procedures for Diagnosing HVAC System Air Leaks & Air Flow Problems
Below we list a catalog of common explanations for inadequate air flow from an HVAC duct system.
Watch out: But keep in mind that even this apparently accurate calculation of the effect of piping on air pressure and airflow loss will not include the effects of leaks or obstructions in the building return air or supply air duct system such as the following:
Air filter or other item that has been sucked into the duct system will block air flow and can risk a fire if drawn into the blower assembly fan, DIRTY AIR FILTER PROBLEMS are perhaps the most common cause of unsatisfactory airflow in an HVAC system.
Blower Fan: dirty blades on a squirrel cage blower assembly fan significantly reduce the blower fan's ability to move air into the HVAC system from the return-air side as well as reducing its ability to push conditioned air into the occupied space.
DIRTY A/C BLOWERS
Fire damper that has become stuck in the closed or partly-closed position interferes with proper airflow through the system
See FIRE & SMOKE DAMPERS, AUTOMATIC
Flex duct defects: Collapsed sections of flex duct block or stop airflow in either supply or return air systems
DUCT ROUTING & SUPPORT (see our photo, above-left).
Leaks in the supply air duct system are a very common HVAC duct defect that results in poor heating or cooling air flow.
See LEAKY DUCT CONNECTIONS
Return air inlets: Return air inlet grilles that are obstructed with dirt, debris, or furniture or that are improperly located or are just too small mean that because the heating or cooling system is "starved for air", the supply air flow into occupied spaces will also be reduced. RETURN AIR REGISTERS & DUCTS
Zone dampers that are stuck partly closed obstruct air supply into that building area, or if stuck "open" when the zone damper should be closed, airflow to other building areas will be reduced.
ZONE DAMPER CONTROLS
Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
AC system suddenly quit delivering supply air to some rooms in the building
(June 29, 2011) pam said:
I am trying to troubleshoot an a/c system that overnight quit supplying air to the upstairs and two rooms downstairs. (coil is fine, air handler/blower operating fine, no observable fault of (exterior) duct system. the rooms without air are getting none at all.
I'd look for:
- a damper that someone closed in the ductwork
- a filter that came loose and blew into the ductwork
- a duct that came disconnected
- a flex duct that had something fall on it, squashing it shut
Question: ok to run supply air ducts inside of cold air returns?
(May 2, 2012) email@example.com said:
can supply ducts be run within cold air returns? I was inspecting a new home being built in my area and noticed several areas where there were heat ducts running within cols air returns for a substantial length. Does this comply with codes?
The only place where running coaxial heating ducts makes any sense to me is within an air to air heat exchange system.
For example, if a building is bringing in fresh outdoor air and also exhausting stale indoor air, we may run one duct inside the other in order to transfer heat in the desired direction, thus reducing building energy costs.
May 2, 2012) Supply duct inside a return return said:
I noted at least two instances in the new home where supply ducts were inside a return air joist spaces between the floor joist. wondered if this was within code. These were inside for a distance of ten or more feet. Looks like in cooling season these supplies would probable become a huge area for condensation to form and drip. This also would greatly reduce the volume of air the retun may have.
Building codes often cannot and do not try to anticipate every snafu that people can imagine, instead specifying overall performance objectives.
Running a supply air duct inside of a return air passage transfers energy between the two, as we explained above. If we are only talking about recirculating building air rather then the impact on overall heating or cooling costs may be minimal, certainly of less impact than running either supply or return ducts through unconditioned space, particularly if the ducts are not well insulated.
In my OPINION there is also a risk of un-detected cross-leakage out of supply into return ducts that might reduce the effectiveness of the system.
Question: need to replace collapsed flex-duct
(Jan 9, 2013) Larry said:
If a flexible supply duct under our double wide has a 6' collapsed section, does it need replaced?
Certainly yes, Larry. Otherwise you are restricting air supply to the living area and increasing heating & cooling costs.
Ask a Question or Search InspectApedia
Questions & answers or comments about inadequate supply air in HVAC duct systems and its effect on heating or cooling air flow adequacy.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
"Air Conditioning & Refrigeration I & II", BOCES Education, Warren Hilliard (instructor), Poughkeepsie, New York, May - July 1982, [classroom notes from air conditioning and refrigeration maintenance and repair course attended by the website author]
Fiberglass: Indoor Air Quality Investigations: Fiberglass in Indoor Air, HVAC ducts, and Building Insulation
Carson, Dunlop & Associates Ltd., 120 Carlton Street Suite 407, Toronto ON M5A 4K2. Tel: (416) 964-9415 1-800-268-7070 Email: firstname.lastname@example.org. The firm provides professional home inspection services & home inspection education & publications. Alan Carson is a past president of ASHI, the American Society of Home Inspectors. Thanks to Alan Carson and Bob Dunlop, for permission for InspectAPedia to use text excerpts from The Home Reference Book & illustrations from The Illustrated Home. Carson Dunlop Associates' provides extensive home inspection education and report writing material.
The Illustrated Home illustrates construction details and building components, a reference for owners & inspectors. Special Offer: For a 5% discount on any number of copies of the Illustrated Home purchased as a single order Enter INSPECTAILL in the order payment page "Promo/Redemption" space.
TECHNICAL REFERENCE GUIDE to manufacturer's model and serial number information for heating and cooling equipment, useful for determining the age of heating boilers, furnaces, water heaters is provided by Carson Dunlop, Associates, Toronto - Carson Dunlop Weldon & Associates Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on any number of copies of the Technical Reference Guide purchased as a single order. Just enter INSPECTATRG in the order payment page "Promo/Redemption" space.
The Home Reference Book - the Encyclopedia of Homes, Carson Dunlop & Associates, Toronto, Ontario, 25th Ed., 2012, is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. Field inspection worksheets are included at the back of the volume.
Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on these courses: Enter INSPECTAHITP in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Horizon Software System manages business operations,scheduling, & inspection report writing using Carson Dunlop's knowledge base & color images. The Horizon system runs on always-available cloud-based software for office computers, laptops, tablets, iPad, Android, & other smartphones