InspectAPedia tolerates no conflicts of interest. We have no relationship with advertisers, products, or services discussed at this website.
Air filters on HVAC systems:
This article series answers almost any question you might ask about air filters for central heating or air conditioning systems. We explain how an air conditioning service technician will diagnose certain common air conditioning system failures or defects.
In these articles we are referring to filters installed on central air conditioning or central heating systems that move air through air handlers and duct systems.
Standalone or portable "air cleaners" are generally ineffective in buildings where a problem particle reservoir is present, and they are not capable of removing an indoor air quality problem.
Green links show where you are. © Copyright 2017 InspectApedia.com, All Rights Reserved.
First locate and document the placement of the HVAC system air filters - for examination and regular changing during the cooling season.
In our photo at left you can see a blue and white electrostatic air cleaner on the air handler.
But notice at the upper left of the photo just below the brown metal of the air handler body: see that silver sheet metal handle?
Removing the two screws on either end of the pull-out will permit you to expose another air filter that is in this location - the handle is a tip-off that the air handler is meant to be opened at this location in order to remove/replace an air filter.
Are these the only two air filters on this system? Nope. Our discussion of cascaded air filters found at AIR FILTERS, OPTIMUM INDOOR includes photos of a front-end air filter found at the return air register.
If you can't find the air filter on your air conditionig or heating system see AIR FILTER LOCATION.
In sum, finding a filter on a duct system or air handler is no promise that it's the only air filter installed. Inspect the system thoroughly. If more than one air filter is provided, document the location of all of the filters installed.
Next inspect the air conditioning filter type and condition. What about filters that are missing completely or are very dirty? What problems can a dirty or blocked air conditioner filter cause for the air conditioning system and how do we fix these snafus?
That's what we'll cover in this article.
Filter accessibility: Air filters which are hard to access are rarely changed as often as necessary. We frequently see HVAC systems designed by someone who obviously has never had to service them.
Placement of filters and air handler access doors in very hard-to-access locations such as at the far end of a minuscule attic behind a forest of trusses means that the system is very unlikely to receive the periodic inspection and maintenance it needs.
We prefer to see A/C and heating filters placed at the building side of the air return register or grille, so as to protect the return duct from debris accumulation. The more common filter placement on many systems is right at or in the air handler.
After reading the text just below, if you still cannot find your heating or air conditioning system air filter read our detailed instructions on how to find air filters in our article: Air Filter Location. Just below we summarize some common locations where air filters are found.
Change your air filters every month when the air conditioning system is in operation. Make sure you find all of the filters as some systems have multiple filters and even multiple types of filters installed, such as a fiberglass or pleated paper filter, a washable filter, and an electrostatic air cleaner. These last two are cleaned, not replaced, when they're dirty.
See our detailed article about clogged air filters found
at DIRTY AIR FILTER PROBLEMS
Excerpts are below.Dirty Air Filters: are a source of increased operating costs and poor cooling system operation. Dirty air filters can:
The filters on an air conditioning or hot air heating system should be changed monthly when the system is in use. Discuss with your heating/cooling service professional the possible need to clean the blower fan and duct work.
Bending over the end of an air conditioner or heating air handler filter such as shown in the photo at left above is a bad idea. If the filter does not fit there will be bypass leakage past the filter, soiling the blower fan, slowing air flow, and leading to more costly cleaning and service later.
Watch out: Furthermore when you bend the filter as this owner did, you interrupt the structural integrity of the filter's frame, risking filter collapse.
A collapsed air filter can be drawn right into the blower fan, causing damage to the fan motor or even leading to a fire! For an example
see HEAT RECOVERY VENTILATOR FIRE.
The photo at right shows how a college HVAC maintenance crew kept the A/C system running when the school did not have the proper filter size in stock. This filter installation also will have severe bypass leakage around the filter where the pleated section contacts the edges of the filter slot.
Installing a filter that is the wrong size for the heating or air conditioning air handler defeats the purpose of air filters because of leakage and it may be unsafe. Install a properly-sized filter in locations like this as soon as possible and watch out for unsafe filter collapsing.
At DIRTY COOLING COIL / EVAPORATOR COIL we give another example of what can happen if an air filter or air handler insulation fall against the cooling coil in an air conditioner or heat pump system.
. I have purchased the correct sizes. Although marked by "air flow" arrows, I'm still confused as to which way they should be installed - does the "webbed grill" side face in or out?
I know this may be a "no brainer" but it is a first for me and I want to make sure I place them correctly. - Beverly Upperman
[Click to enlarge any image]
Think about the problem we need to avoid: if an air filter gets sucked into a duct or worse, into a blower fan assembly, it can jam the blower fan, cause a motor overheat, and even cause a fire.
So we want the air filter to be placed so that its reinforced side will prevent it from being drawn into the duct or blower system.
Air filters have an arrow on their edges to give us a clue about how they should be placed. Insert the air filter so that the arrow is facing in the same direction as the direction of air flow through the filter.
Our photo above shows a Trian pleated air filter. On the side of the filter you will see the arrow showing that the filter should be placed so that air will move through the filter in the same direction as pointed-to by the arrow. Below is a closeup of that airflow direction arrow:
So if you are placing a filter on an HVAC system central air return grille, air is "returning" or "entering" the grille from the building, so air is flowing from the building into the duct system at that location. So the arrow would point the same way - into the duct system.
Our photo above shows the attic location of the air handler for an air conditioning system. The red arrows indicate the direction of air flow:
The blower fan itself and the supply plenum and remaining ductwork are not visible in this cramped-condition attic air handler photo.
Watch out: There is an air conditioning system maintenance lesson here: when the installer locates an air handler where it is difficult to access, requiring squirming through roof truss webs and over loose piles of insulation in an attic, for example, nobody wants to go there to service the unit. An air filter in this location is a horrible design as it's likely to go for years without change.
See AIR FILTER LOCATION for more locations where you may find the air filter on a heating or air conditioning system.
Watch out: installing an air filter facing the wrong way can cause a fire if the filter material is drawn into the blower fan assembly, or it can cause a blocked cooling coil and cooling coil icing if the filter is in the supply plenum ahead of the cooling coil.
See "Loose Supply Plenum Insulation Falls onto A-Coil" discussed at DIRTY COOLING COIL / EVAPORATOR COIL where we discuss dirty, clogged, or totally-blocked cooling coils.
The same college HVAC maintenance staff who was struggling with improperly-fit air filters we discussed earlier was also faced with the task of coming up with a much larger air filter for the air conditioner air handler over their computer center.
Watch out: beware of cutting and modifying a store-bought air filter to fit your system.
The neatly-taped "built-up" air filter shown in this photo was nicely constructed but we don't recommend this practice:
Air filter suppliers and manufacturers have no trouble providing air filters of special dimensions. Furthermore if the filter is built by a manufacturer it's more likely that they'll understand the structural and strength requirements of the filter as well as the required airflow characteristics and filtering ability. We list some suppliers of air filters at SOURCES FOR AIR FILTERS
Incidentally, except unusual cases with special requirements, wouldn't it have made sense for the HVAC or duct system designer to have specified a filter that is one of the many standard sizes?
See our detailed article at Missing or Leaky Air Filters. Excerpts are below.
Look closely at this photograph. On the right we can see a tan "Air Filter Cover" plate which marks the intended location of the HVAC air filter. But there is an open slot to the left of the air filter cover, possibly where another filter was previously being installed. When the new air filter slot was constructed and nicely covered (so as not to leak) the old slot was simply left open.
You can see my piece of adhesive tape bending into the opening, demonstrating (not too scientifically) that there was airflow into the unit from this location.
This is a great way to draw attic insulation fiberglass into the air handler and to blow it into the living area. And of course any other unwanted attic dust and debris is also being invited into the air handling system and blown into the occupied space.
Failure to properly filter dust from the return air supply will load the fan and cooling coil, dirty the duct system, and lead to the problems listed above. As the ductwork debris level increases you increase the risk of forming an allergen or mold reservoir, especially if there are water or condensate leaks into the duct system interior.
If an air filter is not present on your air conditioner or warm air heating furnace system, have one installed. Installing an air filter is normally a minor expense involving placement of a rack to hold the air filter at each return air register, and installation of the air filter itself.
The alternative to installing and maintaining good air filtration on any air conditioner or warm air heating system is dirty ductwork and a dirty air handler. Duct cleaning or duct replacement can be a significant expense. Cleaning up a moldy HVAC system, where mold may have been caused by coil icing which was caused by a dirty coil or filter is still more costly.
Continue reading at AIR FILTER CLEANER EFFECTIVENESS or select a topic from closely-related articles below, or see our complete INDEX to RELATED ARTICLES below.
Or see AIR FILTER FAQs
Or see AIR FLOW TOO WEAK.
Or use the SEARCH BOX found below to Ask a Question or Search InspectApedia
Or use the SEARCH BOX found below to Ask a Question or Search InspectApedia
Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Please see the heating & air conditioning air filter questions & answers at AIR FILTER FAQs
Questions about air filters: buying, installing, using, and problems with HVAC air filters .
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website