InspectAPedia tolerates no conflicts of interest. We have no relationship with advertisers, products, or services discussed at this website.
Water pressure loss diagnosis, first steps in troubleshooting loss of water pressure:
This article describes gently shaking the well tank to determine if it contains water as part of diagnosing lost water pressure at a building.
Gently shaking the water pressur tank may be a quick simple way to find out if there is water in the water tank. Water pressure tank test & troubleshooting: how to diagnose loss of water pressure or loss of water in a building - shaking the well tank to see if it contains water. Shaking the water tank, a simple gentle test can start the process of troubleshooting why a building has lost water pressure.
One can become easily confused by the diagnosis offered by simply "shaking" a water pressure tank. Shaking the tank can tell you that the water tank is empty but not why the water tank is empty.
There may be a trick to this but we don't see how shaking the water pressure tank diagnoses a ruptured bladder or other very specific causes of the absence of water, but as a starting point, gently shaking the well tank can, however, tell us some things about the state of the building water supply system.
How to diagnose loss of water or loss of water pressure in a building: gently shaking the water pressure tank - are we out of water?
We use this procedure often, by gently shaking or wiggling the well tank to see what's going on.
If the well tank is at its normal "full" level of water it will be heavy and chances are you won't move the water tank at all. We also know that the water pump has probably shut off at its normal "cut out" pressure recently since running water in the building will empty the well tank in just a minute or three.
If the well tank is empty or nearly so, it is quite light and can be easily moved. Recently when we were restoring water to a home that had been winterized, we tried turning on the well pump and we heard the pump motor run.
We gently wiggled the water tank and learned that it was empty, so we figured that the pump was not delivering water - in fact the pump had lost prime.
We quickly shut off the pump motor so as to avoid damaging it. Then we proceeded to PRIME the PUMP using a GARDEN HOSE. [separate article] That was all we needed to do to get the water system working again.
Be careful: do not wildly shake the well tank nor any other plumbing component since doing so can cause a pipe to break or at least leak.
What Does it Mean if Our Well Tank is Empty?
The water tank could be empty simply because you ran all of its water out into the home and the water pump never came on to replenish the water supply. Some of the possible causes of an empty water tank and no water in the home include:
We discuss in detail how to diagnose loss of water pressure or how to diagnose and fix poor water pressure
at DIAGNOSE LOSS OF WATER PRESSURE - be sure to read that article.
Some examples of what we discuss there are listed just below:
Loss of electrical power to the pump or pump control - nothing is running the water pump. Is power turned on? Is there power at the pump control and is there power to the pump?
A bad water pressure control switch on the water pump - perhaps the switch is not turning on the pump.
This can be checked by manually closing the pump relay - DON'T TRY THIS YOURSELF - SHOCK HAZARD - unless you are qualified and trained.
A well water supply pipe failure in the well or between the well and the building, so water is not being delivered to the home. (Or in cold climates, the line may have frozen).
Loss of prime in an in-building pump, or an internal pump failure such as broken vanes - the pump motor runs but no water is delivered.
(An in-building pump could also run and no water be delivered if the well has run dry.) A shallow well jet pump well line could have a bad foot valve (in the well) and so be losing prime. A leak in the well line can also lead to loss of prime.
A Failed Water Pump: A failed or failing in-well submersible water pump stops delivering water at all, or periodically overheats and temporarily stops working. Such a pump is probably at end of life, unless the problem is traced to a voltage, switch, or wiring problem.
Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Ask a Question or Search InspectApedia
Questions & answers or comments about diagnosing lost water pressure at a home or other building .
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Carson, Dunlop & Associates Ltd., 120 Carlton Street Suite 407, Toronto ON M5A 4K2. Tel: (416) 964-9415 1-800-268-7070 Email: email@example.com. The firm provides professional home inspection services & home inspection education & publications. Alan Carson is a past president of ASHI, the American Society of Home Inspectors. Thanks to Alan Carson and Bob Dunlop, for permission for InspectAPedia to use text excerpts from The Home Reference Book & illustrations from The Illustrated Home. Carson Dunlop Associates' provides extensive home inspection education and report writing material.
The Illustrated Home illustrates construction details and building components, a reference for owners & inspectors. Special Offer: For a 5% discount on any number of copies of the Illustrated Home purchased as a single order Enter INSPECTAILL in the order payment page "Promo/Redemption" space.
TECHNICAL REFERENCE GUIDE to manufacturer's model and serial number information for heating and cooling equipment, useful for determining the age of heating boilers, furnaces, water heaters is provided by Carson Dunlop, Associates, Toronto - Carson Dunlop Weldon & Associates Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on any number of copies of the Technical Reference Guide purchased as a single order. Just enter INSPECTATRG in the order payment page "Promo/Redemption" space.
The Home Reference Book - the Encyclopedia of Homes, Carson Dunlop & Associates, Toronto, Ontario, 25th Ed., 2012, is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. Field inspection worksheets are included at the back of the volume.
Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on these courses: Enter INSPECTAHITP in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Horizon Software System manages business operations,scheduling, & inspection report writing using Carson Dunlop's knowledge base & color images. The Horizon system runs on always-available cloud-based software for office computers, laptops, tablets, iPad, Android, & other smartphones