InspectAPedia tolerates no conflicts of interest. We have no relationship with advertisers, products, or services discussed at this website.
Guide to TP valves:
How to install, inspect, troubleshoot, repair pressure / temperature relief valves or straight pressure relief valves used on heating boilers, steam boilers, water heaters, and even on water pressure tanks. This article explains what TP or pressure relief safety valves are, why they are needed, how they work, and what goes wrong.
We describe how to test (or when not to test) relief valves, how to know that this important safety device is in trouble, including by simple visual inspection, and we answer just about any question about these important safety devices.
Green links show where you are. © Copyright 2017 InspectApedia.com, All Rights Reserved.
This guide to relief valve inspection, testing, installation, repair, answers most questions about the use of these safety devices on heating equipment such as central heating system boilers, water heaters, steam generators and even pressurised water tank. This information aids in troubleshooting, inspection, diagnosis, and repairs.
We include a discussion of temperature and pressure relief valves used as safety devices on heating boilers and other pressurized vessels.
We also discuss:
Leaking or Previously Leaking Pressure/Temperature Relief Valves are Dangerous. Attic boiler pressure control tanks - Old Heating Boilers (steam or hot water) may have No Relief Valve at All - Check the Attic.
List of Common Boiler Temperature/Pressure Relief Valve Defects. Temperature/Pressure Relief Valve Testing Advice. Photo examples of unsafe, dangerous pressure/temperature relief valve installations.
Troubleshooting heating system boiler controls and switches.
Lots of controls are installed on modern water heaters, hot water cylinders, hot water and steam heating boilers. Many of these devices are principally concerned with safety. The combination of these devices provide a tremendous margin of safety on home and commercial heating boilers, as evidenced by the rarity with which we read in modern times of boiler explosions.
Before these devices were in common use, and even today if the devices are improperly installed, poorly maintained, or damaged, the heating systems they are supposed to protect are in fact un-protected.
Watch out: A defective relief valve is a latent safety hazard in that the valve does not by itself cause a water heater or heating boiler to explode, but it may fail to protect against that event should other dangerous conditions causing over temperature or over pressure arise in a heating boiler or water heater.
Check the article series links given above to find details for each type & application of temperature & pressure safety valve used on plumbing & heating systems found in or around buildings. Below are a few examples to whet your interest.
Pressure and Temperature Relief Valve on heating boilers: a TP valve is installed on all modern heating boilers to release hot water and pressure should the boiler's internal pressure or temperature rise to an unsafe level.
Our photo at page top shows what the typical boiler relief valve looks like. You may find this valve connected at the top of a heating boiler, at its side, or (less desirable) very nearby on boiler hot water piping.
Our photo at left shows an older (obsolete) type of pressure relief safety device that may be mounted close to the boiler but not right on it. This type of pressure relief device may not sense boiler temperature, just boiler pressure.
You can see that this pressure relief valve (shown above) has been leaking - it may be unsafe, as we discuss further below. Both the page top relief valve and the one in this photo are missing their discharge tubes.
Watch out: shown above is a single example of an unsafe condition at an antiquated pressure safety valve. A more complete explanation and illustration of safety hazards around TPR valves are provided in detail in each of the TPR valve categories listed above in this article.
Above is another unsafe temperature/pressure relief valve installation: the test lever that would be used to manually open, test or flush the TP valve is blocked first by having been placed up against a plaster wall and second by having had foam insulation sprayed into an opening that some smarter plumber cut into the wall to permit the lever to move.
Watch out: any obstruction that prevents the test lever on a TPR valve from being lifted or opened can also prevent the valve from opening in response to excessive pressure or temperature in the heating equipment it is supposed to protect. The result risks an exploding water heater or boiler.
See BLEVE EXPLOSIONS
The data tag that should be found on a boiler relief valve (photo at left) gives key information and lets the owner or inspector know if the proper type of safety device has been installed.
The maximum pressure and/or temperature that the relief valve will allow is marked on the valve's metal tag.
Compare this data with the boiler capacity which will be given on the heating boiler or water heater's data tag. Use the Input BTUh value of the heating appliance when comparing to the venting capacity of the T&) valve.
At an inspection of Vassar Temple in Poughkeepsie, NY we observed that a pressure relief valve with capacity to handle 40,000 BTUs but the heating boiler was rated for 4,000,000 BTUh!
The heating boiler was unsafe - it would normally be a simple repair to install the proper valve. The service tech had simply installed a residential-range TPR valve on a huge commercial hydronic boiler.
We told Rabbi Steve Arnold that we were worried that if the boiler exploded it would kill all of the Reform Jewish worshippers in Poughkeepsie.
He replied, no, only during the high holy days.
See RELIEF VALVE LEAKS for details.
We don't know if the valve has stopped leaking because a problem has been fixed (such as something else causing boiler overpressure) or if the valve has stopped leaking simply because its internals have become clogged with mineral debris which has been left behind as hot water evaporated.
The pressure temperature relief valve shown at left was dripping, but visual inspection showed that it was clogged with mineral debris left behind as boiler water leaked out and evaporated.
The mineral debris can, as you see in this photo, obstruct movement of the spring and valve internal parts, preventing it from opening when it's needed.
At RELIEF VALVE DISCHARGE TUBE we include a catalog of methods to detect past or ongoing or current leakage at the TPR valve.
The relief valve should be piped to a few inches from the floor with the end of the discharge tube always in a visible location so that if it is leaking or open the building owner or manager can observe that (unsafe) condition.
A client described finding her son and his friends in the basement playing "steam boat". They had tied a string through the little hole in the relief valve discharge lever, running the string up over a boiler pipe near the ceiling.
By pulling on the string the boys created an exciting blast of hot steamy water coming out of the boiler. Luckily none of them was scalded by this game.
But when the TP relief valve discharge extension is missing from a heating device, someone can be badly scalded.
At a home inspection in New York a real estate agent burst into tears while telling us how her son had lost an eye when he and friends played with a boiler relief valve and he was shot in the face with scalding water. A proper discharge tube could have prevented this tragedy.
See RELIEF VALVE DISCHARGE TUBE for complete details about the installation specifications & inspection defects of TPR valve drain piping.
Watch out: While it is possible to "open" a boiler TP relief valve by lifting its "test" lever, unless you are a trained heating service technician or plumber, and unless you have a spare TP valve of the proper size in your hand, we advise against "testing" a TP relief valve by opening this lever during a building inspection.
And in our OPINION, even though T&P valve instructions provided by the manufacturer recommend annually testing the valve using its try-lever, that's better done by your trained heating service technician or plumber during annual service. Besides a leak problem that could require you to shut down the equipment and make you sorry you ever touched the valve, there are scalding-burn hazards.
Either ask your service technician to test the TPR valve or just confine your own TPR valve check to the following steps:
Below: a temperature and pressure relief valve that opens at 15 psig, used on a Mr. Steam MS90E series steambath generator. That installation is described at STEAM BATH / SHOWER GENERATOR INSTALLATION.
Some equipment such as some gas fired water heaters may use an automatic gas shutoff valve instead of a conventional water-dumping pressure/temperature relief valve.
An automatic gas shutoff valve will close to stop the fuel supply to a gas fired water heater if the temperature is found to be too high and thus unsafe.
WATTS Water Heater Controls - automatic gas shutoff - provides details about that automatic gas shutoff control that uses a manual reset
Details about the installation, testing, and functions of this device are at AUTOMATIC GAS WATER HEATER SHUTOFF
Continue reading at RELIEF VALVE DISCHARGE TUBE or select a topic from closely-related articles below, or see our complete INDEX to RELATED ARTICLES below.
Or see BLEVE EXPLOSIONS
Or see RELIEF VALVE LEAKS
Or use the SEARCH BOX found below to Ask a Question or Search InspectApedia
Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Thanks for the information. Is there any requirement that the fitting and pipe extension is required to be made from copper? I came across a boiler where the fitting off the T&P and the extension to the floor is made of PVC. - Kevin 7/26/2011
Kevin the relief valve would itself tap into a metal fitting on the boiler or on older installations on metal heating piping. But the discharge tube on many new installations is plastic; it's a pipe that rarely sees service and whose job is to divert hot water to the floor rather than onto a bystander. In that application most code officials accept PVC.
Water is shooting out a valve on the well head in the front yard. What might be the problem - Sue 8/21/11
Sue: regarding "Water is shooting out a valve on the well head in the front yard. What might be the problem"
Hard to guess intelligently with no information, but certainly yours is a well piping and pump question not a heating system pressure relief valve question (the article above on this page).
You may have a well piping leak - most likely, or on occasion a well casing leak combined with an artesian well. Take a look RELIEF VALVE, WATER TANK and also
at WELL PIPING LEAK DIAGNOSIS and call your plumber.
Hot water furnace. My gauge goes up to 32 pounds then trips. Shut of furnace and still happens. My hot water tank is heated by furnace. I shut off valves on lines going to my hot water tank and problem stops. Should I suspect internal leak in hot water heating core allowing internal pressure in tank to leak back to furnace causing pressure to rise. - Will 8/22/11
If your heating boiler pressure is going up to 32 psi, a pressure higher than normal boilers heated to 180 or even 200 °F, and high enough to open the pressure/temperature relief valve, then I suspect:
- a tankless coil leak that is sending house water pressure into the boiler
- a malfunctioning automatic water feeder/pressure reducer valve feeding too-high starting pressure into the boiler
You can diagnose these easily enough.
Turn off the water supply into the tankless coil or water heater.
When the boiler is COLD, and assuming you've got a typical one-family home that is one or at most two stories, drain off boiler water to drop the starting pressure - cold - at the boiler down to 12 psi.
With the hot water system still turned off and the boiler left OFF you should not see any pressure increase inside the boiler. If you do, either we've missed something, or you've got a bad water feeder valve.
Then with the boiler turned on, the boiler should heat up to a temperature at or below 200 °F and pressure in the boiler should stay below 30 psi, probably around 20 psi.
Then with the hot water system turned on and the boiler COLD AND OFF (just for simplicity of diagnosis) and a starting boiler pressure of 12 psi, if you see the boiler pressure increase, you've confirmed a hot water system leak into the boiler interior.
I have a water heating system with radiators and no tank. My pressure goes to over 40 psi and the safety valve opens. I touched the pipe going to the expansion tank and it's cold so it looks like no water goes in there when it should.
If I shut off the water supply line and drain some water the pressure reduces, however after draining it seems as the amount of water is not enough to go all the way up to the 2nd floor radiator. I checked it by opening the bleed valve and nothing comes out since there is not enough water to fill it all the way up. It heats great when the supply line is open but the pressure goes way over normal. Based on the scenario below I am suspecting a bad feeder/pressure reducer valve. Do you think this might be causing the problem. Any info would be greatly appreciated. Thank you. - May0 12/4/11
I ran a test for the feeder/pressure reducer valve and it's fine. It shuts off the water exactly at 12 psi. Once the systems turns on and starts heating the water, the pressure keeps rising way over 30 psi. I watched it and it went over 40 psi when the water temperature was 150 F. I really don't know what might be causing it. I looked at the boiler unit and I can't see any signs of leaks. Shouldn't the expansion tank take care of this? Thinking logically the water should escape there and therefore reduce the pressure in the system. I don't think any water goes in that tank.
I shut off the valve on the pipe going to the expansion tank. I drained it - there was hardly any water in there. I opened the valve and I was touching the pipe to see if it will get hot once the water goes in there. All this was done while the pressure was over 40 psi. The pipe didn't get hot making me think no water went in there. After that I opened the drain valve on the tank and the water started coming out reducing the pressure immediately. What could be causing the pressure to rise so high? Is the expansion tank's job to at least partially help regulate the pressure in the system? Thanks for your advise.
Mayo, the diagnostic procedure you need is at RELIEF VALVE LEAKS.
Also take a look at WATER PRESSURE TOO HIGH: DANGERS for some examples of causes of abnormal water pressure.
I have a 20 year old SlantFin cast iron oil boiler. I have had 3 different technicians clean and set it up and I still have the same problem.
The pressure valve leaks pressure/water when the boiler runs for a long time. When just using hot water or if only one zone calls for heat, it is fine. However, if multiple zones call for heat such as first thing in the morning when the programmable thermostats turn up, the pressure rises to about 30 PSI after about 10-15 minutes which is enough to make the valve open and trickle water. The colder it is in the house the bigger the puddle. Any help or suggestions would be appreciated. - Tom Dionne 3/28/12
Dionne, check the temperature on your boiler when the TP valve is leaking - if it is too high that could be the problem - fixed by adjusting or repairing the aquastat control. The diagnostic procedure you need is
at RELIEF VALVE LEAKS.
Also see WATER PRESSURE TOO HIGH: DANGERS for other causes and effects of of abnormal water pressure.
After showers we hear a loud "ccssshhh" noise which sounds like it may be from the hot water tank. What could this be. It happens a couple of times after shower - Julia 8/21/12
Julia, have someone standing at the water heater and other water handling equipment in the building so that first we know where the noise is coming from. That's the first step in diagnosing this problem. Otherwise an answer here would be just too-wild speculation.
I regularly have to have my pressure relief valve changed after a year or so because it starts to leak. My oil company says that happens with anti-freeze. Is there a special one to use with anti-freeze? FYI: I am on city water but do not have a pressure relief valve. - Mike 10/22/12
Balderdash. Either you're getting a series of defective TP valves installed (unlikely) or there is a cause of abnormal temperature or pressure at your heating boiler that needs to be properly diagnosed and fixed. The diagnostic procedure you need is at RELIEF VALVE LEAKS.
My boiler is set at 190 degrees, but always shuts off at 170. Any ideas? - Mark 10/26/12
Mark, your aquastat may be improperly installed (lacks temperature sensing grease or has bad contact between the aquastat temperature sensor and the sensor well sides in the boiler) or the device may be defective, or your temperature gauge may be off. See AQUASTAT CONTROLS for details.
hi i have water heater 40000 btu natural gas what kind of pressure relief valve i need ? thank you - Paul 12/11/12
Paul, the installation instructions for your water heater will tell you exactly what temperature/pressure valve is required for your unit. The specifications will include:
Watch out: installing a TP valve that does not meet the water heater's specifications is dangerous and risks an explosion
I like this set of sensible and logical inspection steps. However, the Watts 374A 30PSI pressure relief valve clearly states on its paper owners/users tag atop the metal specifications tag that the homeowner should activate it yearly to ensure proper function.
I'd rather do what you are suggesting because it avoids the possibility of trapping any boiler water sediment/foreign material in the valve and preventing it from seating fully. But, wouldn't further 'flushing' of valve with more water usually rectify this? Like with Schrader valve with air in inner tube of bicycle tire or for auto tubeless tire valves? - Christopher 1/9/2013
Thanks for the good question Christopher.
Normally we always want to follow the product manufacturer's directions - they have a great interest in safe proper use of their equipment. And I agree that sometimes you can stop a leaky TP valve by repeated flushing of the valve to get debris off the valve seat. But I also have opened a TP valve to flush it and had the valve spit out part of the valve seat washer - leaving me with gushing hot boiler water at scalding temperatures.
The advice to "test" the TP valve by opening its test lever once a year is "safe" advice for the manufacturer to give. But it's not so safe for the homeowner because in my OPINION:
Therefore a safer suggestion for all homeowners is to ask their heating service tech to check the TP valve at the time of annual service. The service tech has a replacement TP valve right with him or her, in the service truck, and s/he knows how to replace the valve it if keeps on leaking.
One danger (I may have missed) happened to me. The T & P valve had a slow leak which drained outside building. At a persistent 4 degrees above 0 F, the water drip outside eventually froze and sealed the drain pipe at the exit point. Once sealed the pressure built until the T & P valve exploded and the final six week repair cost came in at just over $36,000. T & P valves are a real hazard to home owners! - B.T. 1/27/2013
Excellent point; We've talked about the issues of draining to a remote or unobserved location, but not about the freeze risk. Thank goodness no one was killed.
Actually you are describing a triple fault that led to an explosion:
Had your boiler had a different weakest-link than the TP valve itself, the whole boiler could have exploded, causing still more damage and risking injury or even death to building occupants. For example, had your device been draining a water heater the unit would become a rocket, shooting up through the building - details are
at BLEVE EXPLOSIONS.
(Jan 24, 2014) Rene said:
First of all this site is amazing. The writing, pictures, and diagrams are everything I have tried to find online. My question is about an old hydrotherm gas boiler for a hydronic hot water system.
The boiler does not have a pressure relief valve and I could not a pressure overflow tank in the attic. It is a 700sq ft. unit in a 4 unit house and the psi goes up to 50psi when the thermostat is raised above 80 degrees. I am obviously worried about this high psi. I have been lowering the temperature and releasing water to bring the psi down.
My questions are:
1. Can a pressure release valve be installed, if so where would it be installed?
2. A year ago one of the radiators busted and was replaced with a baseboard heater and that only heats up when the temperature is set high. One plumber said I should swap it out and that could fix the high psi issue, is there any truth to that statement? Does baseboard heat require more psi to heat up?
Watch out: It would be unusual (and unsafe) for a heating boiler to have no means of safety release of excess pressure. If there is no attic overflow or expansion tank (or if not attic, in some other upper building location) and no temperature/pressure relief valve connected directly to the boiler, typically there would have been a red B&G or equivalent pressure relief valve installed on piping near the boiler.
See BLEVE EXPLOSIONS
Take a look at the pair of photos 9th down from the page top photo - where text below the pair of photos showing a red pressure relief valve reads
"This type of relief valve responds only to water pressure and may be located at some distance from the heating boiler itself."
You may find an equivalent installed on your system. That approach was common on older systems and was permitted then, though it offers less safety protection than a modern TP valve connected right on the boiler.
You can ask your plumber or heating tech to install a TP valve directly on the boiler only if the boiler includes an available tapping that would fit the valve, at a suitable location such that the valve's sensor is immersed in boiler water, and where the tapping is big enough (typically 3/4" dia NPT) to accept the device.
Send along some photos of your system and I may be able to comment further, but basically this is a safety topic to discuss with your heating service tech and the service manager.
No one in their right mind would leave a heating boiler with no pressure relief protection - the risk is a BLEVE explosion.
Regarding cold baseboard, perhaps the system is partly air-bound and could be corrected by strategic installation of air bleeder valves at the two ends of the baseboard run or at another suitable location.
(Jan 27, 2014) renetruj said:
Thank you DanJoeFriedman. How would I send you photos so you can see if I have a tapping to place a TP valve on this old hydrotherm boiler? Do you know of any sites that have a full listing of hydrotherm models, my boiler's plates and information are all missing or eroded?
Use the CONTACT us link found at the top or bottom of any InspectApedia page.
About model identification, without the unit data tags you may be able to speak directly with Hydrotherm to ask for help - I would not want to guess based on just a box photo - since some boiler models may look alike externally.
(July 21, 2014) Ian said:
I have a two year old closed vented system. The meters show just over 1 bar pressure which I top up every 6 months. I have noticed the pressure relief pipe is dripping constantly, but can find nothing to indicate why this would be happening. It is a very slow but constant leak, but the positioning of it is causing some brickwork to become slowly saturated and damp smell inside the house.
Ian we discuss this problem in FAQs and article above on this topic - look for
- a bad pressure reducer valve or water feed valve
- a tankless coil leaking into the heating system boiler
- a defective relief valve
-abnormal operating temperatures
Watch out this is an unsafe condition. The cause of the dripping TP valve needs to be found and fixed and the valve should probably be replaced too.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website