InspectAPedia tolerates no conflicts of interest. We have no relationship with advertisers, products, or services discussed at this website.
Water pressure tank or water storage tank troubleshooting guide:
This article describes how and why to diagnose problems right at the water tank in order to help distinguish among intermittent water pressure loss, total water pressure loss, and poor water pressure or flow in a building.
How does the water tank affect building water pressure & how does the water tank affect building water quantity? How does the water tank affect well pump life & how to decide if water pressure tank replacement is necessary & Typical cost of various well, pump, and water tank repairs.
How a Bad Water Pressure Tank Can Cause Water Pressure Loss or Complete Water Supply Loss. Shaking the Water Pressure Tank to Diagnose its Condition.
The process of water tank troubleshooting starting with simple visual clues is explained.
How to Diagnose & Fix Water Pressure Tank Problems
After explaining the relationship between the water tank and water flow or pressure in buildings, this artilce series provides easy steps to troubleshoot and repair water pressure & water pressure tank problems.
This article explains how a problem with the water pressure tank can cause a variety of problems in a building such as
[Click to enlarge any image]
Air discharge at plumbing fixtures
Pulsating water pressure
Poor water pressure
Complete loss of water pressure
Damage to well or water pumps and their controls
Leaks or wet areas in the building
The process of diagnosis and the costs of the repair for water tanks are explained.
Consumer advice on saving money on well repair costs
includes a review of the parts and labor costs of a typical well pump and pressure tank replacement case.
How a Bad Water Pressure Tank Can Cause Water Pressure Loss or Complete Water Supply Loss
If the building water supply stops and takes minutes to hours to recover,
you may have problem with the well flow rate. But the problem of lost water supply and pressure could be
more mechanical: a bad well pump.
The well pump, in turn, could have been damaged or hastened to the end of its
life by a bad water pressure tank which has caused well pump short-cycling. Short cycling of the pump motor can burn up
the pump relay control.
Water tank short cycling: A bad or defective water pressure tank which has lost its air charge or which cannot keep its air charge
will cause well pump short cycling - rapid turning on and off of the water pump. This frequent pump switching on and off
is hard on the pump (damages the pump) and also on the pump switches and controls (switch contacts can become burned).
Short cycling is especially risky with an older water pump, and might push it over the edge of failure.
When the water pump fails the building will simply lose water pressure (and water supply) completely (unless it by luck the building is served by an artesian well).
Our photo (above left) illustrates a conventional internal bladder water pressure tank. As no water pump is in view we infer that this system may support a well using a submersible well pump.
Old water pumps may stop when hot: A water pump might be at end of its life and about to burn up but still work after a cool-down cycle.
In other words when the pump has been working hard and the motor is hot the pump may stop running. Since the water pump may have been
overheated due to short cycling, the actual root cause of its stopping may be the water tank (loss of air or a bad pump control) not
the pump itself.
After the pump has been off for a while it may magically start working again: some water
pumps have an internal thermal overload switch that shuts them off combined with an automatic thermal switch reset.
This is most likely to be found on water pumps that are inaccessible such as a submersible water pump.
In this case water pressure and supply will stop completely but will return after the pump cools down. But this failure is likely to be recurrent.
More on short cycling, water tank air, and how to fix the problem:: To review loss of air charge, water pump short cycling, water pump pressure control settings, and other water tank repairs be sure to
see WATER PUMP & WATER TANK REPAIRS
Water tank air bladder problems such as a burst bladder or one which has become collapsed and stuck to itself can also cause
water pump short cycling and the loss of water pressure or flow shown above. Less common in our experience but possible is water tank inlet
clogging due to a high level of sediment in the water supply, leading to similar symptoms.
More often water sediment clogs the sensor of
a water pressure regulator or it may clog a water filter, both of which lead to reduced water pressure and ultimately complete loss of water supply.
Our complete list of causes of loss of water pressure is discussed and water problems are diagnosed in detail at WATER PRESSURE LOSS DIAGNOSIS & REPAIR where we review
the all of the things that can cause loss of water pressure or loss of water entirely in a building.
Shaking the Water Pressure Tank to Diagnose its Condition
Testing a home water tank: Some plumbers or homeowners check to see if their water tank contains any water
by simply "shaking" the water pressure tank. Be careful: moving an empty water tank around can cause plumbing leaks or
even a burst pipe. There may be a trick to this but shaking the water pressure tank alone is not going to reliably
diagnoses a ruptured bladder in a captive air water tank). Shaking the tank can tell you that the water tank is empty but not why
the water tank is empty.
Why is there no water in the tank?: The water tank could be empty simply because you ran all of its water out into the home and
the water pump never came on to replenish the water supply. The possible causes of an empty water tank and no water in the home include
causes we list in detail just below:
What are the Causes of Low or Poor Water Pressure or Loss of Water Pressure in a Building?
Loss of electrical power (pump does not run) to the pump or pump control - nothing is running the water pump. Is power turned on? Is there power at the pump control and is there power to the pump?
Bad water pressure control switch (pump does not run, pump does not respond to changes in water pressure, pump won't shut off) a failing pressure control switch on the water pump - perhaps the switch is not turning on the pump.
This can be checked by manually closing the pump relay - DON'T TRY THIS YOURSELF - SHOCK HAZARD - unless you are qualified and trained. Pressure Control Switch problems are discussed further
at CAUSES OF SHORT CYCLING.
Also be sure to
review WELL PUMP PRESSURE CONTROL ADJUSTMENT for instructions on how to adjust the water pump pressure control switch.
Our photo shows a new switch we installed on a one line jet pump in 2005.
Bad water pressure regulator: (poor municipal water pressure) if the building is connected to a municipal water supply there may be a water pressure regulator installed, usually close to the water meter or where the water supply pipe enters the building.
Clogged water filter (pump cycles on and off very rapidly, reduced water pressure in the building) a clogged water filter can cause rapid pump cycling on and off - discussed further
at CAUSES OF SHORT CYCLING
Clogged water supply piping (reduced water flow) can cause poor water flow in a building. This can occur suddenly from debris clogging a delivery pipe, often at a turn or "elbow" in the piping, but that's not common. If the building water supply piping is blocked usually this is a long-standing problem. We discuss how to diagnose clogged water supply piping or blocked pipes as a cause of reduced or poor water pressure in our article
at WATER PIPE CLOG DIAGNOSIS.
Bad water tank: (pump cycling on and off or "short cycling water pump") where buildings use a private pump and well and on some buildings with poor municipal water supply quantity or pressure, a water pressure tank is installed.
See WATER TANKS HOW THEY WORK
Gently moving or "shaking" the water tank can tell you if the tank contains any water at all. The water tank could be empty simply because the well ran out of water (water was pulled out of the well faster than it could recover), or perhaps because the water pump never came on to replenish the water supply.
Some of the possible causes of an empty water tank and no water in the home include other symptoms discussed in this list of loss of water pressure. Water tanks that use
an internal bladder can have a ruptured bladder.
Steel water tanks may not be as badly rusted as the rusty water tank in this photo, but they may have pinhole leaks that result in lost air charge in the water tank.
See WHAT IS SHORT CYCLING or a bladder that's stuck to itself (pump always comes on immediately).
Well water supply pipe failure (pump runs, reduced or no water flow into the building) A well water supply pipe failure in the well or between the well and the building, so water is not being delivered to the home. (Or in cold climates, the line may have frozen)
Examples of this problem include frozen pipes, pipe leaks causing loss of water (inside the well or underground between well and building), or air leaks into the well piping, causing loss of prime (with jet pump systems). Even when a submersible pump is located in the well (and there is no loss of prime problem), if the water piping is leaking between the pump and the building water pressure may be reduced or lost.
Loss of water pump or well pump prime (pump runs but no water is delivered) in an in-building pump, or an internal pump failure such as broken vanes - the pump motor runs but no water is delivered. An in-building pump could also run and no water be delivered if the well has run dry.
A shallow well jet pump well line could have a bad foot valve (in the well) and so be losing prime. A leak in the well line can also lead to loss of prime as it lets water out or air into the well piping.
Some water pumps, particularly jet pumps, include a removable plug atop the pump assembly, giving access to the water pumping chamber in order to add
water to "prime the pump" in the event that the water pump has become air bound. This photograph shows such a plug on top of our one line jet pump.
Water Pump Internal Parts Failure: (pump runs but no water is delivered) a pump failure such as broken vanes in the pump assembly, worn out and leaky internal pump bearings or parts, or clogging with sediment or minerals can result in a pump whose motor runs but whose water output is reduced.
Water Pump Motor Failure: (pump motor stops or does not start at all): A failed or failing in-well submersible water pump stops delivering water at all, or periodically overheats and temporarily stops working. Such a pump is probably at end of life, unless the problem is traced to a voltage, switch, or wiring problem.
Water Table Level Fluctuations: (seasonal reduction in water flow or water quantity): in some areas, fluctuations in the level of ground water such as a drop in the level of groundwater during the dry season or during droughts, can result in a reduced well recovery rate or complete loss of well water.
Well is Failing: (reduced or no water flow, increasingly slow well recovery rate) the well itself may be deteriorating, with less water flowing into the well or water flowing into the more slowly than in the past.
Reductions in well flow rate occur over time when minerals clog the rock fissures that lead water into the well, or sudden reductions in well flow rate (and total water quantity) can occur if the well casing is cracked (perhaps by nearby blasting or equipment movement) or if someone drills another well nearby and happens to tap into the same water aquifer.
See WELL LIFE EXPECTANCY
Bad water pressure regulator?
See WATER PRESSURE REDUCER / REGULATOR (not usually installed on private well and pump systems, often present on municipal water supply systems that use an in-building local water pump and pressure tank to boost pressure)
Continue reading at WATER TANK REPAIR PROCEDURES or select a topic from closely-related articles below, or see our complete INDEX to RELATED ARTICLES below.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Smart Tank, Installation Instructions [ copy on file as /water/Smart_Tank_Flexcon.pdf ] - , Flexcon Industries, 300 Pond St., Randolph MA 02368, www.flexconind.com, Tel: 800-527-0030 - web search 07/24/2010, original source: http://www.flexconind.com/pdf/st_install.pdf
Typical Shallow Well One Line Jet Pump Installation [ copy on file as /water/Jet_Pump_Grove_Elect_Jet_Pumps.pdf ] - , Grove Electric, G&G Electric & Plumbing, 1900 NE 78th St., Suite 101, Vancouver WA 98665 www.grovelectric.com - web search -7/15/2010 original source: http://www.groverelectric.com/howto/38_Typical%20Jet%20Pump%20Installation.pdf
Typical Deep Well Two Line Jet Pump Installation [ copy on file as /water/Jet_Pump_Grove_Elect.pdf ] - , Grove Electric, G&G Electric & Plumbing, 1900 NE 78th St., Suite 101, Vancouver WA 98665 www.grovelectric.com - web search -7/15/2010 original source: http://www.groverelectric.com/howto/38_Typical%20Jet%20Pump%20Installation.pdf
Water Fact Sheet #3, Using Low-Yielding Wells [ copy on file as /water/Low_Yield_Wells_Penn_State.pdf ] - , Penn State College of Agricultural Sciences, Cooperative Extension, School of Forest Resources, web search 07/24/2010, original source: http://pubs.cas.psu.edu/FreePubs/pdfs/XH0002.pdf
Water pressure tanks - how to diagnose the need for air, how to add air, stop water pump short cycling to avoid damage - water storage water pressure tank safety.
WATER PUMP REPAIR GUIDE an specific case offers an example of diagnosis of loss of water pressure, loss of water, and analyzes the actual repair cost
Carson, Dunlop & Associates Ltd., 120 Carlton Street Suite 407, Toronto ON M5A 4K2. Tel: (416) 964-9415 1-800-268-7070 Email: firstname.lastname@example.org. The firm provides professional home inspection services & home inspection education & publications. Alan Carson is a past president of ASHI, the American Society of Home Inspectors. Thanks to Alan Carson and Bob Dunlop, for permission for InspectAPedia to use text excerpts from The Home Reference Book & illustrations from The Illustrated Home. Carson Dunlop Associates' provides extensive home inspection education and report writing material.
The Illustrated Home illustrates construction details and building components, a reference for owners & inspectors. Special Offer: For a 5% discount on any number of copies of the Illustrated Home purchased as a single order Enter INSPECTAILL in the order payment page "Promo/Redemption" space.
TECHNICAL REFERENCE GUIDE to manufacturer's model and serial number information for heating and cooling equipment, useful for determining the age of heating boilers, furnaces, water heaters is provided by Carson Dunlop, Associates, Toronto - Carson Dunlop Weldon & Associates Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on any number of copies of the Technical Reference Guide purchased as a single order. Just enter INSPECTATRG in the order payment page "Promo/Redemption" space.
The Home Reference Book - the Encyclopedia of Homes, Carson Dunlop & Associates, Toronto, Ontario, 25th Ed., 2012, is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. Field inspection worksheets are included at the back of the volume.
Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on these courses: Enter INSPECTAHITP in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Horizon Software System manages business operations,scheduling, & inspection report writing using Carson Dunlop's knowledge base & color images. The Horizon system runs on always-available cloud-based software for office computers, laptops, tablets, iPad, Android, & other smartphones