RIDGE VENT, ATTIC INSPECTION - CONTENTS: Guide to Inspecting Attic and Under-Roof Ventilation - what's at the ridge?How to Correct Inadequate Attic Venting to Stop Attic Condensation, Ice Dam Leaks, Attic Mold, & Roof Structure Damage. How to detect roof venting deficiencies, attic insulation defects, and attic condensation problems
InspectAPedia tolerates no conflicts of interest. We have no relationship with advertisers, products, or services discussed at this website.
Roof venting at the ridge, inspect from attic: this article describes common attic ventilation defects easily observed at the ridge or high point of the roof, as visible from the attic or building interior.
We also provide a MASTER INDEX to this topic, or you can try the page top or bottom SEARCH BOX as a quick way to find information you need.
This article describes inspection methods and clues to detect roof venting deficiencies, insulation defects, and attic condensation problems
It describes proper roof ventilation placement, amounts, and other details. This discussion is part of "How to Correct Improper or Inadequate Attic or Under-Roof Ventilation in buildings" in our discussion of "Attic Condensation".
You need the gap at the ridge (or "peak") of the roof for the ridge vent to work. Of course some roof shapes such as pyramid or shed roofs merit special techniques to obtain effective intake and exit venting.
But for a simple gable-styled roof structure, here is what a ridge vent looks like from inside the attic of a home.
The ridge vent cut at the roof ridge or peak extends the entire length of the ridge, stopping just a foot or so from either end, and should give 1.5” to 2.5” of open space (no plywood) on either side of the ridge board for attic air to escape out through the ridge vent.
Fake ridge vents: As depicted by the pair of photographs above, sometimes we find that a builder has installed a ridge vent from outside but s/he failed to cut away the roof plywood to provide the exit air path to properly vent the attic. In this case this lazy man's faux ridge vent installed outside should be removed along with any ridge cap shingles below it.
The ridge vent slot should be cut to remove roof sheathing as we described just above (or best, following instructions of the ridge vent manufacturer).
Do not cut into the rafters themselves. Then install the ridge vent again and you'll have a working roof exit vent system.
Roofing Felt Obstructed ridge vents: It’s less common for us to find that a builder cut away plywood for the ridge vent, but that s/he installed building paper or more likely roofing felt over the opening before installing the ridge vent.
In this case just cut away the building paper to expose the underside of the plastic ridge vent mesh, plastic Cor-A-Vent material (looks like a plastic version of the edge of a cardboard box) or the opening into the aluminum ridge vent (depending on which type of ridge vent was installed).
Check that the ridge vent material itself is not blocked by building paper (which you can simply cut away).
Shingle-obstructed ridge vent warning: If when inspecting from the attic and looking up into the slot of removed-plywood at the ridge of the roof you see the under side of a roof shingle, either the roofer made the ridge vent a bit longer than needed, or something else is going on that we’d need to check from outside.
In any case, do not cut away roofing shingles over the ridge vent as you might invite a roof leak.
If your attic or under-roof cavity has a problem with moisture or mold, installing continuous, un-blocked, aggressive exit venting at the ridge is an important step.
Continue reading at ATTIC VENTILATION or select a topic from closely-related articles below, or see our complete INDEX to RELATED ARTICLES below.
Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
(Aug 5, 2014) Karen Sue Smith said:
For 7 years and repeated repair attempts My new Building has Leaked Now they want to put a ridge cap on that will not vent. Should This be allowed They Installed a door and it has leaked aroun the outer edge and through the ceiing, Caulking has been their soulution for that. But I know that won't last UG Been Too Patient I Know
I agree that caulks or sealants may not be the best or most reliable fix for a leaky roof, but before doing much more I'd get some help finding where the leaks are actually originating. It sounds as if a desperate repair person has been running amok slapping band-aids all over the roof but never hitting the right spot. Flashing errors at windows and doors, for example need to be repaired.
Ask a Question or Search InspectApedia
Questions & answers or comments about attic moisture, condensation & ventilation: check the ridge vent from inside the attic
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
John Annunziata, P.E. - NY Metro ASHI during informal chapter discussions about roof and attic ventilation options (1986-1996).
"Energy Savers: Whole-House Supply Ventilation Systems [copy on file as /interiors/Energy_Savers_Whole-House_Supply_Vent.pdf ] - ", U.S. Department of Energy energysavers.gov/your_home/insulation_airsealing/index.cfm/mytopic=11880?print
"Energy Savers: Whole-House Exhaust Ventilation Systems [copy on file as /interiors/Energy_Savers_Whole-House_Exhaust.pdf ] - ", U.S. Department of Energy energysavers.gov/your_home/insulation_airsealing/index.cfm/mytopic=11870
"Energy Savers: Ventilation [copy on file as /interiors/Energy_Savers_Ventilation.pdf ] - ", U.S. Department of Energy
"Energy Savers: Natural Ventilation [copy on file as /interiors/Energy_Savers_Natural_Ventilation.pdf ] - ", U.S. Department of Energy
"Energy Savers: Energy Recovery Ventilation Systems [copy on file as /interiors/Energy_Savers_Energy_Recovery_Venting.pdf ] - ", U.S. Department of Energy energysavers.gov/your_home/insulation_airsealing/index.cfm/mytopic=11900
"Energy Savers: Detecting Air Leaks [copy on file as /interiors/Energy_Savers_Detect_Air_Leaks.pdf ] - ", U.S. Department of Energy
"Energy Savers: Air Sealing [copy on file as /interiors/Energy_Savers_Air_Sealing_1.pdf ] - ", U.S. Department of Energy
Humidity: What indoor humidity should we maintain in order to avoid a mold problem?
"Weather-Resistive Barriers [copy on file as /interiors/Weather_Resistant_Barriers_DOE.pdf ] - ", how to select and install housewrap and other types of weather resistive barriers, U.S. DOE
Books & Articles on Building & Environmental Inspection, Testing, Diagnosis, & Repair
Carson, Dunlop & Associates Ltd., 120 Carlton Street Suite 407, Toronto ON M5A 4K2. Tel: (416) 964-9415 1-800-268-7070 Email: firstname.lastname@example.org. The firm provides professional home inspection services & home inspection education & publications. Alan Carson is a past president of ASHI, the American Society of Home Inspectors. Thanks to Alan Carson and Bob Dunlop, for permission for InspectAPedia to use text excerpts from The Home Reference Book & illustrations from The Illustrated Home. Carson Dunlop Associates' provides extensive home inspection education and report writing material.
The Illustrated Home illustrates construction details and building components, a reference for owners & inspectors. Special Offer: For a 5% discount on any number of copies of the Illustrated Home purchased as a single order Enter INSPECTAILL in the order payment page "Promo/Redemption" space.
TECHNICAL REFERENCE GUIDE to manufacturer's model and serial number information for heating and cooling equipment, useful for determining the age of heating boilers, furnaces, water heaters is provided by Carson Dunlop, Associates, Toronto - Carson Dunlop Weldon & Associates Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on any number of copies of the Technical Reference Guide purchased as a single order. Just enter INSPECTATRG in the order payment page "Promo/Redemption" space.
The Home Reference Book - the Encyclopedia of Homes, Carson Dunlop & Associates, Toronto, Ontario, 25th Ed., 2012, is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. Field inspection worksheets are included at the back of the volume.
Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on these courses: Enter INSPECTAHITP in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Horizon Software System manages business operations,scheduling, & inspection report writing using Carson Dunlop's knowledge base & color images. The Horizon system runs on always-available cloud-based software for office computers, laptops, tablets, iPad, Android, & other smartphones