Why Both Ridge & Soffit Venting are Needed under Building Roofs
ROOF VENT SOFFIT + RIDGE NEEDED - CONTENTS: How do a soffit intake and ridge outlet vent work together on a roof and why are both needed? Adding a ridge vent alone can increase building heating costs. Adding soffit venting alone is ineffective. How to Correct Inadequate Attic Venting to Stop Attic Condensation, Ice Dam Leaks, Attic Mold, & Roof Structure Damage
InspectAPedia tolerates no conflicts of interest. We have no relationship with advertisers, products, or services discussed at this website.
Here we explain why a functional roof venting system needs both intake venting at the eaves or soffits and outlet venting at the roof peak or ridge.
This article series explains How to Correct Inadequate Attic Venting to Stop Attic Condensation, Ice Dam Leaks, Attic Mold, & Roof Structure Damage.
Our photo at page top shows a modern synthetic mesh type ridge vent (with modest airflow capacity) and our photo at left shows a typical installation of continuous soffit or eaves intake venting at the lower roof edges of a building.
Both Ridge and Eaves or Soffit Ventilation are Needed in buildings. This article describes inspection methods and clues to detect roof venting deficiencies, insulation defects, and attic condensation problems
in buildings. It describes proper roof ventilation placement, amounts, and other details.
Beware of adding a ridge vent without soffit vents (the worst) or soffit vents without a ridge vent (bad) or only gable-end vents (usually bad).
The up-draft of air from the building (convection
current of rising warm air which moves up through most buildings) will be increased and will mean unnecessary heat loss if you have a ridge vent to vent air out without also providing good intake venting at the soffits or eaves.
Installing only a ridge vent and no or inadequate soffit venting is likely to result in unnecessary heat loss from the building as convection currents of rising warm air in the attic, unable to easily draw
in air from outside, will "suck" warm air from the building, thus increasing unnecessary heat loss and increasing the risk of ice damming.
Providing a lot of easy air intake at the building eaves avoids this problem.
Installing only soffit venting and no ridge vent works better than a ridge-only vent and this design was used on many residential buildings.
But it's not nearly as effective as a ridge and soffit vent combination, first because air moves through the attic
space only when wind is blowing in the right direction, towards one of the walls of the Building which has a vented roof overhang, and second, because there is no high exit point to permit warmer air to exit by natural convection.
To be scrupulously fair, on a few buildings with very large gable end vents, lots of insulation in the attic floor, and perhaps lucky house siting, I have seen attics that were perfectly dry and free of condensation, ice dams, and mold. But these have been the exception, not the rule, at least for inspections in northern climates subject to cold winters and hot humid summers.
A High-Capacity Ridge Vent Moves More Air than a Low-Profile Good-looking Vent
The popular plastic mesh type ridge vent shown in this photograph is popular where ridge vents are installed on new homes or as retrofits. Builders and owners like the ability to nail roof shingles over the easily-stored, transported, and installed roll-out plastic mesh that is simply laid across an opening cut along the building's ridge.
But we have observed that this ridge vent design passes much less air than the older, uglier aluminum ridge vent shown in our sketch above. We prefer the older product which moves air.
Continuous High Capacity Eaves or Soffit Intake Venting Provides Adequate Intake Air Under Roofs
As we show in this pair of photos, continuous soffit intake venting will provide optimum intake air flow between every rafter pair.
Installing Continuous High Capacity Eaves or Soffit Intake Venting Works Best to Avoid Attic Moisture, Mold, & Ice Dams
Here are examples of inadequate intake ventilation: vents at the soffits are intermittent or "spot vents" or are simply too small.
Don't install intermittent or occasional or faux soffit intake venting or vents with too little opening area such as we show in the photo at left.
Not only are the openings too small to pass enough air (obstructed further by the louvers and insect screens), intermittent soffit intake vents or little round or rectangular soffit spot vents are singularly ineffective in providing good under-roof or attic ventilation.
Continuous soffit/eaves intake venting is the proper location for the intake air, in order to assure that the entire under-side of the roof sheathing is vented and kept dry. Not what is shown in our photo (left).
Where we inspect attics with "spot vents" in the soffits (those little round
louvered vents ranging from about 3/4" diameter (photo at left) to 2" in diameter or even 4" in diameter are completely ineffective, never moving enough air.
In these attics of buildings in climates where moisture is often a concern, we find moisture stains in the attic at the building eaves, sometimes moldy building insulation, and on occasion serious attic moisture and condensation problems.
Where we inspect attics where even larger vent openings are provided in the soffits or eaves, if the openings are intermittent, we see wet and often moldy roof sheathing on those roof sections where no venting is provided (the "in-between-vent" roof sections), even though at other roof sections where vents are present
the sheathing often looks clean and dry.
This is compelling visual evidence that air is not moving up the under-side of the sections of roofing where no intake vents are
present at the building eaves. Venting needs to be provided between every rafter pair at the eaves and ridge.
Just as we want continuous intake venting along the building eaves, continuous ridge venting is the optimum exit path for warm rising air in an attic, thus pulling new cooler, drier outside air into the under-roof area from between every rafter pair. (C)Daniel Friedman - copyright protection trap.
Continue reading at ROOF VENTILATION SPECIFICATIONS or select a topic from closely-related articles below, or see our complete INDEX to RELATED ARTICLES below.
Or see ROOF VENTILATION FAQs for questions & answers on venting hard-to-vent roofs in buildings of various age, design, and situation.
Questions & answers or comments about attic moisture, condensation & ventilation: why are both soffit intake and ridge outlet needed?
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
"Energy Savers: Whole-House Supply Ventilation Systems [copy on file as /interiors/Energy_Savers_Whole-House_Supply_Vent.pdf ] - ", U.S. Department of Energy energysavers.gov/your_home/insulation_airsealing/index.cfm/mytopic=11880?print
"Energy Savers: Whole-House Exhaust Ventilation Systems [copy on file as /interiors/Energy_Savers_Whole-House_Exhaust.pdf ] - ", U.S. Department of Energy energysavers.gov/your_home/insulation_airsealing/index.cfm/mytopic=11870
"Energy Savers: Ventilation [copy on file as /interiors/Energy_Savers_Ventilation.pdf ] - ", U.S. Department of Energy
"Energy Savers: Natural Ventilation [copy on file as /interiors/Energy_Savers_Natural_Ventilation.pdf ] - ", U.S. Department of Energy
"Energy Savers: Energy Recovery Ventilation Systems [copy on file as /interiors/Energy_Savers_Energy_Recovery_Venting.pdf ] - ", U.S. Department of Energy energysavers.gov/your_home/insulation_airsealing/index.cfm/mytopic=11900
"Energy Savers: Detecting Air Leaks [copy on file as /interiors/Energy_Savers_Detect_Air_Leaks.pdf ] - ", U.S. Department of Energy
"Energy Savers: Air Sealing [copy on file as /interiors/Energy_Savers_Air_Sealing_1.pdf ] - ", U.S. Department of Energy
Humidity: What indoor humidity should we maintain in order to avoid a mold problem?
"Weather-Resistive Barriers [copy on file as /interiors/Weather_Resistant_Barriers_DOE.pdf ] - ", how to select and install housewrap and other types of weather resistive barriers, U.S. DOE
Carson, Dunlop & Associates Ltd., 120 Carlton Street Suite 407, Toronto ON M5A 4K2. Tel: (416) 964-9415 1-800-268-7070 Email: email@example.com. The firm provides professional home inspection services & home inspection education & publications. Alan Carson is a past president of ASHI, the American Society of Home Inspectors. Thanks to Alan Carson and Bob Dunlop, for permission for InspectAPedia to use text excerpts from The Home Reference Book & illustrations from The Illustrated Home. Carson Dunlop Associates' provides extensive home inspection education and report writing material.
The Illustrated Home illustrates construction details and building components, a reference for owners & inspectors. Special Offer: For a 5% discount on any number of copies of the Illustrated Home purchased as a single order Enter INSPECTAILL in the order payment page "Promo/Redemption" space.
TECHNICAL REFERENCE GUIDE to manufacturer's model and serial number information for heating and cooling equipment, useful for determining the age of heating boilers, furnaces, water heaters is provided by Carson Dunlop, Associates, Toronto - Carson Dunlop Weldon & Associates Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on any number of copies of the Technical Reference Guide purchased as a single order. Just enter INSPECTATRG in the order payment page "Promo/Redemption" space.
The Home Reference Book - the Encyclopedia of Homes, Carson Dunlop & Associates, Toronto, Ontario, 25th Ed., 2012, is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. Field inspection worksheets are included at the back of the volume.
Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on these courses: Enter INSPECTAHITP in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Horizon Software System manages business operations,scheduling, & inspection report writing using Carson Dunlop's knowledge base & color images. The Horizon system runs on always-available cloud-based software for office computers, laptops, tablets, iPad, Android, & other smartphones