POST a QUESTION or READ FAQs about how to diagnose & repair problems with the air handler or blower unit / fan assembly in a warm air furnace or air conditioning system
InspectAPedia tolerates no conflicts of interest. We have no relationship with advertisers, products, or services discussed at this website.
Indoor air handler or blower unit for A/C or heat pump or furnace systems:
How to inspect & repair the
indoor components of air conditioners and heat pumps: the air conditioning system indoor air handler units, blower units, or AHU's, (also called fan coil units) including the air conditioner blower fan, the indoor cooling coil or "evaporator coil", air
conditioning system filters, and the causes, cures, and prevention of air handler leaks that lead to rust, damage, and mold contamination in the
air conditioning system.
Quick troubleshooting guide for air handling units or blower assemblies in air conditioners, heat pumps, some furnaces. Dirty, contaminated air conditioner blower fans, reduced air output, fan cleaning advice. Air Conditioning air handler unit (AHU) leaks. Causes & Photographs of Mold Growth in Air Conditioning Blower Fans. How to Keep the HVAC Blower Assembly Clean.
Air Conditioning Blower Fan, Cooling Coil, Fan Coil Unit Leaks, Mold, and Filter Problems &: Repairs.
We also provide a MASTER INDEX to this topic, or you can try the page top or bottom SEARCH BOX as a quick way to find information you need.
Air Handling Unit Troubleshooting - Quick Checks to fix no air flow or weak air flow
Basic air handler unit or blower unit troubleshooting checks
Here we provide air handler unit or blower assembly troubleshooting by expanded annotated information from the US EPA who provided suggestions for investigating the air handling unit during an indoor air quality investigation.
Is the system turned on? Check thermostat to see that it is calling for heat or cooling, service switches at the equipment, check fuses or circuit breakers serving the equipment; for cooling systems check for a condensate drip tray overflow switch that may have turned off the system.
see COOLING COIL or EVAPORATOR COIL for a description of diagnosis and repair of cooling coil problems since this component is normally located within the air handler chassis as well. A cooling coil which is blocked by debris or ice and frost can obstruct air flow and reduce air conditioning system output
Is the condensate pan clean and is condensate draining out of the pan?
Dirty A/C or Heat Pump Blower Units - Dirt-blocked air conditioner air handler fans
We also discuss how to improve indoor air quality by installing a cascaded air filter system at the air conditioning (or heating system) air handler to
provide optimal air particle filtration for people with asthma, allergies, or indoor mold or other IAQ concerns.
Filters protect the blower assembly: The typical A/C system circulates air through the building duct work using a "squirrel cage" blower fan.
It is very important for you to check and change air filters at least monthly when the system is in use to protect the
blower fan from dirt clogging.
Cupped fan blades can become blocked by debris: The blades of a squirrel-cage fan are cupped in order to cause the spinning cage to move air.
Dirt accumulation on the blades fills-in this cupped area, ultimately changing the "cup" to a simple flat area. The fan will spin
just fine. I've seen the cubic feet per minute of air conditioning air-flow literally double when a very dirty
squirrel cage fan fan of this type was cleaned or replaced.
Cleaning an air conditioner squirrel cage fan with compressed air? If the blower fan blades have significant dirt accumulation,
you should have the system professionally cleaned. While this is a fairly costly service call (requiring blower disassembly and removal for
cleaning) it can make a dramatic improvement in system performance.
Do not permit a simple "blow out" of the blower by compressed air if
the air handler/blower are in the living area. Some HVAC service companies use a foaming cleaner for removing debris from an
evaporator coil. That same material might assist in cleaning a squirrel cage fan.
Otherwise we recommend removing the fan
and cleaning it thoroughly outside. Clean the remainder of the fan cabinet and housing before returning the air handler to service.
Leaks, Dirt, Rodents Getting Into HVAC Blowers, Blower Compartments, Air Plenums
Very dirty, wet, leaked-into, or rodent-infested blower compartments risk indoor air quality and health issues in buildings.
The air handler unit in the photo at left needs cleaning and a check for unsafe wiring due to leaks.
Leaks into the blower compartment
of an HVAC air handler invite mold problems too.
The return air plenum in the photo at right has both a dead mouse and some other sort of trash that probably fell down
a return air floor grille.
Mice in HVAC systems are a potential viral or bacterial hazard as well as an indicator of poor housekeeping.
These conditions suggested that there had not been regular inspections of this equipment.
Causes & Photographs of Mold Growth in Air Conditioning Blower Fans
Notice the multiple colors and textures of mold growing on this air conditioner squirrel cage blower fan. Mold, depending on its genera/species, moisture conditions, and growth substrate material, can grow on many different
surfaces where some organic material is available for "food".
We might find mold growing in an air conditioner on plastic, on air cabinet or duct insulation facing, hidden in fiberglass insulation, or on other materials.
Most likely the mold growing on this blower fan found a home in some of the organic constituents of common house dust: skin cells and dust mite fecals.
Very often the mold we sample and identify in air conditioner blower cabinets is a very common genera, Cladosporium sp. - a mold so common it's called "the king of molds." Kicking up leaves outdoors exposes you to more Cladosporium sp. than the mold on this
But we also find some genera/species of more toxic molds that will grow right on top of other molds that are already present. So while air cabinet conditions may start by producing one mold of not too much concern, other more
highly allergenic or even toxic molds could be present.
The fact that the mold in this photograph includes multiple colors and textures of material suggests that more than one genera or species of mold is present.
How to Handle Small Areas of HVAC System Mold Contamination
If the total area of moldy material
is small (say less than 30 sq.ft. of contiguous mold) we would not bother to take a mold sample back to our lab for identification. Instead we'd suggest that the moldy surfaces be cleaned or non-cleanable material like insulation, replaced, and the cause for its growth corrected.
We might, however, sample even a small amount of visible mold as part of a larger building diagnostic program if there were illness or air quality complaints associated with the building.
Examples of condensate spill-over inside of an air handler blower compartment, a condition creating a risk of mold growth inside the HVAC system are
at BLOWER LEAKS, RUST & MOLD
More information about the potential of toxic mold growth in fiberglass ducts or fiberglass HVAC duct insulation as well as other fiberglass insulation products and more example photographs of that condition are
at FIBERGLASS INSULATION MOLD.
How to Keep the HVAC Blower Assembly Clean
We noted at DIRTY A/C BLOWERS that a dirty blower fan reduces the blower assembly air flow rate, increasing heating and cooling costs, and sometimes leading to actual system operating failures such as FROST BUILD-UP on AIR CONDITIONER COILS that forms not just frost but solid ice if the air flow rate across even a clean cooling coil is just too slow.
At BLOWER FAN ASSEMBLY CLEANING we describe and illustrate a detailed, thorough cleaning of the blower assembly in an air handler that is used for both heating and air conditioning.
BLOWER OPERATION: For effective operation of this system it is essential that it never be operated without air filters in place.
See AIR FILTERS for HVAC SYSTEMS.
COOLING MAINTENANCE TIP: The HVAC blower assembly should be serviced every two years. Without proper service the system may have no more than a five year lifetime.
ENERGY CONSERVATION: Keeping the fireplace flue closed (if you have one) when not in use will improve both heating and cooling efficiency in all buildings. or select a topic from closely-related articles below, or see our complete INDEX to RELATED ARTICLES below.
Continue reading at BLOWER LEAKS, RUST & MOLD or select a topic from closely-related articles below, or see our complete INDEX to RELATED ARTICLES below.
Thanks to Mark Cramer, Tampa Florida, for assistance in technical review of the "Critical Defects"
section and for the photograph of the deteriorating gray Owens Corning flex duct in a hot attic. Mr. Cramer is a Florida home inspector and
home inspection educator.
Thanks to Jon Bolton, an ASHI, FABI, and otherwise certified Florida home inspector who provided photos of failing Goodman gray flex duct in a hot attic.
Wikipedia provided background information about the definition of HEPA and airborne particle interception.
 US EPA - Mold Remediation in Schools and Commercial Building [ copy on file as /sickhouse/EPA_Mold_Remediation_in_Schools.pdf ] - US EPA
"Air Conditioning & Refrigeration I & II", BOCES Education, Warren Hilliard (instructor), Poughkeepsie, New York, May - July 1982, [classroom notes from air conditioning and refrigeration maintenance and repair course attended by the website author]
Carson, Dunlop & Associates Ltd., 120 Carlton Street Suite 407, Toronto ON M5A 4K2. Tel: (416) 964-9415 1-800-268-7070 Email: firstname.lastname@example.org. The firm provides professional home inspection services & home inspection education & publications. Alan Carson is a past president of ASHI, the American Society of Home Inspectors. Thanks to Alan Carson and Bob Dunlop, for permission for InspectAPedia to use text excerpts from The Home Reference Book & illustrations from The Illustrated Home. Carson Dunlop Associates' provides extensive home inspection education and report writing material.
The Illustrated Home illustrates construction details and building components, a reference for owners & inspectors. Special Offer: For a 5% discount on any number of copies of the Illustrated Home purchased as a single order Enter INSPECTAILL in the order payment page "Promo/Redemption" space.
TECHNICAL REFERENCE GUIDE to manufacturer's model and serial number information for heating and cooling equipment, useful for determining the age of heating boilers, furnaces, water heaters is provided by Carson Dunlop, Associates, Toronto - Carson Dunlop Weldon & Associates Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on any number of copies of the Technical Reference Guide purchased as a single order. Just enter INSPECTATRG in the order payment page "Promo/Redemption" space.
The Home Reference Book - the Encyclopedia of Homes, Carson Dunlop & Associates, Toronto, Ontario, 25th Ed., 2012, is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. Field inspection worksheets are included at the back of the volume.
Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on these courses: Enter INSPECTAHITP in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Horizon Software System manages business operations,scheduling, & inspection report writing using Carson Dunlop's knowledge base & color images. The Horizon system runs on always-available cloud-based software for office computers, laptops, tablets, iPad, Android, & other smartphones