Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
AFUE DEFINITION, RATINGS
AGE of CHIMNEYS & FIREPLACES
AGE of AIR CONDITIONERS & HEAT PUMPS
AGE of HEATERS, BOILERS, FURNACES
AIR CONDITIONING & HEAT PUMP SYSTEMS
AIR FILTERS for HVAC SYSTEMS
AIR HANDLER / BLOWER UNITS
AIRBOUND HEAT SYSTEM REPAIR by WATER FEED VALVE
ANODES & DIP TUBES on WATER HEATERS
ANTIFREEZE for BOILERS
ANTI SCALD VALVES
APPLIANCE DIAGNOSIS & REPAIR
APPLIANCE EFFICIENCY RATINGS
ASBESTOS IDENTIFICATION IN buildings
BACKDRAFTING HEATING EQUIPMENT
BACKFLOW PREVENTER VALVE, HEATING SYS
BACKFLOW PREVENTER, HEATER WATER FEEDER
BACKUP HEAT for HEAT PUMPS
BANGING HEATING PIPES RADIATORS
BIOGAS PRODUCTION & USE
BLOWER DOORS & AIR INFILTRATION
BLOWER FAN CONTINUOUS OPERATION
BLOWER FAN OPERATION & TESTING
BLUE vs YELLOW COMBUSTION FLAMES
BOILER CHEMICAL TREATMENTS
BOILER COMPONENTS & PARTS
BOILER CONTROLS & SWITCHES
BOILER LEAKS CORROSION STAINS
BOILER LEAKS, HOW TO LOCATE
BOILER NOISE SMOKE ODORS
BOILER OPERATING PROBLEMS
BOILER OPERATING STEPS
BOILER PRESSURE & TEMPERATURE SETTINGS
BOOKSTORE - InspectAPedia
BTU USAGE MONITORS
BUILDING SAFETY HAZARDS GUIDE
CAPACITORS for HARD STARTING MOTORS
CARBON DIOXIDE - CO2
CARBON MONOXIDE - CO
CHEMICAL TREATMENTS for BOILERS
CHIMNEY INSPECTION DIAGNOSIS REPAIR
CHIMNEYS & Flues - Asbestos Transite Pipe
CHINESE DRYWALL HAZARDS
CIRCULATOR PUMPS & RELAYS
COOL OFF HEAT, Thermostat Switch
COMBUSTION AIR for TIGHT buildings
COMBUSTION GASES & PARTICLE HAZARDS
COMBUSTION PRODUCTS & IAQ
COMPLETE COMBUSTION, Stoichiometric
CREOSOTE FIRE HAZARDS
Curved Brick Chimneys - Sulphation
CONDENSING BOILERS/FURNACES DAMAGE
CONVECTOR HEATERS - HYDRONIC COILS
DEFINITION of HEATING & COOLING TERMS
DEFINITIONS of ELECTRICAL TERMS
OIL LINE CONTROLS & VALVES
DEW POINT CALCULATION for WALLS
DEW POINT TABLE - CONDENSATION POINT GUIDE
DIAGNOSTIC GUIDES A/C / HEAT PUMP
DIAGNOSE & FIX HEATING PROBLEMS-BOILER
DIAGNOSE & FIX HEATING PROBLEMS-FURNACE
DIRECT VENTS / SIDE WALL VENTS
DIRECTORY of OIL TANK EXPERTS
DRAFT HOODS - gas fired
DRAFT MEASUREMENT, CHIMNEYS & FLUES
DRAFT REGULATORS, DAMPERS, BOOSTERS
DUCT SYSTEM & DUCT DEFECTS
DUST, HVAC CONTAMINATION STUDY
DUST SAMPLING PROCEDURE
ELECTRIC MOTOR DIAGNOSTIC GUIDE
ELECTRIC MOTOR OVERLOAD RESET SWITCH
ELECTRICAL POWER SWITCH FOR HEAT
EVAPORATIVE COOLING SYSTEMS
FAN, AIR HANDLER BLOWER UNIT
FAN AUTO ON Thermostat Switch
FAN, COMPRESSOR/CONDENSER UNIT
FAN CONVECTOR HEATERS - HYDRONIC COILS
FAN LIMIT SWITCH
FAN NOISES, HVAC
FILTERS, AIR for HVAC SYSTEMS
FILTERS, OIL on HEATING EQUIPMENT
FIRE SAFETY CONTROLS
FIREPLACES & HEARTHS
FLAME COLOR, BLUE vs YELLOW COMBUSTION
FLOODED HEATING EQUIPMENT REPAIR
FLUE SIZE SPECIFICATIONS
FLUE VENT CONNECTORS
FREEZE-PROOF A BUILDING
FUEL OIL TYPES & CHARACTERISTICS
FUEL UNIT, HEATING OIL PUMPS
FURNACE CONTROLS & SWITCHES
FURNACE HEAT EXCHANGER LEAKS
FURNACE OPERATION DETAILS
FURNACE OPERATING TEMPERATURES
GALVANIC SCALE & METAL CORROSION
GAS BURNER Flame & Noise Defects
GAS FIRED WATER HEATERS
GAS PIPING, VALVES, CONTROLS
GAUGES ON HEATING EQUIPMENT
GEOTHERMAL HEATING SYSTEMS
HEAT EXCHANGER LEAK TEST
HEAT LOSS in BUILDINGS
HEAT LOSS DETECTION TOOLS
HEAT LOSS INDICATORS
HEAT LOSS PREVENTION PRIORITIES
HEAT LOSS R U & K VALUE CALCULATION
HEAT PUMPS, DIAGNOSIS, REPAIR
HEAT TAPES & CABLES on Roofs for Ice Dams
HEATING COST FUEL & BTU Cost Table
HEATING COST SAVINGS METHODS
HEATING LOSS DIAGNOSIS-BOILERS
HEATING LOSS DIAGNOSIS-FURNACES
HEATING OIL CLOUD WAX GEL POINT
HEATING OIL EXPOSURE HAZARDS, LIMITS
HEATING OIL - OLD, USEABLE?
HEATING OIL PIPING TROUBLES
HEATING OIL SHELF LIFE
HEATING OIL SLUDGE
HEATING OIL TANKS
HEATING OIL TYPES & PROPERTIES
HEATING OIL USAGE RATE
HEATING SMALL LOADS
HEATING SYSTEM INSPECT DIAGNOSE REPAIR
HEATING SYSTEM NOISES
HEATING SYSTEM SERVICE FAQs
HEATING SYSTEM TYPES
HIGH EFFICIENCY BOILERS/FURNACES
HOT WATER HEATERS
HOT WATER IMPROVEMENT
HUMIDITY LEVEL TARGET
ROOF ICE DAM LEAKS
INSULATION INSPECTION & IMPROVEMENT
LOW VOLTAGE BUILDING WIRING
LOW VOLTAGE TRANSFORMER TEST
GAS LP & NATURAL GAS SAFETY HAZARDS
MANUALS & PARTS GUIDES - HVAC
METHANE GAS SOURCES
MIXING / ANTI-SCALD VALVES
MIX VALVE SCALD PROTECTION, Best Practices
MOTOR OVERLOAD RESET SWITCH
Natural Gas Combustion
NO HEAT - BOILER
NO HEAT - FURNACE
NOISE / SOUND DIAGNOSIS & CURE
NOISE AIR CONDITIONER / HEAT PUMP
NOISE, DUCT VIBRATION DAMPENERS
NOISE, HEATING SYSTEMS
NOISE, WATER HEATER
ODORS GASES SMELLS, DIAGNOSIS & CURE
ODORS FROM HEATING SYSTEMS
OIL BURNER FUEL UNIT
OIL BURNER INSPECTION & REPAIR
OIL BURNER NOISE SMOKE ODORS
OIL BURNER NOZZLE & ELECTRODES
OIL BURNERS, RETENTION HEAD
OIL BURNER SOOT & PUFFBACKS
OIL FILTERS on HEATING EQUIPMENT
OIL FILTER MISSING
OIL FUEL TYPES & CHARACTERISTICS
OIL HEAT FIRE SAFETY CONTROLS
OIL LINE CLOGGING FIX
OIL LINE QUICK STOP VALVES
OIL LINE SAFETY VALVES, OSVs
OIL FILL PIPE LEAKS
OIL PUMP FUEL UNIT
OIL SPILL CLEANUP / PREVENTION
OIL TANK ABANDONING PROCEDURE
OIL TANKS, BURIED
OIL TANK GAUGES
OIL TANK INSPECTION & TROUBLESHOOTING
OIL TANK LEAKS & SMELLS
OIL TANK PIPING & PIPING DEFECTS
OIL TANK PRESSURE
OIL TANK REGULATIONS
OIL TANK REMOVAL COs
OIL TANK REMOVAL FINANCIAL AID
OIL TANK SAFETY
OIL TANK SLUDGE
OIL TANK STANDARDS - UL
OIL TANK LEAK TEST METHODS
OIL TANK TESTING & REMOVAL COs
OIL TANK WATER REMOVAL
PLASTIC Plexvent / Ultravent RECALL
PULSE COMBUSTION HEATERS
PRESSURE REDUCING VALVES
PRESSURE REGULATOR, WATER
PUFFBACKS, OIL BURNER
PUMPS, PONY PUMPS
RADIANT HEAT Floor Mistakes to Avoid
RADIANT HEAT TEMPERATURES
RADIANT SLAB FLOORING CHOICES
RADIANT SLAB TUBING & FLUID CHOICES
RELIEF VALVE LEAKS
RELIEF VALVES - TP Valves on Boilers
RELIEF VALVES - STEAM TP VALVES
RELIEF VALVES - Water Heaters
RELIEF VALVES - Water Tanks
Reset Switch - Heater Primary Control
Reset Switch Broken - Quick RepaiR
RESET SWITCH - ELECTRIC MOTOR
Reset Switch - Stack Relays
SAFETY HAZARDS & INSPECTIONS
SAFETY HAZARDS GUIDE
SAFETY, HEATING INSPECTION
SAFETY RECALLS CHIMNEYS VENTS HEATERS
SOLAR HEATING SYSTEM DESIGNS
SOOT on OIL FIRED HEATING EQUIPMENT
SPILL SWITCHES - Flue Gas Detection
SPLIT SYSTEM AIR CONDITIONERS & HEAT PUMPS
STACK RELAY SWITCHES
STAIN DIAGNOSIS on BUILDING INTERIORS
STEAM HEATING SYSTEMS
Thermal Expansion Cracking of Brick
THERMAL EXPANSION of HOT WATER
THERMAL EXPANSION of MATERIALS
THERMAL IMAGING, THERMOGRAPHY
THERMAL MASS in BUILDINGS
THERMAL TRACKING & HEAT LOSS
THERMOSTATS, HEATING / COOLING
THERMOSTATS, WATER HEATER
THERMOSTATIC EXPANSION VALVES
TRANSITE PIPE CHIMNEYS & FLUES
VIDEO GUIDES: Heating System Videos
VIDEO GUIDES - InspectAPedia.com
WATER HEATER SAFETY
WATER HEATERS for HOME HEATING USE?
WATER HEATER NOISES
WATER HEATER SCALE - De-Liming Procedure
WATER HEATER SCALE PREVENTION
WATER SOFTENERS & CONDITIONERS
WINTERIZE A BUILDING
WOOD, COAL STOVES & FIREPLACES
WOOD STOVE SAFETY
ZONE VALVES, HEATING
This article explains the operation, use, and reset button on Cad Cell Relay Controls: a guide to inspecting and re-setting the cad cell relay safety device on oil burners. We describe how the cad cell relay and the cad cell sensor itself are tested. We explain how the cad cell works to "see" the oil burner flame, what goes wrong in an oil burner that the cad cell "eye" can detect, and how cad cell sensors are tested using several methods including a VOM. We include cad cell trouble spots - particular oil burner installations or conditions that can make it hard for the cad cell to sense even a good flame.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
This article series answers most questions about central heating system troubleshooting, inspection, diagnosis, and repairs. We describe how to inspect, troubleshoot and repair heating and air conditioning systems to inform home owners, buyers, and home inspectors of common heating system defects.
The articles at this website describe the basic components of a home heating system, how to find the rated heating capacity of an heating system by examining various data tags and components, how to recognize common heating system operating or safety defects, and how to save money on home heating costs. Contact us to suggest text changes and additions and, if you wish, to receive online listing and credit for that contribution.
How to Reset the Cad Cell Relay on an Oil Burner for Boilers & Furnaces
How to Test the Oil Burner Cadmium Cell Relay Switch & Switch Sensor
Watch out: Honeywell's instructions for R4184D and R8184G,M,N,P Protectcorelay® series of oil burner controls advises 
However this instruction pertains to the control itself. The cad cell relay sensor is a plug-in replaceable part that can be cleaned or field-replaced if appropriate.
Button & Switch Tests of The Cad Cell Relay
Using a Honeywell R8184G primary control as an example we illustrate the reset button (red arrow in our photo, below left) and the safety switch lever (black arrow, below left). The red button is the "reset button" on this control.
On some equipment the round reset button is accompanied by a small thin lever or "switch" (the black arrow in our photo above left). On some older controls the safety switch lever is a thin silver metallic lever protruding through the control cover rather than the nice chubby black switch shown above.
If your control incorporates that little lever (which will also protrude out through the control cover) you can test the control by holding the lever down or in the opposite of its normal position (you may have to move it to one side instead of down depending on how the control is mounted).
Holding the switch lever out of its normal position for a short time will cause the safety switch to shut down the equipment and the reset button will pop out - sticking out further from the control cover. To re-start the burner, push the red reset button back in.
Resistance Testing the Cad Cell Sensor using a VOM or Digital VOM
Honeywell's description of their cad cell sensor used on their R4184D and R8184G,M,N,P Protectcorelay® series of oil burner controls describes it as follows:
Testing the Cad Cell Sensor Itself: Our photo of a cad cell relay being tested by our oil heating company service tech (Bottini Oil, Poughkeepsie, NY), shows how an expert can check on the cad cell function without disassembling the equipment.
When the oil burner is firing, an ohmmeter reading of 1/2 ohm (close to zero) to a maximum of about 500 to 600 ohms (see note below) is normal.
When the oil burner is not firing, the reading across the cad cell terminals should be close to infinity, that is, high resistance. That is, the cad cell is not seeing any flame.
If the cad cell fails, or more likely if a dirty oil burner flame soots up the face of the cad cell device, the soot blocks view of the flame and cad cell resistance will increase. (That's why at zero flame and when it's dark in the combustion chamber the cad cell will read infinite resistance.)
Significantly, Honeywell's Protectorelay installation and testing instructions do not include a recommendation for testing the resistance of the cad cell sensor. Instead the company recommends the test sequences described above, and note that if the cad cell is not responding to the flame, you should replace it  But before doing so
Thanks to reader Tony for the following comment:
Other Cad Cell Sensor & Oil Burner Cad Cell Primary Control Troubles
Watch out: here are some other cad cell sensor troubles that can give odd readings, or that can cause the cad cell control to switch the heating system off on "reset"
Automated LED Readouts Give Cad Cell Relay Condition
On more advanced primary oil burner controls such as the Honeywell R7184 Series Primary Controls, the control unit itself is capable of monitoring the status of the cad cell relay.  A series of LED flashes indicates the cad cell resistance in ohms (for this control) as follows:
Notes to the Cad Cell Resistance Table
The control will work properly at any of the resistances indicated in the first three lines of the cad cell relay table above. In other words, the cad cell resistance should be below 1600 ohms for this control. The utility of reading the number of flashes and thus inferring the cad cell resistance is that higher resistances can indicate trouble brewing and dirty oil burner operation or a poor sooty flame.
To observe the cad cell condition for this primary control, Honeywell instructs "While the [oil] burner is firing, and after the ignition has been turned off, press and release the reset button (hold 1/2 second or less) to check cad cell resistance. The LED will flash 1 to 4 times depending on the cad cell resistance. For proper operation, it is important that the cad cell resistance is below 1600 ohms.
How to Service or Replace the Cad Cell Relay on an Oil Burner
Above we showed you the face of a cad cell and explained that it can become soiled and blocked by oil burner soot, particularly if the oil burner is itself running "dirty" or improperly.
Cleaning or replacing an oil burner cad cell is pretty easy, but this is a job for the service technician since it's necessary to turn off power to the oil burner and partly disassemble the oil burner to access the cad cell sensor.
Often by removing a lock screw or two, the voltage transformer (the black box atop[ the oil burner in this photo) is simply hinged back and one can see the yellow wire entering the oil burner tube and leading to the cad cell sensor.
The cad cell relay sensor will be mounted in a little bracket and positioned where it can "see" the flame when the oil burner is operating.
If the oil burner has not been operating properly, say has been producing too much smoke and soot, even after it has been adjusted it may be necessary to inspect and clean soot from the cad cell sensor so that it has a non-sooty clear view of the flame.
Or the technician, if s/he has any doubt about the sensor, will simply replace it. It's a simple plug-in part (two pins on the sensor plug into a receptacle that is secured by a bracket inside of the oil burner tube).
To order a new cad cell for most Honeywell Protectorelay controls order Honeywell part no. 130367 Cad Cell.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
Question: Cadmium poisoning report: could my heating boiler cad cell be involved?
I received and respect your response to my recent email. I do not expect a response to this email, but wanted to ask a question because I have exhausted every resource I can think of. In June 2010, I learned that I had long-term carbon monoxide exposure.
After months of treatment, I am very improved. I do biochemical testing and I ordered several tests on myself as no one had done any lab testing or even thought it could be relevant to the downstream effects of CO poisoning. I have very high levels of cadmium in my blood, indicating a "recent" (un definable term) exposure. I wonder if the cadmium could have come from the cad cell relay on the gas hot water heater.
To my knowledge, I was not in contact with any of the common sources of cadmium. I will be testing my home and my family members' blood. Over the past six months, I have put together a team of over 20 people to help treat the effects of the poisoning. I am doing well and believe that some of the data I have collected might be of interest to you. Please let me know if that is the case. I know you are very busy--and I love your site. - A.S. Louisville KY
Reply: Cad Cell Seems Unlikely to Be a Hazard, Here's What & How to Check
The cad cell that is used as a flame sensor in heating equipment is quite well sealed-up. After all cad cells are used in a combustion chamber and exposed to challenging conditions such as high temperature and vibration. We do not know how much cadmium is used in that flame-sensing device - the manufacturer could tell you.
But if nevertheless you suspect that the heating boiler or water heater oil burner cad cell sensor itself is a source of cadmium, it would make sense to have the cad cell removed with care, placed in a sterile clean container, and tested for leakage. I'm somewhat doubtful that you'd find something. My reasoning is that if the cad cell were damaged most likely it also would not be working and you'd have noticed - you'd have no heat because the oil burner would stop running.
Cadmium is used in other products, including some paints. If you've been hanging around an artist's studio ask about her paints. Some other common sources of cadmium include those listed below, all of which seem to us to be potentially greater total cadmium reservoirs than a single sensor in a heating appliance:
As you are consulting a panel of experts, it makes sense to ask them to look at your personal case history and to compare that with the environments in which you've spent time, checking to see if you've been exposed to a particularly likely source of cadmium.
Question: proper ohms readings at a cad cell relay
at times i can`t get an under 2000, or even 3000 ohm reading after ruling out or correcting the following:
- Samuel Zapata
Question: my oil fired furnace fires up but the blower in the air handler doesn't turn on
I have a oil-furnace,my system fire up,blower didn't come on system shut down .I replaced the limit control, system fired up,blower came on ran a few sec. then shut down. I suspect cleaning or replacing the flame detector. I see soot on cabinet,am I close? - Victa
Victa, that's a reasonable first guess.
Question: my oil burner keeps tripping at the cad cell relay
My oil burner keeps tripping at the cad cell relay I replaced the cad cell sensor and it's still doing it the burner will run for 10 to 12 hours fine and then trip off should I replace the whole relay - Bill
My oil furnace comes on sometimes I have to hit the reset button on the relay, then it goes on then off periodically while heating the house. What is likely the problem? - Ed
Bill and Ed: if the oil burner keeps tripping the cad cell relay and the relay sensor has been replaced, more likely the burner is running at too high a smoke level - running dirty- and needs cleaning and adjustment. The root cause could be several things: inadequate combustion air, bad nozzle, improper electrode adjustment etc.
Question: My furnace is not firing even though the thermostat is calling for heat
My furnace is not firing even though the thermostat is calling for heat. It is only when I hit the relay reset will the burner fire. The furnace then will run until its satisfied then turn off like normal. It runs correctly one or two more times when the thermostat is calling but then the same issue will occur. I tried to clean the eye on the sensor but it didn't make any difference. I also jumped out the thermostat (without hitting the reset) and the furnace did not fire. Should I just buy a new cad eye sensor or does this sound like a different issue all together? - Adam Kelly
Question: red reset button on the Protectorelay control keeps popping
The reset button on the oil primary keeps popping daily. I have had the oil furnce tech in to clean the furnace and replace the nozzle, filter, etc. I have replaced the fan motor last year and recently replaced the photo cell. I have heard the fan motor turn on however no light-off since the cleaning. What could be my possible problems and fixes? Tranformer?? Weak primary?? Thanks, Trent - Trent 1/6/12
Question: we keep losing heat and the cad cell and protectorelay trips off
My oil furnace occasionally does not light. It has been cleaned, inspected and gapped and the transformer was changed. It fired w/o problem for approximately one week then began to trip the cad. When reset, the transformer can be heard working when it lights (a faint buzz) yet when it does not light there is not a sound from the transformer. Both the old and new transformers were bench tested and function fine. Since the blower and transformer are wired to the same leads and the blower always works what should I have the technician check next? - Brian C 2/12/12
A repeated tripping cad cell usually means the system is running dirty or losing flame; it's easy to check and rule out a bad cad cell sensor itself as part of the troubleshooting - described in the article above.
Question: oil fired water heater won't start - I pressed the reset, nothing happens
my hot water oil-fired burner does not come on just put 50 gallons of fuel in, the boiler must have been down at least 1 to 2 months,what should i do, i have call for heat but no flashing lights on the transformer for my diagnostics so i cant reset the system nothing happens this is the first time this happend ran out of fuel before but always had no prolem starting back up, what should i do,it cant be the cad cell because i cant start the motor i need some help asap thank you!!!!! - Harvey 3/12/12
If really NOTHING happens, then your system has lost electrical power.
If the burner motor turns on but the burner won't ignite, quite possibly if the burner won't start and run it's because someone needs to bleed air from the fuel line; also when a system has been shut down for a long time it makes sense to change the filter, fuel unit screen, and to inspect, clean, and if appropriate change the oil burner nozzle, then check air settings and flame smoke level.
Question: thermostat calls for heat but nothing happens, how do I test the safety switch?
Eventhough I have the thermostat calling for heat my furnace still hasn't fired up. Is it possible that the (R8184G) not sending the signal or needs replacing? Is there anyway of testing this switch? - Russ 11/11/12
Yes as in the article above
Question: flame sensor keeps tripping, service tech says cleanout is needed
so last winter we had a power outage, all was well until then. After, the flame sensor would trip once and a while, then got progressively worse. I've replaced the sensor, and the controller, but the issue remains. If I short the sensor (after ignition) the system runs. I've cleaned the sensor, thinking it was fouling, but if I move the sensor to a viewing port (holding it in place) it appears to work fine. The port where the light comes in appears to be clear. We did have a service person come out shortly after the initial issue, but he said "I don't know, I can do an annual service, maybe it will help" - nope. Short of replacing the furnace, I'm stuck. - Gunter 12/14/12
Questions & answers or comments about cad cell relay safety controls on oil burners
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.