Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
AIR HANDLER / BLOWER UNITS
AIRBOUND HEAT SYSTEM REPAIR by WATER FEED VALVE
BACKDRAFTING HEATING EQUIPMENT
BACKUP HEAT for HEAT PUMPS
BLOWER FAN OPERATION & TESTING
BOOKSTORE - InspectAPedia
CIRCULATOR PUMPS & RELAYS
CONVECTOR HEATERS - HYDRONIC COILS
COOL OFF HEAT, Thermostat Switch
DEFINITION of Heating & Cooling Terms
DIAGNOSTIC GUIDES A/C / HEAT PUMP
DIAGNOSE & FIX HEATING PROBLEMS-BOILER
DIAGNOSE & FIX HEATING PROBLEMS-FURNACE
DUCT SYSTEM & DUCT DEFECTS
ELECTRIC HEAT, DIAGNOSIS, REPAIR
ELECTRIC MOTOR OVERLOAD RESET SWITCH
ELECTRICAL POWER SWITCH FOR HEAT
FAN, AIR HANDLER BLOWER UNIT
FAN AUTO ON Thermostat Switch
FAN, COMPRESSOR/CONDENSER UNIT
FAN CONVECTOR HEATERS - HYDRONIC COILS
FAN LIMIT SWITCH
FLOODED HEATING EQUIPMENT REPAIR
HEATING LOSS DIAGNOSIS-BOILERS
HEATING LOSS DIAGNOSIS-FURNACES
HEATING SYSTEM INSPECT DIAGNOSE REPAIR
LOW VOLTAGE BUILDING WIRING
LOW VOLTAGE TRANSFORMER TEST
MANUALS & PARTS GUIDES - HVAC
NO HEAT - BOILER
NO HEAT - FURNACE
ODORS FROM HEATING SYSTEMS
OIL FILTERS on HEATING EQUIPMENT
PULSE COMBUSTION HEATERS
RESET SWITCH - Heater Primary Control
RESET SWITCH BROKEN - Quick Repair
RESET SWITCH - ELECTRIC MOTOR
Reset Switch - Stack Relays
STEAM HEATING SYSTEMS
THERMOSTATS, HEATING / COOLING
THERMOSTATS, WATER HEATER
THERMOSTATIC EXPANSION VALVES
Heating aquastat repair: guide to diagnostic troubleshooting for heating boiler aquastat controls: this article describes common operating problems with heating system aquastat controls and how these troubles are diagnosed and fixed. We discuss aquastat problems such as improper adjustment, improper wiring, and relay buzzing or failures.
Green links show where you are. © Copyright 2013 InspectAPedia.com, All Rights Reserved.
If you have not already done so, we suggest reviewing the basic operation of a heating boiler aquastat described at AQUASTAT CONTROL and then see AQUASTAT HI LO DIFF SETTINGS to be sure your control has been set properly.
Question: are there re-built primary controls for boilers?
i had an issue with my boiler , i figured it out it was my aquastats l8124,any icalled my local place and was told a used one was 190.00 rebuilt?? i was told by another place there are no rebuilt aquastats.help!!!!!!
Some heating equipment suppliers can provide re-built as well as new primary controls. The folks who told you there are no rebuilt aquastats - well I'm not sure if that's because they didn't know or they didn't sell.
Question: Buzzing sounds from heating controls
When my oil burner is starting up I hear a loud buzzing from the boiler room.
Reply: check for a bad relay or a relay that is being impeded by the control cover
Buzzing noisy aquastats, also any other heating controls that use relays, such as some cad cells, stack relays, and circulator relays: if you hear a buzzing sound coming from your aquastat check to see if the control cover is pressing down on one of its relays. Details, photographs, and an explanation are at HEATING SYSTEM NOISES.
Also check for a bad relay in the control. Often a failing relay unit will buzz in a heating system control.
Question: Boiler won't run: when one of my three thermostats calls for heat the circulator runs but the boiler does not
I have a three zone hot water baseboard heating system. I have three zone valves and only one circulator pump. My zone valves are made by honeywell and I believe they are the newer version. When I raise the thermostat (upstairs zone) I can hear the circulator pump kick on, the switch on top of the zone valve is in open position and I can hear a click come from the boiler.
The problem is that the boiler never comes on to heat the water to a sufficient temperature. When I put my hand on the pipe directly coming out of this zone valve the it is warm at best. My baseboards upstairs never really get that hot and are unable to raise the temperature in the upstairs of the house. When I operate the other thermostats in the other zones of the house, the furnace kicks on and heats the the water to temperature. What could be causing the furnace to not kick on in the in the one zone? - Joe.
Reply: from reader Joe P.
If it is only in the one zone you describe: it may be that the boiler is up to temperature and does not need to "kick on". Observe the temperature on the gauge. Small loops/zones do not take the heat away as fast. Also, there could be blockage. I have also seen in homes that set the thermostats to low, that freezing occurs in the loop, and thus, poor heat output. You also may have air in the lines which will have to be purged. Turn down t-stat to lower temperature so that all heating goes to the troubled loop and see what happens.
Clarification: Turn down the t-stats to the two other loops (that are working) so that all heat goes to the troubled loop that you have activated (via t-stat for troubled loop).
Joe, from your description we can exclude the case that the boiler does not run because it's already up to temperature - since you say that you feel no heat in the problem circulator piping and baseboards. We like Joe P's advice to see what happens when you turn down or up thermostats to the other zones. Here are more diagnostics:
Heating zone air bound or stuck zone valve: Joe P. refers to a possible blockage in the problem heating zone. Indeed if the zone is air-bound (see AIRBOUND HEAT SYSTEM REPAIR by WATER FEED VALVE) or if the zone valve motor is itself stuck (see ZONE VALVES) then even though the system circulator runs, it never pushes hot boiler water out into the problem heating zone and therefore it never pushes cold water back from the problem heating zone into the boiler where that cooler water would cause the boiler to turn on.
Question: Boiler sometimes won't run": some of my zone thermostats call for heat, the circulator runs, but the boiler won't come
When one or sometimes two of my three heating zone thermostats call for heat, the circulator runs, but for two of the zones, the boiler won't come on until the third zone thermostat is also calling for heat. - DF
Reply: check for a bad control, switch, or relay
This problem could be due to a wiring error or a control problem, as we detail below.
Burn-up on Honeywell Type L8182A, C L8151A Aquastat control board leaves one or two heating zones inoperative
We recently observed the symptoms, debugging, and solution to a similar no-heat in one zone problem. The zone was not air bound. Three thermostats control three individual zone circulators (Taco brand).
The thermostat for zone 3 in a house would call for heat, trip on the circulator, but the boiler would not turn on unless one of the other zones was calling for heat.
The second service tech (from Bottini Fuel, Poughkeepsie, the first fellow said he couldn't see anything wrong), traced the problem to a burned-out circuit on the aquastat control board. We replaced the aquastat and indeed now any thermostat that calls for heat can both turn on the circulator and if appropriate (based on temperatures at the boiler) turn on the boiler's oil or gas burner when it should.
Our photo of this very Honeywell L8124A aquastat control circuit board, with the wires removed, shows brown burn marks around the ZC terminal on the device. (Photo above left). Aside from more sophisticated circuit testing, you might spot this kind of trouble by simple visual inspection of electrical controls and components. Nothing should look "burned-up".
Watch out: a mis-wired multiple zone or multiple circulator pump system can also prevent one or more of the zones from operating correctly. So can a mix of different brands of zone valves that require different wiring.
Question: temperature difference between on and off too great
I have a 17 year old Rheem boiler which works just fine. However the temperature differential between on and off has become too great despite my setting the thermostat to 5 degrees. It is time for a new thermostat, but I don't know what to buy.
The cover on my thermostat says honeywell aquastat type l8100. eco thermostat. The body says L4005A2080. another part of the body says C0704. I have a blue and white wire to connect to the gas control. There is one bare copper wire going from the center of the thermostat screw on to the left side. That's all the description I have. - Alan 8/21/12
take a look at our room thermostat troubleshooting information at THERMOSTATS, HEATING / COOLING - it would be a shame to replace equipment when all that was needed was to blow or vacuum dust off of the existing unit.
Question: Boiler will run but the circulator pump(s) do not ever start.
I finally figured that none of the circulators is running. Because there are three circulator pumps and circulator relays, each controlled by an individual wall thermostat, it seems unlikely that all of them are bad. What should I check? - Charlie G., Calais, Maine.
Reply: check the aquastat control settings for crossed or reversed HI LO controls, then check primary control relays
The photo (above left) illustrates Charlie's aquastat with improper settings for the HI and LO. The HI is set to 180 and the LO is set to just under 200!. Sorry Charlie G. but that's not going to work right.
We have found this problem lots of times when a homeowner or someone else messed around with the HI, LO, and DIFF settings on the aquastat without having a good idea of what those dials do. Aquastat manufacturers such as Honeywell make clear that
If you "cross the controls" - that is, if you set the LO to a temperature that is less than 20 degrees lower than the HI setting, you have basically locked out the circulators.
The oil burner runs, but the LO control is preventing the circulator from coming on. Take a look at the definitions of HI and LO above and this will be more obvious.
Our photo immediately above shows settings that OK - the HI is set to a little over 180 and the LO is set to 160.
Question: my heating boiler won't start
this morning the boiler was not heating. It worked very well during the night. No light in the furnace. I turn off and turn on the gas igntion and nothing happened. What can be the problem? has the damper related to this issue? I change the button from one side to another side and nothing. Also, how can I switch on the spill gas? I think that the problem is the sensor, because it was smoke near the boiler area and maybe the sensor shut off the gas but I do not know where is it. My boiler is UTICA model. - Anon 11/7/12
Anon, with just the information you state, I'd start at the beginning of our no-heat for boilers, see DIAGNOSE & FIX HEATING PROBLEMS-BOILER - troubleshooting. Indeed there could be a bad flue gas spill sensor, but I wouldn't start there.
Question: Indirect fired water heater operation when a tankless coil is also available
I have a strange config. My DHW tank is a zone (tank was added after the fact), but only triggers the LO setting, so it doesn't get the the hotter water that my heating zones get. To complicate things, the water still passes through the tankless and the "Temp-A-Rator" mixing valve.
So, in effect, I pre-heat my hot water. Bypassing the tankless would be expensive and I guess I'd need to then have the tank wired so that it triggers a higher water temp (additional aquastat?). I also don't understand this [apparently obsolete] mixing valve. Is it manual? Should I replace it? Ok, I'm rambling. Would appreciate any and all thoughts. - Chris - Chris 5/10/12
When domestic hot water is made by a separate tank heated by a zone on the heating boiler, we call that an indirect-fired water heater system. The LO and DIFF settings have nothing to do with that water heating method - the LO and DIFF make sense and are used when there is a tankless coil in use.
The heating zone, control, and circulator pump (or zone valve) that heats your separate hot water tank just looks like another heating zone as far as the heating boiler and its controls are concerned. Hot water from inside the boiler itself circulates through a heating coil in the bottom of the hot water tank in response to a thermostat on the hot water tank.
But if a heating boiler uses a tankless coil as a pre-heater or post-heater for the water entering the hot water tank, then indeed you've got two water heating methods in parallel - which can be confusing. In fact, you can think of them separately, and controlled separately.
Take a look at the water piping that brings cold water from the building water supply into your hot water heating tank. If the cold water runs first through the tankless coil, then yes you are pre-heating water entering the hot water heater tank. Some plumbers pipe in the opposite direction, that is, allowing hot water leaving the hot water tank to pass through the tankless coil for a boost that takes effect when the hot water in the separate tank is nearly used up or is cool.
See INDIRECT FIRED WATER HEATERS for details of how these systems work.
Question: L4081B aquastat doesn't seem to be behaving like it should
Great information here. I had to read a few times to put it all together, but I think I finally got it. I have an L4081B aquastat and it doesn't seem to be behaving like it should.
If there is no call for heat but the boiler cycles on, I'd expect that ON cycle to be driven by the LO and DIFF controls just as you describe.
Question: my heater won't turn off; replacing the thermostat did no good, what do I try next?
my heater just don't stop heating my house i tried a new thermostat what should i try next please - Frank Carr 11/12/2012
Reply: things to check when the heat won't turn off, & some Safety Warnings
Buddy said: Frank, You may have a problem with your boiler controls or a check valve in the hot water piping system.
Take a look at "Guide to Heating System Boiler Check Valves & Flow Control Valves" [found at CHECK VALVES, HEATING SYSTEM ] to see if this information helps you determine if a check valve is sticking open. In any case, you will probably need the services of a service technician to check out the controls or a plumber to replace a check valve if it is sticking open. - Buddy 11/12/2012
Daniel (Moderator) said:
Question: how do I find a replacement Aquastat for a L8024B1048 (triple aquastat) ?
I have a Gas Hydrotherm 86000 Model R108 furnace. I cannot find a replacement Aquastat. I have called Hydrotherm they say call Honeywell. Honeywell say its discontinued they have no information for a universal replacement.The hot water tankless is disconnected as I have a gas hot water tank.
I heat most of the time with a coal stove so the only time the furnace runs is if I go away for a few days. I'm 73 retired firefighter (36 yrs) . The furnace is in good shape hate to replace just because cant find aquastat. Do you have any Ideas for a replacement universal aquastat relay.attached is all I have on unit.
Any suggestion is welcome.I usually have to clean contacts to get it running when I use it. - J.M. 12/28/2012
Photo (left) of a Honeywell L8024B & the wiring diagram below were provided by reader J.M.
Reply: parts substitution & replacements for the Honeywell L80241048B,D triple aquastat
Contact your local heating supplier with the part number (inside the cover check that you correctly identified your Honeywell Aquastat as the Honeywell L8024B1048 (triple aquastat, also the L8024D) - that's probably all they need) from the original aquastat; there are tables of substitution and changeout part numbers and names for just about every control ever made. I'm sure they'll be glad to help you select the correct one. In fact I'm confused that you report not obtaining help from Honeywell themselves; we have usually found that the company's technical support personnel to be informed and helpful.
I'm not sure about the L8024B series information you've received, and I understand that there is not necessarily "universal" replacement for all applications, but in fact the Honeywell L8124 series (AQS8124B1039 or the Honeywell Multi Function Aquastat L8124B1039) can substitute for many of the controllers in the L8124 and L8024 aquastat line.
We regularly see that controller advertised as replacing the Aquastat models with part numbers L8124B1039, L8124B1021, L8024B, and L8024D. indeed it might work for you as well. Also check out the Honeywell, the L7224U Universal Aquastat controller.
Be sure to review your control and how it was used with your heating service supplier;
I would be quite surprised if they couldn't immediately give you the part you need, but if you don't have success let us know and we will research further.
The wiring schematic for the Honeywell L8024B triple aquastat (thanks to your photos) is reproduced at left.
Your aquastat, the L8024B controller, also sold in the L8024D model, is being used in your case to control a Hydro-Therm natural gas-fired heater and possibly a circulator pump; often a review of exactly how a controller is being used in a given application can make more clear just what replacement aquastat will work best.
If you cannot find a suitable replacement control such as the 8124B 1039, we may find a "new old stock" (NOS) L8024B,D, etc. series control available from a reseller.
Reader question: Honeywell R8182D replaced three times
My Honeywell R8182d 1111 keeps tripping the red safe button. This is the 3rd unit installed, they seem to last about 5 years and quit. I installed a new aquastat control about two weeks ago. It worked fine for 2 days, then went away for 4 days and when we returned the Beckett oil burner afg was off.
Iif i knew what to replace I would. I'm concerned about the heating season. We use the furnace for heating our hot water ,Utica external 40 gal tank, (not tankless). can you help with your expert advice? thank you, J.& J. 8/24/2013
The reader ultimately let us know that the new control had been defective. Details about this case are now at HEATING SERVICE SNAGS
Reader Question: my bad heating system aquastat only runs after we give it a good smack
Thank you for a wonderful and informative website! We have an boiler for our radiator system in our home but it's not starting up unless we smack the cover of the aquastat repeatedly ... and then it clicks a few times the burner flames eventually starts up - after a few smacks. If you can provide any insight to our problem, we'd greatly appreciate it. Thank you, J.D. 11/27/2013
Reply: smacking the aquastat - things to check: loose wires, buzzing, overheating, burning, damaged aquastat control
Nice question. Where is the aquastat mounted? On the boiler itself or remotely say, on or next to the oil burner? I ask because part of diagnosing why smacking or tapping on an electrical control does something involves figuring out what you may be jiggling in the control when you rap, tap, or smack it.
I suspect a loose wire, loose connection, failing aquastat relay, or possibly a bad connection between the aquastat's temperature sensor and the sides of the well into which the sensor is inserted.
Of course there may be some other issue we haven't thought-of - something that would be immediately apparent to an astute heating service technician.
Start by turning power off (watch out for fatal electrocution hazards) and checking that all of the connections are tight. Don't forget to check the thermostat wires too. Also listen for buzzing relays in the aquastat.
In the aquastat photo above left I'm pointing to a relay that may be buzzing if it's failing.
While the cover is off of the control, look with care for evidence of overheating or burning around any of the wire connectors or contacts At below left are burn marks around the lower-left power-connection screw.
In my photo at above right I'm pointing to burn marks on the printed circuit board of a Honeywell L8124A aquastat on the reverse side of the oveheated wire connection terminal shown above-left. This aquastat was behaving erratically for a year or more before a sharp heating service tech from Bottini Oil (Poughkeepsie) spotted the damage. We replaced the control.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the search box below to ask a question or to search the InspectApedia.com website.
Ask a Question or Enter Search Terms in the InspectApedia search box just below.
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.
We provide links just below to several aquastat installation, setting, and adjustment documents in response to reader requests and comments that people sometimes have difficulty finding this information. But readers looking for specific aquastat control information should always first try the control manufacturer.