Questions & answers help diagnose and fix water pump short cycling on and off:
Frequently asked questions about rapid on-off cycling of a well pump or water pump or its pressure control switch.
This article series explains how to diagnose all of the various causes of well pump short cycling - what causes the well pump to run too often or to turn on and off too rapidly.
Green links show where you are. © Copyright 2017 InspectApedia.com, All Rights Reserved.
Short cycling of a water pump which is defined at SHORT CYCLING WATER PUMP means that the water pump or "well pump" turns on and off too rapidly or too frequently when water is being run in the building.
If this is the problem with your water pump, this article (below) describes the most common causes of this problem.
The most-common cause of pump short-cycling is loss of air in the water pressure tank.
On 2017-03-06 18:21:37.624343 by (mod) - telegraphing pressure control switch"telegraphs" - I'm not sure what you mean, but if you 're saying that the pressure switch is clicking continually, the cause is probably one of those listed in the article above - starting with a waterlogged pressure tank.
On 2017-03-06 18:09:05.934506 by TomMy well and pump are 1600 ft from the house. the pressure switch is in the well casing and i have a buryied pressure tank 2 ft from the pitless adapter. i also have another pressure tank in the house 1600 ft away. the problem is the pressure switch continualy telegraphs when ever you are running water. how can i slve this problem ?
On 2017-01-29 01:03:13.111864 by JACK
I have a brand new X-trol wx-203 and my system is still short cycling. When the pump kicks on, it runs for about 3 seconds. Then it drops to the 30 psi turn on pressure in about 35 seconds.
Again runs for 3 seconds to get to the 50 psi turn off. It consistently runs like this. This is a 30 gallon pressure tank shouldn't it take longer than that to kick on.
On 2017-01-25 23:51:48.581089 by MarlonPump don't cut off
On 2017-01-25 23:50:36.894108 by MarlonWhy my Haitun water pump clicks on and off so rapidly
On 2016-11-29 14:01:37.131169 by (mod) - water flows back into cistern after pump stopsCheck for a bad foot valve in the well
On 2016-11-29 06:13:06.387853 by JaredMy pump operates normally, but once the tank is filled with water and the pump shuts off, the water is pushed back into the cistern and the pump turns back on when it reaches the proper low end pressure.
On 2016-11-27 22:39:29.888330 by (mod)IF your tank uses an internal bladder AND IF the air valve is mounted on the tank (not on water piping) THEN yeah, if water comes out that suggests a leaky or torn internal bladder.
On 2016-11-27 21:00:32.492492 by RickI checked the pressure in the bladder tank. When I checked it was 43psi but water came out as well. Shouldn't it only be air?
On 2016-11-08 15:11:47.160646 by (mod) pressure drops after pump turns offJohn:
On 2016-11-08 12:27:47.909815 by johnI have lotsa water but immediately after pump shuts off at 50 it drops to 30 n refills my tank, this happens a few times every minute. And no water is running anywhere in the house. Where's goin,bad check valve? Or is this a bad bladder?
On 2016-10-22 19:05:02.455163 by (mod)Anon
On 2016-10-21 16:45:47.261575 by AnonymousMy pump keeps coming on and off all the time even at night when everybody is in bed
On 2016-10-12 22:14:47.678562 by ToeverMy well pump was short cycling. Changed the switch and gauge. Seemed to help except, when the pump cut in the hose and well cap would jerk and jump violently. Pressure jumped instantly to 70 and cut out. Today I checked pressure in tank - Cut in is 40 psi and the tank was 45 so I dropped it to 38. Still short cycling. Stitch is 40/60. I would empty the tank and start over but afraid of the way the pump will react (jumping violently).
On 2016-09-28 15:34:16.985890 by (mod)Anon: your well pump is short cycling as described in the article above.
On 2016-09-28 15:33:54.989863 by (mod)David:
On 2016-09-28 07:21:04.851533 by Anonymouswater pump runs in a short cycle. if i open the faucet the pump will in short and off like pulse
On 2016-09-04 17:16:42.310561 by David
Yesi have a question because the well guy I had come out and look at it says the well is dry. I don't beleave that reason being the water will work I can use about 45 to 50 gallons and then it quiets working
I can go flip the breaker and wait about 30 to 45 min and flip breaker back on and poof I have water again but I use 45 to 50 gallons it will cut off so I left it on this time did not flip breaker another water will flow through the sink and stop for about 5-8 min then the water will flow again and cut off it will burn my pump up so I keep going to flip breaker so it want burn my pump up does any one have a suggestion
On 2016-09-03 18:19:38.727740 by (mod)If water comes out of an air valve on the tank itself then the tank is waterlogged or if it's a bladder type tank the bladder has probably leaked or burst.
On 2016-09-03 08:55:30.066546 by AnonymousMy pump runs for about 2 seconds and then shuts down. It turns on about every minute or so. Can I test the air pressure by pushing the pin on the air inlet valve? If water comes out is that an indication of no air pressure? And should air be leaking out when I press that pin? The tank does build up pressure if no water is used for awhile. The short cycles will eventually build pressure, but obviously doesn't hold because the pump will only run for about 2 seconds, regardless if the water is running or not.
On 2016-07-05 16:39:43.866545 by (mod)If you are pumping into a closed system, that is there are no fixtures running water and no piping leaks, then if the pump can't reach cut-off pressure I suspect that the pump impeller is clogged or damaged.
On 2016-07-04 23:32:22.950801 by David WithamPump system feeds camp from lake (non-potable). System 40 yrs, old been updated in Spring often. This year could not get to raise pressure to 50. Bought and installed new pressure switch, gage and bladder tank; still can not get pressure above 26 lbs. Pressure drops to 0 them pumps again to 26 and recycles.
On 2016-06-30 15:43:14.910132 by AnonymousCan iflush pump and 1line pipe by taking hose from house to flush and prime pump at the same time
On 2016-06-21 00:16:22.592314 by (mod)5-20 years - check the water tank warranty;
On 2016-06-20 22:27:17.868069 by dave wolfendendoes have an idea of the life span of air tank with a bladder replaced the pressure switch . switch will not hold if i hold the lever on the side it comes on and shuts right off any ideas would be helpful
On 2016-05-23 20:57:39.846889 by (mod)Check for
On 2016-05-23 16:09:43.248639 by Don1/2 HP Water pump Goulds New switch 30/50. Pump kicks on and then goes off and then a minute later kicks on and goes off
On 2016-05-22 05:34:01.065546 by ChrisI installed a new 1/2 horse shallow well pump and 20 gallon tank. Water is not from a well but gravity flow from a 10,000 gallon elevated tank 300 feet away. The pump runs fine until it builds up pressure to 55 lbs and then starts to turn on and off rapidly until it blows the breaker if not shut off. Replaced the new pressure switch. Lowered the tank pressure to 28 lbs of air as reccomended by the pump instructions. No luck. why won't it stay off when pressure is reached?
On 2016-05-10 19:01:43.170685 by (mod)Anon:
On 2016-05-10 19:01:25.871978 by (mod)Re-posting a comment made on an older .htm version of this web page
On 2016-04-11 20:46:02.255072 by (mod)Lonnie,
On 2016-04-08 23:33:27.255258 by LonnieMy water in my house is getting cold then hot when we take a shower we have a well and we have never had this problem before anyone have a answer to this problem?
On 2016-03-13 23:54:59.870842 by (mod)Kristina the pump gauge should not contain water - it's leaky and needs to be replaced. Watch out: left in place the leak could become worse and could enter the building. Basically you remove water pressure from the system - you don't have to drain it dry if you don't mind getting wet and spilling a little water - then you prepare a new gauge, then remove the old one and put in the new one in the same spot.
On 2016-03-13 22:43:30.198308 by KristinaHi, my pump gauge is full of water. It's new. The pump is not cutting in properly. Not much water. What can I try to fix this.
On 2016-02-29 21:18:09.124266 by AndréI have a 80 liters tank horizontal with a bladder type.
On 2016-02-06 16:02:49.144362 by (mod)Ron,
On 2016-02-06 00:13:51.915878 by RonHad a new jet pump installed about 1.5 years ago. All was well until about a month ago. Everytime we turn on a faucet, use the washer, flush, etc., the pump comes on for a few seconds. Never happened before. Used a tire pressure gauge and the psi on the old WELL-X-TROL reads 45. Any ideas before I call the plumber.
On 2016-01-07 00:53:52.078143 by (mod)John, unless the water tank is a special model it is not intended to be installed on its side and doing so makes failure likely. It's possible that the internal bladder of this tank has been damaged or burst.
On 2016-01-07 00:07:38.144624 by John MillerI have a friend who has a weltrol tank on it side outside and there is an air leak ..it is also short cycling...it was installed laying down ,,not sure how long its been that way atleast 4 years ....Could it be a hole in the tank or bad bladder it is a weltrol wx 202
On 2016-01-06 10:56:43.570059 by (mod)When the water tank is a type that uses an internal bladder, you can't let the air out of the tank unless you do so through the air valve on the tank top. So if the pump is short cycling the problem may be that the bladder is burst or stuck to itself in the tank. Sometimes we can push the bladder open again by briefly pushing the pressure up a bit at the tank - but take care not to exceed the maximum rated pressure the tank can contain or it could burst and kill someone nearby.
On 2016-01-06 00:43:56.449439 by CourtneySorry for so many of these it is a Well-x-troll WX203.
On 2016-01-06 00:39:19.064922 by CourtneySorry is cycles 4 times for every time the toilet is flushed.
On 2016-01-06 00:18:26.754755 by CourtneyLast week we replaced both of our hot water tanks. My husband let ir out of our well tank accidentally. I noticed the well short cycling. So we added air to 28 psi we have a 30/50 switch. But it is still short cycling if we flush a toilet it clicks on/off at least twice. Any help would be greatly appreciated.
On 2016-01-03 16:46:07.932562 by (mod)Sharon:
On 2016-01-02 01:13:37.750659 by SharonOUR pump kicks on about every 20 seconds when we are running water upstairs in the bathroom...including sink, bathtub and toilet...this does not happen in the laundry room or kitchen..this is a tri level.,can you help
On 2015-12-08 00:02:05.746952 by (mod)Joey: in the article above we list common causes of short cycling water pumps; the most usual cause is loss of air charge in the pressure tank.
On 2015-12-07 23:10:14.477935 by joeySorry didnt put my name in last comment.
On 2015-12-07 23:09:13.909107 by AnonymousOh yea this is a new 3/4 horse submersible pump with new check valve, 30/50 pressure switch, and bladder tank with 28 psi.
On 2015-12-07 23:06:53.976899 by JoeyPump is short cycling constantly while building pressure and my pressure switch is about 25 feet from presssure tank. Could this be the problem?
On 2015-09-19 17:48:08.559814 by (mod)IF the pump is turning on and off every few seconds it is short cycling - the common causes with links to repair procedures are in the article above. Check first for a waterlogged pressure tank.
On 2015-09-19 17:25:28.684161 by LarryI replaced water pressure valve switch and now when the water is running it kicks on and off until the water is cut off.What do I need to do to fix this issue? Thanks
On 2015-09-19 13:38:00.738884 by AnonThanks for this information.
On 2015-09-15 20:39:47.876975 by ValarieHi,
On 2015-09-15 05:11:31.367021 by nylanHi.
On 2015-08-11 21:21:10.019688 by (mod)Very good going, Dave, that problem can be tough to find.
On 2015-08-11 20:38:10.302277 by AnonymousThank you I checked the gate valve and found the gate had come off the stem. I replaced it with a ball valve, No more problems.I will be telling my frends about this site.
On 2015-08-10 21:59:13.697533 by (mod)Dave:
On 2015-08-10 18:52:25.004002 by DaveMy water pump is cycling on and off,every 2-3 sec. when a tap is opened. I have replaced the switch with a 20-40 psi switch and checked that the pressure tank ( bladder type ) has 18 psi in it.. any ideas would be helpfull. Tks
Ran fine for quite a while but is now constantly short cycling,I removed the bladder tank and blocked off the fitting again ran fine for a while but now back to short cycling again. Was it a mistake to pressurise directly to the house and shoul;d I reinstate the header tank?
You need either a pressure tank installed to prevent short cycling of the pump, or you need a special hydropneumatic pump control that combines the pump with a pressure switch - shown at left. This is essentially is a switch that can turn a pump on and off when needed without short cycling.
In our photo at left that silver domed gadget above the red pressure-sensitive water pump works with the silver micro-pressure tank to provide a boost to water delivered (typically) from a rooftop water tank. No water pressure tank is used with this system.
These systems are typically used as water pressure boosters and not as the primary water source pump. The little silver dome dome is a miniature pressure tank itself, pre-charged to 7 psi and the whole system is calibrated to avoid short cycling of the water pump.
This equipment is distributed by bombasrowa.com and is widely distributed in Mexico where often we want simply to boost the pressure delivered by a rooftop water storage tank. Keep in mind that the total flow rate and building water service from this sort of system is of limited capacity.
Often we see pressure sensitive water pumps or inline pump controllers used with rainwater harvesting systems and cisterns or rooftop water tank systems serving small buildings. Submersible models of these pumps are also available for installation in the water tank.
Similar devices are sold by Aqua Group in India: the Aquatex APS hydropneumatic system. This approach floats a very small internal-bladder type pressure tank atop the water pump. Other models are used in marine applications such as the Shurflo and the Jabsco.
A third option might be to use an in-line pump controller. An inline pump controller can be added to an existing system and works with most water pumps. The inline pump controller senses pressure changes similarly to the pressure-sensitive water pump system we described above, and turns the pump on or off as needed. Some inline pump controllers include an additional sensor to shut off the pump if the water supply is lost, thus protecting the pump from damage.
Pressure sensitive pump references & sources
(July 5, 2015) Peggy said:
we just had a new pump and pressure switch on Saturday, it is doing the same thing. It will run for so long and then just stop, no water at all but when it comes back on, it full force no trickle....any ideas?
If we are sure that the pump is good and it runs but no water is delivered the pump may not be primed properly. If you leave it running it can be ruined - even though new.
Then see if there is a disconnected or leaky well pipe or there is no water in the well. Perhaps a blocked well screen or foot valve could also be at fault.
10 Aug 2015 Dave said:
My water pump is cycling on and off,every 2-3 sec. when a tap is opened. I have replaced the switch with a 20-40 psi switch and checked that the pressure tank ( bladder type ) has 18 psi in it.. any ideas would be helpfull. Tks
Watch the pressure switch. It's possible that water is not entering the tank or that your tank is waterlogged and includes a pressure gauge that's stuck, giving a false reading. Gently rock the tank (don't break any connections) and you can usually tell if it's empty (it'll be light), and similarly, if no water is entering the tank its pressure and temperature and weight wont' change.
If you are dead certain the pressure tank accepts water and is being pumped up I cannot imagine why you'd have sort cycling every 2-3 seconds. I'd be looking for an obstruction that lets water into the tank such as a bladder stuck on itself or a nearly closed or blocked valve.
This article series describes the most likely water pump short cycle causes include the following, listed more or less in the order of probability:
Our complete diagnostic list of all known causes, diagnostic steps, and repair procedures for well pump short cycling is
at WATER PUMP SHORT CYCLING DIAGNOSIS TABLE
If you are not sure what "water pump short cycling" means or how it is recognized, see
SHORT CYCLING WATER PUMP.
Intermittent water pump cycling which is discussed at
INTERMITTENT WATER PUMP CYCLING When No Water is Running means that the water pump comes on for no apparent reason.
Loss of water pressure means that the pressure with which water enters a plumbing fixture has become too slow, or is sometimes too slow or weak in water flow rate, or water flow may stop entirely.
See WATER PRESSURE LOSS DIAGNOSIS & REPAIR
Continue reading at WATER PUMP SHORT CYCLING CAUSES or select a topic from closely-related articles below, or see our complete INDEX to RELATED ARTICLES below.
Or see WATER PUMP SHORT CYCLING FAQs for diagnostic questions that explain why the pump cycles on and off quickly
Or see WATER TANK AIR, HOW TO ADD
Or use the SEARCH BOX found below to Ask a Question or Search InspectApedia
Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website