Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
AFUE DEFINITION, RATINGS
AGE of HEATERS, BOILERS, FURNACES
BACKDRAFTING HEATING EQUIPMENT
BACKFLOW PREVENTER VALVE, HEATING SYS
BANGING HEATING PIPES RADIATORS
BOILER CONTROLS & SWITCHES
BOILER LEAKS CORROSION STAINS
BOILER NOISE SMOKE ODORS
BOILER OPERATING PROBLEMS
BOOKSTORE - InspectAPedia
BTU USAGE MONITORS
CHEMICAL TREATMENTS for BOILERS
CHIMNEY INSPECTION DIAGNOSIS REPAIR
CIRCULATOR PUMPS & RELAYS
DEFINITION of HEATING & COOLING TERMS
DIAGNOSE & FIX HEATING PROBLEMS-BOILER
DRAFT MEASUREMENT, CHIMNEYS & FLUES
DRAFT REGULATOR, DAMPER, BOOSTER
FILTERS, OIL on HEATING EQUIPMENT
FIRE SAFETY CONTROLS
FLOODED HEATING EQUIPMENT REPAIR
FLUE VENT CONNECTORS
FREEZE-PROOF A BUILDING
FUEL OIL TYPES & CHARACTERISTICS
FUEL UNIT, HEATING OIL PUMPS
GAS BURNER FLAME & NOISE DEFECTS
GAS PIPING, VALVES, CONTROLS
GAUGES ON HEATING EQUIPMENT
HEATING COST SAVINGS METHODS
HEATING LOSS DIAGNOSIS-BOILERS
HEATING OIL PIPING TROUBLES
HEATING SYSTEM INSPECTION GUIDE
HEATING SYSTEM NOISES
HIGH EFFICIENCY BOILERS/FURNACES
GAS LP & NATURAL GAS SAFETY HAZARDS
MANUALS & PARTS GUIDES - HVAC
MOTOR OVERLOAD RESET SWITCH
NO HEAT - BOILER
NOISE, HEATING SYSTEMS
ODORS FROM HEATING SYSTEMS
OIL PUMP FUEL UNIT
PUFFBACKS, OIL BURNER
RELIEF VALVE, TP VALVE, STEAM BOILER
RESET SWITCH, HEATER PRIMARY CONTROL
RESET SWITCH, ELECTRIC MOTOR
RESET SWITCH, STACK RELAY
SAFETY, HEATING INSPECTION
SAFETY RECALLS CHIMNEYS VENTS HEATERS
SOOT on OIL FIRED HEATING EQUIPMENT
SPILL SWITCH, FLUE GAS DETECTOR S
STACK RELAY SWITCHES
STEAM HEATING SYSTEMS
THERMOSTATS, HEATING / COOLING
VIDEO GUIDES: HEATING SYSTEMS
ZONE VALVES, HEATING
A guide to using air bleed valves to get rid of unwanted air in hot water heating systems: fix cold or noisy hot water heating radiators or baseboards.
Here we explain how to diagnose and repair problems with air bleed valves and we describe methods used to remove un-wanted, air from noisy or air-bound hot water heating system pipes, radiators, convectors, and baseboards. We illustrate how to buy and add air bleeders at baseboard elbows using a baseboard tee and air bleeder valves.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Carson Dunlop's sketch (left) shows a common location for the air bleed valve on a cast iron radiator. The advice to leave this valve alone is intended for home inspectors who don't want to risk spilling water on someone's floor or opening a valve to find that they can't close it again. But if your hot water radiator or convector is staying cold even though the heating boiler is running and hot, it may be air-bound and you'll need to bleed out the air.
Why is it necessary to get this air out of heating lines?
Air trapped in hot water heating piping, radiators, baseboards, or convectors makes the heating system noisy with gurgling or bubbling sounds if there is just a little air in the heating system.
But if the volume of air becomes too great, the heating system will simply stop delivering heat to the occupied spaces, some or all of them, in the building. Why? A heating circulator pump is capable of pushing water around in the loop of heating baseboard but is often not capable of overcoming a section of baseboard that contains a large bubble of air. It's necessary to remove such air blocks. If air blocking has been recurrent a previous owner may have installed air bleeders at strategic points.
See AIRBOUND HEAT SYSTEM REPAIR by WATER FEED VALVE if the cold radiator, convector, or baseboard problem seems to affect all of the heating radiation devices on all or part of an individual heating piping loop or zone.
Automatic air purge devices (photos at page top & below) are available and are usually installed right at the heating boiler but sometimes additional ones are needed at higher levels in the building.
The two most common locations for automatic air bleeder valves on hot water heating systems are on top of the heating boiler itself (photo below left), or on a special air-scoop and air purging device found on the hot water heating piping just over or near the heating boiler (photo below right).
Manual air bleeder valves (photo above) can be opened slightly and carefully, to permit air to escape. Some heating convectors may have a tapping closed by a plug (photo at left) where an air bleeder valve can be installed - much more convenient than having to remove and replace the plug itself to get air out of the heating system piping.
[Click to enlarge any image]
As soon as water starts coming out of an air bleeder valve it can be closed.
The most common location for manual air bleeder valves on hot water heating systems are on heating radiators and convector units (every one), and at the ends of heating baseboard sections where there has been a previous problem with becoming air bound.
Identification Photos of Types Hydronic Heating (hot water heat) air vents or air purge valves & where to buy them
We distinguish among several types of heating system air bleeder valves or air vents (in order from left to right):
Where to buy air bleeder valves: see your local plumbing & heating supplier. For a list of air eliminator, air purge, air bleed valve manufacturers & sources
Where to install air bleeder valves:
Question: can I change a manual air bleeder to an automatic one
Can an automatic bleeder be screwed in where the manual bleeder is on my radiator or will i have a puddle of water on my floor when auto bleeder starts working? - Darrell 11/20/12
Yes you can change a manual air bleeder to an automatic one provided you choose a device that works in the position in which you need to mount it.
You are correct to worry about unintended leaking, since most automatic air bleeders require (to work) that their screw cap be left loose. So it makes sense to use these conversions where someone will quickly notice if there is a leak, and to avoid them otherwise. In my OPINION.
Hydronic heating air vents and air purge devices: types, where to buy; How to diagnose and fix heating system noises & air in hot water heating system pipes. Service Procedures to force air out of an air-bound hot water heating system. How to bleed a hydronic (hot water) heating system: how to purge air out of heating system boilers, radiators, baseboards, or piping. What is a baseboard tee, how do they work with baseboard air bleeder valves, how to install air bleeders, vents, purgers.
Continue reading at AIR BLEED VALVE INSTALLATION or select a topic from the More Reading links shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
Please see AIR BLEEDER VALVE DIAGNOSIS
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References