Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
Ask a Question or Search InspectAPedia
InspectAPedia ® Home
CHIMNEY INSPECTION DIAGNOSIS REPAIR
BACKDRAFTING HEATING EQUIPMENT
CARBON MONOXIDE - CO
CHIMNEY COMPONENT DEFINITIONS
CHIMNEY FIRE ACTION / PREVENTION
COMBUSTION GASES & PARTICLE HAZARDS
COMBUSTION PRODUCTS & IAQ
FLAME COLOR, BLUE vs YELLOW COMBUSTION
HOME HEATING SAFETY
Moisture / Frost Damaged Chimney
ODORS & SMELLS DIAGNOSIS & CURE
Safety Recalls, Chimneys, Vents, Heaters
STAIN DIAGNOSIS on BUILDING EXTERIORS
WOOD, COAL STOVES & FIREPLACES
WOOD STOVE SAFETY
How to build or inspect a wood-framed chimney chase: this article describes wood-enclosed metal chimneys, how a chimney chase should be constructed, and how those structures can be inspected for leaks, damage, or unsafe conditions. This article describes how to perform a visual inspection of wood framed chimney chases used to enclose factory-built metal chimneys for safety and other defects. Chimney inspection methods and chimney repair methods are also discussed.
Green links show where you are. © Copyright 2013 InspectAPedia.com, All Rights Reserved. Author Daniel Friedman.
Chimney Chase Construction SNAFUs to Avoid
Our photographs show a typical wood-framed chimney chase constructed to house an insulated metal chimney and/or a Type-B gas vent. The photo at above left shows an incomplete chimney chase with poor workmanship - incomplete installation of housewrap, missing chimney flashing, and who knows what at the chimney top.
Our photo at above right shows vinyl siding has fallen off of the chimney chase, permitting leaks into the structure. Below we show common leaky conditions at the top of a wood-framed chimney enclosure.
The most common defect we find at wood-framed chimney chase ways is an improperly-constructed top flashing that is not sloped to drain properly (above left). Often people try to fix a leak at the the chimney top by smearing on roofing mastic (above right). We find that this is not a durable repair.
A close-look at the top of a mastic-coated wood-framed chimney chase may show that the top is still concave, sloping in towards the chimneys and that the combination of heat and sunlight has dried and cracked the sealant. (Photos below).
Because the top of chimneys is not readily accessible, leaks in this location may remain un-diagnosed for too long, risking insect damage, rot, and mold in the structure below.
Watch out: before buying materials and starting to hammer away at constructing a chimney chase for your home, be sure to check with your local building code officials. A building permit is required in most jurisdictions, and the applicable building codes and inspections are important fire safety checks on your chimney chase design and construction.
Common Specifications & Construction Details for a Wood-Framed Chimney Chase
Our photo (left) shows the remains of a metal chimney passing through the framed chimney chase enclosure as it passed through the first floor of occupied space in a building that suffered severe damage from a chimney chase fire. The factory-built insulated metal chimney was venting an oil fired heating boiler.
How to Identify Common Leak points & Hazards at Wood Framed Chimney Chases
Details of this topic have been moved to a new article found at CHIMNEY SHROUDS. Excerpts are just below.
A "Chimney Crown" as popularly used in the fireplace industry may refer to a decorative top shroud installed atop a wood-framed chimney chase, as illustrated here. Steve Werner, a home inspector and chimney shroud installer with Chimney King , a custom chimney "crown" designer in Gurnee IL, provided us with the following wood framed chimney chase top pans along with comments.
At above right we can see the newly fabricated chimney chase top pan that has been corbelled out to increase its footprint or horizontal size dimensions to accommodate a decorative top shroud.
Contributor & technical review: Stephen Werner General Manager Chimney King, LLC P.O. Box 8 Gurnee, IL 60031 Corporate (847) 244-8860 Fax (847) 244-8694 Email: firstname.lastname@example.org
Frequently Asked Questions (FAQs) about wood chimney chase construction, inspection, hazards, codes, & top terminations or decorative chimney shrouds
Questions & answers or comments about wood-framed metal chimney enclosures: construction, clearances, fire stopping, leaks, safety.
Ask a Question or Enter Search Terms in the InspectApedia search box just below.
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.