Submersible Well Pumps Torque Solutions Stop damage & pump losses due to twisting of the submersible pump
SUBMERSIBLE PUMP TORQUE PROBLEMS & SOLUTIONS - CONTENTS: how to stop the pump from unscrewing itself or breaking well piping due to torque or twist forces when the submersib le pump starts and stos. Submersible Well Pumps for Drinking Water Wells - Problems & Repair Advice.
InspectAPedia tolerates no conflicts of interest. We have no relationship with advertisers, products, or services discussed at this website.
Submersible well pump torque problems & solutions:
Here we explain how to use a torque arrestor & other methods to stop damage to well pump wiring & piping caused by twisting forces as the pump starts.
This article series describes the components of a submersible well pump water system, how the pump, well and controls work, what the well pump components look like, and what they do. We give submersible well pump troubleshooting advice and invite questions. We include definitions of water well and water well drilling terms, the typical capacity of drilled water well pumps, and we include descriptions of methods used to fish materials out of a water well if you've dropped the pipe, well pump, or tools down into the well casing.
Question: how to stop the submersible pump from un-screwing its pipe connections
2016/08/15 Rodney said:
The submersible pump keeps unscrewing itself even after I glued the threaded coupler. I have to pull it out a 3rd time now. How can I make sure this doesn't happen again. Or is there a more serious problem at hand?
It has great pressure and it works great but right about on the 3rd or 4th day the pump quits I'm sure it's the same thing. I'll know for sure when u pull it tomorrow.
Reply: Solutions for submersible pump well piping torque problems: unscrewing the pump, piping breaks, wiring damage, casing damage, lost pumps, lost piping.
I suspect that a torque produced when the pump starts is the cause of this un-screwing of the coupler. The rotating torque produced when the submersible well pump turns on tends to rotate the pump in a direction that un-screws the coupling to the drop pipe. The higher the submersible pump horsepower the greater the starting torque or twist motion forces will be.
This same rotating torque can, if the well piping is not centered in the well casing an bore, abrade the well piping ultimately causing it to break or leak. A well pipe slapping around in the well will also damage electrical wiring descending to the well pump.
Finally, the torque imparted by a starting submersible pump can also twist well piping so that that force along leads to pipe breakage, especially when PVC well piping is used.
Approaches to Handling Well Pump Torque Problems
Well and plumbing experts address the well piping torque problem using several approaches. We discuss these in more detail below.
Keep the well piping centered in the well using spacers like the well pump cable protector shown here. This helps avoid pipe and wire abrasion damage.
Use a torque arrestor at the pump and at intervals on well piping. Depending on where you live, local plumbing codes may require the use of torque adapters on submersible pump installations.
Use welded pipe sections and metal piping to resist pipe breaks and damage
Watch out: If your pump is short-cycling for other reasons such as a waterlogged pressure tank, starting more often than needed, the torque problem will be multiplied, increasing the risk of repeated breaks in well piping.
For high horsepower submersible well pumps, use an electrical controller that slowly spins-up the submersible pump motor to full speed. Watch out: some spin-up controllers may, however, cycle so frequently that that system may itself damage the well pump motor shaft or well piping.
So, Rodney, you may have to use welded iron pipe to resist pipe breakage due to torque forces.
But in the photos above and below I'm showing another possibility that will work on some submersible well pump systems: a rubber pump torque arrester produced by Everbilt (and a number of other suppliers too) and sold at plumbing and building suppliers.
This photo was taken in a New York Home Depot store where the Everbilt Torque Arrestor sells for under $15.00. The part number is 1001 098 335. Everbilt torque arrestors are made in Canada and sold across North America. Similar products are sold in other countries.
This rubber torque arrestor device attaches around the well piping and then is expanded so that its rubber rib is just snug against the interior of the well casing.
The torque arrestor, by pressing against the well casing sides, is designed to absorb and dampen the twisting torque motion imparted by the submersible pump at the start of a pump-on cycle (a similar force may occur at the end of a pump on cycle too).
The rubber torque arrester shown fits inside of well casings from 4" to 8" in diameter. Below we show the submersible pump torque arrestor assembled.
Some wells may need multiple torque arrestors depending on well depth. Here is a slightly edited version of what Merrill Manufacturing™, a manufacturer of torque arrestors says about installing these devices:
The first torque arrestor should be placed no more than 3' above the pump, near the bottom of the well. Use additional rubber torque arrestors at intervals of 75' to 100' along the rising well pipe above the first torque arrestor.
Place the torque arrestor around the drop pipe so that each half is spaced evenly. Install the lower pipe clamp and tighten. Install the upper pipe clamp (leave loose) and then push down on the torque arrestor to spread the center portion so it fits the inside of the casing. Just a snug fit, do not spread it so much that it is hard to get it in the casing.
Then tighten the upper clamp. It is very important that the upper clamp is as tight as possible. This will make it easier to remove the pump at a later date. - source; "Torque Arrestor Installation", Merrill Manufacturing, 315 Flint Drive
PO Box 392
Storm Lake, IA 50588-0392
800-831-6962 retrieved 2016/09/22, original source: https://www.merrillmfg.com/product/torque-arrestor-installation
Watch out: don't spread the torque arrestor so that it fits more than just snug in the well casing or you may later have trouble inserting or removing the well piping from the well.
Really? Some plumbing experts gripe that these torque arrestors don't work well and cause trouble later when you are pulling well piping. Also, bits of debris, gravel, sand, rust flakes falling down the well bore and resting on the upper rim of the torque arrestor may cause it to jam in the well casing.
A second function of the torque arrestor is to keep the well piping centered in the well. This can be a problem if the well bore is not straight or if the well piping flops around in the well casing when the pump starts. Other devices are sold for centering well piping: you don't have to use a torque arrestor just for that purpose. All well experts do advise, however, that you use centering spaces to keep well piping centered in the well casing. Otherwise movement of the well piping in the casing is likely to lead to wear, piping leaks, and possibly well casing damage.
In deeper wells or with heavier pumps welding the pipe connections may be required to manage pump torque.
Here is what Franklin Water says about pump torque:
During starting of a submersible pump, the torque developed by the motor must be supported through the pump, delivery pipe or other supports. Most pumps
rotate in the direction which causes unscrewing torque on right-handed threaded pipe or pump stages.
All threaded joints, pumps and other parts of the pump support system must be capable of withstanding the maximum torque repeatedly without loosening or breaking. Unscrewing joints will break electrical cable and may cause loss of the pump-motor unit.
Now for the kicker:
To safely withstand maximum unscrewing torques with a minimum safety factor of 1.5, tightening all threaded joints to at least 13.57 N-m per motor horsepower is recommended (Table 2A). It may be necessary to tack or strap weld pipe joints on high horsepower pumps, especially at shallower settings. - Source: 50Hz Submersible Motors, Application, Installation, Maintenance [PDF], Franklin Electric Co, Tel: 800-348-2420, Retrieved 2016/08/15, original source: franklinwater.com/media/123156/50_HZ_AIM.pdf
We introduced the different types of drilled wells and bored wells
at DRILLED WELLS, STEEL CASINGS. This article discusses submersible in-well pumps - those water pumps located within the well bore or casing itself, typically close to the bottom of the well.
Rather than an in-well submersible water pump, other wells use a one line or two line jet pump (depending on well depth) - in those wells the pump is above ground rather than in the well. Those well types are discussed in more detail at WATER PUMP, ONE LINE JET used in shallow wells
and TWO LINE JET PUMP used in deep wells
Continue reading at PUMP, SUBMERSIBLE OPERATION or select a topic from closely-related articles below, or see our complete INDEX to RELATED ARTICLES below.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
 Deep Well Jet Pumps, Government of Alberta, Agriculture and Rural Development, toll free in Alberta at 310-FARM web search 07/24/2010, original source: http://www1.agric.gov.ab.ca/$department/deptdocs.nsf/all/agdex639
 Betta-Flo Jet Pump Installation Manual, National Pump Co., LLC., includes helpful well pump troubleshooting tips as well as basic jet pump installation details. Web search 07/24/2010, original source: http://www.nationalpumpcompany.com/Documents/OIM/Betta%20Flo%20IOM%20Jet%20Pump.pdf
 Water Fact Sheet #3, Using Low-Yielding Wells [ copy on file as /water/Low_Yield_Wells_Penn_State.pdf ] - , Penn State College of Agricultural Sciences, Cooperative Extension, School of Forest Resources, web search 07/24/2010, original source: http://pubs.cas.psu.edu/FreePubs/pdfs/XH0002.pdf
 Smart Tank, Installation Instructions [ copy on file as /water/Smart_Tank_Flexcon.pdf ] - , Flexcon Industries, 300 Pond St., Randolph MA 02368, www.flexconind.com, Tel: 800-527-0030 - web search 07/24/2010, original source: http://www.flexconind.com/pdf/st_install.pdf
 Typical Shallow Well One Line Jet Pump Installation [ copy on file as /water/Jet_Pump_Grove_Elect_Jet_Pumps.pdf ] - , Grove Electric, G&G Electric & Plumbing, 1900 NE 78th St., Suite 101, Vancouver WA 98665 www.grovelectric.com - web search -7/15/2010 original source: http://www.groverelectric.com/howto/38_Typical%20Jet%20Pump%20Installation.pdf
 Typical Deep Well Two Line Jet Pump Installation [ copy on file as /water/Jet_Pump_Grove_Elect.pdf ] - , Grove Electric, G&G Electric & Plumbing, 1900 NE 78th St., Suite 101, Vancouver WA 98665 www.grovelectric.com - web search -7/15/2010 original source: http://www.groverelectric.com/howto/38_Typical%20Jet%20Pump%20Installation.pdf
 Water Ace Jet Pump Installation Manual, instructions from Water Ace Pump Co., web search 08/28/2010, original source: http://www.waterace.com/pdf/R510%20R520%20and%20R100%20Jet%20Pumps%20Manual.pdf
Consumer hotline: 800-942-3343 - instructions for the installation and maintenance of
Water Ace shallow well pump Model R510 1/2 HP
Water Ace deep well pump Model R100 convertible 1HP and
Water Ace deep well jet pump Model R250 convertible 1/2 hp.
Quoting from the company's website:
The Water Ace Pump Company is a dynamic, rapidly growing retail pump manufacturer, backed by a tradition of over 125 years of excellence. We offer a complete line of sump, sewage, lawn sprinkler, swimming pool, submersible well and jet pumps as well as pressure tanks and accessories.
 Water Ace Jet Pump Installation Manual, from Water Ace Pump Co., web search 08/28/2010, original source: http://www.waterace.com/pdf/RTS5%20RTS7%20RTS10%20RC5%20and%20RC10%20Jet%20Pumps%20Manual.pdf
Consumer hotline: 800-942-3343 - instructions for the installation and maintenance of Water Ace pump models:
Water Ace Shallow Well 1-line Jet Pump Models RTS5 (1/2HP), Model RTS7 (3/4 HP) and RTS10 (1HP)
Water Ace Deep Well 2-line Jet Pump Models RC5 (1/2 HP) and RC10 (1HP)
 Water Ace Submersible Well Pump Installation Manual, from Water Ace Pump Co., web search 08/28/2010, original source: http://www.waterace.com/pdf/23833A019%20Well%20Pumps%20Eng.pdf
Spanish and French language submersible well pump installation manuals are available from the company.
Consumer hotline: 800-942-3343 - instructions for the installation and maintenance of Water Ace pump models:
 "Overshot Definition", OilGasGlossary.com. Oil & Gas Field Technical Terms Glossary, Web Search 04/21/2012, original source: http://oilgasglossary.com/overshot.html
 AGE water well equipment, including AGE Riserless Pump Systems, AGE Developments, 38 Harris Road
Malaga WA 6090 Australia, Tel: (08) 9209 2844, Website: agedevelopments.com.au
Access Water Energy, PO Box 2061, Moorabbin, VIC 3189, Australia, Tel: 1300 797 758, email: firstname.lastname@example.org Moorabbin Office: Kingston Trade Centre, 100 Cochranes Rd, Moorabbin, VIC 3189
Australian supplier of: Greywater systems, Solar power to grid packages, Edwards solar systems, Vulcan compact solar systems, water & solar system pumps & controls, and a wide rage of above ground & under ground water storage tanks: concrete, steel, plastic, modular, and bladder storage tanks.
Smart Tank, Installation Instructions [ copy on file as /water/Smart_Tank_Flexcon.pdf ] - , Flexcon Industries, 300 Pond St., Randolph MA 02368, www.flexconind.com, Tel: 800-527-0030 - web search 07/24/2010, original source: http://www.flexconind.com/pdf/st_install.pdf
Typical Shallow Well One Line Jet Pump Installation [ copy on file as /water/Jet_Pump_Grove_Elect_Jet_Pumps.pdf ] - , Grove Electric, G&G Electric & Plumbing, 1900 NE 78th St., Suite 101, Vancouver WA 98665 www.grovelectric.com - web search -7/15/2010 original source: http://www.groverelectric.com/howto/38_Typical%20Jet%20Pump%20Installation.pdf
Typical Deep Well Two Line Jet Pump Installation [ copy on file as /water/Jet_Pump_Grove_Elect.pdf ] - , Grove Electric, G&G Electric & Plumbing, 1900 NE 78th St., Suite 101, Vancouver WA 98665 www.grovelectric.com - web search -7/15/2010 original source: http://www.groverelectric.com/howto/38_Typical%20Jet%20Pump%20Installation.pdf
Water Fact Sheet #3, Using Low-Yielding Wells [ copy on file as /water/Low_Yield_Wells_Penn_State.pdf ] - , Penn State College of Agricultural Sciences, Cooperative Extension, School of Forest Resources, web search 07/24/2010, original source: http://pubs.cas.psu.edu/FreePubs/pdfs/XH0002.pdf
Crystal Clear Supply provides portable ceramic water filter purifiers and portable reverse osmosis water treatment equipment - see http://www.crystalclearsupply.com/category_s/7.htm
Handbook of Disinfectants and Antiseptics, Joseph M. Ascenzi (Editor), CRC, 1995, ISBN-10: 0824795245 ISBN-13: 978-0824795245 "The evaluation of chemical germicides predates the golden age of microbiology..." -
This well-focused, up-to-date reference details the current medical uses of antiseptics and disinfectants -- particularly in the control of hospital-acquired infections -- presenting methods for evaluating products to obtain regulatory approval and examining chemical, physical, and microbiological properties as well as the toxicology of the most widely used commercial chemicals.
Potable Aqua® emergency drinking water germicidal tablets are produced by the Wisconsin Pharmacal Co., Jackson WI 53037. 800-558-6614 pharmacalway.com
Principles and Practice of Disinfection, Preservation and Sterilization (Hardcover)
by A. D. Russell (Editor), W. B. Hugo (Editor), G. A. J. Ayliffe (Editor), Blackwell Science, 2004. ISBN-10: 1405101997, ISBN-13: 978-1405101998.
"This superb book is the best of its kind available and one that will undoubtedly be useful, if not essential, to workers in a variety of industries. Thirty-one distinguished specialists deal comprehensively with the subject matter indicated by the title ... The book is produced with care, is very readable with useful selected references at the end of each chapter and an excellent index. It is an essential source book for everyone interested in this field. For pharmacy undergraduates, it will complement the excellent text on pharmaceutical microbiology by two of the present editors."
The Pharmaceutical Journal: "This is an excellent book. It deals comprehensively and authoritatively with its subject with contributions from 31 distinguished specialists. There is a great deal to interest all those involved in hospital infection ... This book is exceptionally well laid out. There are well chosen references for each chapter and an excellent index. It is highly recommended." The Journal of Hospital Infection.: "The editors and authors must be congratulated for this excellent treatise on nonantibiotic antimicrobial measures in hospitals and industry ... The publication is highly recommended to hospital and research personnel, especially to clinical microbiologists, infection-control and environmental-safety specialists, pharmacists, and dieticians."
New England Journal of Medicine: City Hospital, Birmingham, UK. Covers the many methods of the elimination or prevention of microbial growth. Provides an historical overview, descriptions of the types of antimicrobial agents, factors affecting efficacy, evaluation methods, and types of resistance. Features sterilization methods, and more. Previous edition: c1999. DNLM: Sterilization--methods.
U.S. Army Field Manual 21-10, Field Hygiene and Sanitation, 1988, web search 07/02/2010, original source: http://www.enlisted.info/field-manuals/fm-21-10-field-hygiene-and-sanitation.shtml The purpose of this manual is to assist individual soldiers, unit commanders, leaders and field sanitation teams in preventing disease and environmental injuries. The manual provides information on preventive medicine measures (PMM) to the individual soldier as well as essential information for the unit commander, unit leaders, and the unit field sanitation team on applying unit level PMM.
When Technology Fails, Matthew Stein, Chelsea Green Publisher, 2008,493 pages. ISBN-10: 1933392452 ISBN-13: 978-1933392455, "... how to find and sterilize water in the face of utility failure, as well as practical information for dealing with water-quality issues even when the public tap water is still flowing". Mr. Stein's website is www.whentechfails.com/
Books & Articles on Building & Environmental Inspection, Testing, Diagnosis, & Repair
Carson, Dunlop & Associates Ltd., 120 Carlton Street Suite 407, Toronto ON M5A 4K2. Tel: (416) 964-9415 1-800-268-7070 Email: email@example.com. The firm provides professional home inspection services & home inspection education & publications. Alan Carson is a past president of ASHI, the American Society of Home Inspectors. Thanks to Alan Carson and Bob Dunlop, for permission for InspectAPedia to use text excerpts from The Home Reference Book & illustrations from The Illustrated Home. Carson Dunlop Associates' provides extensive home inspection education and report writing material.
The Illustrated Home illustrates construction details and building components, a reference for owners & inspectors. Special Offer: For a 5% discount on any number of copies of the Illustrated Home purchased as a single order Enter INSPECTAILL in the order payment page "Promo/Redemption" space.
TECHNICAL REFERENCE GUIDE to manufacturer's model and serial number information for heating and cooling equipment, useful for determining the age of heating boilers, furnaces, water heaters is provided by Carson Dunlop, Associates, Toronto - Carson Dunlop Weldon & Associates Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on any number of copies of the Technical Reference Guide purchased as a single order. Just enter INSPECTATRG in the order payment page "Promo/Redemption" space.
The Home Reference Book - the Encyclopedia of Homes, Carson Dunlop & Associates, Toronto, Ontario, 25th Ed., 2012, is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. Field inspection worksheets are included at the back of the volume.
Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on these courses: Enter INSPECTAHITP in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Horizon Software System manages business operations,scheduling, & inspection report writing using Carson Dunlop's knowledge base & color images. The Horizon system runs on always-available cloud-based software for office computers, laptops, tablets, iPad, Android, & other smartphones