InspectAPedia tolerates no conflicts of interest. We have no relationship with advertisers, products, or services discussed at this website.
Goodman furnace & plastic vent safety recall:
This document provides residential heating furnace safety information about the Goodman Furnace Heating Vent Safety High Temperature Plastic Vent HTPV Recall By Goodman Manufacturing, a Houston TX air conditioning and heating firm.
To be clear, Goodman did not itself manufacture the HTPV piping but rather obtained it from other HTPV manufacturers. Nonetheless, the Goodman HTPV vent is a serious safety hazard because it risks release of dangerous, potentially fatal carbon monoxide gas in buildings if this defective furnace vent has not been replaced.
Goodman plastic heater vents were recalled by the company originally in 1998 and in an updated notice in 2009 (as Plexvent™ or Ultravent™) , because of the possibility of carbon monoxide leakage hazards. Cracks in the flue venting system were reported due to corrosion and cracking. Our literature review indicates that there were about 10,000 Plexvent & Ultravent HTPV flue gas venting systems used to vent combustion products from some Goodman mid-efficiency furnaces that were in turn manufactured between October 1988 & July 1994.
Heating equipment model & brand using recalled Goodman HTPV: the heating system models involved include GUP, GDP, GUPS, GDPS, GUPI, GDPI, GUPX, GDPX, GMP and GMPV. Goodman-manufactured heaters to which this recall pertains were sold under the brands of Goodman: Janitrol, GMC, Hamilton Electric, Franklin, Liberty & Sears or Kenmore.
HTPV location, installation method, & appearance or color: Goodman HTPV vent piping may be found installed vertically up thorough a building's roof or horizontally as a side-wall direct vent instllation.
Gooodman HTPV pipe in the [few] we've seen is a plastic vent piping that is black or gray in color.
Goodman HTPV pipe is usually marked with a stamping along a side of the plastic pipe with the imprint of the brand Plexvent, Plexvent II, or Ultravent . These brand names may also appear on stickers affixced to the flue vent connectors such as elbows or couplings.
Goodman HTPV photos: [If you can provide us with a photo of the Goodman HTPV that was the subject of this recall, please Contact Us.]
US CPSC Notice: Goodman Announcement of Recall to Replace HTPV Pipes
For Immediate Release Contact: Jane Francis
February 24, 1998 (301) 504-0580 Ext. 1187
Release # 98-073
CPSC, Goodman Announce Recall to Replace HTPV Pipes
WASHINGTON, D.C. - Since August 1996, Goodman Manufacturing Company, L.P., of Houston, Texas, in cooperation with the U.S. Consumer Product Safety Commission (CPSC), has been conducting a program to replace high-temperature plastic vent (HTPV) pipe used to vent about 8,000 Goodman
mid-efficiency gas furnaces. The HTPV pipe used in these vents could be susceptible to corrosion, cracking and joint separation, which could result in the release of carbon monoxide into living areas, presenting a deadly threat to consumers.
Although Goodman did not manufacture HTPV pipe, some models of Goodman furnaces were vented using HTPV material
produced by other companies. Goodman voluntarily undertook its replacement program to help ensure the safety and comfort of its gas-appliance customers and has already replaced many HTPV systems.
For each Goodman furnace that is horizontally vented with HTPV pipe, Goodman will continue to arrange for replacement of the vent with a new, approved vent at no
charge. Alternatively at the homeowner's option, Goodman will continue to replace the entire furnace and vent with a brand new, high-efficiency Goodman furnace and suitable vent for only the manufacturer's price for the new furnace itself, with no charge for labor, associated materials or dealer markup.
Owners of Goodman furnaces that are vented with HTPV pipe should contact their local heating contractor for more information or call Goodman at (800) 394-8084.
The U.S. Consumer Product Safety Commission protects the public from unreasonable risks of injury or death from 15,000 types of consumer products under the agency's
jurisdiction. To report a dangerous product or a product-related injury and for information on CPSC's fax-on-demand service, call CPSC's hotline at (800) 638-2772 or CPSC's teletypewriter at (800) 638-8270. To order a press release through fax-on-demand, call (301) 504-0051 from the
handset of your fax machine and enter the release number.
Consumers can obtain this release and recall information at CPSC's web site at http://www.cpsc.gov or via Internet gopher services at gopher.cpsc.gov. Consumers can report product hazards to email@example.com. To establish a link from your web site to this press release on CPSC's web site,
create a link to the following address: http://www.cpsc.gov/cpscpub/prerel/prhtml98/98073.html.
022498,CPSC, Goodman Announce Recall to Replace HTPV Pipes
Recall & Warranty or Claims Coverage for Goodman Plexvent or Ultravent Recalled venting systems
Goodman HTPV Claims prior to 1 October 2009: For Plexvent or Ultravent installations for which a valid claim was submitted on or before 10/1/2009 and with repairs completed and documented by 1/1/2010 the homeowner could receive a new venting system installed by a professional at no cost or [depending on un-stated variables] a new high-efficiency Goodman heating system and venting system for the manufacturer's price of just the furnace - that is, you buy a new heater and the vent system is installed free
Goodman HTPV Claims after 1 October 2009:
Plexvent vent system owners may receive up to $400 as a credit towards the purchase and installation of a new vent system or towards the purchase of a new Goodman furnace that does not require an HTPV vent.
Ultravent vent system owners could receive a rebate of up to $250. towards a replacement HTPV vent system or or towards the purchase of a new Goodman furnace that does not require an HTPV vent.
TECHNICAL NOTES on the Plastic Heating Vent Safety Concern:
Ontario, 1-2 yrs ago, 3 mfgs:
Coming apart at cemented joint and also general pipe cracking
on plastic vents used on mid-range efficiency gas furnaces and boilers.
They had an 8/96 deadline to replace all units - as the entire unit
incl. vent was listed as an entire unit, couldn't just replace the
vent so replaced a bunch of entire systems. Thousands done that way.
Class action lawsuit against manufacturers, Ontario New Home Warranty
Each manufacturer had to get its unit re-listed, some went to stainless steel
vents, most went to a new plastic with an exterior additional induced
draft fan so even if cracks inside, flue gases won't leak into the
OPINION: some furnace blower fans defeat the furnace's heating efficiency by exhausting heat
from the house. Some thoughts that are adding complexity - second
fan, but it's probably interlocked so will shut down heat if fan
2/7/97 tc Daniel Friedman with Giddings at CPSC:
Flexco, Hardin Cooley, mid efficiency furnaces and boilers,
GE Resin - Ultratemp - failed in 2-6 years;
AGA certified furnaces and boilers -
He estimates in US they are in
350,000 homes - boilers in Northeast and Furnaces in more temperate
St first boiler mfgs supplied the vent with the heater
Later the material was "specified" but not included with the heater
The Fix for these Plastic Heater Vents:
Stainless steel and power vent
Ontario first observed the failures - before in US
a second-generation - 1993-4 - pipe performed better but has no data to prove it's long term performance is ok - UL has changed its standards. Radel -- is a replacement pipe.
How to Identify the problem Plastic Heating Vents:
Plex-vent is marked - the revised mix is Plex-vent-2 - both are black
Ultra-vent - see date code on the pipe - gray pipe - new is post 8/93
CEL-vent - black pipe - revised mix is Celvent-2
CPSC sees fewer field failures with the new stuff - but no long
term data yet. Says the second-generation plastic is no longer
specified by the heater mfgs.
Chevron Sued GE
Consumer class action ongoing in Tennessee
He (Giddings) sent ASHI a letter 9/96 - to Paterkevich - will re-fax to me
got a mumbled reply from some unknown ASHI guy
Typical cost to cure defective or unsafe plastic heating vent pipes is $400-$600.
Other information sources on the plastic heater vent safety recall:
Carson Dunlop tech notes
the CPSC letter to ASHI
GAMA - Gas Appliance Mfgs Assoc - or maybe AGA or Dan's reference - Doug DeWerth
UL had meetings in June '94 on problems with plastic vent piping and the UL Standard 1738 - what were the pre and post revision standard texts?
Don Fugler, at Canadian Meeting Association of CMHC - Research and QA - per
Steve Bliss at the Journal of Light Construction?
Don Fugler, CMHC Canadian Home Mortgage Corp? -
613-748-2658 in Ottowa - ?? what's this note about
2/8/97 Actions Taken by DF
ASHI Reporter article (done)
JLC Article - poss extra exposure in tract homes (done)
get info first from varied sources
and review my notes with CPSC &C
Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Ask a Question or Search InspectApedia
Questions & answers or comments about the Goodman furnace and Plastic Heater Vent Safety Recall.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Domestic and Commercial Oil Burners, Charles H. Burkhardt, McGraw Hill Book Company, New York 3rd Ed 1969.
National Fuel Gas Code (Z223.1) $16.00 and National Fuel Gas Code Handbook (Z223.2) $47.00 American Gas Association (A.G.A.), 1515 Wilson Boulevard, Arlington, VA 22209 also available from National Fire Protection Association, Batterymarch Park, Quincy, MA 02269. Fundamentals of Gas Appliance Venting and Ventilation, 1985, American Gas Association Laboratories, Engineering Services Department. American Gas Association, 1515 Wilson Boulevard, Arlington, VA 22209. Catalog #XHO585. Reprinted 1989.
The Steam Book, 1984, Training and Education Department, Fluid Handling Division, ITT [probably out of print, possibly available from several home inspection supply companies] Fuel Oil and Oil Heat Magazine, October 1990, offers an update,
Principles of Steam Heating, $13.25 includes postage. Fuel oil & Oil Heat Magazine, 389 Passaic Ave., Fairfield, NJ 07004.
The Lost Art of Steam Heating, Dan Holohan, 516-579-3046 FAX
Principles of Steam Heating, Dan Holohan, technical editor of Fuel Oil and Oil Heat magazine, 389 Passaic Ave., Fairfield, NJ 07004 ($12.+1.25 postage/handling).
"Residential Hydronic (circulating hot water) Heating Systems", Instructional Technologies Institute, Inc., 145 "D" Grassy Plain St., Bethel, CT 06801 800/227-1663 [home inspection training material] 1987
"Warm Air Heating Systems". Instructional Technologies Institute, Inc., 145 "D" Grassy Plain St., Bethel, CT 06801 800/227-1663 [home inspection training material] 1987
Heating, Ventilating, and Air Conditioning Volume I, Heating Fundamentals,
Boilers, Boiler Conversions, James E. Brumbaugh, ISBN 0-672-23389-4 (v. 1) Volume II, Oil, Gas, and Coal Burners, Controls, Ducts, Piping, Valves, James E. Brumbaugh, ISBN 0-672-23390-7 (v. 2) Volume III, Radiant Heating, Water Heaters, Ventilation, Air Conditioning, Heat Pumps, Air Cleaners, James E. Brumbaugh, ISBN 0-672-23383-5 (v. 3) or ISBN 0-672-23380-0 (set) Special Sales Director, Macmillan Publishing Co., 866 Third Ave., New York, NY 10022. Macmillan Publishing Co., NY
Installation Guide for Residential Hydronic Heating Systems
Installation Guide #200, The Hydronics Institute, 35 Russo Place, Berkeley Heights, NJ 07922
The ABC's of Retention Head Oil Burners, National Association of Oil Heat Service Managers, TM 115, National Old Timers' Association of the Energy Industry, PO Box 168, Mineola, NY 11501. (Excellent tips on spotting problems on oil-fired heating equipment. Booklet.)
Carson, Dunlop & Associates Ltd., 120 Carlton Street Suite 407, Toronto ON M5A 4K2. Tel: (416) 964-9415 1-800-268-7070 Email: firstname.lastname@example.org. The firm provides professional home inspection services & home inspection education & publications. Alan Carson is a past president of ASHI, the American Society of Home Inspectors. Thanks to Alan Carson and Bob Dunlop, for permission for InspectAPedia to use text excerpts from The Home Reference Book & illustrations from The Illustrated Home. Carson Dunlop Associates' provides extensive home inspection education and report writing material.
The Illustrated Home illustrates construction details and building components, a reference for owners & inspectors. Special Offer: For a 5% discount on any number of copies of the Illustrated Home purchased as a single order Enter INSPECTAILL in the order payment page "Promo/Redemption" space.
TECHNICAL REFERENCE GUIDE to manufacturer's model and serial number information for heating and cooling equipment, useful for determining the age of heating boilers, furnaces, water heaters is provided by Carson Dunlop, Associates, Toronto - Carson Dunlop Weldon & Associates Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on any number of copies of the Technical Reference Guide purchased as a single order. Just enter INSPECTATRG in the order payment page "Promo/Redemption" space.
The Home Reference Book - the Encyclopedia of Homes, Carson Dunlop & Associates, Toronto, Ontario, 25th Ed., 2012, is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. Field inspection worksheets are included at the back of the volume.
Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on these courses: Enter INSPECTAHITP in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Horizon Software System manages business operations,scheduling, & inspection report writing using Carson Dunlop's knowledge base & color images. The Horizon system runs on always-available cloud-based software for office computers, laptops, tablets, iPad, Android, & other smartphones