Water Softener Troubleshooting & Diagnostic Procedures
DIAGNOSE WATER SOFTENER PROBLEMS - CONTENTS: How to Diagnose & Fix a Water Softener that Is Not Working Properly - How to diagnose water softener operation problems. CHECKLIST for an inoperative water softener
POST a QUESTION or READ FAQs about how to diagnose water softener operating problems: how long the softener runs, how much water is in the brine tank, how much salt, how salty or soft is the household water, more.
InspectAPedia tolerates no conflicts of interest. We have no relationship with advertisers, products, or services discussed at this website.
Diagnose & Fix Water Softener Problems:
This article series describes procedures for diagnosing and repairing water softener or water conditioner problems including water conditioner control settings and adjustment or repair, brine tank and brine tank float cleaning and repair, and the proper amount of water softening or conditioning that is needed.
This water softener repair article describes what to check first if the softener is not working properly. Also see the FAQs at the end of this article for examples of water softener problems & solutions.
Water Softener Checklist: if the Softener is Not Working Check These First
if the water softener doesn't seem to be doing anything,
check these items:
Check the water softener bypass valve: You want first to see that the water softener is not on "bypass" - is household water flowing through the unit? A sketch of an Autotrol bypass valve is shown at left.
Details about how to use the water softener bypass valve are at BYPASS VALVE.
This valve is an option and may not be installed on your unit. But there may be standard plumbing valves or globe valves that accomplish the same purpose.
Check power to the water softener: If the unit uses electricity to run a timer be sure it's plugged in to a live outlet and has power. Some water conditioners use a low-voltage transformer to power the control - be sure that device is present, plugged in, and working. You can use a simple VOM to check that the transformer is outputting DC at the proper voltage level.
Manually regen cycle: Then try a manual regen cycle - you'll see on most units a lever you can push on the control box to start that process
Set the water conditioner controls: Set the right doses and regen cycles for your water hardness and level of water usage
Watch the water conditioner timer: it is possible that the timer mechanism itself has failed. You should see the timer wheels or clock wheels turning and, if you try setting a regen cycle at every day (just for starters) you should see and hear the system go through a regeneration cycle automatically the very next night.
Feel and test the water supply: if you still can't get a lather when bathing the water may be insufficiently treated, or if the water feels slimy and you have trouble washing soap off, the water may be over-treated. Test the water for hardness so that you know how to set the controls.
How to Get a Water Softener Working & Confirm that It Works Correctly
Before replacing a water softener - a step that may not be necessary, here are some things to try:
Make sure that the water softener is actually "on" and working, that is, that the system has electric power, valves turned on, not left on "bypass"
Make sure the water softener is clean and that no debris is blocking any water passages or tubing.
If the salt tank has stayed "full" for a long time, either no salt is being used (improper operation) or a crust of salt has formed over a virtually empty tank. Poke around into the salt to be sure the salt tank is really there.
Test the water softener output water for hardness and if you like, also test the output water salt level for excess salt
Check the water softener control adjustments. If the equipment appears to be working, but water is still too hard (or has too much mineral content) you can increase the salt dose or the backwash/regeneration cycle frequency.
If the water softener is leaving too much salt in the water, reduce the salt dose on your softener's controls. You may see this as a thin salty film left at faucets or in a dishwasher. Mineral scale may also be a thin hard white deposit but is a separate problem not a too-much-salt problem.
Call for professional help with the water softener. If the equipment is not visibly broken, damaged, leaking, and/or you don't want to mess with it yourself, most water softener companies will be glad to send a service technician to your home to inspect, clean, adjust, and test the equipment.
Try these water softener diagnosis and repair steps before rushing to replace the water softener itself.
Master Table of Water Softener Problems, Causes, Repair Procedures
Water Softener Problem
Water Softener Problem Cause
Water Softener Problem Repair
Water Softener Won't Regenerate
Water softener regeneration cycle inadequate
No electrical power
Check that the softener is plugged-in, that its electrical circuit is powered-on, that a switch, pull chain, breaker or fuse are all "on" and working.
If the timer does not operate the softener won't cycle; replace the timer.
Power failure caused timer or clock to be improperly set
Re-set the day of week and time of day on the water softener timer after an electrical power failure or after the softener has been powered "off" for a time.
Water Softener regeneration cycle delayed, stuck, or continuously "on"
Softener is not drawing brine from the brine tank
Comnmon causes: clogged or stuck rine tank float valve assembly, clogged drain line flow control, clogged injector or injector screen, low water pressure, internal leak in the control.
Break up the crust, then add salt if needed. The salt level should be above the water level in the brine tank. Normally the water level reaches 6-8" in the brine tank during a regeneration cycle. For diagnosing brine tank problems
Insufficient water into the brine tank opr insufficient salt dose or related brine tank problems can cause the water softener regen cycle to be too short or can cause the softener to fail to produce enough soft water.
Check for a cracked or leaky distributor tube; check for a bad O-ring or Tube Pilot.
Internal valve leak
Replace the control head valve seals, O-rings, spacers and/or piston.
Control Head program wheel not rotating (mechanical water softner controls) with timer motor
Pull cable out of the control head cover and rotate the trip-wheel manually. Program wheel must move without binding and clutch must give positive “clicks” when program wheel strikes regeneration stop. If it does not, replacethe timer assembly or control head.
Control head not measuring water flow or hardness (these features are not present on all water conditioners)
For a mechanical water conditioner control head, check output by observing rotation of small gear on front of timer (Note - program wheel must not be against regeneration stop for this check). Each tooth to tooth is approximately 30 gallons (model dependent). If not performing properly, replace the control head.
Water usage + hardness exceeds water softener capacity
Measure water hardness and daily or weekly water usage quantity; compare these with the water softener capacity specifications; try increasing the salt dose, regen cycle frequency and regen cycle duration.
Excessive salt usage
Improper salt dose setting
Check the salt dose setting on the softener control head;
Check the regeneration cycle frequency setting at the softener control.
Improper water level in the brine tank
Check for a stuck brine tank float, a clogged drain line, a clogged drain line flow control, a plugged injector system, for a timer not cycling, or for a clogged brine tank float valve. For details
Note: Not advisable for cooking & Bathing purpose use for floor cleaning & flushing.
Can I know what is the best way to remove the hardness of water. - Shobia 6/20/12
Reply: water softener capacity must be able to handle level of water hardness
Shobia it does sound as if you'd need water treatment to make that water usable in the home; if you call two local water treatment companies they will be glad to propose systems to meet your needs, and typically don't charge for that advice. Using hardness as an example, it's quite simple to check the level of hardness you need to deal with against the capacity of the water softener system proposed.
I can't say more as I don't understand your data - hardness is usually expressed in milligrams per liter or grains per gallon, not parts per million.
Reader Comment from Cullman 8/26/12:
You need larger size water softener to remove this high hardness. Also TDS (total dissolved solids) level is very high , so for drinking water I suggest using Reverse osmosis system at the kitchen sink. Ph level is good.
Thanks Cullman for the helpful suggestions to Shobia - Ed.
Reader Question: Water softener keeps regenerating & water remains hard
About once a year my softener will have salt in the tank and will run regenerating. But nothing happens and the water remains hard running throughout he house.
Maybe something is clogged? What should I look to do. Thanks so much. - Rob P. 7/24/12
Rob, check for a stuck float switch in the brine tank;
Reader Question: Can I replace the resin media inside of a water softener?
8/31/14 Ron Fix It Man said:
My softener is 13 years old and I have read the resin becomes ineffective in about that life time. Iron out has been used with little benefit. Effectiveness of the softener has declined unless greater amounts of salt per cycle are used. Troubleshooting reveals no improper cycle operation. Is it true the resin has a limited life? Can it be restored, say with a wash of dilute muratic acid? If not, where can it be purchased?
Reply: procedure to replace water softener treatment tank resin media
Indeed it is possible to replace the resin in a water softener.
Water softener resin can last for 20 years or even longer, but may have a shorter life depending on the chemistry of the water being processed in the water softener. But I would not start down the "replace water softener resin" path before diagnosing the problem with my water softener to be sure I'm making the proper and necessary repair.
If you've done that and are ready to replace the resin in the softner tank, details of just how to replace the resin in the water softner, where to buy resin, and other advice are
at SOFTENER RESIN REPLACEMENT
White Scale Deposits on Plumbing Fixtures: hard water indicators
Question: White Deposits on Faucets: why does my water keep leaving water marks on my plumbing fixtures? Should I replace my water softener?
I currently have a water softener system in my home BUT, there are always water marks on my chrome fixtures and on my windows,mirrors,etc.
What can I do to improve this system or should I just replace it with a different one?
I realize that soft water does not mean non-staining water but I was hoping for better results.
Can you help of advise? - C.T.
Reply: Diagnose, clean, adjust, and test your water softener before buying a new one
We speculate that there are several likely explanations for what you describe:
The water softener is not working adequately or not properly adjusted, does not remove enough minerals, and minerals continue to be deposited on your fixtures
The water softener is not adjusted properly and excess salt is being sent through your system, depositing salt on the fixtures.
The water softener unit is dirty, and needs cleaning and perhaps also adjustment
The water softener simply has stopped working - broken, perhaps leaking, clogged, or with a control that no longer functions.
The water softener regeneration system is not working: no salt in the salt tank, or improper regeneration cycle or salt dose setting, or the regeneration control timer may be stuck.
Watch out: too often a water softener failure or operating problem that could have been corrected by a simple adjustment, cleaning, or repair, is in stead "repaired" by installing new equipment.
Since a new water softener just installed is more likely to be clean and properly adjusted, the old problem may indeed go away, and you may think that replacement was needed, but if simple cleaning and adjustment of the old water softener would have been sufficient, you have faced an unnecessary expense.
Reader Question: corroded drains & faucets - does this mean a water softener problem?
Our drains and faucets are starting to corrode and rust. we have always used a water softener and maintained it. Is this an indication that there is a problem with our softener? - Sharon Osterby 9/16/12
Sharon I'm not sure the problem is with your water softener or with the chemistry of your water. If the softener is not working you might see white mineral build-up at faucet strainers and openings; If the water chemistry is aggressive that might be a factor in plumbing corrosion.
Start by testing your softened water to see if it is effectively treated, and if not, clean, adjust, repair the water softener first.
If you suspect a problem with water chemistry (say the softener is working normally and the water at the tap is not hard) then I suggest asking a water treatment company to test your water. Such vendors often will test your water at no charge (they want to sell you equipment) or if you're doubtful, pick up a sterile bottle from your local water test lab and ask their recommendations for what screening tests to perform.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
 North Dakota Standards for Water Softeners, North Dakota General Authority Law, Chapter 62-04-08, Water Softener Units http://www.legis.nd.gov/information/acdata/pdf/62-04-08.pdf. "The objective of this chapter is to provide a standard of quality, capacity,
and performance for water softener units. Water softener performance
is to be based upon referee tests procedures described in section
 Culligan Mark 10 Water Softener 1994-1998 Installation and Operating Instructions (covering models manufactured after 1995) (1-96) 01881948.pdf available from www.culligan.com
 Water Softeners, CMHC, Canadian Mortgage and Housing Corporation, cmhc-schl.gc.ca/en/co/maho/wawa/wawa_005.cfm - October 2008. Canada Mortgage and Housing Corporation acknowledges the contribution of Health Canada to the development of this document. For further questions regarding water treatment and water quality, contact Health Canada at firstname.lastname@example.org or call 613-957-2991 or 1-866-225-0709.
 "Commercial Water Softener Installation and Operating Instructions", IBC Filtration & Water Treatment Products (Australia) for commercial, industrial and residential application www.ibcwater.com.au (07) 3219 2233
 "Non electric water softener,
Installation and Operating Instructions", IBC Filtration & Water Treatment Products (Australia), op.cit.
 "Water Softener Twin Tank Installation and Operating Instructions", IBC Filtration & Water Treatment Products (Australia), op.cit.
 Our Water Hardness Table used at originated with but was edited and added to from http://www.bestfish.com/tips/110598.html and also from http://www.water-research.net/hardness.htm
 Thanks to reader Gail Sanchez for discussing water softener backups and floods after an electrical outage - August 2010
 Water Right, 1900 Prospect Court
Appleton, Wisconsin 54914, Tel: 920-739-9401, Website: http://www.water-right.com/ and their water softener manuals are available online at http://www.water-right.com/library/literature/literature_manuals.html
 General Electric Corporation, Operation Manual, 740/760 [Water Conditioner or Water Softener] Control, 255 and Performa Series Valves, (268, 268 FA), General Electric Corp. 2007
Builder's Guide to Wells and Septic Systems, Woodson, R. Dodge: $ 24.95; MCGRAW HILL B; TP;
Quoting from Amazon's description: For the homebuilder, one mistake in estimating or installing wells and septic systems can cost thousands of dollars. This comprehensive guide filled with case studies can prevent that. Master plumber R. Dodge Woodson packs this reader-friendly guide with guidance and information, including details on new techniques and materials that can economize and expedite jobs and advice on how to avoid mistakes in both estimating and construction. Chapters cover virtually every aspect of wells and septic systems, including on-site evaluations; site limitations; bidding; soil studies, septic designs, and code-related issues; drilled and dug wells, gravel and pipe, chamber-type, and gravity septic systems; pump stations; common problems with well installation; and remedies for poor septic situations. Woodson also discusses ways to increase profits by avoiding cost overruns.
Country Plumbing: Living with a Septic System, Hartigan, Gerry: $ 9.95; ALAN C HOOD & TP;
Quoting an Amazon reviewer's comment, with which we agree--DF:This book is informative as far as it goes and might be most useful for someone with an older system. But it was written in the early 1980s. A lot has changed since then. In particular, the book doesn't cover any of the newer systems that are used more and more nowadays in some parts of the country -- sand mounds, aeration systems, lagoons, etc.
"International Private Sewage Disposal Code," 1995, BOCA-708-799-2300, ICBO-310-699-0541, SBCCI 205-591-1853, available from those code associations.
"Manual of Policy, Procedures, and Guidelines for Onsite Sewage Systems," Ontario Reg. 374/81, Part VII of the Environmental
Protection Act (Canada), ISBN 0-7743-7303-2, Ministry of the Environment,135 St. Clair Ave. West, Toronto Ontario M4V 1P5 Canada $24. CDN.
Manual of Septic Tank Practice, US Public Health Service's 1959.
Builder's Greywater Guide, Art Ludwig; Buy New: $10.17. Installation of Greywater Systems in New Construction & Remodeling; A Supplement to the Book "Create an Oasis With Greywater" (Paperback).
Quoting a review from Amazon: I recommend that you get the 3 companion books on greywater treatment "Create an Oasis", "Branched Drain Greywater Systems" and "Builder's Greywater Guide". The information in these volumes will keep most of us far more informed than most of the regulators, the system builders, and the experts-in-theory. These volumes are real-world gems.
Art Ludwig has cut to the core of wastewater issues. He's obviously done all of his homework, mulled-over the variables, and come up with a common sense, economically reasonable, environmentally responsible approach to wastewater. I expect to save money that I would have spent on a post-septic tank, aerobic unit that would seemingly have been ecologically responsible; but because of the technological overkill, ultimately that system would have defeated my altruistic environmental concerns.
... These books talk the talk and walk the walk better than anything else that I've seen. Buy a set for yourself, a set for your neighbors, and a set for the regulators.
The Toilet Papers: Designs to Recycle Human Waste and Water : Dry Toilets, Greywater Systems and Urban Sewage (Paperback) Sim Van Der Ryn, Wendell Berry; Quoting from an Amazon review: With a title like "Toilet Papers" and from a distinguished eco-architect like Sim Van der Ryn, I needed no intro or review to buy a copy of this little, but well researched historical over-view of effluent mitigation and current eco-friendly toilet design.
This book is filled with good line drawings and photographs to depict everything from the historical perspective to the current dry toilets and their construction..
Quality issues in harvested rainwater in arid and semi-arid Loess Plateau of northern China,
K. Zhu, L. Zhang, W. Hart, M. Liu, H. Chen (out of print, find by search and deferred order).
Amazon's description may be helpful: Loess soils cover vast areas in the arid and semi-arid regions of northern China. Due to the lack of reliable surface water and ground-water, rainwater harvesting has played a prominent role in farmers' domestic usage and agricultural irrigation. An economical and valid type of water storage cistern with optimum design of components has been introduced to rural areas in the Loess Plateau. Different collection alternatives showed apparent variations in rainwater quality. By using different catchments, such as mortar roofs and cement-paved courtyards, compacted land or road surfaces, rainwater can be effectively collected for storage in cisterns. This study focused mainly on the quality of rainwater harvested from the different catchment systems and stored for different periods of time. By analysis of the water samples stored in these cisterns, it was evident that rainwater quality could be improved significantly by self-purification during the storage. With emphasis on rainwater quality affected by the
different catchment systems, it was found that the measured inorganic compounds in the rainwater harvested from roof-yard catchment systems generally matched the WHO standards for drinking water, while the concentrations of some inorganic compounds in the rainwater collected from land and road surfaces appeared to be higher than the guideline values for drinking water, but generally not beyond the maximum permissible concentrations. However, Fecal Coliform, which is an important bacteriological parameter for the three catchment systems, exceeded the limits of drinking water to a greater extend. Trace amounts of 55 organic pollutants were identified, including aliphatic hydrocarbons, aromatic compounds and phthalate esters, etc. The analytical results indicated that roof-yard catchments that included the ''first flush'' usually provided safe drinking water with low organic contents, even for rainwater collected immediately after rainfall. In contrast, rainwater harvested from road surfaces had poor quality
with respect to the organic constituents, regardless of stored time.
City eying home water-recycling technology; uses bath and washer water for irrigation., (ReWater Systems' equipment for greywater irrigation):
This is an article from: San Diego Business Journal [HTML] (Digital) available online in digital format. I have not (yet) reviewed it -- DF
Onsite Wastewater Disposal, R. J. Perkins;
Quoting from Amazon: This practical book, co-published with the National Environmental Health Association,
describes the step-by-step procedures needed to avoid common pitfalls in septic system technology.
Valuable in matching the septic system to the site-specific conditions, this useful book will help you install a reliable system in
both suitable and difficult environments. Septic tank installers, planners, state and local regulators, civil and sanitary engineers,
consulting engineers, architects, homeowners, academics, and land developers will find this publication valuable.
Onsite Wastewater Treatment Systems, Bennette D. Burks, Mary Margaret Minnis, Hogarth House 1994 - one of the best septic system books around, suffering a bit from small fonts and a weak index. (DF volunteers to serve as indexer if Burks/Minnis re-publish this very useful volume.)While it contains some material more technical than needed by homeowners, Burks/Minnis book on onsite wastewater treatment systems a very useful reference
for both property owners and septic system designers. We refer to it often.
While Minnis says the best place to buy this book is at Amazon (our link at left), you can also see this book at Minnis' website at http://web page .pace.edu/MMinnisbook
Septic Tank/Soil-Absorption Systems: How to Operate & Maintain [ copy on file as /septic/Septic_Operation_USDA.pdf ] - , Equipment Tips, U.S. Department of Agriculture, 8271 1302, 7100 Engineering, 2300 Recreation, September 1982, web search 08/28/2010, original source: http://www.fs.fed.us/t-d/pubs/pdfimage/82711302.pdf
Water Wells and Septic Systems Handbook, R. Dodge Woodson. This book is in the upper price range, but is worth the cost for serious septic installers and designers.
Quoting Amazon: Each year, thousands upon thousands of Americans install water wells and septic systems on their properties. But with a maze of codes governing their use along with a host of design requirements that ensure their functionality where can someone turn for comprehensive, one-stop guidance? Enter the Water Wells and Septic Systems Handbook from McGraw-Hill.
Written in language any property owner can understand yet detailed enough for professionals and technical students this easy-to-use volume delivers the latest techniques and code requirements for designing, building, rehabilitating, and maintaining private water wells and septic systems. Bolstered by a wealth of informative charts, tables, and illustrations, this book delivers:
* Current construction, maintenance, and repair methods
* New International Private Sewage Disposal Code
* Up-to-date standards from the American Water Works Association
Wells and Septic Systems, Alth, Max and Charlet, Rev. by S. Blackwell Duncan, $ 18.95; Tab Books 1992. We have found this text very useful for conventional well and septic systems design and maintenance --DF.
Quoting an Amazon description:Here's all the information you need to build a well or septic system yourself - and save a lot of time, money, and frustration. S. Blackwell Duncan has thoroughly revised and updated this second edition of Wells and Septic Systems to conform to current codes and requirements. He also has expanded this national bestseller to include new material on well and septic installation, water storage and distribution, water treatment, ecological considerations, and septic systems for problem building sites.
Carson, Dunlop & Associates Ltd., 120 Carlton Street Suite 407, Toronto ON M5A 4K2. Tel: (416) 964-9415 1-800-268-7070 Email: email@example.com. The firm provides professional home inspection services & home inspection education & publications. Alan Carson is a past president of ASHI, the American Society of Home Inspectors. Thanks to Alan Carson and Bob Dunlop, for permission for InspectAPedia to use text excerpts from The Home Reference Book & illustrations from The Illustrated Home. Carson Dunlop Associates' provides extensive home inspection education and report writing material.
The Illustrated Home illustrates construction details and building components, a reference for owners & inspectors. Special Offer: For a 5% discount on any number of copies of the Illustrated Home purchased as a single order Enter INSPECTAILL in the order payment page "Promo/Redemption" space.
TECHNICAL REFERENCE GUIDE to manufacturer's model and serial number information for heating and cooling equipment, useful for determining the age of heating boilers, furnaces, water heaters is provided by Carson Dunlop, Associates, Toronto - Carson Dunlop Weldon & Associates Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on any number of copies of the Technical Reference Guide purchased as a single order. Just enter INSPECTATRG in the order payment page "Promo/Redemption" space.
The Home Reference Book - the Encyclopedia of Homes, Carson Dunlop & Associates, Toronto, Ontario, 25th Ed., 2012, is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. Field inspection worksheets are included at the back of the volume.
Special Offer: For a 10% discount on any number of copies of the Home Referen
ce Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on these courses: Enter INSPECTAHITP in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Horizon Software System manages business operations,scheduling, & inspection report writing using Carson Dunlop's knowledge base & color images. The Horizon system runs on always-available cloud-based software for office computers, laptops, tablets, iPad, Android, & other smartphones
Support InspectApedia.com & See Fewer Advertisements
From Google's Contributor website: Contribute a few dollars each month. See fewer ads. The money you contribute helps fund the sites you visit.