Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
OIL STORAGE TANKS
ABANDONING OIL TANKS
AGE of OIL TANK
ANODES & DIP TUBES on WATER HEATERS
BURIED OIL TANK ADVICE
BURIED OIL TANKS, FINDING
COMBUSTION PRODUCTS & IAQ
DEFINITION of Heating & Cooling Terms
DIAGNOSE & FIX HEATING PROBLEMS-BOILER
DIAGNOSE & FIX HEATING PROBLEMS-FURNACE
DIRECTORY of OIL TANK EXPERTS
FILTERS, OIL on HEATING EQUIPMENT
FIRE SAFETY CONTROLS
FLOATING UP OIL STORAGE or SEPTIC TANKS
FLOODED HEATING EQUIPMENT REPAIR
FLOODED WATER HEATER REPAIR
FUEL OIL TYPES & CHARACTERISTICS
FUEL UNIT, HEATING OIL PUMPS
GALVANIC SCALE & METAL CORROSION
GAUGES ON HEATING EQUIPMENT
HEAT TAPES, Heat, Insulation prevent Freeze-Up
HEATING COST FUEL & BTU Cost Table
HEATING COST SAVINGS METHODS
HEATING OIL CLOUD WAX GEL POINT
HEATING OIL EXPOSURE HAZARDS, LIMITS
HEATING OIL - OLD, USEABLE?
HEATING OIL PIPING TROUBLES
HEATING OIL SHELF LIFE
HEATING OIL SLUDGE
HEATING OIL TANKS
HEATING OIL TYPES & PROPERTIES
HEATING OIL USAGE RATE
HEATING SYSTEM NOISES
HOME BUYERS GUIDE TO OIL TANKS
NOISE CONTROL for HEATING SYSTEMS
NOISES COMING FROM WATER HEATER
ODORS & SMELLS DIAGNOSIS & CURE
ODORS FROM HEATING SYSTEMS
OIL FILTERS on HEATING EQUIPMENT
OIL FUEL TYPES & CHARACTERISTICS
OIL FILL PIPE LEAKS
OIL SPILL CLEANUP / PREVENTION
SOOT on OIL FIRED HEATING EQUIPMENT
STAIN DIAGNOSIS on BUILDING INTERIORS
THERMAL TRACKING & HEAT LOSS
VIDEO GUIDES: Heating System Videos
VIDEO GUIDES - InspectAPedia.com
WINTERIZE A BUILDING
Oil tank leaks at the fill or vent piping: this article discusses the causes of leaks at oil tank fill or vent piping, what the leak and other hazards are, and what to do about oil tank piping leaks.
Green links show where you are. © Copyright 2013 InspectAPedia.com, All Rights Reserved.
It is very common for there to be leakage around the oil filler pipe or vent pipe where they are connected to the top of an oil tank. If the tank is buried these leaks may go undetected for some time, but on an above ground oil tank, inside or outside, the seepage is quickly visible and also can be smelled by most owners shortly after an oil delivery.
There are the reasons for the leakage:
Heating oil leak problems at oil tank fittings and pipe threads
The pipe threads (NPT) which are cut into an oil tank top tapping intended to accept the filler pipe or vent pipe are not precisely machined - they are a bit rough.
So are the threads on most large-diameter iron piping used to screw into the tapping.
Having installed a few of these, we can testify that it requires some very careful workmanship to make a leak-tight joint, combining cleaning of the threads, use of a high quality pipe dope rated for use on petroleum products, and turning the pipe into the tapping with sufficient force to seal it without damaging threads. In sum, often the connection is simply not very tight.
Heating oil leak problems due to pressurized oil storage tank fill procedures
Wrong. Oil companies recognize that the time needed to complete an oil delivery is part of their profit or loss picture. Modern oil delivery trucks are designed to pump heating oil into the tank under pressure in order to speed the delivery process.
Photo at left: the oil delivery operator is demonstrating the correct and thoughtful way to fill an indoor or buried oil storage tank. During oil tank filling the driver is listening to the tank whistle or tank alarm to avoid over-filling the tank - a common source of seepage and occasional heating oil or fuel oil spills. If the plumber or installer locates oil fill and vent pipes where they are difficult to access, don't expect such careful oil deliveries.
In fact most modern oil tank filler caps have a special fitting, often different from one oil company to the next, that permits the installer to "lock" the filler hose to the filler pipe during the fill-up procedure.
Usually an oil storage tank is filled right to its top during an oil delivery. This is because the way that the delivery driver knows that the tank is full is that s/he is (supposed to be) listening at the filler pipe. Tank fill or vent valves are (supposed to be) equipped with a whistling noisemaking device that indicates when the tank is full as the heating oil reaches the sounding device.
So if, unlike the driver in our photo above, the oil delivery pumper is not listening, say s/he went aside to smoke a cigarette or make a cell call, or if the tank top fittings are not absolutely tight, it is common to see some leakage around the tank top after a fill-up. We discuss details of oil tank pressures created during the oil tank filling operation at Oil Tank Pressures.
When and what should you do something about a leak at the top fittings of an oil tank?
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the search box below to ask a question or to search the InspectApedia.com website.
Ask a Question or Enter Search Terms in the InspectApedia search box just below.
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.