Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
AFUE DEFINITION, RATINGS
AGE of HEATERS, BOILERS, FURNACES
BACKDRAFTING HEATING EQUIPMENT
BACKFLOW PREVENTER VALVE, HEATING SYS
BANGING HEATING PIPES RADIATORS
BOILER CONTROLS & SWITCHES
BOILER LEAKS CORROSION STAINS
BOILER NOISE SMOKE ODORS
BOILER OPERATING PROBLEMS
BOOKSTORE - InspectAPedia
BTU USAGE MONITORS
CHEMICAL TREATMENTS for BOILERS
CHIMNEY INSPECTION DIAGNOSIS REPAIR
CIRCULATOR PUMPS & RELAYS
DEFINITION of Heating & Cooling Terms
DIAGNOSE & FIX HEATING PROBLEMS-BOILER
DRAFT MEASUREMENT, CHIMNEYS & FLUES
DRAFT REGULATORS, DAMPERS, BOOSTERS
FILTERS, OIL on HEATING EQUIPMENT
FIRE SAFETY CONTROLS
FLOODED HEATING EQUIPMENT REPAIR
FLUE VENT CONNECTORS
FREEZE-PROOF A BUILDING
FUEL OIL TYPES & CHARACTERISTICS
FUEL UNIT, HEATING OIL PUMPS
GAS BURNER Flame & Noise Defects
GAS PIPING, VALVES, CONTROLS
GAUGES ON HEATING EQUIPMENT
HEATING COST SAVINGS METHODS
HEATING LOSS DIAGNOSIS-BOILERS
HEATING OIL PIPING TROUBLES
HEATING SYSTEM INSPECTION GUIDE
HEATING SYSTEM NOISES
HIGH EFFICIENCY BOILERS/FURNACES
LP & Natural Gas Safety Hazards
MANUALS & PARTS GUIDES - HVAC
MOTOR OVERLOAD RESET SWITCH
NO HEAT - BOILER
NOISE, HEATING SYSTEMS
ODORS FROM HEATING SYSTEMS
OIL PUMP FUEL UNIT
PUFFBACKS, OIL BURNER
RELIEF VALVES - STEAM TP VALVES
Reset Switch - Heater Primary Control
RESET SWITCH - ELECTRIC MOTOR
Reset Switch - Stack Relays
SAFETY, HEATING INSPECTION
SAFETY RECALLS CHIMNEYS VENTS HEATERS
SOOT on OIL FIRED HEATING EQUIPMENT
SPILL SWITCHES - Flue Gas DetectionS
STACK RELAY SWITCHES
STEAM HEATING SYSTEMS
THERMOSTATS, HEATING / COOLING
VIDEO GUIDES: Heating System Videos
How to diagnose & fix a too-cold steam radiator? No steam system heat in some or all building areas? What to check first. Troubleshooting cold steam radiators: this article describes the diagnosis & repair of cold steam heating convectors or steam radiators. We also describe how to fix a steam radiator that is too hot. And we list less common causes of cold steam radiators in buildings and we describe how to fix these conditions.
Green links show where you are. © Copyright 2013 InspectAPedia.com, All Rights Reserved.
Our page top heating system illustration is provided compliments of Carson Dunlop Associates.
If your heating system uses hot water (not steam) radiators, convectors, or baseboards, in other words, not steam heat, see COLD HOT WATER BASEBOARD / RADIATOR for help in diagnosing and fixing radiators that won't get hot. This article series answers most questions about all types of heating systems and gives important inspection, safety, and repair advice. If you don't know what kind of heat your building uses, we explain how to figure out the answer at HEATING SYSTEM TYPES. If your heating system is not working properly, see NO HEAT - BOILER or NO HEAT - FURNACE.
Make sure that your room thermostat is set to a temperature higher than the temperature in the room - so that it is calling for heat.
Make sure that your heating boiler is working, that is that the heating boiler turns on and off normally. A steam boiler will usually turn on right away in response to the thermostat being turned up or on a call for heat.
Make sure that the control valve at the heating radiator is "open" or "on" as we describe just below.
Steam boiler operating problems that can lead to inadequate heat - radiators not hot enough or distant radiators not heating up - diagnostic checks.
If you steam radiator is too hot in a two-pipe steam system, according to the U.S. DOE, check the steam traps:
Frequently-Asked Questions about troubleshooting steam heat radiators & convectors
Question: trouble finding the cause of cold steam radiators in two buildings - traced to internal leak in steam boiler
I have done all the above. Pitched the radiator, changed the air valve, even putting a larger orifice air valve and removing the radiator to check the open and closed position of the supply valve. I still get cold radiators. The larger steam supply valves are properly pitched in the basement and the boiler runs a sufficient amount of time to build up pressure. Is there anything else?? - Robert
This problem exists in both a private house and in a six family dwelling. Both have a one pipe system. In the private house, only the second fl rear (about 3 radiators) are cold. The radiators directly below are hot. In the 6 family, both apartments on the 2nd fl are cold or get hot on one side only. - Robert
Reader Diagnosis: cold radiators traced to boiler leaks caused by condensate return line leaks
If anyone has this problem check for leaks, cracks or holes in the sections of the steam boiler. Also check return lines for leaks. It seems if fresh water is constantly being fed to the boiler, a corrosive reaction takes place in the sections of the boiler.
In this case there were leaks undetected in the return lines which caused water to be added constantly.
The fresh water ate at the sections in the chamber causing two small holes. This in turn did not allow enough pressure to build up for steam to reach the radiators. After replacing boiler all radiators were very hot and also at a much faster rate. - Robert
Thanks for your comments, and I apologize that we didn't catch them sooner. Sometimes the volume of comments leaves us behind.
And your reminder that abnormal water consumption increases corrosion in the boiler is very important since, as you explain, the result can be leaks in the boiler itself.
Unfortunately the good news of a correct diagnosis can lead to the bad news of a costly repair - the need for a replacement of the steam boiler.
We're always smarter in hindsight - and now I also see that your observation that lower radiators got hot but upper level radiators all did not, could have pointed to a steam pressure problem. Too often an amateur "fixes" the problem by trying to set up the steam pressure at the control switch - not the right approach.
Questions & answers or comments about how to troubleshoot cold steam radiators, baseboards, or convector heaters.
Ask a Question or Enter Search Terms in the InspectApedia search box just below.
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.