Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
AIR CONDITIONING & HEAT PUMP SYSTEMS
BACKDRAFTING HEATING EQUIPMENT
BACKUP HEAT for HEAT PUMPS
BANGING HEATING PIPES RADIATORS
BLOWER FAN OPERATION & TESTING
BOOKSTORE - InspectAPedia
BTU USAGE MONITORS
CARBON MONOXIDE - CO
CIRCULATOR PUMPS & RELAYS
DIAGNOSTIC GUIDES A/C / HEAT PUMP
DIAGNOSE & FIX HEATING PROBLEMS-BOILER
DIAGNOSE & FIX HEATING PROBLEMS-FURNACE
DIRECT VENTS / SIDE WALL VENTS
DRAFT REGULATORS, DAMPERS, BOOSTERS
DUCT SYSTEM & DUCT DEFECTS
ELECTRIC HEAT, DIAGNOSIS, REPAIR
ELECTRIC MOTOR DIAGNOSTIC GUIDE
FAN, AIR HANDLER BLOWER UNIT
FLOODED HEATING EQUIPMENT REPAIR
FLUE SIZE SPECIFICATIONS
GAS BURNER Flame & Noise Defects
GAS PIPING, VALVES, CONTROLS
GEOTHERMAL HEATING SYSTEMS
HEAT PUMPS, DIAGNOSIS, REPAIR
HEATING COST SAVINGS METHODS
HEATING OIL PIPING TROUBLES
HEATING OIL TANKS
HEATING SYSTEM NOISES
HEATING SYSTEM TYPES
GAS LP & NATURAL GAS SAFETY HAZARDS
MANUALS & PARTS GUIDES - HVAC
MIXING / ANTI-SCALD VALVES
MOTOR OVERLOAD RESET SWITCH
NOISE, HEATING SYSTEMS
ODORS FROM HEATING SYSTEMS
OIL FILTERS on HEATING EQUIPMENT
OIL FILL PIPE LEAKS
OIL SPILL CLEANUP / PREVENTION
PLASTIC Plexvent / Ultravent RECALL
PUFFBACKS, OIL BURNER
RELIEF VALVE LEAKS
Reset Switch - Heater Primary Control
RESET SWITCH - ELECTRIC MOTOR
Reset Switch - Stack Relays
SAFETY, HEATING INSPECTION
SAFETY RECALLS CHIMNEYS VENTS HEATERS
SOLAR HEATING SYSTEM DESIGNS
SOOT on OIL FIRED HEATING EQUIPMENT
STEAM HEATING SYSTEMS
THERMOSTATS, HEATING / COOLING
VIDEO GUIDES: Heating System Videos
WINTERIZE A BUILDING
WOOD, COAL STOVES & FIREPLACES
WOOD STOVE SAFETY
ZONE VALVES, HEATING
Hot water heating system air scoops, air separators & air scoops: what they do, where they belong, how they work to prevent noise and loss of heat in hydronic heating systems. In this heating system article series we explain how to Identify the parts & components of Hot Water Heating Boilers and hot water heating systems including oil burners and their parts, boiler parts, hot water baseboard and its parts, hot water radiators, and hot water convector units and their parts and controls. Each simple definition includes links to detailed articles discussing how to identify, inspect, diagnose, and repair each component of the heating system.
This article series answers most questions about central hot water heating system troubleshooting, inspection, diagnosis, and repairs. We describe how to inspect, troubleshoot and repair heating and air conditioning systems to inform home owners, buyers, and home inspectors of common heating system defects.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Air Scoops, Air Separators, Air Purgers on Hot Water Heating Systems Eliminate Air and Noise & Prevent Air Bound Loss of Heat
Hot water heating systems, whether using baseboards, convectors, radiators, or even radiant tubing, can be noisy if there is air circulating in the system. Worse, as we discuss at AIRBOUND HEAT SYSTEM REPAIR by WATER FEED VALVE, if the amount of air is excessive, the circulator pump(s) may not be able to circulate hot water at all and portions of the heating system (radiators, baseboards etc) may just stay cold.
Air is dissolved in cold water in any hydronic heating system. When we heat the water, some of that air returns to a gas form as air bubbles that cause noise heard at circulator pumps, in the hot water piping, or in radiators or baseboards.
Air might also enter a hot water heating system due to a leak in piping that lets water out when the system is hot and lets air in when the heating system is cold. Of course there are other causes of noise in heating systems, but air in the piping is perhaps the most common noise complaint.
Taco™, a manufacturer of heating system components and controls, provides this clear explanation of the function of the air scoop or air separator on a hot water heating system:
Also see AIR BLEEDER VALVES that work with air scoops to remove un-wanted air from hydronic (hot water) heating systems. Air in heating distribution piping, boilers, radiators, can prevent hot water circulation and thus stop heat from being delivered to the occupied space. If your heating system is having trouble with noise or cold baseboards or radiators, see AIRBOUND HEAT SYSTEM REPAIRS.
For a complete list of diagnostic articles for radiators or baseboards that do not get hot when they should includes see AIR-BOUND HEATING SYSTEMS.
Air Troubles on Hot Water Heating Systems & the Air Scoop
Install the air scoop in the right direction: Notice the arrow cast into the body of the Taco™ air scoop (photo above, sketch at left) and on the sketch of the Sparco™ air purger below?
If a check valve is installed, make sure it too is installed in the right direction. Your system may not use a check valve if its circulator pump incorporates an internal flow check valve (IFC).
If your hot water heating system is noisy, is not automatically purging air, or is air bound, in addition to purging un-wanted air manually and finding and fixing any leaks that are letting air into the heating distribution piping or boiler, be sure that your air scoop is properly installed.
Make sure the air vent is working: Even if the air scoop is properly installed and located (see Taco's sketch, above), if the "Hy Vent" or "Float Vent" or automatic air purge valve (these are all synonyms from different manufacturers) is not working the system may not successfully purge air. See AIR BLEEDER VALVES, and see AIRBOUND HEAT SYSTEM REPAIR by WATER FEED VALVE.
At above left we illustrate another air purger manufactured by Sparco.
At above right we include a sketch of Bell & Gosset's inline air separator (IAS). The B&G inline air separator has the same function as the air scoops discussed above, but its internal workings are a bit different. Here is B&G's explanation of how their IAS works:
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Try the search box just below or if you prefer, post a question or a comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.