InspectAPedia tolerates no conflicts of interest. We have no relationship with advertisers, products, or services discussed at this website.
Electric motor motor noise diagnosis: this article describes the causes, diagnosis, cure & prevention of noises traced to the electric motor component of an oil burner, air conditioner, or other electric-motor driven equipment. The sketch of an oil burner shown above is provided courtesy of Carson Dunlop Associates.
For HVAC compressor motors that hum
see HUMMING sounds from A/C or Heat Pump system
2. Motor shaft end play
Excessive electric motor noise can be caused by excessive motor shaft end play - the distance the shaft can move in and out of the motor.
Beckett (1989)  notes that a new electric AC motor will have no more than .035" of movement in and out. Push the shaft all the way "in", and measure its outwards movement. (Automotive feeler gauges can sometimes assist).
If electric motor shaft end play is more than .060" and if noise is a problem, the motor could be suspect.
3. Motor is improperly mounted or aligned
Motor vibration noise can be caused by misalignment of the motor due to its mounting position or due to bad shaft couplings to driven devices such as fans or fuel units.
We find this problem also on hot water heating circulator motors.
Realign the motor or replace a bad coupling. - Beckett (1989) 
4. Electrical phase problems
If the motor is a 3-phase unit running only on one phase there may be an open circuit, blown fuse/tripped breaker, or unbalanced voltages. Any of these conditions can cause motor vibration.
Check for open circuit, blown fuse, tripped breaker, uneven voltages on the three phases. - Beckett (1989) 
Bad motor bearings cause vibration at the shaft support at either end of the motor.
Check for bearing damage (loose, side play, noise, visible damage); Usually motor bearing damage is caused by improper mounting or motor misalignment.
We've seen a whole series of hot water heating system circulator motors that were destroyed and replaced, one after another until finally a more experienced tech noted that the motor mount was askew. Beckett (1989) 
7. Loose coupling between electric motor and driven appliance
A bad coupling between the motor drive shaft and the driven fan, fuel unit, or other component can cause vibration and noise as well as motor damage.
Replace the bad coupling; If there is a loose sheave, tighten the set screws or replace that component.
Adapted & expanded from Beckett (1989)
Other Noises at HVAC Equipment
Watch out: some noises at HVAC equipment could be a sign of dangerous operation. For example, rumbling, stumbling noisy oil burners, especially accompanied by smoke, or oil smells, could be a sign of pending PUFFBACKS, OIL BURNER.
Squealing motors may be traced to failed bearings, overheating, and on occasion the risk of an electrical fire.
Continue reading at ELECTRIC MOTOR OFF on RESET or select a topic from closely-related articles below, or see our complete INDEX to RELATED ARTICLES below.
Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Ask a Question or Search InspectApedia
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
 Beckett Oil Burners, "Burner Motor Service Facts", Beckett Corporation, Technical Information, 15 June 1989 [copy on file as PDF].
 "Noise and Moisture, Using scare tactics” may be necessary when installing a new heating system", George Lanthier, Fuel Oil News, M2MEDIA360, 1030 W. Higgins Road Suite 230, Park Ridge, IL 60068 847-720-5600
02/1/2006. According to Fuel Oil News, George Lanthier owns Firedragon Enterprises and is the author of nine books on oil heating and heating systems. He is a teaching consultant and expert witness on oil heating systems. He can be contacted at 132 Lowell Street, Arlington, MA 02474-2756. His phone number is (781) 646-2584 and he can be faxed at (781) 641-7099. He can also be contacted through his Web site at www.FiredragonEnt.com.
The ILLUSTRATED HOME illustrates construction details and building components, a reference for owners & inspectors. Special Offer: For a 5% discount on any number of copies of the Illustrated Home purchased as a single order Enter INSPECTAILL in the order payment page "Promo/Redemption" space.
TECHNICAL REFERENCE GUIDE to manufacturer's model and serial number information for heating and cooling equipment, useful for determining the age of heating boilers, furnaces, water heaters is provided by Carson Dunlop, Associates, Toronto - Carson Dunlop Weldon & Associates Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on any number of copies of the Technical Reference Guide purchased as a single order. Just enter INSPECTATRG in the order payment page "Promo/Redemption" space.
The HOME REFERENCE BOOK - the ENCYCLOPEDIA of HOMES, Carson Dunlop & Associates, Toronto, Ontario, 25th Ed., 2012, is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. Field inspection worksheets are included at the back of the volume.
Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on these courses: Enter INSPECTAHITP in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The HORIZON SOFTWARE SYSTEM manages business operations,scheduling, & inspection report writing using Carson Dunlop's knowledge base & color images. The Horizon system runs on always-available cloud-based software for office computers, laptops, tablets, iPad, Android, & other smartphones