Gas Fireplace Direct Vent Termination Cap Clearance Distances
POST a QUESTION or READ FAQs about the installation or diagnosis of sidewall vent or direct vent chimney or flue exhaust systems for heating appliances: oil, gas, other fuels firing heating appliances & fireplaces
InspectAPedia tolerates no conflicts of interest. We have no relationship with advertisers, products, or services discussed at this website.
Direct vent chimneys or exhaust for gas fireplaces & gas fireplace inserts:
This article gives typical clearance distance requirements between the termination cap of a gas fireplace or fireplace insert and other building or site features such as windows, doors, other mechanical system components, air intakes, exhausts.
This article series describes side wall vent systems for conventional & mid-range-efficiency heating boilers, furnaces & water heaters. We include for comparison, low temperature side wall vent systems used by high efficiency or condensing boilers, furnaces & water heaters.
We also provide a MASTER INDEX to this topic, or you can try the page top or bottom SEARCH BOX as a quick way to find information you need.
Clearance Distances for the Exterior Vent Termination of a Direct-Vent Gas Fireplace / Heater
The clearance distancess shown above and at the top of this page are between the vent termination cap of a gas fireplace and the air inlet side of an A/C or heat pump compressor/condenser.
At CLEARANCE DISTANCE, HVAC a reader commented that his building inspector did not accept the safety of this installation.
[Click to enlarge any image]
Reviewing manufacturer's installation instructions for a typical gas fireplace direct-vent exhaust termination cover or cap we find that the clearance distances to other building features or mechanical systems are similar but not necessarily identical to the Direct Vent Gas Appliance clearances given in the preceding table.
This may be because that a typical gas fireplace heater does not use a power-exhaust vent or also because of different BTUH ranges.
Minimum Clearance Distance Requirements for the Exterior Vent Termination of a Gas Fireplace Heater8
Direct vent gas fireplace exhaust termination item clearance distance
Distance required (Canada)1
Distance required (USA)2
Clearance above paved sidewalk or a paved driveway located on public property
Clearance above paved sidewalk or a paved driveway located on public property
Clearance to a mechanical air supply inlet
3' (91cm) above if within 10' (3m) horizontally
Clearance distance from gas vent termination cap to adjacent building
Clearance distance from gas vent termination cap to any mechanical air-supply inlet
48" (Travis 2016)
Clearance to the side of any non-mechanical supply air inlet
36" (Travis 2016)
Clearance to each side of center line extended above [the gas] meter/regulator assembly
Clearance to gas service or gas meter regulator vent outlet
36 " (90cm)
Clearance above any non-mechanical supply air inlet
36 "(Travis 2016)
Clearance distance to bushes, garden
sheds, fences, decks or utility buildings
24" (Majestic 2016)
Clearance distance horizontally to any surface such as exterior walls, for vertical terminations
24" (Travis 2016)
Clearance distance to any vinyl surface
24" (Travis 2016)
Vertical clearance to ventilated soffit located above the terminal within a horizontal distance of 2 feet (61cm)
from the center line of the terminal (check with the local code)
Clearance below a veranda, porch, deck or balcony (must have two open sides)
18" (Travis 2016)
Clearance below ventilated soffits
18" (Travis 2016)
Clearance to or below any unventilated soffit
or below any roof surface
11" (Travis 2016)
Clearance distance above the roof line (for above-roof vents)
12" (Travis 2016)
Clearance distance to vinyl surfaces such as vinyl siding or vinyl trim
Clearance above any grade, veranda, porch, deck, or balcony
12" (30 cm)
12" (30 cm)
Clearance to window or door that may be opened
12" (30 cm)
9" (23 cm)8
Clearance to permanently closed window
Clearance to outside corner / corner walls: with approved Termination Caps
3" (Travis 2016)
Clearance to inside corner: with approved Termination Caps
Clearance to roof eaves
6" (Travis 2016)
Clearance to outside corner: with Manufacturer's Special Termination Cap 6
1-6" (15cm)6, 8
Clearance to inside corner: with Manufacturer's Special Termination Cap 6
6" (15cm)6, 8
1-6" (15cm)6, 8
Clearance to non-mechanical air supply inlet to building or the combustion air inlet to any other appliance
9" (23 cm)
Clearance under balcony, porch, or veranda
Clearance from outside corner walls
3" (Travis 2016)
Opinions On Additional Recommended Cleareance Distances from a Direct Vent Gas Fireplace Exhaust Opening to other Building Features or Equipment
Distance to an air conditioner or heat pump compressor/condenser unit to the nearest point of a direct vent gas heater or gas fireplace exhaust
24 inches to 6 feet [Note 6]
The table of gas fireplace vent clearances above is derived from the codes, standards, and example gas fireplace installation manuals cited in this article.
Watch out: the final legal authorities for acceptable clearance distances from the direct vent opening/hood on a gas fireplace to building features are the manufacturer of the specific gas fireplace (see the I&O manual for your fireplace) and your local building code inspector.
Be sure to check the Installation & Operation manual for your fireplace as the manufacturer's specifications could differ from the gas fireplace vent opoening clearances table above.
Notes from the original source cited below:
1. CSA B149.1, Natural Gas and Propane Installation Code
2. ANSI Z223.1/NFPA 54, National Fuel Gas Code
3. A vent shall not terminate directly above a sidewalk or paved driveway which is located between two single family dwellings and serves both dwellings.
4. Permitted only if veranda, porch, deck, or balcony is fully open on a minimum of two sides beneath the floor.
5. Clearance in accordance with local installation codes and the requirements of the gas supplier
5.a 3 feet (91cm) within a height of 15 feet (4.5m) above the meter / regulator assembly
5.b 3 feet (91cm) above - if within 10 feet (3m) horizontally
6. This is the author's OPINION considering that heat from the gas exhaust vent blowing onto an A/C compressor unit condensing coil could imact the coil's ability to condense refrigerant back to liquid form, affecting the condenser unit's efficiency and life. I'm considering the situation in which the hot gas exhaust blows onto the air intake side of a condensing coil.
(Most modern condenser units draw cooling air in from the unit sides and push it out the unit's top). Also see CLEARANCE DISTANCE, HVAC
7. This is a Regency Fireplace Producucts termination cap; other manufacturers may have similar options. See the additional sources below.
8. Watch out: check with the manufacturer of your heater and venting system for specific venting instructions and clearances to combustibles or to other features as these distances may vary from one appliance and manufacturer to another. For example the Travis Industries direct vent clearances include some distances that are different from the tables given above.
DuraVent (and other manufacturers) warn that if a gas appliance, fireplace heater or other heater is not properly installed the system may be unsafe.
A major cause of vent related fires is failure to maintain clearances (air spaces) to combustible materials. It is of utmost importance that double wall direct vent pro be installed only in accordance with these [the manufacturer's] instructions.
Additional sources of direct vent gas fireplace clearance information:
DuraVent, "Direct Vent Pro Venting System for Direct Vent Gas Stoves and Fireplaces", M&G Duravent, Inc., Tel: 800-835-4429, Website: www.duravent.com, retrieved 2016/04/07, original source: http://www.duravent.com/docs/product/l954_w.pdf
Note: This gas fireplace insert installation manual expects the fireplact to be vented vertically through an existing chimney.
Excerpt: Venting system must be installed by a Mendota approved person according to Figure 3. pg. 8 with clamps securely in place and all joints leakproof.
There must not be any obstruction such as bushes, garden
sheds, fences, decks or utility buildings within 24”
(610 mm) from the front of the termination hood.
Do not locate termination hood where excessive snow or
ice build up may occur. Be sure to check vent termination
area after snow falls, and clear to prevent accidental
blockage of venting system. When using snow blowers,
make sure snow is not directed towards vent termination
R.H. Peterson Co., "REALFYRE PREMIUM GAS LOGS OWNER'S MANUAL" [PDF] Robert H. Peterson Co. 14724 East Proctor Avenue, City of Industry, CA 91746 USA Website: http://www.rhpeterson.com/, Tel: 800 332 3973
Travis Industries House of Fire, "4415 HO GSR2 (WITH SCREEN) INSTALLATION MANUAL", [PDF], Travis Industries, Inc., 12521 Harbour Reach Dr., Mukilteo WA 98275, USA (2014), retrieved 2016/04/07,original source: http://www.fireplacex.com/TravisDocs/100-01353.pdf
This manual includes a detailed description of allowable vertical vent terminations using 0, or 2 45° or 2 90° Offsets in the flue vent piping as well as horizontal vent termination and routing restrictions.
Question: what is the required clearance between adjacent houses & a neighboring direct vent fireplace?
Is there a minimum distance between brick houses in Toronto for venting termination of a fireplace using direct vent? - A.W., 12/30/2012
Reply: 4 feet or local codes
I have not found building code citations that refer to nearby or adjacent buildings when specifying clearances for direct vent fireplaces, though some of the fireplace installation manuals we reviewed specified a minimum of four feet to the nearest separate building.
It seems likely that your local building code inspector would agree that the clearance requirements for the building in which the fireplace is installed would set the minimum acceptable clearances that would then apply also to a nearby or adjacent building.
In other words, if the fireplace vent distances and position relative to your own building windows or doors were LESS THAN those to the windows & doors on the building where the fireplace is installed, and presuming for a moment that the fireplace was installed properly, meeting local building permit and code requirements, then a violation probably exists.
If the fireplace vent distances and position relative to your own building windows and doors is GREATER THAN those to the windows and doors where the fireplace is installed, and presuming for a moment that the fireplace was installed properly, meeting local building permit and code requirements, then a violation probably does not exist.
Take some some sharp photos of the installation that concerns you, or make a sketch and send those along and we may be able to comment further.
Continue reading at DIRECT VENTS / SIDE WALL VENTS or select a topic from closely-related articles below, or see our complete INDEX to RELATED ARTICLES below.
 "Instructions for Installing FIELD Type AF Barometric Draft Controls," Form No. 31 DC 30666, Field Corporation, Mendota, IL 61342, web search 04/02/2011, original source: http://www.fieldcontrols.com/pdfs/04592700.pdf, Field Controls, Kingston, North Carolina 28501, Tel: 919-522-3031
 Tjernlund Draft Controls, A Series (single action for oil, solid fuel, and fan-assisted gas burners) and B Series (double action for gas heating appliances), web search 04/02/1011, original source: http://www.tjernlund.com/Tjernlund_8500490.pdf , Tjernlund Products, Inc., 1601 Ninth Street, White Bear Lake MN 55110-6794, Tel: 651-426-2993 or 800-255-4208 website: www.tjernlund.com Email: email@example.com
 "Gas Side Wall Power Venters", Tjernlund Corporation, 1601 9th Street
White Bear Lake, MN 55110-6794 Tel: 800-255-4208, Website: tjernlund.com/gassidewall.htm, Quoting: Side Wall Vent Systems save time and money and are excellent for electric to gas/oil, renovations, new construction or for replacing deteriorated chimneys. Side wall venting saves costly materials and labor on two, three or more story runs. It also increases living space by cutting out interior chases. Proven safety interlocks assure proper exhaust, a feature conventional chimneys do not offer in today's homes and buildings.
 "Oil Side Wall Vent Systems", Tjernlund Corporation, 1601 9th Street
White Bear Lake, MN 55110-6794 Tel: 800-255-4208, provides SS2 SideShot Wall Vent System. Website: .tjernlund.com/oilsidewall.htm Quoting: The SideShot® models SS1 and SS2 SideWall Vent Systems include the UC1 Universal Control ... [ and are ] designed for oil fired heating equipment or a deluxe gas vent system. Factory wired safety and operating controls allow simple interlock with any burner. ... SS2 features a self-cleaning stainless steel, backward inclined impeller and sealed ball bearing motor for virtually maintenance free installations.
Tjernlund Corporation also provides a Sidewall Venting sizing tool for oil fired heating equipment (www.tjernlund.com/Sizing/Oil.htm) and a separate tool for gas fired heating equipment (www.tjernlund.com/Sizing/gas.htm).
 Bradford White Sidewall Power Venter Kit, Field Controls, Tel: 252-522-3031, Website: www.fieldcontrols.com
 National Fuel Gas Code (Z223.1) $16.00 and National Fuel Gas Code Handbook (Z223.2) $47.00 American Gas Association (A.G.A.), 1515 Wilson Boulevard, Arlington, VA 22209 also available from National Fire Protection Association, Batterymarch Park, Quincy, MA 02269. Fundamentals of Gas Appliance Venting and Ventilation, 1985, American Gas Association Laboratories, Engineering Services Department. American Gas Association, 1515 Wilson Boulevard, Arlington, VA 22209. Catalog #XHO585. Reprinted 1989.
 "Tankless water heater side wall vent termination", Rheem Corporation, Website: http://www.rheem.com/products/tankless_water_heaters/
 "Gold™ CGs Gas-Fired Water Boilers Venting Supplement: sidewall direct exhaust, vertical direct exhaust, sidewall direct vent, vertical direct vent models
 "Be Alert, Keep Sidewall Vents Clear", Vermont Gas Corporation, P.O. Box 467, Burlington VT 05402 Delivery: 85 Swift St, South Burlington VT 05403. Phone: 802.863.4511.
Email: CustomerService@VermontGas.com, web search 4/1/2012, original source: vermontgas.com/winter/vents.html
 "Power Venting, SWG/CV Power Venter, ComboVent Power Venter, Field Controls, FIELD CONTROLS, LLC
2630 Airport Road
Kinston, NC 28504
 "Gas Fired High Efficiency Furnace Down Flow & Direct Vent (Sealed Combustion) Thermo Pride Model CMA1-50N & CMA2-75N Installation and Service Manual", Thermo Pride, Thermo Products LLC, PO Box 217, North Judson, IN 46366, Tel: 574-896-2133, retrieved 12/30/2012, original source: www.thermopride.com/pdf/mg-508.pdf, copy on file as Thermo_Pride_CMA1-50N_CMA2-75N_Installation_mg-508.pdf
Carson, Dunlop & Associates Ltd., 120 Carlton Street Suite 407, Toronto ON M5A 4K2. Tel: (416) 964-9415 1-800-268-7070 Email: firstname.lastname@example.org. The firm provides professional home inspection services & home inspection education & publications. Alan Carson is a past president of ASHI, the American Society of Home Inspectors. Thanks to Alan Carson and Bob Dunlop, for permission for InspectAPedia to use text excerpts from The Home Reference Book & illustrations from The Illustrated Home. Carson Dunlop Associates' provides extensive home inspection education and report writing material.
The Illustrated Home illustrates construction details and building components, a reference for owners & inspectors. Special Offer: For a 5% discount on any number of copies of the Illustrated Home purchased as a single order Enter INSPECTAILL in the order payment page "Promo/Redemption" space.
TECHNICAL REFERENCE GUIDE to manufacturer's model and serial number information for heating and cooling equipment, useful for determining the age of heating boilers, furnaces, water heaters is provided by Carson Dunlop, Associates, Toronto - Carson Dunlop Weldon & Associates Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on any number of copies of the Technical Reference Guide purchased as a single order. Just enter INSPECTATRG in the order payment page "Promo/Redemption" space.
The Home Reference Book - the Encyclopedia of Homes, Carson Dunlop & Associates, Toronto, Ontario, 25th Ed., 2012, is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. Field inspection worksheets are included at the back of the volume.
Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on these courses: Enter INSPECTAHITP in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Horizon Software System manages business operations,scheduling, & inspection report writing using Carson Dunlop's knowledge base & color images. The Horizon system runs on always-available cloud-based software for office computers, laptops, tablets, iPad, Android, & other smartphones