Chimney cleanout doos & opening questions and answers:
Frequently-asked questions & answers about how to find, install, or repair a cleanout opening or access in a chimney.
This article series describes chimney cleanout access doors or ports. We explain that in addition to using the chimney cleanout as a service port to remove debris that has fallen to the bottom of a masonry chimney, the cleanout door and the type of debris found inside can tell us something about the condition of the chimney flue even though we cannot see most of it.
Green links show where you are. © Copyright 2017 InspectApedia.com, All Rights Reserved.
[Click to enlarge any image]
Questions & answers about chimney cleanouts & cleanout openings, posted originally at CHIMNEY CLEANOUT DOOR
On 2017-11-20 by (mod) - what if there is no cleanout at the woodstove chimney?
A woodstove into a vertical metal chimney may have a tee with a removable cleanout. But if you're venting into a masonry flue, then Investigate further. I'm not clear on "falls straight down" - to where? To a crawl space? Basement? Chimney base? Sometimes there's an outdoor cleanout door.
Beware of a chimney with no cleanout or an opening with no door - I'd worry about more than cleaning it, as there can also be draft snafus.
For safety it'd be smart to have the chimney inspected before use. (I know it's getting cold but ...) And you had a permit, right? The permit/inspection can improve the new stove's safety.
IF you have to add a cleanotu door, check out CHIMNEY CLEANOUT CLEARANCE to COMBUSTIBLES https://inspectapedia.com/chimneys/Chimney_Cleanout_Clearance.php
You might want to see WOOD STOVE OPERATION & SAFETY https://inspectapedia.com/heat/Wood_Stoves.php
On 2017-11-20 by Ross
My question, I just put in a wood stove and their is no clean out that I can see. From the top of the chimney it looks like it it falls straight down in the cavity of the house. What do I need to do?
On 2017-11-07 by (mod) - metal chimney tee face or bottom removable cap for cleanout access
I'm not quite sure what you're looking for, but typically what I see on the bottom of the tee is a removable cap. Obviously you wouldn't open it without a bucket below to catch the debris that will fall out
On 2017-11-06 by Dennis Mock
I have a new chimmey system for my wood stove. My question is about the type of cleanout side that needs to attach to the bottom of the triple wall 6" T. Do they make anything like that or will I have to fab one up?
On 2017-06-26 by Crumps Chimney Company
I know it can be a pain to chase a leak, but it can be found and corrected! I suggest
1. Find a Chimney Professional with 10 plus years experience.
2. Have this professional on call when it's raining!
3. Also have them come out before a rainy day to get a grasp on the situation!
4. Someone who's just a certified chimney sweep, will not be enough experience, you need a seasoned person who have seen it all, and have in place a continuous education program for there company,
5. You hound elect to pay $ 300.00 for a good inspection! I hope this helps! Best to you! Ken
On 2017-04-29 23:54:04.521379 by (mod) -
Perhaps a chimscan camera run by your chimney sweep can inspect the flue interior to see the height at which water is entering the flue; it can be anywhere from chimney top - bad rain cap, to top crown - bad seal at chimney top around the flue, to wind-blown rain along the chimney exterior (you tuck pointed it but still there could be leaks), to roof spillage or surface runoff that flows towards the building and leaks into the chimney base. Follow the water.
More points of leaks into chimneys are at CHIMNEY DAMAGE, FROST & MOISTURE - http://inspectapedia.com/chimneys/Chimney_Water_Damage.php
at CHIMNEY STAINS & LEAKS http://inspectapedia.com/chimneys/Chimney_Stains_Leaks.php
and a few more
at CHIMNEY STAINS, INDOORS -http://inspectapedia.com/chimneys/Chimney_Interior_Stains.php
Also review CHIMNEY REPAIRS, TOP & CLAY FLUE TILE http://inspectapedia.com/chimneys/Chimney_Top_Tile_Repairs.php to be sure that all of the repairs at the very chimney top crown were done properly
On 2017-04-29 22:59:58.049764 by Joan
My chimey clean-out door is in the basement. It has leaked water in heavy rainstorms for 17 years. I've spent hundreds of $$ - nothing works. (Tuckpointed the chimney, installed a VERY expensive cap with a grate on top of the chimney, last summer a new roof.) I have a gas fireplace and don't even need a clean-out. Does anyone have any advice?
On 2017-04-24 by (mod) - Smoke moving down into a basement from a first floor suggests safety concerns
Smoke moving down into a basement from a first floor suggests a couple of problems to be found and fixed:
1. the chimney draft is inadequate - could be a problem with chimney leaks in from above or below the fireplace on the first floor, subverting the draft, or could be a bad chimney cap or downdrafts or inadequate chimney height
- you need an inspection from a competent, expert chimney sweep, perhaps certified by the National Chimney Sweeps guild. (Start by checking that the chimney cleanout door is closed and snug).
2. There may be improper and unsafe connections between chimney flues if there are multiple flues
3. There may be improper and unsafe connections in a single chimney flue between floors in the building
On 2017-04-24 by hyjr12
when my wife lights a fire on the main floor (1st) I get smoke in the basement. I had the both flues replaced last year and the fire box sprayed to cover some minor holes.
I cant figure out where the smoke is coming from. I had a new furnace installed last year and the out going pipe is properly sealed to the chimney.
On 2017-04-21 by (mod) re: risk of fire when using a home vacuum cleaner to clean out a chimney baseHY
On 2017-04-20 by hyjr12can you use a shop vac to clean out the ash in the clean out door?
On 2017-04-02 by (mod) re: paint for chimney cleanout doorsSure, Kenny, you can paint a metal cleanout door on a chimney: I would recommend use of a high grade exterior paint specified for use on metal.
On 2017-04-02 by kennythe empty cleanout door on a chimney can you paint it
On 2017-03-29 by (mod) re: raw masonry below the chimney thimbleMark I don't quite understand the question.
On 2017-03-29 by MarkWant to replace my chimney liner, is there a pipe which goes from the bottom of the thimble down to the close out door or is it just open below the thimble? Thanks
On 2017-02-27 by (mod) re: cedar block basement walls?Cedar block basement walls? That's not a material with which I'm familiar. Please use the page top or bottom CONTACT link to send me some sharp photos and we can comment further.
On 2017-02-27 by Venida Brown
Question: My clean-out door fell off and I'm going to replace it but the area around the frame of the door is crumbling. My basement walls are cedar block and I've had a small leak for year. I've had work done on the chimney and around the chimney such as sealing the outside base with liquid cement and tare.
None of these things stopped the leak. My basement has been water proofed but I have a real bad problem. Who should I call to repair this? Thank you help.
On 2017-02-23 by (mod) re: need for a chimney cleanout doorBrian:
On 2017-02-22 by Brian Nevilleinterior cleanout door has fallen out of cement foundation on my chimney for oil furnace. Do I still need cleanout door for oil furnace? How do I seal door back in ? just cement interior of door then hold it tight till set.. Then skim coat chimney door frame rim?
On 2016-11-09 by (mod) re: refractory cement to repair fireplace
Pat, there are refractory cements rated for high heat that are used in masonry fireplace construction. Don't use regular cement, nor caulk.
On 2016-11-09 by Pat
We have a masonry fireplace with a door that closes tight once the wood is loaded in - it has a great draw and is an excellent source of heat once the unit has warmed up. We opened up all of the cleanouts and now want to seal them back in and are not sure which product to use.
They had been fixed in with some sort of mortar or cement, which we had to chip out (not easy), so expect that we need to put them back in with the same type of product. Your suggestions would be appreciated.
On 2016-05-20 by Anonymous) hello this is Debra, my husband said Thank-you for your advice!!! He agrees with your solutions and is going to give them a try!! We hope for the best, once again thanks for taking the time to respond. God Bless you & yours!!!
On 2016-05-17 by (mod) re: fixing an old chimney cleanout that leaksDebra:
On 2016-05-16 by email@example.com
chimney box (is from an old furnace, so its not in use-it is empty) when it rains water fills in the old chimney clean-out and leaks into basement from the bottom of the clean-out door. I tried sealing it many times but to no avail it just keeps leaking! What do i do?
does this problem needs to be fixed from the outside of my house underground, by the chimney? please help! my basement is flooding!
On 2015-10-28 by Art Tate
My home is 25 years old. I have a wood burning fireplace with an ash dump 15 ft. deep with a clean out door at the bottom. It is full now at the top but there is no ash at the bottom.
The pit is made of a matrix of concrete block. I have rammed rods down into it which opens it up a little but it soon clogs again. The fireplace has been use extensively. Is there a way to clean this pit out?
On 2015-06-17 by (mod) re: Dublin chimney ash dump repairHey Don thanks for the question.
On 2015-06-16 by Don in Dublin
Hi, I had a chimney ash dump that went to the exterior (outside)of a masonry chimney. The interior was in the floor of the burn box. The door and entire frame of the ash dump assembly on the exterior was falling out of the mortar and brick of the chimney.
I had a chimney repair company come out and they removed the exterior ash dump door and bricked in the chimney where it had been. On the interior they removed the ash dump assembly and put in fire brick.
So the entire ash dump has been removed and bricked in now. They also put on a top sealing damper. I burned several fires over the winter and the chimney seemed to draw ok once the fire was actually going. Smoked some at first. However, with no fire and all the ash cleaned out completely the fire place just smells. It is so bad that it stinks up the entire living room. Almost to the point of the room being unusable.
Doesn't matter if the lower damper and top damper are closed or open. It just smells all the time now.
Is this a problem created because the ash dump was removed and bricked in? If so, should this chimney repair company have known this would cause a problem if they knew what they were doing.
Is there some kind of code (I'm in Ohio) that says every masonry fire place must have an ash dump?
(Sept 10, 2011) Do I need cleanout doors? said:
I have two cleanout doors--the ash cleanout from the fireplace. (I never use that cleanout) and the cleanout door for the heating area, which I also don't use. (The gas furnace and gas water heater both go directly into the flue). So I'm wondering--do I need EITHER of these doors or can I seal them up? Thanks!
As long as the cleanout doors are properly fitted, snug, not leaky, they're not interfering with draft, and should be left intact to permit chimney inspection.
(Oct 24, 2012) grant said:
i have a wooden enclosed fireplace. in the attic three sides are closed the one facing the interior has been left open . do i need to enclose it as well. if so what material do i use?
I am unclear on what you're describing, Grant. A "wooden" enclosed fireplace sounds to me like kindling designed to set a house on fire.
If you mean you have a zero-clearance metal fireplace enclosed in a wood structure or chimney chase, that can be safe provided the installation followed the manufacturer's installation instructions, including fire safety clearances (and of course complied with local codes).
I'm unclear on what was left open in the attic and what was enclosed and of course we don't know what type of chimney was installed. So I'm too chicken hearted to recommend specific steps or materials for an installation I know so little about.
Watch out: for safety I suggest asking your local building department of fire department to inspect this installation for safety and code compliance.
(Feb 26, 2014) Anonymous said:
I was told to fill clean out area with insulation to stop draft?
Is that correct?
Anon I'm unclear what area you plan to fill with insulation but this does not sound like a safe, recommended treatment of a chimney. See my inspection recommendation for the reader just above.
(5 Oct 2014) Nathan Miller said:
I have a fireplace with a chimney that slopes about thirty degrees above the damper towards the outer wall of the chimney, leaving it very difficult to clean debris above the damper.
This space is about four feet from my chimney flue. Now I have installed a cleanout door on the outside of the chimney, twelve by twelve. My glue is eleven by eleven. I put fire brick on the wall where part of the flue liner was broken out. Now my question, do I need to insulate the clean out door somehow?
This question was originally posted at ANGLED CHIMNEYS
Chimney cleanout doors are not normally insulated - and I'd be worried lest someone try doing so, especially if they applied a combustible material.
But you do want to be sure the door closes tightly so as not to subvert the chimney draft.
(Nov 29, 2014) Dazy said:
I have a gas insert now in my old fireplace... may I , and HOW, can I fill the old Chimney cleanout because I get alot of cold draft from it?
Dazy I moved your question and our reply into the article series above at
SEALING a CHIMNEY CLEANOUT DOOR
so that I had more room for a detailed reply. Let me know if question sremain.
(Dec 16, 2014) D.Burrows said:
We have a gas furnace in a furnace room, connected to an exterior brick chimney below grade. the chimney clean out door from time to time water appears on its ledge. Would the be condensation from the chimney? or another problem.
You or your chimney sweep will need to open the cleanout door to answer this question; if the chimney is flooded from outside water sources that's a different topic from condensation running down the flue.
Continue reading at CHIMNEY CLEANOUT DOOR or select a topic from closely-related articles below, or see our complete INDEX to RELATED ARTICLES below.
Or see DRAFT REGULATOR SOOT INSPECTION for another spot where it may be possible to inspect for clues about the condition of a chimney and its safety.
Or use the SEARCH BOX found below to Ask a Question or Search InspectApedia
Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website