Total Well Water Quantity Explained
How Much Water is In the Well?
WELL QUANTITY TOTAL - CONTENTS: How much water can we take out of a well before we run out? What is the water quantity that a well can deliver, how do we measure or estimate this figure?Well Flow Rate, Well Yield, & Water Quantity Explained - Problems & Repair Advice for wells. Well diagnosis & repair procedures including how to determine the total quantity of water that can be drawn from a well over a given period.
Definition of the Total Quantity of Water Available From a Water Well
This article series describes how we measure the amount of water available and the water delivery rate ability of various types of drinking water sources like wells, cisterns, dug wells, drilled wells, artesian wells and
well and water pump equipment. The well sketches at page top and at left, courtesy of Carson Dunlop Associates.
People sometimes confuse things by describing what we call the well 'flow rate" as the "water quantity" available from a well. They're different.
You could have a great well water flow rate - say 20 gallons per minute - but if it the water will only run at that rate for five minutes before you run out, the well has a very poor water quantity (5 minutes x 20 gpm = 100 gallons of water) and it's not a satisfactory well.
So watch out for errors or deliberate misrepresentation about well capacity when buying a property. A true well flow rate is not what we can measure in the building over five minutes, it's the ability of a well to deliver a sustained water flow rate over a longer period, usually measured over 24-hours.
When a local health department or building department approve the flow rate of a water well, that rate should have been measured by a plumber or well driller and should represent something more than a five minute test. The standard period over which a well flow rate must be measured varies among communities. Find out what the standard is for your area.
The amount of water that can be pumped out of a well at any given time is limited by the size of the static head and the
well recovery or well flow rate, and of course by the pump rate the gallons per minute that the pump itself can or is set to
Well pumps are usually intended to pump water out of a well slowly enough that the pump and well don't run dry. Some pump systems have fittings that recycle the very last water in the well through the pump, ceasing delivery of it to the building, to protect the pump from overheating.
For these reasons, we've occasionally found clients dissatisfied with their well after they install a new, more powerful water pump. The owners install a more powerful pump to increase water pressure in the home, but the effect may be also to draw water out of the well faster than ever before, thereby disclosing a marginal well flow rate that they had not understood.
For this reason it's a dangerous simplification to simply assert "we can put on a bigger pump" when water flow rate is poor in a building. See WATER PRESSURE LOSS DIAGNOSIS & REPAIR for more diagnosis of bad water pressure.
Remember that water quantity (how much water we can obtain) is not the same thing as water pressure (how fast water comes out of the tap). Water quantity comes from what the well can deliver. Water pressure is the amount of force with which the water pump can push water into the building piping and fixtures. Higher water pressure does give us more gallons per minute flow but that's describing a condition at the plumbing fixture. It's not measuring how much water the well can deliver.
Watch out: Measurements like the well depth (WELL DEPTH, HOW TO MEASURE), well flow rate (WELL FLOW RATE), well recovery rate are all useful, but taken by themselves some of these numbers can give a false reading about the basic question of how much water is in the well? What we really need to know is the total quantity of water that can be drawn from the well and the quality of that water: is it potable, hard (mineral laden), smelly, dirty, requiring treatment for any aesthetic or health-concern contaminant?
Why A Poor Flow Rate Well Might Seem to Work Acceptably
If our well has a huge static head, say 300 gallons of water, and considering that at most buildings, certainly at residential properties, most water usage occurs in two big surges, in the morning and in the evening (giving the well time to recover between), the well could have a terrible recovery rate, say 1/2 gallon a minute or less, but we might never notice it in the building. We're always running off of the "reserve" or static head.
But over time, as minerals and debris clog those rock fissures that feed water into our well, and if we started with just a small recovery rate of less than a gallon, our well may not continue to deliver the water quantity we need.
A Good Flow Rate or Good Well Recovery Rate is Best
A well with a good recovery rate, flowing at say 5 gpm or more, is more likely to continue to give good service over time, and we might get by with a small static head if the flow rate is good enough.
These are the parameters that a well driller is considering when they decide how deep to go in drilling and how much well flow rate is going to be acceptable.
Well Flow Rates are Not a Simple Number, and Need to Be Measured Over Time
Because ground water typically flows into a drilled well through multiple rock fissures or other underground passages, and because these passages are at different depths, the actual total flow rate into a well is made up of flow from multiple individual openings. Each of these may have its own characteristic flow rate and also flow duration. For example a fissure may flow at a high rate for 20 minutes and then drop to a slow rate or even stop entirely.
This is why the flow rate at a new well is typically measured over a long period, say 24 hours. If you measure the flow rate at a well for just a few minutes, you can have no idea of the well's actual ability to deliver water over any sustained time of usage.
Well Flow Rates Can Change
Someone drilling a new well nearby can tap into the same water table causing it to drop
Local blasting can change the level of a local water table. Local blasting can also change water quality. The well at one of our properties gave seemingly limitless quantity from a shallow 29' deep drilled well from about 1920 up to about 1999. Then the town was improving the nearby roadway and had to do some blasting. The well quantity did not change but suddenly wells along this section of roadway had red silt in their water - it has remained a problem for some home owners in the area.
Seasonal water level variations: Local ground water table levels are often lower at different seasons (less in dry weather)
Permanent water level shifts & Global Warming: Local ground water tables may drop permanently. In some areas of Florida so much water has been pumped from below ground that salt water has begun to intrude into the aquifer. Changing sea levels due to global warming can be expected to affect coastal drinking water wells by raising the level of salty water.
Definition of Safe Total Yield for a Well
We define safe well yield as the combination of total water quantity that can be drawn out of a well without dropping the water level in the well low enough to introduce air into the system or damage the well pump.
A well with a large static head and/or a well with a very good flow rate may have a high safe yield while a well with a small static head and the bad luck to also have developed a low well flow rate will have a very small safe yield - in some cases less than 50 gallons of water.
If a poor safe yield is likely to be permanent, solutions include increased water storage capacity in the building, steps to increase the well yield, or installation of a drawdown cutoff device that prevents the pump from dropping water in the well to a level that risks air entry into the piping or damage to the pump.
Continue reading at WELL YIELD DEFINITION or select a topic from closely-related articles below, or see our complete INDEX to RELATED ARTICLES below.
In a companion article, WELL FLOW TEST PROCEDURE, we describe both valid and questionable ways people measure well yield, and we offer some simple steps any home owner or home buyer can take to check the adequacy of water pressure and water quantity at a building.
Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
What would be the optimum measurement for replenishment or rate of recovery? "Gallons per hour".
(July 15, 2014) Andre said:
Bring a new device and technology to market to measure key well data.
We want to use industry standard to measure static water and rate of replenishment. Static water levels will be measured every second and averaged out daily. What would be the optimum measurement for replenishment or rate of recovery? "Gallons per hour".
The minimum well recovery rate you'd want to meet would be that established by some mortgage lenders - say 5 gpm. But that's a *minimum* that would give a sustainable well flow rate of the same number. Be sure to read our articles about well flow rate, well yield, well recovery rate and static head so that you've got a clear understanding of how those measures are used.
Question: Could my well water level drop when using because I am in a shallow supply?
(Aug 15, 2014) Jim Park said:
My well pump will only deliver water to my lawn sprinklers for 10 min. then runs dry. After 15 to 20 min. things will work again but again only for 10 min. I have no problems in the house with showers, washers, etc. Could my well water level drop when using because I am in a shallow supply?
If the sprinkler system uses water at a high GPM rate your lawn watering may be exhausting the well. If that's the case and if a well protection switch is instllalled, it may be shutting down the pump for a time - or the well may simply be running out, then recovering on the schedule you describe. Check for those conditions.
Ask a Question or Search InspectApedia
Questions & answers or comments about water well flow rate, well recovery rate, and well water quantity - does your well run out of water?.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Carson, Dunlop & Associates Ltd., 120 Carlton Street Suite 407, Toronto ON M5A 4K2. (416) 964-9415 1-800-268-7070 firstname.lastname@example.org. Thanks to Alan Carson and Bob Dunlop, for permission to use illustrations from their publication, The Illustrated Home which illustrates construction details and building components. Carson Dunlop provides home inspection education including the ASHI-adopted a Home Inspection Home Study Course, and publications such as the Home Reference Book, the Home Reference eBook, and report writing materials including the Horizon report writer, and home inspection services. Alan Carson is a past president of ASHI, the American Society of Home Inspectors.Access Water Energy, PO Box 2061, Moorabbin, VIC 3189, Australia, Tel: 1300 797 758, email: email@example.com Moorabbin Office: Kingston Trade Centre, 100 Cochranes Rd, Moorabbin, VIC 3189
Australian supplier of: Greywater systems, Solar power to grid packages, Edwards solar systems, Vulcan compact solar systems, water & solar system pumps & controls, and a wide rage of above ground & under ground water storage tanks: concrete, steel, plastic, modular, and bladder storage tanks.
Smart Tank, Installation Instructions [ copy on file as /water/Smart_Tank_Flexcon.pdf ] - , Flexcon Industries, 300 Pond St., Randolph MA 02368, www.flexconind.com, Tel: 800-527-0030 - web search 07/24/2010, original source: http://www.flexconind.com/pdf/st_install.pdf
Typical Shallow Well One Line Jet Pump Installation [ copy on file as /water/Jet_Pump_Grove_Elect_Jet_Pumps.pdf ] - , Grove Electric, G&G Electric & Plumbing, 1900 NE 78th St., Suite 101, Vancouver WA 98665 www.grovelectric.com - web search -7/15/2010 original source: http://www.groverelectric.com/howto/38_Typical%20Jet%20Pump%20Installation.pdf
Typical Deep Well Two Line Jet Pump Installation [ copy on file as /water/Jet_Pump_Grove_Elect.pdf ] - , Grove Electric, G&G Electric & Plumbing, 1900 NE 78th St., Suite 101, Vancouver WA 98665 www.grovelectric.com - web search -7/15/2010 original source: http://www.groverelectric.com/howto/38_Typical%20Jet%20Pump%20Installation.pdf
Water Fact Sheet #3, Using Low-Yielding Wells [ copy on file as /water/Low_Yield_Wells_Penn_State.pdf ] - , Penn State College of Agricultural Sciences, Cooperative Extension, School of Forest Resources, web search 07/24/2010, original source: http://pubs.cas.psu.edu/FreePubs/pdfs/XH0002.pdf
WATER PUMP REPAIR GUIDE an specific case offers an example of diagnosis of loss of water pressure, loss of water, and analyzes the actual repair cost
Carson, Dunlop & Associates Ltd., 120 Carlton Street Suite 407, Toronto ON M5A 4K2. Tel: (416) 964-9415 1-800-268-7070 Email: firstname.lastname@example.org. The firm provides professional home inspection services & home inspection education & publications. Alan Carson is a past president of ASHI, the American Society of Home Inspectors. Thanks to Alan Carson and Bob Dunlop, for permission for InspectAPedia to use text excerpts from The Home Reference Book & illustrations from The Illustrated Home. Carson Dunlop Associates' provides extensive home inspection education and report writing material.
The Illustrated Home illustrates construction details and building components, a reference for owners & inspectors. Special Offer: For a 5% discount on any number of copies of the Illustrated Home purchased as a single order Enter INSPECTAILL in the order payment page "Promo/Redemption" space.
TECHNICAL REFERENCE GUIDE to manufacturer's model and serial number information for heating and cooling equipment, useful for determining the age of heating boilers, furnaces, water heaters is provided by Carson Dunlop, Associates, Toronto - Carson Dunlop Weldon & Associates Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on any number of copies of the Technical Reference Guide purchased as a single order. Just enter INSPECTATRG in the order payment page "Promo/Redemption" space.
The Home Reference Book - the Encyclopedia of Homes, Carson Dunlop & Associates, Toronto, Ontario, 25th Ed., 2012, is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. Field inspection worksheets are included at the back of the volume.
Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on these courses: Enter INSPECTAHITP in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Horizon Software System manages business operations,scheduling, & inspection report writing using Carson Dunlop's knowledge base & color images. The Horizon system runs on always-available cloud-based software for office computers, laptops, tablets, iPad, Android, & other smartphones