ARTESIAN WELLS, Well Spools - CONTENTS: Flowing artesian wells: types, construction, troubleshooting & repair. Characteristics, diagnosis, & repair of well casing leaks at an artesian well. Illustration source: Michigan DEP Flowing Well Handbook 
InspectAPedia tolerates no conflicts of interest. We have no relationship with advertisers, products, or services discussed at this website.
This article describes the construction of artesian water wells. We describe types of artesian wells, how water flow from the artesian well is controlled, special artesian well parts like the well spool, and we discuss special problems for artesian wells and the property aroudn them when there is a leak in the well casing.
In a topographically-controlled flowing artesian well, pressure that pushes water to the top of the well casing is developed by surrounding land and/water that create water pressure in the well that is higher than the surrounding land pressure. Sketch courtesy Michigan DEP. - Ed.
Questions about well spools & artesian well casing leak repair using well sleeves
Our water pump in the well recently went out and we hired a crew to replace the pump. However I am concerned if he used correct procedure and if caused more problems than we started with.
When he first strated pulling up the drop pipe the "spool" was stuck and he had problems with pulling it up at first, once it came free he set it back down and took the cable off.
Then he came up to the house and told me he is going to pour some acid down to soak over night and loosen up the "spool" so he could pull it up, he dumped about 2 gallons of it down there and the next day he pulled everything up again.
Later when he started blasting out the black water a bunch of sand came out and he told us we need an entirely new well because there is a hole in the case, and sleeving the case wasn't an option. However after he left I was looking at the pipes and wire left that was pulled up and they have some bad corrosion just above the water level. I am wondering if the acid he poured down the casing ate through the casing where it sat overnight and caused the hole? Also there was no sand to be found in the old pump which makes me more suspicious.
What is a Well Spool, Why a Well Spool may be Needed, How they are Installed on Artesian Wells
Your description of "a bunch of san dcame out..." may indeed be the first indicator that a homeowner sees pointing to a hole or crack in the well casing of an artesian well.
Below we describe well spools used for flowing artesian wells and possibly in other wells with a very high-rising static head.
Our illustration of a well spool at left, edited from a schematic provided by Baker Manufacturing illustrates the part of this assembly - you can see why it's called a "spool" - it looks like one. Baker Manufacturing produces and sells well spools and pitless adapters for 4", 5" and 6" diameter well casings and water wells.
The well spool is held in position by a hold-down spider [purple assembly at imiage top] and set screws to keep the spool from being pushed up in the casing by the pressure of water rising in the well casing, and O-rings seal the well spool to the well casing itself. . - Ed. [Illustrasted adapted from & permission & tech review requested 6/27/12]
Is this acid treatment normal and safe for the casing? Is he telling me the truth that no one ever "sleeves" the case and that its not an option?
Thank you ahead of time for any information about this, I am not made of money and can't afford to be taken advantage of. Thanks again - B.T. 4/25/12
Reply: Description of well casing repair sleeves to repair well casing leaks at residential water wells
A competent onsite inspection by an expert usually finds additional clues that help accurately diagnose a problem, and I'm not at all sure I have a full picture of what's going on with your well.
That said, here are some things to consider about well spools, leaks in the well casing, and using acid to free up a stuck well spool in your well. Regarding your well driller's use of acid to free up a stuck well spool, our OPINION is that like you, dumping any potentially toxic or harmful chemical into a well makes us very nervous.
OPINION: when you are not comfortable with advice you've received about how your well should be repaired ("you need a new well"), start by asking your well driller to explain his reasoning in a little more detail. Most contractors are quite honest and are not out to gouge you, but they were not English majors and may not be expert in communication.
Types of well spools used to keep artesian wells from overflowing in freezing & non-freezing climates
Well Spool Installation Using Clamp-on Pitless Adapter
A well spool is a special seal around the well piping used to seal a well casing in wells at which the static head of water level in the well casing rises above the frost level. Basically it's a "spool-shaped" plumbing fitting that incorporates round flanges at its top and bottom, threaded to accept well pipe fittings above and below the spool.
Well spools are required on artesian wells or "flowing wells" in freezing climates. Without this component the upper well casing could be split by freezing water.
Our illustration (left) shows a low-pressure well spool using a clamp-on pitless adapter in a design suitable for artesian wells whose head pressure is equal to or less than 5 psi (a head of 11.5 ft.) - courtesy Michigan DEP.
Speaking with more precision, an artesian well is one in which water rises in the well casing high enough to deliver water to a building, and higher than the local groundwater table, due to water pressure within the drinking water aquifer, but stopping below the top of the well casing itself.
A "flowing artesian well" is one in which pressure from within the aquifer will, left alone, actually push water right up the well casing and out of its top.
Well Spool Installation for low-pressure artesian wells & non-freezing climates
Our illustration of a low-pressure well spool at left is provided by the Michigan DEP Flowing Well Handbook and  illustrates the part of this assembly more clearly than our earlier sketch.
Unlike the Baker well spool shown earlier, this version shoss the well spool being held down by an assembly accessed just under the well cap and installed quite near the top of the well - a design suitable only for non-freezing climates or for a well cap that is located below grade in a well pit where it is protected from frost. [Permission & tech review requested 6/27/12]
If your well incorporates a well spool that means that left alone water would rise in the well casing above the frost level in your area, risking well damage. And if the well spool becomes stuck, special methods may be needed to loosen it before the well piping and pump can be pulled from the well.
In non-freezing climates the well spool is not needed; instead the well installer relies on the well cap installed at the top of the well casing to keep the artesian well from overflowing.
Other Methods for Controlling Water Flow From Artesian Wells
An alternative to using a well spool to "cap" or withstand the pressure within an artesian well involves using any of several methods to first provide sufficient water pressure to supply the building and second a method to allow excess water to drain to an approved location.
Approved Artesian Well excess water discharge methods
Gate valve installed near top of an above-ground well casing.
Excess flow from the well casing can be occasionally drained, using a gate valve (normally left with handle removed) and a screened outlet to protect against drawing contaminants in through the faucet mouth; the faucet gate valve drains through air (an air gap, hence no cross connection risk) into a buried drain line that conducts excess water to a ditch, river, pond, or the surface.
This excess artesian well flow discharge is permitted with written permission from a local health department official and is not expected to be constant.
Illustration adapted from: Michigan DEP Flowing Well Handbook 
Elevated water storage tank: water from the artesian well feeds a non-pressurized water storage tank. A drain line exiting from the top of the water storage tank passes a gate valve used to control the flow rate out of the discharge line and then through a discharge tube that spills the drainage water across an air gap (hence no unsanitary cross connection) to a drain line that removes excess water to an acceptable destination.
The receiving flow drain line must be at least 2x the diameter of the storage tank discharge tube.
In this artesian well control design, a one line jet pump or equivalent is used to move water from the non-pressurized water storage tank into a water pressure tank that in turn delivers water to the building plumbing system at sufficient pressure (typicallty 20-40 or 30-50 psi).
Illustration source: Michigan DEP Flowing Well Handbook 
Unapproved Artesian Well excess water discharge methods
Leakage around the well casing draining by diversion pipe to a lake or stream. Leaks around the well casing should be repaired by grouting the casing - a step that can be a challenge in high-flow high-pressure artesian wells.
Allowing a leak around the well casing to continue wastes water and risks cross-contamination of the aquifer during periods of change in water flow and pressure.
Buried artesian well overflow pipe with check valve. Figure 8 at left (Illustration adapted from: Michigan DEP Flowing Well Handbook ) illustrates several defects in this approach to well flow control: the confining layer is not sealed, the check valve in the discharge line is not an approved protection against a cross-connection or back flow that risks contaminating the aquifer, and the sketch shows an improper pitless adapter installation that is not pressurized.
Submerged inlet [and outlet] drainage pipe from the artesian well casing: using a non-pressurized buried line connected directly to the well casing above the pitless adapter as a means to control the maximum static water head height in the well casing - water drawn from the casing is discharged to a lake or stream.
The risk is that under changing condtions in the aquifer and inside the artesian well, water can flow backwards from the lake or stream, forming a cross connection and back-contaminating the aquifer.
Problems with Leaks in the Steel Casing of an Artesian Well
Leaks in the well casing are a problem because of the risk of leaks of surface contaminants into the well.
Our sketch at far left crams more parts into a small space than you'd find in a real water well - we've got the submersible pump up there near the top of the well casing; actually the pump will be located a few feet or more off of the well bottom, and actually in most water wells the steel casing extends from the ground surface down into bedrock but the well bore itself continues down through that rock to a deeper depth - the casing does not extend to the very bottom of the well. - Ed.
The Michigan DEP sketch above (figure 7) illustrates an improper means of getting rid of water leaking around the well casing of an artesian well. Illustration adapated from: Michigan DEP Flowing Well Handbook 
As the Michigan DEP points out,
Sealing the annular space surrounding the well casing is critical, since an
ineffective seal or absence of a seal can result in the uncontrolled discharge of
water on the outside of the well casing pipe.
When ground water breaks out on the
outside of the well casing, erosion of the confining geologic layer and other
overlying materials can occur.
The uncontrolled discharge of ground water from
flowing wells can cause flooding of the well site and adjacent properties and
damage to nearby structures. 
More Reading provides a complete list articles closely related to this one..
Frequently Asked Questions (FAQs) about artesian well spools
Ask a Question or Search InspectApedia
Questions & answers or comments about artesian wells: construction, troubleshooting, repair, & parts including well spools
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
 J.E. Johns, TecWel; D.N. Cary, Seal-Tite International; J.C. Dethlefs, ConocoPhillips; B.C. Ellis, Seal-Tite International; and M.L. McConnell and G.L. Schwartz, ConocoPhillips, " Locating and Repairing Casing Leaks with Tubing in Place - Ultrasonic Logging and Pressure-Activated Sealant Methods", Society of Petroleum Engineers, Offshore Europe, 4-7 September 2007, Aberdeen, Scotland, U.K., Document 108195 (Conference Paper), 2007
 Link-Pipe, Inc., 27 West Beaver Creek Road - Unit #2
Richmond Hill, ON
CANADA L4B 1M8, Link-Pipe manufactures "no-dig" pipe repair products for wells. Tel: 800-265-5696 or email: firstname.lastname@example.org or website: http://www.linkpipe.com/wells.htm
 Prentice Creel and Ronald J. Crook, Halliburton Energy Services, Inc., " Injectrol® and PermSeal Sealants Repair Leaks, Restore Integrity to Casings", Halliburton Service Center, 877-263-6071, web search 6/27/12, original source: http://www.halliburton.com/public/cem/contents/Papers_and_Articles/web/I_through_O/InjPerm.pdf [copy on file as Injectrol.pdf]
 Rasmussen Well Drilling, Inc., 1793 Hwy 61, Two Harbors MN. Jeremy Rasmussen provides third generation well drilling and plumbing services on the North Shore of Lake Superior. Photos by DJF. Tel 218-834-3387. Email: email@example.com
We serve the north Shore – Lake, Cook, St. Louis, Carlton and Pine counties, including Duluth, Grand Marais, Clouqet, Carlton, Finland, Isabella, Silver Bay, Grand Portage, Saginaw, and everywhere in Northeastern Minnesota.
 New Electric Heat Tapes Help Prevent Fires," US Consumer Product Safety Commission (CPSC) #00936
 Thanks to Mark Cramer, Tampa Florida, for assistance in technical review of the "Critical Defects"
section and for the photograph of the deteriorating gray Owens Corning flex duct in a hot attic. Mr. Cramer is a Florida home inspector and
home inspection educator.
 Baker Manufacturing, 133 Enterprise St., Evansville WI, Tel: 800-356-5130, website: www.baker-mfg.com, web search 6/27/12, original source: http://www.baker-mfg.com/domestic_new/domestic_pitless_units
 Michigan Department of Water Environmental Quality Water Bureau (DEQ), Drinking Water & Environmental Health Section, Well Construction Unit, "Flowing Well Handbook", web search 6/27/12, original source: http://www.michigan.gov/documents/deq/deq-wb-dwehs-wcu-flowwellhandbook_221323_7.pdf [copy on file as Flowing_Well_Book_MI.pdf]. This is an excellent primer for the construction of flowing artesian wells - Ed.
 W. B. Allen, Flowing Wells in Michigan, 1974 U. S. Geological Survey, Water
Information Series Report 2
 ASTM D 5299-92, Standard for Decommissioning of Ground Water
Wells, Vadose Zone Monitoring Devices, Boreholes, and Other Devices
for Environmental Activities, 1993, American Society for Testing
Materials, West Conshohocken, Pennsylvania.
 R. Allen Freeze, & John Cherry, Groundwater, 1979, Prentice Hall, Inc.,
Englewood Cliffs, New Jersey
Home Inspection Education Home Study Courses - ASHI@Home Training 10-course program. Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on these courses: Enter INSPECTAHITP in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Home Reference Book, a reference & inspection report product for building owners & inspectors. Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Home Reference eBook, an electronic version for PCs, the iPad, iPhone, & Android smart phones. Special Offer: For a 5% discount on any number of copies of the Home Reference eBook purchased as a single order. Enter inspectaehrb in the order payment page "Promo/Redemption" space.
The Illustrated Home illustrates construction details and building components, a reference for owners & inspectors. Special Offer: For a 5% discount on any number of copies of the Illustrated Home purchased as a single order Enter INSPECTAILL in the order payment page "Promo/Redemption" space.
The Horizon Software System manages business operations,scheduling, & inspection report writing using Carson Dunlop's knowledge base & color images. The Horizon system runs on always-available cloud-based software for office computers, laptops, tablets, iPad, Android, & other smartphones.
Books & Articles on Building & Environmental Inspection, Testing, Diagnosis, & Repair
Plumbing Diagnosis & Repair: Water supply, drainage, septic systems, water testing, water contamination, defective plumbing materials & products.
The Home Reference Book - the Encyclopedia of Homes, Carson Dunlop & Associates, Toronto, Ontario, 25th Ed., 2012, is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. Field inspection worksheets are included at the back of the volume. Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
Or choose the The Home Reference eBook for PCs, Macs, Kindle, iPad, iPhone, or Android Smart Phones. Special Offer: For a 5% discount on any number of copies of the Home Reference eBook purchased as a single order. Enter INSPECTAEHRB in the order payment page "Promo/Redemption" space.