Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
PLUMBING SYSTEM INSPECT DIAGNOSE REPAIR
AGE of PLUMBING MATERIALS & FIXTURES
AIR DISCHARGE at FAUCETS, FIXTURES
ANTI SCALD VALVES
ANODES & DIP TUBES on WATER HEATERS
BACKUP PREVENTION, SEPTIC
BACKUP PREVENTION, SEWER LINE
BACKWATER VALVES, SEWER LINE
BATH & KITCHEN DESIGN GUIDE
CHEMICAL CONTAMINANTS in WATER
CHEMICAL ODOR SOURCES
CHLORINE IN DRINKING WATER
DEBRIS in WATER SUPPLY, Water Heater
DEPTH of SEPTIC TANK
DRAIN & SEWER PIPING
FAUCETS & CONTROLS, KITCHEN & BATH
FAUCETS, OUTDOOR HOSE BIBBS
FLOOD DAMAGE ASSESSMENT, SAFETY & CLEANUP
FLOOR DRAIN / TRAP ODORS
FLUSHOMETER VALVES for TOILETS URINALS
GAS PIPING, VALVES, CONTROLS
GALVANIC SCALE & METAL CORROSION
HARD WATER - SOFTENERS
HEAT TAPES, Heat, Insulation prevent Freeze-Up
LEAD POISONING HAZARDS GUIDE
LEAD IN DRINKING WATER, HOW to REDUCE
METHANE GAS SOURCES
MIXING / ANTI-SCALD VALVES
MUNICIPAL WATER PRESSURE IMPROVEMENTS
NOISE / SOUND DIAGNOSIS & CURE
ODORS GASES SMELLS, DIAGNOSIS & CURE
ODORS IN WATER
ODORS, SEPTIC or SEWER
ODORS SEWER GAS in COLD WEATHER
ODORS, SULPHUR SMELL SOURCES
ANIMAL or URINE ODOR SOURCE DETECTION
PIPING IN BUILDINGS, Clogs Leaks Types
PLUMBING FIXTURES, KITCHEN, BATH
PLUMBING NOISE CONTROL
PLUMBING VENT DEFINITIONS & CODES
PLUMBING VENT DEFECTS & NOISES
PUMPS, WATER REPAIR
RELIEF VALVE LEAKS
RELIEF VALVES - TP Valves on Boilers
RELIEF VALVES - STEAM TP VALVES
RELIEF VALVES - Water Heaters
RELIEF VALVES - Water Tanks
REPAIR BURST LEAKY PIPES
METHANE GAS HAZARDS
SEPTIC SYSTEM INSPECT DIAGNOSE REPAIR
SHUTOFF VALVE LOCATION, USE
SULPHUR & SEWER GAS SMELL SOURCES
SWEATING (CONDENSATION) on PIPES, TANKS
TOILETS, INSPECT, INSTALL, REPAIR
WATER, WELLS, WATER TANKS: TESTING GUIDE
WATER PRESSURE LOSS DIAGNOSIS & REPAIR
WATER PUMPS & TANKS
WATER SOFTENERS & CONDITIONERS
WATER SOURCE ALTERNATIVES
WATER SUPPLY & DRAIN PIPING
WATER SHUTOFF VALVE LOCATION, USE
WATER SHUTOFF VALVE, WELL PUMP
WATER TESTS, CONTAMINANTS, TREATMENT
WELLS CISTERNS & SPRINGS
WINTERIZE A BUILDING
Types of leaks in water supply or drain piping: this article describes the different types of plumbing leaks that can occur in building supply piping or drain piping. Knowing just what kind of leak is occurring in a building helps pinpoint the problem and also helps specify the necessary plumbing repair.
The articles at this website will answer most questions about freeze protection for piping and other building plumbing and heating system components: how to winterize a building to avoid frozen pipes, and how to thaw frozen water supply & drain piping, wells, & water tanks.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Understanding the types of water leaks that occur in building piping can help you find or watch out for leaks that are not so obvious when water is first turned on in a building. Keep in mind that these are by no means all of the building leaks that can occur.
Others include leaky shower pans, leaky air conditioning condensate drains, bad sump pump drains, leaky water tanks, leaky water heaters, leaks at tankless coils, and leaks from outside the building from roof runoff or surface runoff. Here we focus attention on leaks that occur in building piping:
Also see WELL PIPING LEAK DIAGNOSIS. Also if you are de-winterizing or having frozen see Thawing Frozen Pipes which addresses how to find frozen and burst pipe leaks in buildings, and see Repairing Burst Leaky Pipes.
Types of Leaks in Water Supply Piping
Types of Leaks in Building Drain Piping
Our main article on this topic is found at WELL PIPING LEAK DIAGNOSIS. Excerpts are below.
At WATER PRESSURE PROBLEM DIAGNOSIS TABLE we note that a possible explanation for loss of building water pressure, or loss of well pump prime can be air leaking into a well piping line, as well as water leaking out of the well pipe.
Water will leak out of a well pipe at a bad connection, perforation, or cracked pipe when the well pump is running, particularly if the water system uses a submersible pump that is located in the well itself. If you have this problem you may find a wet spot in the ground near the well piping, provided that the pipe is close enough to the surface.
You will also notice that the well pump is running more often than normal, and that your "apparent" water usage may have increased. Some people even report finding a "water fountain" or geyser in the lawn at a burst water supply pipe from both private wells and from a municipal water main.
Air may leak into a well water pipe at a bad connection, perforation, or other damage when the well pump stops running, particularly if the leak problem is combined with a defective check valve or foot valve in the piping system.
The result may be air discharged from plumbing fixtures (see AIR DISCHARGE at FAUCETS, FIXTURES), improper air charge in the water pressure tank, or loss of pump prime. Short cycling of the water pump or loss of pump prime may result as well.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Check the FAQs just above, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.