InspectAPedia tolerates no conflicts of interest. We have no relationship with advertisers, products, or services discussed at this website.
FAN ON OFF AUTO switch on thermostats, guide to setting, troubleshooting, repair: this article explains the use, setting, and adjustment of the FAN ON- AUTO button or switch or the FAN ON-MAN switch on room thermostats.
How does the FAN ON-MAN switch work?FAN Button AUTO and ON functions on Digital Thermostats. How Should I Set the FAN ON-AUTO or FAN MAN-AUTO Switch on My Thermostat? What to do if the Blower Fan Runs Continuously and Won't Shut Off?
This article series answers most questions about central heating system thermostats & controls, troubleshooting, installation, inspection, diagnosis, and repair.
FAN Button AUTO and ON functions on Digital Thermostats
On most digital thermostats, pressing the "FAN" button repeatedly will cycle the fan control between two positions. Here we are using a Carrier™ digital thermostat for our examples. Our pencil points to the "FAN" switch or button in this case.
FAN switch set to: "ON" will set the blower fan on your heating or air conditioning system run all the time, no matter what.
FAN switch set to: "AUTO" run let the fan be turned on or off automatically under control of the heater or air conditioner itself - when the thermostat asks for heat and the furnace warms up the fan will turn on. At the end of a heating cycle when the thermostat is satisfied, the fan will automatically turn off.
Fan operation in an air conditioning system or heat pump operating in cooling cycle works similarly
On a digital room thermostat when you press the "FAN" button, look closely at the thermostat's digital display - you should see the word AUTO (photo above left) or MAN (Photo above right) appear somewhere in the display to let you know which setting you have selected.
Typically in the AUTO mode in a heating cycle the fan won't actually turn on until the furnace has warmed-up and the fan will turn off shortly after the furnace turns off at the end of a heating cycle.
Running the fan "ON" all the time, which we like to do in lots of cases, distributes air and temperatures more evenly all the time in the home and produces less of a surge of heat or cool air when the heater or air conditioner actually turns on.
The air conditioning or heating wall-mounted thermostat may have a fan or blower control switch with (usually) two set positions "ON" and "AUTO" or sometimes "MAN" or "AUTO"
On these switches located usually on the top, side, or bottom of air conditioning or heating thermostats, the "ON" position is not what you might think. But it's simple, as you'll see.
On some room thermostats the FAN switch may show positions labeled MAN and AUTO instead of ON and AUTO.
On these thermostats "MAN" or "manual" is the same as "ON" in this situation. There are advantages of running an air conditioning or heating blower fan continuously, and "AUTO" is the same as "AUTO which we discussed just above.
Don't mix up the digital thermostat's display of the word AUTO regarding fan control with the display's use of the same word AUTO elsewhere in the thermostat's display window to describe the overall thermostat MODE setting which we discuss
at SWITCH FUNCTIONS on a Room Thermostat.
How Should I Set the FAN ON-AUTO or FAN MAN-AUTO Switch on My Thermostat?
"AUTO" on the fan switch on your thermostat is the normal switch position for the fan control. Setting the fan control to "AUTO" will allow the fan to turn on when the air conditioning system (or heating system) are ready to blow cool (or warm) air into the building, and to turn off automatically when cooling or heating are not needed.
"ON" or "MAN" on the fan switch: there are reasons to leave the fan in the ON position on a heating or cooling system, but we do not recommend that you do this without first asking for advice from your heating and service technician.
If your air conditioner or heating system fan blower unit was designed to permit the fan to run all of the time that's great and you can consider the benefits of continuous fan operation which are described in detail in the articles we list just below.
Our photo (left) illustrates the FAN ON AUTO control switch (as well as the HEAT OFF COOL switch) on a 3M Filtrete 7-Day programmable room thermostat.
Watch out: the Filtrete™ 3M-22 is a battery-operated thermostat. If the batteries fail the thermostat may fail to provide heating or cooling and the building may suffer accordingly.
You might not want to keep the fan in "ON" mode if
Your furnace or air conditioner air handler is not designed for continuous fan duty - it might wear out the fan motor or bearings a bit early (ask your system's manufacturer or your HVAC tech about your system's capability)
Your building's heating system and return air duct design results in blowing uncomfortably cool air out of heating supply ducts when the furnace is not actually in heating mode.
What to do if the Blower Fan Runs Continuously and Won't Shut Off?
Some readers have written to say that their air conditioning blower was running continuously and they didn't know why.
If the blower or fan switch is set to MAN or ON at the thermostat, It could be that the FAN switch had simply been set to force the fan to run all of the time. Change the setting to AUTO and see what happens.
Other causes for an air conditioning blower fan that does not turn off could be a problem with the control circuit board for the air conditioning system, or there could be other operating system problems that are preventing the system from cooling air to the desired temperature.
If the FAN switch is set to MAN or ON at the furnace limit switch (usually a white button on the fan limit switch in the furnace) you can set it from ON to AUTO.
If the blower or FAN switch is set to AUTO and the fan never turns off, call your air conditioning or heating repair company for diagnostic help, or if you've checked the switches we describe above and you want to diagnose the fan yourself, go to our blower fan diagnostic home page
at FAN, AIR HANDLER BLOWER UNIT.
Reader Question: family dispute over how to operate a programmable thermostat & the FAN ON Switch
I am having a dispute with my family regarding the operation of our programmable thermostat. When the actual temp in the house is for example 20 degrees C., and the fan is turned to the ON position, the fan will start blowing 20 degree air. We all agree on that.
However, when the option to use the TEMP UP button to raise the temperature is used, and the temperature is upped to 24 degrees for example(and the current temp is still at 20 degrees at the time that the TEMP UP is pressed), I maintain the IF the FAN is again changed to the ON setting, the furnace will initially blow 20 degrees air which will increase gradually to 24 degrees as the furnace heats up.
My family maintains that the furnace will immediately blow 24 degrees air (even though the current temp reading on the thermostat is 20 degrees). I believe that it will only blow the temp of air associated with the current temp. Can someone explain how it works? Thank you. - Betty 12/12/11
Reply: clarifying what the FAN ON does and the relation between thermostat control settings and temperature of air that's delivered
Let's try to clear up a few thermostat basics that may add fire to the family argument or may quench it a bit:
But in sum, SETTING a temperature on the thermostat simply turns the heater or air conditioner ON. The heater or air conditioner will continue to run until the thermostat senses that the room temperature has reached the SET temperature, then the thermostat will turn that equipment OFF.
When you turn the fan to ON instead of AUTO, that tells the fan to run continuously. The temperature of air that the fan delivers will vary depending on whether or not the thermostat has ALSO turned the heater or air conditioner on or off - a separate function when you leave the fan always on.
Continue reading at BLOWER FAN CONTINUOUS OPERATION or select a topic from closely-related articles below, or see our complete INDEX to RELATED ARTICLES below.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
 Thanks to reader S.R. for discussing loss of heat due to a thermostat wiring mistake, October 2010
 Thank to Mr. Scott Meenen , G&S Mechanical Services , for providing some common thermostat wiring codes also found at Mr. Meenen's web page Malware Deleted 12/9/2014 . Mr. Meenan provides heating, heat pump, and air conditioning repair services in Maryland, Washington D.C., and northern Virginia. He can be contacted at 301-591-1646 or by Email to Malware Deleted 12/9/2014 - 10/2010. Quoting:
We service American Standard, Amana, Arco, Arco-Air, Bryant, Carrier, Coleman Evcon, Comfortmaker, Day/Night/Payne, Dunham-Bush, Fedders, Fredrich, Goodman, General Electric, Heil, Intertherm, ICP, Janitrol, Lennox (Armstrong, Johnson Air-Ease), Miller, Modine, Nordyne, Rheem/Ruud/Weatherking, Sears, Stewart Warner, Trane, Weather King, Williams, White-Westinghouse, Whirlpool, Weil Mclain, York, (Frasier Johnson/Borg Warner) and others.
 Honeywell Controls, the company wants you to use their contact form at this web page: http://www51.honeywell.com/honeywell/contact-support/contact-us.html
Honeywell Consumer Products,
39 Old Ridgebury Road Danbury, CT 06810-5110 - (203) 830-7800
World Headquarters, Honeywell International Inc.,
101 Columbia Road,
Morristown, NJ 07962,
Phone: (973) 455-2000,
Fax: (973) 455-4807 1-800-328-5111
Honeywell product model numbers & instruction Manuals: see http://yourhome.honeywell.com/home/Applications/FindYourModelNumber.aspx
 White Rodgers Thermostats and HVAC controls,
Homeowner information: http://www.emersonclimate.com/en-US/brands/white_rodgers/Pages/wr-homeowner-info.aspx
Contractor information: http://www.emersonclimate.com/en-US/brands/white_rodgers/wr_contractor_info/Pages/white-rodgers-contractor-info.aspx
White Rodgers Product Catalog (don't misspell the company's name as White Rogers Thermostats) -
http://www.emersonclimate.com/Documents/thermostats.pdf - Thermostat Catalog
 White Rodgers 1F90 Low Voltage Digital Comfort-Set thermostat Installation Instructions, PN 37-3654, White-Rodgers Division, Emerson Electric Co., 9797 Reavis Rd., St. Louis MO 63123
 Thermostat wiring color codes & conventions,
Thanks to reader "
Helpful Pointers" Regarding 24V T, 10/7/2012
 Domestic Central Heating Wiring Systems and Controls, 2d Ed., Raymond Ward, Newnes, ISBN-10: 0750664363, ISBN-13: 978-0750664363, Quoting from Amazon.com:
This unique A-Z guide to central heating wiring systems provides a comprehensive reference manual for hundreds of items of heating and control equipment, making it an indispensable handbook for electricians and installers across the country. The book provides comprehensive coverage of wiring and technical specifications, and now includes increased coverage of combination boilers, recently developed control features and SEDBUK (Seasonal Efficiency of Domestic Boilers in the UK) boilers ratings, where known.
In addition to providing concise details of nearly 500 different boilers fuelled by electric, gas, oil and solid fuel, and over 400 programmers and time switches, this invaluable resource also features numerous easy-to-understand wiring diagrams with notes on all definitive systems. Brief component descriptions are provided, along with updated contact and website details for most major manufacturers.
 Proliphix Corporate Headquarters, 3 LAN Drive Suite #100, Westford, MA 01886 Phone: +1.978.692.3375 Toll Free (U.S.): 866-IP-LIVING (866.475.4846) Fax: +1.978.692.3378 - Sales: firstname.lastname@example.org Marketing: email@example.com Customer support: firstname.lastname@example.org http://www.proliphix.com/ - quoting from the company's website: All Proliphix Network Thermostats come with our free Uniphy Remote Management Service. This unique offering lets you monitor and control your HVAC systems by simply pointing your Browser to our secure Proliphix Web Site. Enjoy the convenience of programming a thermostat from any location, using a simple graphical interface. No computer equipment or software is required. And since Proliphix takes care of the network configuration for you, you’ll be up and running in no time. We’ll even proactively monitor your thermostats and send you an immediate email or SMS message when an HVAC problem is detected.
Thanks to reader Harvey Tyler for suggesting clarification about how the heating or cooling thermostat FAN ON OFF switch actually functions on a digital thermostat. 02/03/2009
Domestic and Commercial Oil Burners, Charles H. Burkhardt, McGraw Hill Book Company, New York 3rd Ed 1969.
National Fuel Gas Code (Z223.1) $16.00 and National Fuel Gas Code Handbook (Z223.2) $47.00 American Gas Association (A.G.A.), 1515 Wilson Boulevard, Arlington, VA 22209 also available from National Fire Protection Association, Batterymarch Park, Quincy, MA 02269. Fundamentals of Gas Appliance Venting and Ventilation, 1985, American Gas Association Laboratories, Engineering Services Department. American Gas Association, 1515 Wilson Boulevard, Arlington, VA 22209. Catalog #XHO585. Reprinted 1989.
The Steam Book, 1984, Training and Education Department, Fluid Handling Division, ITT [probably out of print, possibly available from several home inspection supply companies] Fuel Oil and Oil Heat Magazine, October 1990, offers an update,
Principles of Steam Heating, $13.25 includes postage. Fuel oil & Oil Heat Magazine, 389 Passaic Ave., Fairfield, NJ 07004.
The Lost Art of Steam Heating, Dan Holohan, 516-579-3046 FAX
Principles of Steam Heating, Dan Holohan, technical editor of Fuel Oil and Oil Heat magazine, 389 Passaic Ave., Fairfield, NJ 07004 ($12.+1.25 postage/handling).
"Residential Hydronic (circulating hot water) Heating Systems", Instructional Technologies Institute, Inc., 145 "D" Grassy Plain St., Bethel, CT 06801 800/227-1663 [home inspection training material] 1987
"Warm Air Heating Systems". Instructional Technologies Institute, Inc., 145 "D" Grassy Plain St., Bethel, CT 06801 800/227-1663 [home inspection training material] 1987
Heating, Ventilating, and Air Conditioning Volume I, Heating Fundamentals,
Boilers, Boiler Conversions, James E. Brumbaugh, ISBN 0-672-23389-4 (v. 1) Volume II, Oil, Gas, and Coal Burners, Controls, Ducts, Piping, Valves, James E. Brumbaugh, ISBN 0-672-23390-7 (v. 2) Volume III, Radiant Heating, Water Heaters, Ventilation, Air Conditioning, Heat Pumps, Air Cleaners, James E. Brumbaugh, ISBN 0-672-23383-5 (v. 3) or ISBN 0-672-23380-0 (set) Special Sales Director, Macmillan Publishing Co., 866 Third Ave., New York, NY 10022. Macmillan Publishing Co., NY
Installation Guide for Residential Hydronic Heating Systems
Installation Guide #200, The Hydronics Institute, 35 Russo Place, Berkeley Heights, NJ 07922
The ABC's of Retention Head Oil Burners, National Association of Oil Heat Service Managers, TM 115, National Old Timers' Association of the Energy Industry, PO Box 168, Mineola, NY 11501. (Excellent tips on spotting problems on oil-fired heating equipment. Booklet.)
Carson, Dunlop & Associates Ltd., 120 Carlton Street Suite 407, Toronto ON M5A 4K2. Tel: (416) 964-9415 1-800-268-7070 Email: email@example.com. The firm provides professional home inspection services & home inspection education & publications. Alan Carson is a past president of ASHI, the American Society of Home Inspectors. Thanks to Alan Carson and Bob Dunlop, for permission for InspectAPedia to use text excerpts from The Home Reference Book & illustrations from The Illustrated Home. Carson Dunlop Associates' provides extensive home inspection education and report writing material.
The Illustrated Home illustrates construction details and building components, a reference for owners & inspectors. Special Offer: For a 5% discount on any number of copies of the Illustrated Home purchased as a single order Enter INSPECTAILL in the order payment page "Promo/Redemption" space.
TECHNICAL REFERENCE GUIDE to manufacturer's model and serial number information for heating and cooling equipment, useful for determining the age of heating boilers, furnaces, water heaters is provided by Carson Dunlop, Associates, Toronto - Carson Dunlop Weldon & Associates Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on any number of copies of the Technical Reference Guide purchased as a single order. Just enter INSPECTATRG in the order payment page "Promo/Redemption" space.
The Home Reference Book - the Encyclopedia of Homes, Carson Dunlop & Associates, Toronto, Ontario, 25th Ed., 2012, is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. Field inspection worksheets are included at the back of the volume.
Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on these courses: Enter INSPECTAHITP in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Horizon Software System manages business operations,scheduling, & inspection report writing using Carson Dunlop's knowledge base & color images. The Horizon system runs on always-available cloud-based software for office computers, laptops, tablets, iPad, Android, & other smartphones