When & Why to Use 2-Stage Gas Regulators for buildings & Appliances
GAS REGLATORS, TWO STAGE - CONTENTS: Two-stage gas regulator systems for buildings. 2-stage gas regulators improve appliance operation in certain gas piping or building conditions. LP or natural gas regulators or controls. Gas regulator inspection, diagnosis, and repair guide
InspectAPedia tolerates no conflicts of interest. We have no relationship with advertisers, products, or services discussed at this website.
Two-Stage LP or natural gas regulator requirements:
This article explains why, when, and where a two-stage gas regulator system is recommended at a building. Our page top photo shows a a large, remote, and centralized outdoor LP gas storage tank serving multiple homes in a small community in New York.
A second LP gas regulator was required at individual buildings.
Recommendations for use of two-stage gas regulation for LP or Natural Gas fuel systems
In this article series we provide descriptions and photographs of unsafe gas piping, regulators, or controls on heating systems, indications of unsafe or improperly operating gas appliances, gas meters, and other gas installation defects.
This document also provides free sample draft home inspection report language for reporting defects in oil and gas piping at residential properties.
Gas Cylinder or Tank Regulators: Readers concerned with installing, inspecting, or testing LP Gas regulators which are found on outdoor above ground or buried gas cylinders used for storage of LP Gas on site should also see How to Inspect & Test LP Gas Tank or Cylinder Regulators.
General safety warning: improper installation and even improper inspection and testing methods involving natural or "LP" gas can involve
dangerous conditions and risk fire or explosion. If you smell gas you should leave the building immediately and should do so without doing anything that could create a spark such as operating a light switch or telephone. From a safe location, call your gas company's
emergency line and/or your fire department.
The text provided here is a working draft and may be incomplete or inaccurate.
Many residential LP gas installations will be found with a single gas pressure regulator at the storage tank.
A "two stage" LP gas regulation system uses two gas pressure regulators. Gas flows out of the LP Gas storage tank first through a
"high pressure" regulation stage (usually installed right at the LP gas tank) and then through a second "low pressure" regulator
as a second stage (usually installed close to the point of LP gas entry into the building). Two stage LP gas regulation is required for certain
installations but is less often found installed at single family residential properties.
Experts recommend this "two-stage" regulation of LP gas installations, particularly where large LP tanks are installed above or below ground for several reasons:
Large LP gas tanks will be located at a greater distance from the building
Two stages of LP gas regulation helps assure steady, even gas pressure at each appliance in the building, making it easier to maintain the requisite typical eleven inches of water (equivalent pressure) at each appliance.
That's because the low-pressure regulator being used to deliver gas at the proper pressure for the appliances is located closer to the appliances than if it had
been installed right at the more distant gas tank.
Two stage LP gas regulation can (slightly) reduce the LP gas system installation cost by permitting the use of smaller diameter gas piping between
the first stage regulator (at the tank) and the second stage lower pressure gas regulator (at the building).
Two stage LP gas regulation helps avoid gas delivery system freeze-ups in climates where low temperatures are common, because the expansion rate
and gas flow does not have to occur all at one place (at the final regulator). Distributing the pressure drop across two devices means less pressure
drop occurs at each individual regulator device, reducing the tendency to form frost in very cold weather.
Use of two stage LP gas regulation permits a single high pressure line coming from the first regulator to deliver LP gas to multiple
low-pressure regulators at diverse building locations, potentially improving LP gas appliance performance at a large building.
Service people assert that there will be fewer service calls due to loss of gas pilot flame or requirements for gas burner adjustment where
two stage regulation has been employed on an LP gas piping system.
Actual NG or LPG gas pressures vary: [Note: the exact pressure you see in the building at an appliance may vary from these numbers depending on the gas distribution piping system size, diameter, number of appliances served, number of appliances operating, regulator adjustment, and other factors.
See LP or Natural Gas Pressures for a table showing the range of variation
in LP gas pressure in the tank at various temperatures. - Ed.]
Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Ask a Question or Search InspectApedia
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Carson, Dunlop & Associates Ltd., 120 Carlton Street Suite 407, Toronto ON M5A 4K2. Tel: (416) 964-9415 1-800-268-7070 Email: email@example.com. The firm provides professional home inspection services & home inspection education & publications. Alan Carson is a past president of ASHI, the American Society of Home Inspectors. Thanks to Alan Carson and Bob Dunlop, for permission for InspectAPedia to use text excerpts from The Home Reference Book & illustrations from The Illustrated Home. Carson Dunlop Associates' provides extensive home inspection education and report writing material.
The Illustrated Home illustrates construction details and building components, a reference for owners & inspectors. Special Offer: For a 5% discount on any number of copies of the Illustrated Home purchased as a single order Enter INSPECTAILL in the order payment page "Promo/Redemption" space.
TECHNICAL REFERENCE GUIDE to manufacturer's model and serial number information for heating and cooling equipment, useful for determining the age of heating boilers, furnaces, water heaters is provided by Carson Dunlop, Associates, Toronto - Carson Dunlop Weldon & Associates Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on any number of copies of the Technical Reference Guide purchased as a single order. Just enter INSPECTATRG in the order payment page "Promo/Redemption" space.
The Home Reference Book - the Encyclopedia of Homes, Carson Dunlop & Associates, Toronto, Ontario, 25th Ed., 2012, is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. Field inspection worksheets are included at the back of the volume.
Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on these courses: Enter INSPECTAHITP in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Horizon Software System manages business operations,scheduling, & inspection report writing using Carson Dunlop's knowledge base & color images. The Horizon system runs on always-available cloud-based software for office computers, laptops, tablets, iPad, Android, & other smartphones