Warm air furnace installation, troubleshooting, repair FAQs:
Questions & answers about how to repair a home heating furnace - force warm air heat troubleshooting.
This article series answers just about any question about forced air or warm air furnace central heating system troubleshooting, inspection, diagnosis, and repairs in residential buildings and homes. Sketch at page top courtesy of Carson Dunlop Associates.
Green links show where you are. © Copyright 2017 InspectApedia.com, All Rights Reserved.
If you have no heat a all and your heat is by forced or gravity warm air, see HEATING LOSS DIAGNOSIS-FURNACES.
At this website we describe the basic components of a home heating system, how to find the rated heating capacity of an heating system by examining various data tags and components, how to recognize common heating system operating or safety defects, and how to save money on home heating costs. We include product safety recall and other heating system hazards.
If you don't know what kind of heat your building uses, we explain how to figure out the answer in more detail
at HEATING SYSTEM TYPES.
On 2017-02-27 19:40:35.333103 by (mod) - gas furnace burner ignites but won't stay litCheck for a bad thermocouple or flame sensor
On 2017-02-27 18:23:49.097273 by MiguelMy gas furnace ignites but won't stay on for more than a few seconds before it goes out again. The induction fan and blower seem to be working fine. The furnace just seems to go through a series of igniting then going out right away. Sometimes, after a while it will stay on and heat to set temp and shut down appropriately, but then after the temp drops it will go back to a series of igniting then then flame out.
On 2017-02-18 17:43:09.755738 by (mod)Dave,
On 2017-02-18 17:25:34.632108 by Dave
I'm told my very efficient, gas, forced hot air furnace is only operating at 50% because it lacks return air. I thought this furnace was more powerful and more efficient than the old one. I ran two cold air returns and one heat duct to the new large bedroom.
It doesn't do much. I was told to cut a large cold air return into my hardwood floor, in the hallway up stairs. I really don't want to do that. I have easy access in the finished basement dropped ceiling. will that work? Furnace is a Trane XL80 upflow / horizontal, gas-fired 2 stage, fan assisted combustion system the house is a ranch 24'x 60'. We heat 60% of the finished downstairs as well. Thanks for your consideration.
On 2017-01-11 14:10:49.444546 by (mod)Theo
On 2017-01-11 11:41:40.504137 by theoI have a two family home I had thermostat replace on bolt 1 st and the second floor and still the 2nd floor is too hot even when it shut the thermostat off
On 2016-09-26 00:53:43.948029 by SheilaI own a condo, 1,600 sq. ft. In a vintage 3 flat in Chicago. We have radiators and furnace serving all 3 units. We are looking into individual heating units with central air in each unit. How long, would you estimate the work, how messy and how do we have heat during the installation. Also rough estimate of cost for units, installation, labor?
On 2016-06-07 14:04:50.320084 by (mod)Do keep me posted - what you learn will help others, Chuck and stay safe.
On 2016-06-07 12:14:03.672832 by Chuck MilneGood advice about the CM detector. I fitted three 18 months ago, in strategic places i.e. in the utility room the furnace is in, another outside the room, and yet another upstairs in the gallery bedroom. The property is unusual in that it is a voluminous cavern of a living space (100'x 30'x 35' open plan) so my guess is the experts will take it at face value and throw away the standard rule book. I'll keep you posted.
On 2016-06-07 08:48:29.488006 by (mod)It makes sense to be careful where life safety questions are involved. I agree with bringing in a trained, experienced gas heat service technician. Your gas supplier should also be able to help.
On 2016-06-07 07:22:03.569844 by Chuck MilneThanks again for your comments. I did study the link but couldn't determine a definitive answer. Unfortunately it's all getting a bit to technical for me as I'm not an engineer and I don't understand the jargon. Your efforts to help is much appreciated but I think the best way forward is to ask for a second opinion from another company. Kind Regards. Chuck
On 2016-06-03 17:52:36.872207 by (mod)Is your "engineer" actually a P.E. ?
On 2016-06-03 08:28:31.244175 by Chuck Milne
Hi. Sorry, yes my question was basic but just to start the conversation. The system is gas fired warm air and has venting going from the unit to a chimney on the roof. The unit is in a large utility room which has a good sized window which has an air vent.
The engineer has suggested I need to get a builder to punch a hole through the granite wall and install a vent. It has been in the building (Converted Church Hall) for up to 20 years but seems very efficient and we've experience 2 Aberdeen winters. I just thought it prudent to have it serviced but it seems to have opened a can of worms. Any comments would be appreciated
On 2016-06-02 21:10:50.893419 by (mod)Chuck It would be a bit of a stretch for me to pronounce legality having almost no information about your system, fuel, venting, etc. (and technically it's your local code inspector who declares it "legal" or not under building codes.
On 2016-06-02 11:43:10.572433 by Chuck MilneHi. I have inherited a Johnson & Starley warm air heating system. I asked a local engineer to service it and he advised that it was illegal because there was not outside venting in the utility room it is housed in. Is he correct?
On 2016-02-21 14:22:31.432078 by (mod)If the thermostat is calling for heat and the furnace is not turning on, I suspect a loose wire or a bad control board. Intermittents are hard to find. Start by eliminating the thermostat and its wiring from the equation: connect the two thermostat wire terminals at the furnace (the same as the thermostat calling for heat). If the furnace runs OK the issue is in the TT or its wiring.
On 2016-02-21 03:40:09.568536 by RoyI have a gas furnace high efficient Bryant plus 90. It was not heating to the appropriate temperature and at times would not come on until I turned off the power at the furnace and turned it back on. I check the thermostat and cleaned the electronic filters. It worked correctly momentarily but now is back to not coming on at times until I reset it and then doesn't heat to the temperature setting. other times it cycles and works properly.
On 2016-02-04 13:19:31.380237 by AmandaHi. Our hvac system is now making a buzzing sound when the heat comes on. A few days befor I noticed the emergency heat came on for no apparent reason. I am calling for technician, but wondered if anyone had any thoughts? Thank you.
On 2016-01-31 15:27:15.456862 by (mod)You are describing what may be a very dangerous condition. If the furnace heat exchanger is cracked, rusted, or has a hole in it then you may be venting dangerous flue gases including potentially fatal carbon monoxide into the occupied space. My suggestion is to ask for an inspection by a trained heating service company technician.
On 2016-01-31 01:57:56.124828 by JaPeteMy fiancee's house (manufactured) has forced hot air oil furnace. During times he's not there, the thermostat is set at 58. When returning home, the heat is turned up to 72. While the furnace is running, it smells like exhaust coming through the ductwork. The furnace was cleaned 4 months ago. There is no basement in the home, only a crawlspace. This is where the oil tank is located. There is a woodstove set up in another room but is not using the same chimney.
On 2016-01-15 20:12:51.980546 by Real8@cox.netIs the noted furnace 110 or 220 volt supplied
On 2016-01-09 13:41:10.222510 by (mod)check for fuel supply, then check for a bad thermocouple
On 2016-01-09 12:32:52.880380 by neonMy conv. heating system will start but will not ignite and fire the gas burner?
On 2016-01-06 17:20:35.996173 by (mod)I would shut the system off and call for repair; it may be overheating.
On 2016-01-06 17:18:06.890561 by (mod)Re-posting:
On 2016-01-06 17:17:47.099778 by (mod)Re-posting:
On 2016-01-06 17:17:43.336614 by (mod)Re-posting:
On 2016-01-06 17:16:35.465784 by (mod)Re-posting:
On 2016-01-06 17:16:15.271152 by (mod)Re-posting:
On 2016-01-06 17:16:11.692562 by (mod)Re-posting:
On 2016-01-06 17:15:38.152483 by (mod)Anon: please search InspectApedia.com for HEAT EXCHANGER LEAK TEST to see details.
On 2015-10-28 18:19:27.286338 by AnonymousHow to tell if the heat exchanger is gone
On 2015-10-17 23:19:18.914850 by AnonymousI cannot find where to replace the filter. I have a gas heater with forced air. It's not in the furnace.
(Nov 23, 2011) jack said:
I am trying to find the age of my Lennox model GN1-105C gas, gravity fed air, furnace which the only thing I have had to do to it in the last 40 years besides cleaning is change the thermo-couple.
Jack, at the upper left of this page where you see our links to heating-related articles and at the Article Index found at More Reading just above I have added
AGE of HEATERS, BOILERS, FURNACES
please take a look at that article and if questions remain just ask and I'll do my best to assist further.
(Jan 4, 2012) patrick said:
My furnace will not reach the set temperature (winter now). I'd set it to 22c, the room temp starts at 17c, the furnace comes on, but can never hit 22c before it turns off again. I have no leakages. What could be the possible reasons?
Check the building for unusual heat loss points;
Check the furnace BTUh rating against the building size and rough estimate of heat loss
Check the furnace for overheating in the heat exchanger by watching the fan limit switch dial to see if it's cutting off at high temperature
(Jan 17, 2012) Musty smell said:
I have musty smell coming from registers. Furnace is on concrete in basement, but basement is dirt floors and dirt wall. Any ideas how to fix this. I was told when they put it in the basement that the basement smell would not be smelled through duct work. Otherwise, I would have put furnace in garage.
Musty, there is not enough information in your note to reliably diagnose and cure your musty smell complaint, but I can suggest some places to start investigating:
1. leaks into the return duct from unconditioned spaces such as dirt floor and wall basement
2. improper return air source register location picking up air and odors from #1
3. water or moisture sources in the duct system or air handler contributing to mold growth
4. a mold reservoir in the building that has not been found, telegraphed via the HVAC system
(May 7, 2012) MB said:
My furnace "motor" runs on its own and for seemingly no reason. For example the temp in the house today is 67 and the thermostat is set at 58. The motor will run for hours with out the burner or blower turning on. To clarify; I only have heat and not ac.
Check for shorting wires controlling the furnace or fan or thermostat
(Nov 10, 2012) Eddie C said:
My furnace its going on and off. The repair man upon inspetion said: the heat exchange it's cracked and need to be replaced. Is that possible? It is an upflown system fairly modern, i'm unable to tell the brand for i'm away from home. Please advise thanks.
A cracked heat exchanger is unsafe and should be replaced. I can't guess why that'd cause the furnace to cycle on and off; they may be separate problems.
(Dec 24, 2012) Robin G said:
I have a wood stove in my basement (family room). This stove heats 2/3's of my house nicely (via convection up the stair way. However, the family room is unbearably hot and the far end of the house is 5 degrees cooler than desirable. I am thinking of running some duct work with an inline fan (air boost fan) to pump the hot air from my basement over to the other end of the house. The duct inlet temperature will be approximately 120-130 deg. F. The duct insulation will be R5. Length of duct run is approximately 90 feet.
Question: How many CFM and at what static pressure should the fan be rated for? (room size = 14 x 14 ft)
(Dec 29, 2012) William Wotton said:
I have heard that it is not good to leave my oil furnace shut off for extended periods of time...I am heating with wood & would like to keep my furnace as a backup but do not want to keep it on for the sake of keeping it on.
The concerns are:
1. moisture causing rust in a furnace that never is heated to dry out - more of a concern for steel furnaces than cast iron units
2. solidification of soot and creosote deposits making the unit hard to clean
Have the unit thoroughly cleaned before shutting it down; inspect for and fix any unusual moisture sources.
(Nov 5, 2014) Af said:
Low pitch humming now that heating is on. Furnace is in basement and noises come from 2nd floor
Check for a failing transformer or motor.
See these articles
(Feb 15, 2015) RLongfield3rd@hotmail.com said:
I have a gas Lennox Conservalor III forced hot air furnace. Sometimes it shuts off and the temperature drops quickly. When I reset the Carrier thermostat installed by Con Ed, the fan will go on, but no heat. When I go down to the furnace I can hear/see the electric starter spark, but the furnace does not ignite. I then shut off the switch next to the furnace for a couple minutes and then switch it back on and the spark begins again and usually the furnace fire up, but sometimes it takes a couple of times.
This problem occurs sporadically, but during this cool spell it has happened twice in two days. Obviously, if we ware on vacation then we would have suffered broken water pipes etc.
One addition point is that the ‘clean air filter’ message is always present even though I change the filter.
I did inform a company to come in to check it. They went through the same procedure and then just opened exhaust pipes and cleaned them out, but after awhile this problem reoccurred.
Is there something between the spark and ignition of the gas that could be the problem?
Sure; it's time for a detailed inspection by your heating service technician. If the unit is not igniting there may be a burner, fuel, or control problem. Don't force the system to ignite as you may blow yourself up.
Continue reading at FURNACES, HEATING - home, or select a topic from closely-related articles below, or see our complete INDEX to RELATED ARTICLES below.
Or see FURNACE CONTROLS & SWITCHES
Or see NO HEAT - FURNACE
Or see FURNACE OPERATION DETAILS
Or use the SEARCH BOX found below to Ask a Question or Search InspectApedia
Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website