InspectAPedia tolerates no conflicts of interest. We have no relationship with advertisers, products, or services discussed at this website.
This article describes additional hazards and potential defects in Federal Pacific Electric / Federal Noark / and some Federal Pioneer electrical panels besides the problem of circuit breakers that fail to trip. These conditions add force to the argument for complete replacement of the equipment.
Replacement FPE Stab-Lok® circuit breakers are unlikely to reduce the failure risk of this equipment. We recommend that residential FPE Stab-Lok® electrical panels be replaced entirely or the entire panel bus assembly be replaced, regardless of FPE model number or FPE year of manufacture. We do not sell circuit breakers nor any other products. For more information see FPE REPLACEMENT PANELS and FPE REPLACEMENT BREAKERS. This page assists in identifying Federal Pacific Electric Stab-Lok® electrical panels and circuit breakers. More FPE information is in the links listed at the "More Reading" links at the bottom of this article .
It is information for building inspectors, home buyers, home owners, electricians exploring the background of possible hazards associated with Federal Pacific Electric Stab-Lok® circuit breakers and service panels.
OTHER DEFECTS - Federal Pacific Electric Equipment issues extend beyond basic design of the Stab Lok Circuit Breaker
FPE Stab-Lok Circuit Breaker Panels, studies, performance, specifications were not stable
But it's more complicated than that. The company actually changed the design from time to time (without necessarily telling anyone). On the other hand, No one has provided any technical or even anecdotal data suggesting that any of these changes corrected basic design flaws. In addition, there was the problem of equipment UL-listing label swapping and therefore mislabeling individual pieces of equipment, therefore incorrectly stating the use to which individual pieces of equipment could be applied.
FPE-Design and possibly original equipment used to produce Stab-Lok Circuit Breakers sold under other brands
FPE USA stopped making equipment quite a while ago, but Stab-Lok® (TM) panels and circuit breakers continued to be produced in Canada, under the name Federal Pioneer, a Canadian "FPE" company which was later bought by Schneider Electric, also in Canada.
Federal Pioneer Stab-Lok® circuit breakers and panels continue to be available even still as new today. Some of my Canadian contacts claim that the Canadian product was better than the U.S.-made version but my own first-hand view of some of it in the home of a Canadian Home inspector was that it was just as bad. (The circuit breakers had to be held into the panel using adhesive tape!)
Several years ago I called Schneider Electric and was able to speak with a Schneider engineer about this product. I asked if they had changed the design to fix any of the inherent problems with the product series over the U.S. version. I was promised an answer to this question - the engineer was quite polite. But in follow-up calls no one at the company wanted to provide any information about this product.
If a manufacturer cannot, or will not provide their supporting test or other data for a product professionals are forced to err on the safe side by refusing to endorse it.
"Trust me" just doesn't cut it where electrical safety is concerned.
FPE Stab-Lok Circuit Breaker Panels had Other Design Issues Besides the Main Defect: circuit breakers that do not trip reliably
Doughlas Hansen, an ASHI home inspector, educator, and building failures researcher produced an inventory of FPE Stab-Lok electrical panel problems besides the principal and most-serious defect of circuit breakers that could not be relied upon to trip off in the event of an over-current. Again in 2012, Douglas, writing with Redwood Kardon, an electrical expert from CodeCheck updated that original FPE defect inventory.
Hansen organized his critique of FPE Stab-Lok equipment into three categories:
Old equipment, manufactured to "less stringent codes and standards than modern equipment". Under this heading Hansen cites
Over-crowding in the electrical panel (not unique to FPE) and he includes additonal crowding that results of some design features specific to FPE such as failiure to meet code-specified wiring clearances and inadequate space for wire bending. Hansen cites both gutter space and wire bending space defects in FPE panels.
Spring-loaded (adjustable) bus bars no longer permitted by current electrical codes; indeed we have reported elsewhere of a fatality that occured when an electrician opened the front of a spring-loaded bus designed electrical panel.
See SAFETY for ELECTRICAL INSPECTORS
Confusion about the "on" position of circuit breaker switches: in some FPE panel models "down" is "on" for some switches.
Split bus panel design features of some FPE panels are critiqued by Hansen
Accidental breaker tripping: Hansen also notes that it is difficult to remove the panel cover without accidentally tripping some circuit breakers (this is not a feature unique to FPE)
Problems unique to the design of the FPE Stab-Lok circuit breakers - not found in other electrical equipment of the same age. Among these I [DF] would include Hansen's critique of the method of connection of the circuit breaker to the power bus in the electrical panel.
The name "Stab-Lok" is a hint that the breakers are not connecte3d using a clip that binds the breaker to the bus bar but rather a "stabbing blade" that makes the electrical connection. Indeed in the home of another building expert (A.C., Toronto) I observed FPE Stab-Lok breakers that were so loose in their mounting position that they were being held in the panel by cellophane adhesive tape!
Hansen notes that it's common to find scorch marks on the breaker-to-bus connecting parts, but I pose that this may not just be due to a poor connection it may also be due to overcurrents on breakers that were not tripping when they should, combined with arcing at the loose connector.
Doug also points out that because FPE panels included two different connecting bus designs, an "E-shaped" opening and an "F-shaped" opening, it is too easy to try to plug the wrong circuit breaker onto a mis-matched bus, resulting in a damaged, bent and unsafe electrical connection.
Really? I'd include a warning not to try pushing an E-breaker into an F-bus (and vice versa) except that you should be replacing the entire electrical panel, not individual FPE Stab-Lok breakers.
Manufacturing defects and circuit breaker failures. Aronstein, press releases, and many sources have noted that in 1982 when Reliance Electric was in the process of obtaining FPE it was disclosed that FPE product listings had been obtained by deceptive means, that the company's products lost their UL listing, and that deceptive practices in testing and labeling had continued over many years. Actually the problem was noted and discussed in the press as early as 1980.
See EXXON Buys a Scandal 1980
see FPE FRAUD - PRESS RELEASE
Mr. Hansen cites the third defect as the most serious one. A review of research by Jess Aronstein suggests that categories #1 and #2 can be folded together: the failure of FPE Stab-Lok circuit breakers to trip when they should was and remains a combination of circuit breaker design and manufacturing tolerances that permitted the moving parts of the circuit breaker to jam internally.
See FPE HAZARD REPORT - 2017 [PDF] independent research article by Jess Aronstein, supercedes older FPE hazard reports by this author. for the most-complete technical research and testing of these products.
Not only do the circuit breakers fail to trip reliably when they should in response to an overcurrent, the initial response of the breaker to an overcurrent can cause an internal jam-up of its moving parts such that on an subsequent over-current the breaker may fail to trip under even the most extreme over-current loading. And an overcurrent on one leg of a 2-pole breaker causes internal jamming that prevents the breaker from tripping in the future.
Replace the FPE electrical panel, not individual circuit breakers. We have heard from many readers about using replacement FPE circuit breakers in panels where there have already been failures as well as where owners want to add circuits.
Watch out: there is no data supporting the claim that replacement FPE circuit breakers perform better than the original equipment and both field reports and testing suggest that opposite: repalcement FPE breakers do not perform better than the originals and in some cases may in fact be "original" or OEM breakers or breakers made on the same equipment using the same procedures and made to the same standards and specifications as the originals. This appears to be the case for FPE Stab-Lok "replacement" circuit breakers made in Canada, China, and Mexico and sold under several brands including "American".
Watch out: replacing the circuit breaker will also fail to address any of the bus design, burned/damaged bus, panel crowding, or other defects described by Hansen or others. You should replace the FPE Stab-Lok breaker panel entirely rather than replacing individual circuit breakers.
See Hansen's original 2003 article at Federal Pacific Electric Breakers [PDF] - an encyclopedic, non-prioritized inventory of FPE StabLok deficiencies by Douglas Hansen. [www.codecheck.com - Code Check]. This document offers building code inspection guides for field use, and links on codes and failures.
In 2012 Douglas Hansen & Redwood Karden published an Updated Version [PDF at codecheck.com] of this article. See http://www.codecheck.com/cc/ccimages/PDFs/FPE_2012.pdf
Continue reading at FPE REPLACEMENT PANEL or select a topic from closely-related articles below, or see our complete INDEX to RELATED ARTICLES below.
Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Ask a Question or Search InspectApedia
Questions & answers or comments about other FPE Stab-Lok® equipment hazards that have been identified in addition to the failure-to-trip problem.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Aluminum Wiring Information WebsiteAluminum Electrical Wiring Hazards and Repairs: in-depth authoritative info, photos, documents including selection of proper vs. ineffective repair methods. E.g.: Ideal 65 "Twister" purple connector fails in field and lab testing with aluminum wire.
2007 FPE Stab-Lok® TECHNICAL REPORT - an updated test report of independent testing (a large 1.2MB PDF file) using a larger pool of FPE Stab-Lok® circuit breakers than the older CPSC and Wright Malta tests found significantly higher failure rates of FPE Stab-Lok® circuit breakers, including a look at critical safety failures (breaker failed to trip at 200% of rated current or jammed) which found up to 80% failure rate for FPE Stab-Lok® GFCI circuit breakers (n=4), 12% failure rate for double pole FPE Stab-Lok® circuit breakers (n=120), and a 1% failure rate for FPE Stab-Lok® single pole circuit breakers (n=345).
1982 Reliance Electric Co. SEC Quarterly Report: Note C. reports litigation between Reliance and UV Liquidating Trust and contends that "... improper and deceptive practices were employed for many years to secure UL listings for Federal Pacific's circuit protective products..."
Carson, Dunlop & Associates Ltd., 120 Carlton Street Suite 407, Toronto ON M5A 4K2. Tel: (416) 964-9415 1-800-268-7070 Email: firstname.lastname@example.org. The firm provides professional home inspection services & home inspection education & publications. Alan Carson is a past president of ASHI, the American Society of Home Inspectors. Thanks to Alan Carson and Bob Dunlop, for permission for InspectAPedia to use text excerpts from The Home Reference Book & illustrations from The Illustrated Home. Carson Dunlop Associates' provides extensive home inspection education and report writing material.
The Illustrated Home illustrates construction details and building components, a reference for owners & inspectors. Special Offer: For a 5% discount on any number of copies of the Illustrated Home purchased as a single order Enter INSPECTAILL in the order payment page "Promo/Redemption" space.
TECHNICAL REFERENCE GUIDE to manufacturer's model and serial number information for heating and cooling equipment, useful for determining the age of heating boilers, furnaces, water heaters is provided by Carson Dunlop, Associates, Toronto - Carson Dunlop Weldon & Associates Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on any number of copies of the Technical Reference Guide purchased as a single order. Just enter INSPECTATRG in the order payment page "Promo/Redemption" space.
The Home Reference Book - the Encyclopedia of Homes, Carson Dunlop & Associates, Toronto, Ontario, 25th Ed., 2012, is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. Field inspection worksheets are included at the back of the volume.
Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on these courses: Enter INSPECTAHITP in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Horizon Software System manages business operations,scheduling, & inspection report writing using Carson Dunlop's knowledge base & color images. The Horizon system runs on always-available cloud-based software for office computers, laptops, tablets, iPad, Android, & other smartphones