Refrigerant charge quantity for air conditioners & heat pumps:
This air conditioning repair article series discusses the the diagnosis and correction of abnormal air conditioner refrigerant line pressures as a means for evaluating the condition of the air conditioner compressor motor, which in turn, is a step in how we evaluate and correct lost or reduced air conditioner cooling capacity.
We explain how overcharging or undercharging of refrigerant in an air conditioner or heat pump is detected and we list the effects of overcharged or undercharged refrigerant.
Green links show where you are. © Copyright 2017 InspectApedia.com, All Rights Reserved.
Effect of too much refrigerant in the system - overcharging, over-metering, or other high refrigerant pressure situations: normally we want the low side pressure to be as low as possible for refrigeration systems.
Excessive refrigerant in the system raises the system operating pressure and temperature and actually reduces the cooling ability of the system.
[Click to enlarge any image]
Overcharging of the refrigerant in a closed refrigerant system such as a typical residential air conditioner, heat pump, or refrigerator, where no liquid refrigerant receiver is included, has the following effects:
An electric motor may start running backwards due to a failed start capacitor, a reaction to high refrigerant pressure (for refrigeration motors), or other electrical events.
High refrigerant pressure in an A/C unit or heat pump or some other refrigeration motors can cause the equipment to run backwards. Cooling compressors, heat pump compressors and some other electrical motors can run backwards too: well pumps, fans, even an A/C or heat pump compressor.
If the compressor motor is a scroll-type design and in some cases if the motor is a rotary vane type design high refrigerant pressure combined with a loss of electricity can, on return of power, start the motor backwards. Scroll type compressor motors use an anti-restart control (basically a timer) to prevent the compressor from starting to run backwards.
A scroll-type compressor (and possibly a rotary vane A/C compressor motor) can start to run backwards if the motor is suddenly stopped (due to brief power loss or because you foolishly switched its electrical power "off" and back "on" quickly. In that condition, high refrigerant pressure on the outlet side of the compressor motor gives it a backwards push. When power is restored that backwards push gets the motor running backwards.
And as we discuss at CAPACITORS for HARD STARTING MOTORS, a bad start capacitor can let a motor run backwards. We've also found cases of water well pump motors running backwards after a lightning strike.
And at Questions & Answers about compressor/condenser unit fans we include a field report of a backwards running condenser unit fan.
Reader Question: What happens to an overcharged cooling system with too much refrigerant?
Could you describe what will happen with an over charged system? - S.F.
An expert inspection of any individual cooling or air conditioning system is likely to discover things that we miss by email discussions. That said, here are some things to consider:
The most serious problem is damage to the A/C compressor. Damage could occur to the compressor piston or to the refrigerant control flow valve (A/C compressors use a reed type valve that seals the compressor high side outlet) - imagine sending a slug of liquid into any reciprocating piston engine or valve that is designed to move a gas - the piston comes up and slams into liquid - and is destroyed.
Effects of too little refrigerant in the system are described in detail separately at THERMOSTATIC EXPANSION VALVES, REFRIGERANT
How can i measure the quantity of refrigerant in the system? is there any instrument that can be use to measure this? said:
How can i measure or ascertain the quantity of refrigerant in the system? is there any instrument that can be use to measure
1. Please kindly assist me on how to ascertain or measure the refrigerant quantity in a system.
2. Is there any instrument for this measurement?
3. Any relationship between an air-conditioners rated current and the refrigerant quantity?
4. Can the Pressure-Temperature chart be used to ascertain refrigerant quantity?
- S.A. 4/1/2014
On your question of does the electrical current determine the amount of refrigerant in the system, No the rated current - if you mean the equipment amps draw - does not determine the proper refrigerant charge quantity, though an overcharge or undercharge that is causing improper equipment operation or even damage might be reflected in the current draw by the compressor.
I don't know a way to precisely measure the liquid volume of what's in an individual HVAC system, as there are technical demands that I will explain here, but you can get an idea of quantity by looking at pressures, temperatures, ambient temperatures around the unit and tables published by the manufacturers.
You'd think we could just calculate the gas volume and liquid volume at any given time and temperature and pressure - theoretically that's right. But because each HVAC system has some unique installation details such as exact lengths of refrigerant piping (depending on where components are installed and how far apart they are located), the actual physical volume of liquids and gases that are in the system are not trivial to compute.
Consider that at any moment in the operation of a piece of refrigeration equipment the refrigerant inside the device exists in two places - on the high side and on the low side of the system, under high pressure as a high pressure gas, or as a liquid, and on the low side as a gas. Just how much of the refrigerant is on either side of the metering valve varies. But an accurate total of the refrigerant quantity would have to add both of these together and convert them to a common measure (liquid or gas volume with adjustments for temperatures and pressures).
A different data point is at the time of installation: the installer can use a charging cylinder to measure the accurate quantity of refrigerant that was introduced into the system - again with some adjustments for temperature. That's where the charging pressure-temperature chart comes in handy. If the manufacturer says install N liquid ounces of refrigerant X the technician has to consider temperature and possibly pressure when measuring refrigerant volumes.
A refrigerant charging cylinder provides a chart built into the device for making an accurate charge. Electronic refrigerant charging equipment does the same thing, more precisely, using circuitry and temperature (and perhaps pressure) data sensors built into the equipment.
These difficulties explain why on small systems that need a very accurate refrigerant charge, the technician often has to approach the job by first evacuating the system completely and next installing an accurately-measured charge of refrigerant.
There is no simple instrument that reads how much refrigerant by volume (gas, liquid, or more accurately a combination of the two) in a refrigeration system. There are just two times that we know accurately how much refrigerant is inside of the equipment:
Now if an air conditioner, refrigerator or similar HVACR device has not leaked, we would reasonably assume that the amount of refrigerant in the system is exactly what was originally installed. This is the case for thousands of HVACR appliances that run for years without leaking.
Since your wrote again that you still didn't see a clear answer to your question as you posed it, in sum, the short answer is no.
Continue reading at UNDER CHARGED REFRIGERANT, EFFECTS or select a topic from closely-related articles below, or see our complete INDEX to RELATED ARTICLES below.
Or see these
Or use the SEARCH BOX found below to Ask a Question or Search InspectApedia
Also see REFRIGERANT DIAGNOSTIC FAQS
(Sept 6, 2014) Anonymous said:
so very hard work . but this is my course R.A.C
(Apr 28, 2015) Robert Muela said:
my low side is 10 my hi side is 200 why
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
Our recommended books about building & mechanical systems design, inspection, problem diagnosis, and repair, and about indoor environment and IAQ testing, diagnosis, and cleanup are at the InspectAPedia Bookstore. Also see our Book Reviews - InspectAPedia.
Complete List of Air Conditioning & Heat Pump Design, Inspection, Repair Books at the InspectAPedia Bookstore.
Modern Refrigeration and Air Conditioning, A. D. Althouse, C.H. Turnquist, A. Bracciano, Goodheart-Willcox Co., 1982
Principles of Refrigeration, R. Warren Marsh, C. Thomas Olivo, Delmar Publishers, 1979
"Air Conditioning & Refrigeration I & II", BOCES Education, Warren Hilliard (instructor), Poughkeepsie, New York, May - July 1982, [classroom notes from air conditioning and refrigeration maintenance and repair course attended by the website author]
Refrigeration and Air Conditioning Technology, 5th Ed., William C. Whitman, William M. Johnson, John Tomczyk, Cengage Learning, 2005, ISBN 1401837654, 9781401837655 1324 pages
Carson Dunlop, Associates, Toronto, have provided us with (and we recommend) Carson Dunlop Weldon & Associates' Technical Reference Guide to manufacturer's model and serial number information for heating and cooling equipment ($69.00 U.S.).
Air Conditioning Inspection, Diagnosis, Repair, Efficiency all the basics for home owners, inspectors, new repairmen
Asbestos HVAC Ducts and Flues field identification photos and guide
Fiberglass: Indoor Air Quality Investigations: Fiberglass in Indoor Air, HVAC ducts, and Building Insulation