Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
SEPTIC SYSTEM INSPECT DIAGNOSE REPAIR
SEPTIC CARE INSTRUCTIONS
SEPTIC D-BOX INSTALL REPAIR
SEPTIC DRAINFIELD FAILURE DIAGNOSIS
SEPTIC DYE TEST PROCEDURE
SEPTIC FAILURE SIGNS
SEPTIC INSPECTION & TEST GUIDE
SEPTIC LIFE EXPECTANCY
SEPTIC SUPPLIES & PARTS
SEPTIC SYSTEM DESIGN ALTERNATIVES
SEPTIC SYSTEM DESIGN BASICS
SEPTIC SYSTEMS, HOME BUYERS GUIDE to
SEPTIC SYSTEM SAFETY WARNINGS
SEPTIC TREATMENTS & CHEMICALS
SEWAGE BACKUP PREVENTION
SEWAGE EJECTOR / GRINDER PUMPS
SEWER GAS ODORS
SEWER LINE REPLACEMENT
SINKHOLES, WARNING SIGNS
SOAKAWAY BED FAILURE DIAGNOSIS
SULPHUR & SEWER GAS SMELL SOURCES
TOILETS, INSPECT, INSTALL, REPAIR
TRAPS on PLUMBING FIXTURES
TREATMENTS & CHEMICALS, SEPTIC
VIDEO GUIDES: Septic Videos
WATER CONSERVATION MEASURES
WATER SOFTENERS & CONDITIONERS
WATER SUPPLY & DRAIN PIPING
WATER, WELLS, WATER TANKS: TESTING GUIDE
WASHING MACHINES & SEPTIC SYSTEMS
WASTEWATER TREATMENT BASICS
WINTERIZE A BUILDING
This septic system inspection article describes detailed "how to" steps instructing the septic inspection investigator in how to inspect specific septic components for signs of failure.
We describe the criteria for saying a septic system has failed, and we take you step by step through the onsite waste disposal system, from the building to tank to absorption system, with suggestions for examining the condition of each component so that a proper diagnosis of the cause of septic failure and a specification of the appropriate repair can be made.
In the photo at the top of this page, a wet spot appeared in the previously "perfect" yard of this older home within twenty-four hours of the new family moving-in. The buyers had obtained a "septic inspection" but it was improperly performed and missed the chance to discover before purchase that the septic system was in total failure.
Green links show where you are. © Copyright 2015 InspectApedia.com, All Rights Reserved.
Before digging up your septic tank or calling a septic pumper, if you think the septic system is failed because of drain blockage or drains backing up into the building, you should to see Diagnosing Clogged Drains: Is it a blocked drain or the septic system? - A First Step for Homeowners. If you link to that text, please return here using your browser's "BACK" button.
[Click to enlarge any image]
Onsite Waste Disposal System Failure Criteria
Massachusetts Title 5 Septic Law lists specific failure criteria and serves as a good model for septic inspections anywhere. (The photograph shows the septic baffles in a concrete septic tank. While at the time of inspection the sewage was not flowing over the baffles, sewage debris atop the concrete baffle shows that at some point that problem had occurred. Further diagnosis was in order.
Detailed criteria that define when a septic system has failed can be read at SEPTIC FAILURE CRITERIA.
Outside, waste piping conducts sewage (black water and gray water) from the building to the treatment tank or "septic tank," and from the treatment tank to the distribution box. Our photo shows a new waste line carrying sewage down from the home to the septic tank in lower yard. The previous waste line had been broken when driven over by a heavy lawnmower.
Septic drain lines between the house and the septic tank should be of solid, non-perforated material and need to be protected from mechanical damage (such as by vehicles). Piping extending from the distribution box into drain fields is normally perforated, though solid lines might be used if effluent is being processed by more specialized devices such as seepage pits, galleys, or a sand-bed system.
Distribution piping connects the house drain to the septic tank, running between the building and the tank inlet. More distribution piping connects the septic tank outlet to the distribution box and from there to the leach field. Distribution pipes can settle (especially in new construction), break, become blocked or clogged, or become invaded and blocked by tree roots or soils.
Older "orangeburg" pipes which look like black asphalt-soaked cardboard (they are) crush and deteriorate with age. Clay pipes also break and have a tendency to become blocked by tree roots at their joints. You won't know what kind of piping is installed until it is excavated, but the age of the property may be a clue. Homes built from the 1970's on, certainly from the 1980's on, use cast iron or more often plastic ABS or PVC piping for these connections.
This line may become blocked by waste, damaged by collapse of a section, or invaded by roots. Detection of these conditions is fairly easy by routing a snake or power snake from the building drain to the septic tank. An experienced power snake operator can often tell by "feel" that a drain line is collapsed, partially collapsed, or invaded by roots. While you may make a temporary "repair" of such a condition by drain-cleaning, if the line is broken or root-invaded, you should expect to have to excavate and replace it soon.
Also see DRIVING or PARKING OVER SEPTIC
We have reports of children and adults who have died from this hazard (December 1997, California).
In 2000 we consulted in a fatality involving an adult falling into a cesspool. At a building inspection I myself stepped through a hidden, rusted-through steel septic tank cover.
Falling into a septic tank, drywell, or cesspool is quickly fatal, either from being buried by falling soils and debris, or by asphyxiation. Septic gases are highly toxic and can kill in just minutes of exposure. Even leaning over an empty (just pumped) tank has led to collapse and fatality of a septic pumper.
The same failures can occur on the effluent distribution pipe line from the septic tank outlet in to the distribution box as we described earlier on piping from house to the septic tank. Pipes can settle (especially in new construction), break, become blocked or clogged, or become invaded and blocked by tree roots or soils.
How to Determine Where a Septic Blockage Is Located
How would we distinguish among blockages at different points in these distribution lines?
Distribution boxes serve as a connection point to distribute effluent which arrives from the septic tank outlet and is to be sent into two or more individual leach field lines.
Distribution boxes ("D-Boxes") can settle or tip. A damaged or tipped D-box will fail to divert effluent uniformly among the effluent receiving drainfield lines, causing flooding of one leach line. If you see depressions suggesting that there are four leach lines at the property and the end of just one of them is producing wet soil or surface-breakout of effluent, we'd suspect a tipped D-box.
Opening the D-box can also show whether or not effluent is being directed uniformly into each of the leach lines. A tipped D-box can overload one line and cause early failure of the absorption system.
If this is happening, flow adjustment end-caps (eccentric holes) can be installed in the distribution box on the inlet end of each of the drain lines, permitting adjustment of effluent delivery into each line, perhaps relieving the problem line and redistributing effluent into the others.
In a conventional "drain field" of perforated pipes buried in gravel-filled trenches, a drain line may be invaded by tree roots. This is why experts advise keeping tree and shrub plantings away from drain fields.
Vehicle traffic can also collapse this or any outdoor waste piping, which is why experts advise against ever driving over a drainfield or over any other septic system components. See DRIVING or PARKING OVER SEPTIC
Drainfield piping is usually constructed of perforated pipe buried in gravel-filled trenches. It receives effluent from the D-box and allows it to percolate or seep into the soil around the trench where added filtering and bacterial treatment occur.
Like the distribution piping discussed above, individual drainfield pipes can become crushed, shifted, or clogged by tree roots or other debris. More general clogging and failures of the leach field are discussed below. A broken or clogged pipe, once it has been located, may be much less costly to repair than a complete leach field replacement, so this possibility needs to be considered during diagnosis of a "failed" septic system.
Lockwood, in "An Engineer's View of Septic Systems" listed these causes of absorption field failure:
" If the liquid effluent cannot soak into the soil surrounding the leach field, sewage may back up into the system and overflow into the house or puddle on the surface of the ground. There are several possible causes for this problem."
Continue reading at DRAINFIELD RESTORATION APPROACHES
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Design Manuals for Septic Systems
Onsite Wastewater Disposal Books