Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
AIR CONDITIONING & HEAT PUMP SYSTEMS
BACKDRAFTING HEATING EQUIPMENT
BACKUP HEAT for HEAT PUMPS
BANGING HEATING PIPES RADIATORS
BLOWER FAN OPERATION & TESTING
BOOKSTORE - InspectAPedia
BTU USAGE MONITORS
CARBON MONOXIDE - CO
CIRCULATOR PUMPS & RELAYS
DIAGNOSTIC GUIDES A/C / HEAT PUMP
DIAGNOSE & FIX HEATING PROBLEMS-BOILER
DIAGNOSE & FIX HEATING PROBLEMS-FURNACE
DIRECT VENTS / SIDE WALL VENTS
DRAFT REGULATORS, DAMPERS, BOOSTERS
DUCT SYSTEM & DUCT DEFECTS
ELECTRIC MOTOR DIAGNOSTIC GUIDE
FAN, AIR HANDLER BLOWER UNIT
FLOODED HEATING EQUIPMENT REPAIR
FLUE SIZE SPECIFICATIONS
GAS BURNER Flame & Noise Defects
GAS PIPING, VALVES, CONTROLS
GEOTHERMAL HEATING SYSTEMS
HEAT PUMPS, DIAGNOSIS, REPAIR
HEATING COST SAVINGS METHODS
HEATING OIL PIPING TROUBLES
HEATING OIL TANKS
HEATING SYSTEM NOISES
HEATING SYSTEM TYPES
GAS LP & NATURAL GAS SAFETY HAZARDS
MANUALS & PARTS GUIDES - HVAC
MIXING / ANTI-SCALD VALVES
MOTOR OVERLOAD RESET SWITCH
NOISE, HEATING SYSTEMS
ODORS FROM HEATING SYSTEMS
OIL FILTERS on HEATING EQUIPMENT
OIL FILL PIPE LEAKS
OIL SPILL CLEANUP / PREVENTION
PLASTIC Plexvent / Ultravent RECALL
PUFFBACKS, OIL BURNER
RELIEF VALVE LEAKS
Reset Switch - Heater Primary Control
RESET SWITCH - ELECTRIC MOTOR
Reset Switch - Stack Relays
SAFETY, HEATING INSPECTION
SAFETY RECALLS CHIMNEYS VENTS HEATERS
SOLAR HEATING SYSTEM DESIGNS
SOOT on OIL FIRED HEATING EQUIPMENT
STEAM HEATING SYSTEMS
THERMOSTATS, HEATING / COOLING
VIDEO GUIDES: Heating System Videos
WINTERIZE A BUILDING
WOOD, COAL STOVES & FIREPLACES
WOOD STOVE SAFETY
ZONE VALVES, HEATING
Steam heating boiler gauges: this article describes the pressure or sometimes combination & temperature gauges found on most steam heating systems. The steam oiler gauge gives helpful pressure readings that tell us if the boiler is operating normally.
The steam boiler pressure readings at a boiler can help diagnose problems abnormally high pressure levels that often mean problems with the steam heat distribution system or its piping. We give normal low-pressure steam heating boiler pressure numbers and we explain what variations from these data signify.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Pressure and Temperature gauge on steam heating boilers: Residential steam heating systems are almost always designed to operate at very low pressures, perhaps around .5 psi - that' s 1/2 of one psi.
You can see these pressures in our page top photo - both on the gauge and on the pressure controller.
You should see similar settings on the pressure gauge (at left in our photograph) and on the steam pressure control switch (the gray box at right in our photo) on your boiler.
What Are the Normal Hot and Cold Operating Pressures of Residential Steam Heating Boilers?
[Click to enlarge any image]
At left if you enlarge the image you'll see that the steam pressure gauge on this Weil McLain Model 68 steam boiler reads about 0.5 psi - a setting consistent with the pressure set and shown on the scale on the steam pressure control to the right of the gauge.
If your residential steam boiler is operating at higher pressures (take a look at the dial setting on your PRESSURE CONTROL, STEAM BOILERS) , that may be an indication that a service technician or owner was having trouble getting heat distributed through the building. Rather than finding and fixing the problem, someone is trying to "force" the steam around the system.
An experienced steam heat service technician will look at the operating pressure of your steam heating boiler and if it is not set to a normal level, the technician will look for the reason. Examples of problems that can affect the flow of steam heat through the system, leading to attempts to over pressurized the system include
Steam Pressure Gauges on Condensate Recivers
At the right side of our photo of a remote building steam condensate receiver and pump system we see a steam pressure gauge that is used by the service technician to monitor pressure in the steam heating systerm.
This added information can be helpful when a central steam plant is feeding steam to multiple buildings.
In this case the photo shows a condensate receiver and pump in a Poughkeepsie New York building that is across a major street and several thousand feet from a central steam plant.
The steam gauge shown in the photo at left is installed with an isolating valve - that blue handle below the gauge itself. The handle is in the "open" position - allowing steam pressure to be read as you can see that the handle is parallel to the connecting piping.
Watch out: some technicians leave the isolating valve or handle for remote gauges in the closed position when the gauge is not in use. This is a "safe" position that protects from pressure, steam, or condensate loss should the gauge become damaged.
See CONDENSATE RETURN PIPES, PUMPS, STEAM for details about steam condensate return systems & controls.
If your steam boiler has an automatic water feeder you should see the water level always close to the fill-mark and the automatic water makeup valve will normally do this job for you.
When to add water to the steam boiler
If your steam boiler has only a manual valve for adding water, until you know the system's rate of water usage, you should check the water level at least once a week during the heating season.
You'll want to add water whenever the sight glass shows that the water level has dropped to the "add" mark and you should always see some water in the sight glass.
How much water to add to the steam boiler
The sight glass on a steam boiler, combined with a mark or gauge usually placed on the sight glass or on the boiler body behind the glass, will show the proper level to which the steam boiler should be re-filled when it's low on water.
See SIGHT GLASS, STEAM BOILER for details of this component.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References