InspectAPedia tolerates no conflicts of interest. We have no relationship with advertisers, products, or services discussed at this website.
Electric motor start-run capacitor instructions:
Tthis electric motor capacitor article series explains the selection, installation, testing, & use of electric motor starter start and run capacitors used on various electric motors found in or at buildings such as air conditioner compressors, fan motors, some well pumps and some heating equipment. These electric motors use a capacitor to start and run the motor efficiently.
We explain the choice & wiring procedures for a hard start capacitor designed to get a hard-starting air conditioner compressor motor, fan motor, refrigerator, or freezer compressor or other electric motor (such as a well pump) going.
Capacitors are electric devices that get an electric motor running at start-up or that help keep a motor running once it has started. If the capacitor has failed the symptom is that the motor won't start. You may hear it humming or observe that it's getting hot. If you observe this we suggest that to avoid damage you turn off the system while waiting for repairs.
Green links show where you are. © Copyright 2015 InspectApedia.com, All Rights Reserved.
The starting capacitor helps a motor start spinning by creating a high-torque, rotating, electrical field in the motor. In many electric motors there are actually two capacitors, one boosting the start winding (the start capacitor) and a second that remains in the circuit while the motor continues running (the run capacitor).
If the start capacitor has failed the symptom is that the motor won't start. If either or both start and run capacitors are defective the motor may try to start but will hum and won't keep running. You may hear a compressor or fan motor humming or observe that it's getting hot.
Watch out: If you observe a humming electric motor that is not starting we suggest that to avoid damage you turn off the system while waiting for repairs.
Normal start & run capacitors on compressors, fan motors, other electric motors
Air conditioner compressor motors (and lots of other electrical motors) that run on two-phase (220V) or single phase (120V) electrical power usually include a capacitor in the start circuit to help get the motor spinning; a capacitor can be put into the "run" circuit of the motor as well to increase motor efficiency.
Starting capacitor: the starter capacitor gives extra torque or boost to get a motor spinning in the right direction by providing about double that nominal system voltage.
Run capacitor: once the motor has started, a run capacitor may be used to help the motor retain full power, providing 1.5 x the nominal system voltage and varying as needed depending on the load on the motor.
In some old-school class views adding a run capacitor is similar to making two-phase out of one-phase electricity and is a common practice on air conditioners. What these folks really are saying is that "With capacitive reactive power of about 75% of the nominal power of the motor, the comparison of power is slightly lower than that of a three-phase motor of equal size." 
Technical notes: Single phase electric motors such as those used in air conditioner compressors and fan motors contain two different stator windings: an auxiliary starter winding fed by an electric capacitor and a main run winding fed by the principal electrical circuit. The auxiliary starter winding is used to provide an extra boost (and proper direction) to get the motor spinning at start-up. (Three phase electric motors do not use start/run capacitors.)
Electric motors that use start/run capacitors may be PSC (permanent split capacitor) and CSR / CSCR (capacitor start, capacitor run) designs. Unlike a PSC motor, a CSR/CSCR motor must also have a starting relay that will cut the start capacitor out of the electrical circuit once the motor has gotten up to run speed. The run capacitor then remains in the circuit to keep the motor spinning properly.
If your air conditioner has stopped running, a possible problem is the failure of the starting capacitor found on the outside compressor/condenser unit. If that unit has electrical power but the compressor and/or its cooling fan are not running, one of the components to check (and that is easy to replace) is the starter.
When an electrical motor is having trouble starting, such as an air conditioning compressor motor, blower motor, a refrigerator motor or a freezer motor, or even a fan motor, the repair technician may install a simple and inexpensive hard-start capacitor.
The starting capacitor is a simple electrical device which can give an extra voltage jolt or "boost" to get the hard-starting motor spinning.
The starting capacitor in our page top photo is oval in cross section, but most replacement and many newer air conditioner motor starting capacitors are simply cylindrical in shape (photo at left).
Field report: describes diagnosing & replacing a bad starter capacitor on a heat pump that had stopped working
Our Heat Pump was new in 2002. It is a 3 ton unit ProSeries brand by Service Masters. We just had a big birthday party at our house for my 1 year old daughter. 95 degrees outside. House full of Aunts, Uncles, friends, Great Grandparents.
We got through that before the failure. Next morning it is just real gooey in our house. I can feel the blower fan is on. No cool air at all. I had to go to work so I left the house. Come back home in the mid afternoon to find house is hotter than before and my wife reports that the air hasn’t been cooling at all. It’s around 86-88 degrees in the house.
I check the little screw in fuse on the side of the blower unit. Hoping to find a $2 fuse blown. Nope. Fuse looks fine. Getting a little sense of panic because I remember how expensive our last service call cost for this heat pump. Plus it takes two days to get a technician to come out.
The key that I found on your web pages was the fact that the fan on the top of the condenser unit wasn’t running and the Compressor wasn’t running either. This pointed [possibly] to the start capacitor. In my system it is actually a pair of them, a dual capacitor unit. Aha! Finding the start capacitor took about twenty minutes. I work really slowly when I’m trying to not drop a handful of sheet metal screws in the grass [or worse into an electrical component where left in place a dangerous short circuit could occur].
I could see a little bit of bulging on the capacitor and some rust and grunge on the top.
I found a local HVAC Supply house in the phone book and read them the nomenclature from the side of the old Start Capacitor. The order clerk I spoke to was amazingly patient with me. About an hour and a half later I was plugging the new Start Capacitor in and flipping the circuit breaker back on. I put my hand on the coolant line and felt the copper getting cool fast. - James Oiler
Watch out: remember to turn off electrical power to any equipment before opening or working on it. Otherwise you could be electrocuted. Also, remember that an electrical capacitor can retain a large electrical charge even after electrical power has been turned off. You could still be shocked!
Also see HOW TO WIRE up a START CAPACITOR
When testing a compressor, one must discharge the capacitor first! It'll otherwise have enough power stored on it to be at least very painful. (Author and others have been zapped!) Some systems will automatically discharge the capacitor, but shorting its leads [to ground] with a screwdriver (after verifying that the power's off) is a safe way to ensure that you won't get shocked. Motor starting capacitors can hold a charge for days!
If oil has leaked out of a capacitor: Don't touch any oil that leaked out: old capacitors may contain PCB oils, an extremely carcinogenic (cancer causing) material which require special disposal.
Once the capacitor has been discharged (as described just above), then it can be tested with a multi meter. Either use the meter's built in capacitor test function, or use this trick: Charge the capacitor by using the sense current the meter puts out when set to ohms. You should observe a rapidly rising resistance before the meter indicates over range/infinity. Disconnect the test leads, and switch over to volts. Then, reconnect the test leads. A voltage reading should be observed, approaching zero.
If the capacitor doesn't hold a charge, or the resistance reading never approaches infinity, it probably needs replacement.
Also, the capacitor may be defective if the compressor hums but does not start. Visual inspection may reveal it to be bulged, or have a blown out safety plug.
Examples & Sources of Start / Run Motor Capacitors
The following links to chapters in this motor capacitor article series have been retained for compatibility with cached article data.
Question: the capacitor is leaking oil
(June 15, 2015) Larry said:
I noticed my air conditioner's run capacitor is leaking oil - what does this mean?
The capacitor is shot and should be replaced.
Reader Question: replaced both start & run capacitors on AC compressor but compressor won't turn on
(June 15, 2015) Larry said:
Trane Xl1600 heat pump cools down to set thermostat setting and then will not turn compressor back on and blow hot air in the home. This seams to happen when Phoenix temperatures reach 100 degrees. Replaced both start and run capacitors a couple months ago as issue started last summer was working fine until 100 degrees. Any assistance with this would be greatly appreciated.
This question was posted originally at DIAGNOSTIC GUIDES A/C / HEAT PUMP
Larry if replacing the start/run caps didn't fix the trouble I suspect either a failing control board / relay or a compressor motor that is failing beyond the ability of the starting cap to kick it off. Perhaps your tech will check the current draw of the various motors involved to see if that's going on.
Continue reading at MOTOR CAPACITOR TYPES or select a topic from the More Reading links or topic ARTICLE INDEX shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
INDEX to RELATED ARTICLES: ARTICLE INDEX to ELECTRICAL INSPECTION & TESTING
OR use the Search Box found below at Ask a Question or Search InspectApedia
Frequently Asked Questions (FAQs)
(Feb 21, 2014) Anonymous said:
is it possible to rebuild a submersible well pump
Yes ... maybe; it depends on the condition of the pump casing, parts, an in my opinion, an accurate diagnosis of the trouble; at some point rebuilding is not cost effective. Indeed there are specialists (H Shreck in Poughkeepsie used to be one of them) who rebuild electric motors of all kinds.
So to answer your question, I dunno - it depends on what's broken.
Question: fan will start but won't keep running.
(June 1, 2014) Anonymous said:
The fan on my Conquest 80 will not stay on (interior fan). It starts and then stops after a few seconds. It was installed in 2005. Help.
The start capacitor is for getting a motor started, not keeping it running.
Often motors have two windings, a start winding and a run winding. Your motor's run winding may be damaged.
Or your fan motor may require a dual capacitor (start and run) or a separate run capacitor to keep it spinning.
Or your system may have a faulty control.
Question: will a hard start capacitor reduce current drawn and stop tripping a breaker
(June 7, 2014) Joel said:
I have a commercial hood & exhaust fan (120v) running in a food truck that is used for catering. We occasionally need to run off a generator (3000w) and we've found that the fan cause the generator overload to trip. The fan has been tested and observed to draw 8 amps running at full speed. Given this, would it be possible to add a hard start kit, such as SUPCO SPP4E? Will need to confirm the motor size, just wondering if this would help.
The total draw of all items is less than 20 amps and the generator is capable of supplying 25 amps constant.
Thanks for the advice.
Joel I think the problem lies elsewhere and needs some further diagnostics. I suspect that your total current draw is exceeding the ability of the generator - you may be running more than the fan, such as lighting, a cooler, toasters, other electrical appliances. If it were just the fan, drawing 8A, it has no business tripping the breaker.
Put another way if the problem is the fan and there are NO other appliances running, then there is a failing fan motor drawing high current, or an electrical short circuit or other unsafe condition to find and fix.
A start capacitor or a run capacitor won't change the current drawn by the motor.
Question: clarifying dual start-run capacitor nomenclature
(June 16, 2014) Danno said:
(June 18, 2014) Mark said:
Decode a 35/5/440 marking on a motor starting capacitor
35/5 : The first two numbers are the capacitance 35 uF (start) and 5 uF (run).
(Aug 30, 2014) Bob said:
Does Lennox use a dual and a single capacitor
(Aug 30, 2014) Anonymous said:
Thanks Mark, I've included your helpful explanation in the article above.
Anon, thank you for griping about the difference between start and run capacitors. I'll review the text above for clarity and edit as needed.
Run caps are sold as single capacitor (two terminals) for a single purpose (keep the motor running) and rating (rated in mfd or uf) for the motor (such as 45uf for a compressor or 5 uf for a fan motor)
Dual run caps combine two capacitors in a single unit, one for compressor and one for fan, such as a 45/5 MFD unit, and will have 3 terminals as detailed in the text above (compressor, fan and common)
Start caps have the single job of getting a compressor motor spinning and of course are rated at a much higher MFD number. Mark summed it up nicely below and again in the article text above.
Bob if your unit has a start-run capacitor, a dual capacitor, that unit may be the only one present.
Capacitors may be found for the compressor/condenser motor and separately for the fan motor (on some units) - follow the power terminals of the equipment back to their power source.
The capacitors used on your particular Lennox unit will be described in the installation, maintenance and wiring manual or obtained by giving Lennox a call with your product model number.
Question: Marine AC compressor shuts down
(Sept 16, 2014) Ira said:
has anyone checked for a failing start relay?
Question: clicking noise in Goodman Heat Pump
(Oct 6, 2014) Diane said:
(Nov 20, 2014) Daniel said:
If the indoor air handler unit is running but no air is coming out of the air supply registers I suspect that the blower assembly has failed or duct connections have come loose.
Check first for a blocked air filter or crimped air ducts. Watch out: an air filter that got sucked into the blower assembly can cause a fire.
Question: suspect stuck rotor in Panasonic AC Compressor
(May 6, 2015) Mohiddin said:
You might get such a motor running but I'm doubtful it has a useful remaining life.
It sounds to me as if you need a new compressor. Even if you got it running by banging it around, its continued service is doubtful.
Question: old AC unit startup trouble
(May 6, 2015) Bruno , (Architect 5512 (RET> ) said:
Thank you for your absolutely great Web-Site Bruno
Sorry Bruno I don't understand the question
(June 10, 2015) Anonymous said:
1. the compressor needs replacing
2. motor needs replacing
How much should each cost
(July 19, 2015) John said:
(Aug 17, 2015) Paul said:
Paul, that's probably a bad capacitor
(Sept 27, 2015) Anonymous said:
2015/11/26 email@example.com said:
If your motor already used a start/run capacitor, now won't start, and will run if given a spin, then yes replace the capacitor with one of same values.
A bad winding, however, won't be fixed by adding a capacitor.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Support InspectApedia.com & See Fewer Advertisements
From Google's Contributor website: Contribute a few dollars each month. See fewer ads. The money you contribute helps fund the sites you visit.