Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
AIR CONDITIONING & HEAT PUMP SYSTEMS
A/C - HEAT PUMP CONTROLS & SWITCHES
AIR CONDITIONER COMPONENT PARTS
AIR CONDITIONER TYPES, ENERGY SOURCES
AIR FILTER EFFICIENCY
AIR FILTERS, FIBERGLASS PARTICLES
AIR FLOW MEASUREMENT CFM
APPLIANCE DIAGNOSIS & REPAIR
APPLIANCE EFFICIENCY RATINGS
BLOWER DOORS & AIR INFILTRATION
BLOWER FAN CONTINUOUS OPERATION
BLOWER FAN OPERATION & TESTING
BOOKSTORE - Air Conditioning "How To" Books
CAPACITORS for HARD STARTING MOTORS
CLEANING & Legionella BACTERIA
CHINESE DRYWALL HAZARDS
CONDENSATION or SWEATING PIPES, TANKS
DEFINITION of HEATING & COOLING TERMS
DEW POINT CALCULATION for WALLS
DEW POINT TABLE - CONDENSATION POINT GUIDE
DIAGNOSTIC GUIDES A/C / HEAT PUMP
DIAGNOSE & FIX HEATING PROBLEMS-BOILER
DIAGNOSE & FIX HEATING PROBLEMS-FURNACE
DUCTS - Asbestos
DUCT INSULATION, Asbestos Paper
DUCT INSULATION for SOUNDPROOFING
DUCT SYSTEM & DUCT DEFECTS
DUCT SYSTEM NOISES
DUCTS, Asbestos Transite Pipe
DUST, HVAC CONTAMINATION STUDY
ELECTRIC MOTOR OVERLOAD RESET SWITCH
EVAPORATIVE COOLING SYSTEMS
FAN LIMIT SWITCH
FAN NOISES, HVAC
GAS EXPOSURE EFFECTS, TOXIC
GAS DETECTION INSTRUMENTS
HEAT LOSS (or GAIN) in buildings
HEAT LOSS (or GAIN) INDICATORS
HEAT LOSS R U & K VALUE CALCULATION
HEATING SMALL LOADS
INSPECTION CHECKLIST - OUTDOOR UNIT
INSPECTION LIMITATIONS, A/C SYSTEMS
LEED GREEN BUILDING CERTIFICATION
LOST COOLING CAPACITY
LOW VOLTAGE TRANSFORMER TEST
MOTOR OVERLOAD RESET SWITCH
MOLD in AIR HANDLERS & DUCT WORK
OPERATING COST, AIR CONDITIONER
OPERATING DEFECTS, AIR CONDITIONING
REPAIR GUIDES A/C / HEAT PUMP
REPAIR & DIAGNOSTIC FAQs for A/C
THERMOSTATS, HEATING / COOLING
THERMOSTATIC EXPANSION VALVES
WATER COOLED AIR CONDITIONERS
WINDOW / WALL AIR CONDITIONERS
WINDOW / WALL A/C SUPPORTS
Air duct routing & support mistakes to avoid:
This HVAC duct design and repair article describes proper (and improper) Heating & Air Conditioning Duct Routing & Support such as duct routing and support details to prevent or fix loose, sagging, crimped, bent or otherwise defective heating or cooling ductwork.
Crimped, squashed, or sagging ductwork restricts cooling or heating airflow into a building. Air ducts routed in a concrete floor slab also invite many problems including air quality issues and collapsed ductwork that reduces airflow and increases system operating cost.
Green links show where you are. © Copyright 2015 InspectApedia.com, All Rights Reserved.
Air conditioning duct system defects include a remarkably wide range of errors, from failure to supply cool air or failure to even circulate air in the building, to health hazards such as use of asbestos material in or on duct work, to very dangerous conditions such as drawing heating equipment combustion gases into the building cooling (or heating) air.
This article describes errors to avoid when installing ductwork in buildings.
Avoiding these errors will result in improved air flow, lower system operating cost, and may help in avoiding problems of mold or other contaminants in the heating or cooling duct system of a building.
The master document, of which this is a chapter, describes the inspection of residential air conditioning systems (A/C systems) to inform home buyers, owners, and home inspectors of common cooling system defects and repairs.
Sketches adapted from GA recommended construction code & from: 
When heating and cooling ducts are placed in ground contact, such as in the crawl space shown in the photo, not only is the contact going to conduct heat or cooling away from the duct before the air reaches its destination.
Furthermore there is a significant risk of water leaks or accumulation of condensation in the duct in damp or flooding areas (risking a mold or health concern) or rodent entry.
Heating or cooling air ducts should be supported away from ground contact such as in crawl spaces.
Sharp bends in ductwork restrict airflow (and violate ASHRAE or SMACNA guidelines for duct installations).
Restrictions in airflow through duct systems increase the heating or cooling system operating cost and reduce the comfort of building occupants.
This photograph shows flex-duct in an attic making a too-tight 180 degree turn, crimping and restricting airflow in the duct system.
Bends in flex duct should not be acute and should not be less than one duct diameter in radius - Sources: 
Excessive length of ducts is often found where flex-duct is installed by an amateur. If you see a length of flex-duct snaking across an area with multiple unnecessary twists and turns, the combination of length and unnecessary bends reduces airflow, with the costs just cited above.
This photograph shows unnecessary lengths of small-diameter flex duct left by the installer. The small diameter of these ducts also tells us that we're looking at a high-velocity air conditioning system that uses a combination of small-diameter ducts and higher air velocity to deliver cooling air to the conditioned space.
Flex duct runs should be as short and direct as possible without at the same time causing inappropriately sharp bends or kinks.- Sources: 
Flex duct runs should be as short and direct as possible without at the same time causing inappropriately sharp bends or kinks.- Sources:  Illustration adapted from .
The smoothness of the duct interior (flex duct is more resistant to airflow than a solid duct surface) is affected by the degree of flexduct extension. ACCA Manual D includes a friction chart that takes this into consideration (Appendix 2, chart 7).
Incidentally, when installing a length of flexduct, you should not just leave extra duct length "squashed" and in the run. Duct calculations assume that you have removed excess length of flexduct and that the installed length of flex-duct has been "fully extended".Why? For duct interior smoothness and better airflow. Fully extended flex duct will significantly redue the friction losses in the sysem.
Pinched or Crimped Air Ducts Reduce Heating or Cooling Airflow
Other common duct routing errors include sharp bends in duct work, mismatched sizes of duct work among sections, flex duct which has become crimped or pinched to restrict air flow such as in the photo at left, and of course ducts which have become disconnected.
We discuss and illustrate disconnected heating or air conditioning duct defects at DUCT CONNECTIONS.
We show the interior of crimped or squashed flexduct at DUCT DAMAGE, MECHANICAL.
The photo at left violates several of the flex-duct installation guidelines we cite just below:
Vertically installed duct should be stabilized by support straps at a maximum of 6 feet (1829 mm) on center.
Also, for cool air distribution from a blower assembly located below the area served, the height of ductwork determines how much cold air the blower has to push "up" - don't use flex-duct for vertical air supply risers past more than two floors in a building.
- Sources: 
Our photo (below left) illustrates how you may spot an air duct routed through the building floor slab. In this case the furnace return air plenum was also located below the concrete floor. The air duct system in this building had been subject to periodic flooding, as illustrated in our second photo (below right).
A description of the health and functional problems that may be traced to air ducts that were routed in a concrete floor slab as well as our advice on how to properly abandon and seal in-slab air ducts are found at DUCT in CONCRETE FLOOR.
There we describe concerns with ductwork run in floor slabs in the article above, including risks of air duct collapse that interferes with air flow through the system, water leaks into the in-slab duct system (not a problem unique to transite ducts), and rodent or insect infestations or even mold contamination. Odor complaints may be traced to the duct system because of these problems (DUCT & AIR HANDLER ODORS).
Below, reader-contributed photographs of problems in spiral metal ductwork routed in a concrete floor slab illustrate rust, flooding history (below left) and ductwork collapse (below right).
Hopefully needless to say,
SLAB DUCTWORK - catalogs the functional and environmental problems found when HVAC air ducts are routed in or below floor slabs
Continue reading at FLEX DUCT SOURCES or select a topic from the More Reading links shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Question: how much efficiency do I lose if air returns are not located close to the floor
My house is one story on a slab, 1600sq ft. I am converting froms electric baseboard to a gas forced hot air system. All ducts are located in the attic. Since the return ducts will also be in the ceiling how many returns should I have the contractor install? How much efficency will I loose because the returns cannot be located close to the floor? - email@example.com 5/29/11
I agree that you're asking an important question about proper supply and return duct design, but I cannot answer it by email and with so little information. I'd ask the contractor to go over the design with you and to show you how the return air and supply air will be both adequate and balanced. Also pay attention to the locations of the supply and return registers - you don't want the return too close to the supply or you'll have a short circuit in the system that will prevent good operation.
Question: what is the maximum recommended length for runs of flex-duct?
how long I can use the fex duct work?
Reply: A summary of Flex Duct Installation Specifications & Recommendations
Angel, I think you are asking what is the maximum recommended length for flexduct in an HVAC system.
Adding to all that complexity are other factors that can snarl up the delivery of air flow by a heater or air conditioner into a room, such as
OK so those are a bunch of factors that tell us how well a duct system will work.
Flex duct run length rule of thumb
In addition to duct design calculators and worksheets provided by duct manufacturers and HVAC industry associations, people often also do a "sanity check" on the duct design by applying a rule of thumb - much as you are asking about in your question:
Questions & answers or comments about proper HVAC duct routing and support.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References