Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
AIR CONDITIONING & HEAT PUMP SYSTEMS
A/C - HEAT PUMP CONTROLS & SWITCHES
A/C DATA TAGS
A/C DIAGNOSTIC FAQs
A/C TYPES, ENERGY SOURCES
AGE of AIR CONDITIONERS & HEAT PUMPS
AIR CONDITIONER BTU CHART
AIR CONDITIONER COMPONENT PARTS
AIR FILTERS for HVAC SYSTEMS
AIR FLOW MEASUREMENT CFM
AIR HANDLER / BLOWER UNITS
BACKUP HEAT for HEAT PUMPS
BLOWER FAN CONTINUOUS OPERATION
BLOWER FAN OPERATION & TESTING
BOOKSTORE - Air Conditioning "How To" Books
CAPACITORS for HARD STARTING MOTORS
CIRCUIT BREAKER SIZE for A/C or HEAT PUMP
CLEANING & Legionella BACTERIA
COMPRESSOR & CONDENSING COIL, A/C
CONDENSATE HANDLING, A/C
CONTROLS & SWITCHES, A/C - HEAT PUMP
COOL OFF HEAT Thermostat Switch
COOLING CAPACITY, RATED
COOLING COIL or EVAPORATOR COIL
DATA TAGS on AIR CONDITIONERS
DEFINITION of HEATING & COOLING TERMS
DIAGNOSTIC GUIDES A/C / HEAT PUMP
DUCT SYSTEM & DUCT DEFECTS
DUST, HVAC CONTAMINATION STUDY
EDUCATION, HVAC SCHOOLS
ELECTRIC MOTOR DIAGNOSTIC GUIDE
EVAPORATOR COIL or COOLING COIL
EVAPORATIVE COOLING SYSTEMS
EXPANSION VALVES, REFRIGERANT
FAN, AIR HANDLER BLOWER UNIT
FAN AUTO ON THERMOSTAT SWITCH
FAN, COMPRESSOR/CONDENSER UNIT
FAN CONVECTOR HEATERS - HYDRONIC COILS
FAN NOISES, HVAC
GAS DETECTION INSTRUMENTS
GAS LAWS & CONSTANTS
GAUGE, REFRIGERATION PRESSURE TEST
HEAT LOSS (or GAIN) IN BUILDINGS
HEAT LOSS (or GAIN) INDICATORS
HEAT LOSS R U & K VALUE CALCULATION
HUMIDITY LEVEL TARGET
INSPECTION CHECKLIST - OUTDOOR UNIT
INSPECTION LIMITATIONS, A/C SYSTEMS
LOST COOLING CAPACITY
LOW VOLTAGE TRANSFORMER TEST
MANUALS & PARTS GUIDES - HVAC
MOTOR OVERLOAD RESET SWITCH
MOLD in AIR HANDLERS & DUCT WORK
NOISE AIR CONDITIONER / HEAT PUMP
ODORS in AIR HANDLERS & DUCT WORK
OPERATING COST, AIR CONDITIONER
OPERATING DEFECTS, AIR CONDITIONING
OPERATING TEMPERATURES, AIR CONDITIONER
PORTABLE ROOM AIR CONDITIONERS
PRESSURE READINGS, REFRIGERANT
REPAIR GUIDES A/C / HEAT PUMP
REPAIR & DIAGNOSTIC FAQs for A/C
REFRIGERANTS & PIPING
RETROFIT SIZING for A/C or HEAT PUMPS
SEER RATINGS & OTHER DEFINITIONS
SPLIT SYSTEM AIR CONDITIONERS & HEAT PUMPS
THERMOSTATS, HEATING / COOLING
THERMOSTATIC EXPANSION VALVES
WATER COOLED AIR CONDITIONERS
WINDOW / WALL AIR CONDITIONERS
WINDOW / WALL A/C SUPPORTS
The Combined Gas Law: this article describes and defines the Combined Gas Law with examples of using the Combined Gas Law to join the effects of pressure, temperature, and initial volume to explain what happens to air in a water storage tank, LP gas in a gas tank, oil & fumes in an oil storage tank, or air conditioning /heat pump refrigerant liquid & gas volumes inside of an air conditioning or heat pump system.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
The Combined Gas Law combines the effects of Boyle's Law and Charles Law thus considering gas pressure, gas volume, and gas temperature all together. The Combined Gas Law is written as
Example of using the Combined Gas Law to Explain What Happens Inside of a Water Pressure Tank
But inside of our water tank the total space available for air is fixed by the physical size of the tank itself. If we're talking about air inside a water tank, the volume taken up by the air can't get bigger than the tank itself. Charles and Boyle considered individually don't tell us what happens to the air pressure and volume inside of a water tank as temperatures change.
To figure this out we need to look at pressure and temperature simultaneously using the
One would conclude from this calculation that the effects of normal temperature changes in the environment of a water pressure tank will not have a significant effect on the in-tank pressure.
Note 1: A thoughtful reader pointed out that the measurement of temperature in these basic formulas must be counted from absolute zero, (-273 degrees Centigrade / -460 degrees Fahrenheit). Our references for Charle's Law confirm this requirement. Another simpler calculation of the effects of temperature change on water pressure tank internal pressures was suggested by Mr. Pryor. The difference between the starting and ending temperatures in degF. is divided by the starting temperature converted to Kelvins: a temperature change from 60 degF to 90 degF is (90-60)/(460+60) = 5.77% which is indeed only a small increase in pressure inside the water tank.
Continue reading at WATER PRESSURE TANK LAW or select a topic from the More Reading links shown below. or select a topic from the More Reading links shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References