InspectAPedia tolerates no conflicts of interest. We have no relationship with advertisers, products, or services discussed at this website.
Water bacteria tests or potability tests:
How to Interpret the Level of Bacteria Reported in a Well Water Potability Test. This article explains the significance & diagnostic implications of different levels of bacteria found in water during a well test.
If we determine that the source of well water contamination is persistent (for example we've recently disinfected the well and that did not cure the problem) then water treatment may be the best and fastest "cure" for this problem.
Understanding the level of bacterial contamination in a well can help us interpret the meaning of a well water bacteria or potability test. So what was the level of well water contamination detected? This question is explored here.
Interpreting and Acting On the Significance of the Level of Bacteria Found in a Water Test
As we introduced at Water Test Procedure Errors if the source of the contamination is not due to an ongoing situation or a persistent source of well contamination, for example bad ground water source, and assuming that the well has not already been recently disinfected or "shocked" then a disinfection of the water system will solve the problem.
Our photo (left) shows how easily a well might be contaminated by a simple error such as a loose well casing top or the placement of well piping on the ground during well repairs.
Comparing Well Bacteria Test Types & Understanding What the Results Mean
P/A or "Present/Absent" Water Bacteria Tests vs MFT / MPN Bacteria Test
A P/A test for bacteria in well water gives a "yes" or "no" or "OK" or "Not OK" test result. If the P/A result is "unacceptable" that means that there is bacteria in the drinking water above the acceptable level for where you live. Depending on where you live, a P/A test that says your water has an acceptable level of bacteria means that the bacteria level, if cultured on a suitable culture plate, will produce less than one colony per 100 ml of water for both coliform bacteria and for the total bacteria count.
But we have no idea if the actual bacteria level, expressed for example in colony forming units (CFUs) per some measure of quantity of water (say per milliliter or ml) is just barely unacceptable (say a count of 11 when a count of 10 would have been OK) or if the water is stunningly contaminated with bacteria (say a count of 200 cfus, or maybe "TNTC" which is jargon for "too numerous to count").
Why do we care? Because the implications of these numbers are different. For example shocking a well is unlikely to cure a very high bacteria count problem. And conversely, shocking a well and then testing as soon as permitted afterwards may give a "pass" result on water that is actually contaminated by a persistent source that will show up again a few days or weeks later.
We prefer the MFT/MPN test to the P/A test because getting an actual count or "number" of CFU/100ML is diagnostic (as we describe here) whereas a P/A test simply says OK or NOT OK with no indication of
the level of contamination present.
For example, consider two wells with a persistent source of bacterial contamination. If a well that fails at 15 CFU/100mL is "shocked"
the low starting count means it's easier to cover up the persistent problem source and more time may be needed for the bacteria to reappear.
This would affect your follow-up water testing strategy.
See FAILED WATER TESTS - WHEN to RE-TEST
By contrast, if a second well with a persistent source of bacterial contamination fails at >10,000 CFU/ml, first it is very unlikely that any "well shock" treatment will be effective, and
second, the level of contamination is so great that if a seller came up with a subsequent "pass" on a bacteria test without installing purification equipment or without telling me what problem was found
and fixed, we would be very skeptical about the reliability of the follow-up test.
So while a property seller/owner may prefer to "shock" a well and re-test, that procedure, used alone, might or might not be acceptable. What to do after a seller/owner has "done something" to the water supply and re-testing has been done is discussed at WATER RE TESTING
Watch out: a bacteria test on well water is also a great indicator that other contaminants can be present. Often the source of bacteria is surface water that leaks into the well. That means any other contaminants on the ground surface may also be in the well water. Discuss this with your lab - further testing may be in order.
When and How to Shock or Chlorinate a Well - Procedure for Shocking a Well to (temporarily or maybe longer) "Correct" Bacterial Contamination
At WELL CHLORINATION SHOCKING PROCEDURE we provide a description of a common procedure used to sterilize well water and water equipment. The purpose of shock disinfection of a well system is to destroy bacterial contamination present in the well system at
the time of disinfection and is not intended to kill bacteria that might be introduced at a later time.
Therefore it is vital that the well be constructed so that no new contamination may enter the well following completion of the
shock disinfection. In order to achieve a satisfactory disinfection of the system, the bacteria must be brought in contact with a chlorine solution of sufficient strength and remain in contact with that solution for a sufficient time to achieve a complete kill of all bacteria and other microorganisms.
If you are going to have a well disinfected after a failed bacteria or water potability test, follow the well shocking procedures and warnings that we provide at
WELL CHLORINATION SHOCKING PROCEDURE (live link is given below)
This series of articles explains many common water contamination tests for bacteria and other contaminants in water samples. We describe what to do about contaminated water, listing common corrective measures when water test results are
We include water testing and water correction measures warnings for home owners and especially for home buyers when certain conditions are encountered, with advice about what to do when these circumstances are encountered.
If a well potability test "fails" and the well is considered contaminated with bacteria, be sure you have also reviewed WATER TEST PROCEDURAL ERRORS (live link is below)
Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Ask a Question or Search InspectApedia
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Water Supply & Drain Piping, Wells, Pumps, Water Supply Equipment
Access Water Energy, PO Box 2061, Moorabbin, VIC 3189, Australia, Tel: 1300 797 758, email: firstname.lastname@example.org Moorabbin Office: Kingston Trade Centre, 100 Cochranes Rd, Moorabbin, VIC 3189
Australian supplier of: Greywater systems, Solar power to grid packages, Edwards solar systems, Vulcan compact solar systems, water & solar system pumps & controls, and a wide rage of above ground & under ground water storage tanks: concrete, steel, plastic, modular, and bladder storage tanks.
Smart Tank, Installation Instructions [ copy on file as /water/Smart_Tank_Flexcon.pdf ] - , Flexcon Industries, 300 Pond St., Randolph MA 02368, www.flexconind.com, Tel: 800-527-0030 - web search 07/24/2010, original source: http://www.flexconind.com/pdf/st_install.pdf
Typical Shallow Well One Line Jet Pump Installation [ copy on file as /water/Jet_Pump_Grove_Elect_Jet_Pumps.pdf ] - , Grove Electric, G&G Electric & Plumbing, 1900 NE 78th St., Suite 101, Vancouver WA 98665 www.grovelectric.com - web search -7/15/2010 original source: http://www.groverelectric.com/howto/38_Typical%20Jet%20Pump%20Installation.pdf
Typical Deep Well Two Line Jet Pump Installation [ copy on file as /water/Jet_Pump_Grove_Elect.pdf ] - , Grove Electric, G&G Electric & Plumbing, 1900 NE 78th St., Suite 101, Vancouver WA 98665 www.grovelectric.com - web search -7/15/2010 original source: http://www.groverelectric.com/howto/38_Typical%20Jet%20Pump%20Installation.pdf
Water Fact Sheet #3, Using Low-Yielding Wells [ copy on file as /water/Low_Yield_Wells_Penn_State.pdf ] - , Penn State College of Agricultural Sciences, Cooperative Extension, School of Forest Resources, web search 07/24/2010, original source: http://pubs.cas.psu.edu/FreePubs/pdfs/XH0002.pdf
Water pressure tanks - how to diagnose the need for air, how to add air, stop water pump short cycling to avoid damage - water storage water pressure tank safety.
WATER PUMP REPAIR GUIDE an specific case offers an example of diagnosis of loss of water pressure, loss of water, and analyzes the actual repair cost
Crystal Clear Supply provides portable ceramic water filter purifiers and portable reverse osmosis water treatment equipment - see http://www.crystalclearsupply.com/category_s/7.htm
Handbook of Disinfectants and Antiseptics, Joseph M. Ascenzi (Editor), CRC, 1995, ISBN-10: 0824795245 ISBN-13: 978-0824795245 "The evaluation of chemical germicides predates the golden age of microbiology..." -
This well-focused, up-to-date reference details the current medical uses of antiseptics and disinfectants -- particularly in the control of hospital-acquired infections -- presenting methods for evaluating products to obtain regulatory approval and examining chemical, physical, and microbiological properties as well as the toxicology of the most widely used commercial chemicals.
Potable Aqua® emergency drinking water germicidal tablets are produced by the Wisconsin Pharmacal Co., Jackson WI 53037. 800-558-6614 pharmacalway.com
Principles and Practice of Disinfection, Preservation and Sterilization (Hardcover)
by A. D. Russell (Editor), W. B. Hugo (Editor), G. A. J. Ayliffe (Editor), Blackwell Science, 2004. ISBN-10: 1405101997, ISBN-13: 978-1405101998.
"This superb book is the best of its kind available and one that will undoubtedly be useful, if not essential, to workers in a variety of industries. Thirty-one distinguished specialists deal comprehensively with the subject matter indicated by the title ... The book is produced with care, is very readable with useful selected references at the end of each chapter and an excellent index. It is an essential source book for everyone interested in this field. For pharmacy undergraduates, it will complement the excellent text on pharmaceutical microbiology by two of the present editors."
The Pharmaceutical Journal: "This is an excellent book. It deals comprehensively and authoritatively with its subject with contributions from 31 distinguished specialists. There is a great deal to interest all those involved in hospital infection ... This book is exceptionally well laid out. There are well chosen references for each chapter and an excellent index. It is highly recommended." The Journal of Hospital Infection.: "The editors and authors must be congratulated for this excellent treatise on nonantibiotic antimicrobial measures in hospitals and industry ... The publication is highly recommended to hospital and research personnel, especially to clinical microbiologists, infection-control and environmental-safety specialists, pharmacists, and dieticians."
New England Journal of Medicine: City Hospital, Birmingham, UK. Covers the many methods of the elimination or prevention of microbial growth. Provides an historical overview, descriptions of the types of antimicrobial agents, factors affecting efficacy, evaluation methods, and types of resistance. Features sterilization methods, and more. Previous edition: c1999. DNLM: Sterilization--methods.
U.S. Army Field Manual 21-10, Field Hygiene and Sanitation, 1988, web search 07/02/2010, original source: http://www.enlisted.info/field-manuals/fm-21-10-field-hygiene-and-sanitation.shtml The purpose of this manual is to assist individual soldiers, unit commanders, leaders and field sanitation teams in preventing disease and environmental injuries. The manual provides information on preventive medicine measures (PMM) to the individual soldier as well as essential information for the unit commander, unit leaders, and the unit field sanitation team on applying unit level PMM.
When Technology Fails, Matthew Stein, Chelsea Green Publisher, 2008,493 pages. ISBN-10: 1933392452 ISBN-13: 978-1933392455, "... how to find and sterilize water in the face of utility failure, as well as practical information for dealing with water-quality issues even when the public tap water is still flowing". Mr. Stein's website is www.whentechfails.com/
Carson, Dunlop & Associates Ltd., 120 Carlton Street Suite 407, Toronto ON M5A 4K2. Tel: (416) 964-9415 1-800-268-7070 Email: email@example.com. The firm provides professional home inspection services & home inspection education & publications. Alan Carson is a past president of ASHI, the American Society of Home Inspectors. Thanks to Alan Carson and Bob Dunlop, for permission for InspectAPedia to use text excerpts from The Home Reference Book & illustrations from The Illustrated Home. Carson Dunlop Associates' provides extensive home inspection education and report writing material.
The Illustrated Home illustrates construction details and building components, a reference for owners & inspectors. Special Offer: For a 5% discount on any number of copies of the Illustrated Home purchased as a single order Enter INSPECTAILL in the order payment page "Promo/Redemption" space.
TECHNICAL REFERENCE GUIDE to manufacturer's model and serial number information for heating and cooling equipment, useful for determining the age of heating boilers, furnaces, water heaters is provided by Carson Dunlop, Associates, Toronto - Carson Dunlop Weldon & Associates Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on any number of copies of the Technical Reference Guide purchased as a single order. Just enter INSPECTATRG in the order payment page "Promo/Redemption" space.
The Home Reference Book - the Encyclopedia of Homes, Carson Dunlop & Associates, Toronto, Ontario, 25th Ed., 2012, is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. Field inspection worksheets are included at the back of the volume.
Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on these courses: Enter INSPECTAHITP in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Horizon Software System manages business operations,scheduling, & inspection report writing using Carson Dunlop's knowledge base & color images. The Horizon system runs on always-available cloud-based software for office computers, laptops, tablets, iPad, Android, & other smartphones