Water Tank Repair SNAFUs
How to Know if the Right Repair Was Performed to Fix Lost Water Pressure
WATER PRESSURE REPAIR CORRECTLY? - CONTENTS: How to Make the Correct Water Tank or Pump Repair to Fix Lost Water Pressure. How to diagnose loss of water pressure or loss of water in a building. How to decide if water pump. replacement is needed. How to decide if water tank replacement is necessary
Did the well contractor make the "right" repair to the pump and pressure tank?
The illustration at left was provided courtesy of Carson Dunlop Associates, Inc., a Toronto, Ontario education, engineering & home inspection firm.
IF the tank and pump replacement have completely fixed the symptom you were having, then the contractor seems to have made the correct repair.
However given the sequence that you describe, we understand from your email that you'd suspect that there was nothing wrong with the pressure tank and that the problem,
all along, was the well pump.
If the contractor were skilled and diagnosed that a bad tank was hastening the demise of or even causing the demise of the well pump,
it would be poor practice to replace only the pump. Good plumbing practice (or good practice in any diagnostic and repair procedure) is
to identify the underlying cause of a problem so that the correct repair can be made.
While a more sophisticated analysis (perhaps using an ammeter to look at current on the
pump circuit, for example), might have detected at the outset that it was the pump that needed replacing, it is very common in all trades
for a repair person to first replace, among the possible causes of a problem, the items which are less costly and most accessible - in this case,
the water pressure tank. (Presuming your pump is a submersible down in the well.)
Save and examine plumbing parts that were removed for replacement
Look at the water pressure tank that was removed - it may be possible to open it and confirm for yourself that the bladder was shot.
A water pump that has been removed can be tested on a test bench; in some cases it is economical to bring a pump to an electric motor repair shop for analysis and repair.
Why don't people do this? There are not enough such shops around, and second, people don't want to wait a week with no water while their pump is being repaired.
How to check on the success and reliability - the "prognosis" of a an expensive well pump and water pressure tank repair job
First of all, there should be no leaks, anywhere, on the equipment which was repaired. If something was left wet, wipe it off and check for leaks. We don't pay my plumber if s/he leaves her/his work leaking. We call the boss.
Second, everything worked-on should be working normally to your eye and ear.
An expert plumber or well contractor can check the operation of your system by a combination of observation and electrical testing, such as measuring the amperage draw on the well pump circuit during pump operation. If these parameters are in normal range you should be ok insofar as the equipment is concerned.
Your repair person should have made these checks. Ask him or her.
If you have been in the home for several years you should have an idea whether or not you've had a history of the well running out of water. You can understand more about your well and how the well itself is performing by noting its technical statistics such as well depth, water level, pump depth, static head, and well flow rate - topics we discuss at this website.
If it is determined that you have a low-yield well, there are several solutions besides just drilling a new well - itself a shot in the dark.
Readers of this document should also see Water pressure tanks - how to diagnose the need for air, how to add air,
stop water pump short cycling to avoid damage - water storage water pressure tank safety.
Continue reading at WELL PUMP / TANK REPAIR ADEQUACY or select a topic from closely-related articles below, or see our complete INDEX to RELATED ARTICLES below.
Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Ask a Question or Search InspectApedia
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Mark Cramer Inspection Services Mark Cramer, Tampa Florida, Mr. Cramer is a past president of ASHI, the American Society of Home Inspectors and is a Florida home inspector and home inspection educator. Mr. Cramer serves on the ASHI Home Inspection Standards. Contact Mark Cramer at: 727-595-4211 mark@BestTampaInspector.com
John Cranor is an ASHI member and a home inspector (The House Whisperer) is located in Glen Allen, VA 23060. He is also a contributor to InspectApedia.com in several technical areas such as plumbing and appliances (dryer vents). Contact Mr. Cranor at 804-747-7747 or by Email: email@example.com
Access Water Energy, PO Box 2061, Moorabbin, VIC 3189, Australia, Tel: 1300 797 758, email: firstname.lastname@example.org Moorabbin Office: Kingston Trade Centre, 100 Cochranes Rd, Moorabbin, VIC 3189
Australian supplier of: Greywater systems, Solar power to grid packages, Edwards solar systems, Vulcan compact solar systems, water & solar system pumps & controls, and a wide rage of above ground & under ground water storage tanks: concrete, steel, plastic, modular, and bladder storage tanks.
Smart Tank, Installation Instructions [ copy on file as /water/Smart_Tank_Flexcon.pdf ] - , Flexcon Industries, 300 Pond St., Randolph MA 02368, www.flexconind.com, Tel: 800-527-0030 - web search 07/24/2010, original source: http://www.flexconind.com/pdf/st_install.pdf
Typical Shallow Well One Line Jet Pump Installation [ copy on file as /water/Jet_Pump_Grove_Elect_Jet_Pumps.pdf ] - , Grove Electric, G&G Electric & Plumbing, 1900 NE 78th St., Suite 101, Vancouver WA 98665 www.grovelectric.com - web search -7/15/2010 original source: http://www.groverelectric.com/howto/38_Typical%20Jet%20Pump%20Installation.pdf
Typical Deep Well Two Line Jet Pump Installation [ copy on file as /water/Jet_Pump_Grove_Elect.pdf ] - , Grove Electric, G&G Electric & Plumbing, 1900 NE 78th St., Suite 101, Vancouver WA 98665 www.grovelectric.com - web search -7/15/2010 original source: http://www.groverelectric.com/howto/38_Typical%20Jet%20Pump%20Installation.pdf
Water Fact Sheet #3, Using Low-Yielding Wells [ copy on file as /water/Low_Yield_Wells_Penn_State.pdf ] - , Penn State College of Agricultural Sciences, Cooperative Extension, School of Forest Resources, web search 07/24/2010, original source: http://pubs.cas.psu.edu/FreePubs/pdfs/XH0002.pdfmaterials, clogging, etc.
Books & Articles on Building & Environmental Inspection, Testing, Diagnosis, & Repair
Carson, Dunlop & Associates Ltd., 120 Carlton Street Suite 407, Toronto ON M5A 4K2. Tel: (416) 964-9415 1-800-268-7070 Email: email@example.com. The firm provides professional home inspection services & home inspection education & publications. Alan Carson is a past president of ASHI, the American Society of Home Inspectors. Thanks to Alan Carson and Bob Dunlop, for permission for InspectAPedia to use text excerpts from The Home Reference Book & illustrations from The Illustrated Home. Carson Dunlop Associates' provides extensive home inspection education and report writing material.
The Illustrated Home illustrates construction details and building components, a reference for owners & inspectors. Special Offer: For a 5% discount on any number of copies of the Illustrated Home purchased as a single order Enter INSPECTAILL in the order payment page "Promo/Redemption" space.
TECHNICAL REFERENCE GUIDE to manufacturer's model and serial number information for heating and cooling equipment, useful for determining the age of heating boilers, furnaces, water heaters is provided by Carson Dunlop, Associates, Toronto - Carson Dunlop Weldon & Associates Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on any number of copies of the Technical Reference Guide purchased as a single order. Just enter INSPECTATRG in the order payment page "Promo/Redemption" space.
The Home Reference Book - the Encyclopedia of Homes, Carson Dunlop & Associates, Toronto, Ontario, 25th Ed., 2012, is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. Field inspection worksheets are included at the back of the volume.
Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on these courses: Enter INSPECTAHITP in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Horizon Software System manages business operations,scheduling, & inspection report writing using Carson Dunlop's knowledge base & color images. The Horizon system runs on always-available cloud-based software for office computers, laptops, tablets, iPad, Android, & other smartphones