InspectAPedia^{®}  Question? Just ask us! 
InspectAPedia
 
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair 
InspectAPedia ^{®} Home WATER PUMPS, TANKS, TESTS, WELLS, REPAIRS FILTERS, WATER GREYWATER SYSTEMS WATER CONSERVATION MEASURES WATER CONTAMINANT LEVELS WATER FILTERS, HOME USE WATER HAMMER NOISE DIAGNOSE & CURE WATER HEATERS WATER ODORS, CAUSE CURE WATER PUMP REPAIR GUIDE WATER PRESSURE LOSS DIAGNOSIS & REPAIR WATER PUMP SHORT CYCLING WATER PURIFIERS WATER SOFTENERS & CONDITIONERS WATER TANK REPAIR PROCEDURES WATER TANK: USES, TROUBLESHOOTING WATER TESTS, CONTAMINANTS, TREATMENT WATER TREATMENT EQUIPMENT CHOICES WELLS CISTERNS & SPRINGS WELL CHLORINATION & DISINFECTION WELL FLOW RATE WELL WATER PRESSURE DIAGNOSIS WELL YIELD IMPROVEMENT WINTERIZE A BUILDING More Information 
Here we define the static head in a well and we explain how the well's static head can compensate for a well with a poor flow rate. Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved. Static Head: Well Water Starting Quantity  What is the Static Head of Water in the Well?This article series describes how we measure the amount of water available and the water delivery rate ability of various types of drinking water sources like wells, cisterns, dug wells, drilled wells, artesian wells and well and water pump equipment. The sketch at page top, courtesy of Carson Dunlop, shows how the static head of water in a well is located and estimated. Details are below. The static head inside a water well tells us how much water is available to the pump after the well has rested, water has risen to its maximum height inside the well, and the pump is about to turn on. This sketch, courtesy of Carson Dunlop offers a graphic explanation of well static head. The static head in a well is is not the total amount of water than can be pumped out of the well, it's just where we start. [Click to enlarge any image] After all, we will also have to include the rate at which water runs in to the well while we're pumping water out. Looking at our rough well sketch below and repeated at Components of a Drilled Well with a Submersible Water Pump and just considering the vertical arrows at the left side, we see that we have
How to calculate the gallons of water per foot of a well casingWe have about 1.5 gallons of water per foot of depth of a well when we're using a standard residential 6" well casing. The height of water column inside the well and available to the pump is less than the total well depth. With the exception of artesian wells, the well water column height does not extend from the well bottom to the top of the ground. Rather the top of the water in a conventional drilled or dug well at rest will be somewhere between the well bottom and well top, depending on the seasonal water table and other factors. In an artesian well natural water pressures in the aquifer would force well water out at the top of the well casing. For artesian wells the well is usually constructed with a seal inside the well casing to prevent water from rising above the point at which a water supply pipe exits the well casing. In an artesian well the static head water height will normally be from the well bottom to the point at which the casing seal has been installed. Static head location in a wellIn this sketch, distance (h) is the "static head" which is the total volume of water available to the pump. The static head in a drilled well extends from the water intake at the pump (since water can't jump up to the pump intake) upwards to the highest point that water reaches inside the well casing when the well has rested and reached its normal maximum height. Well water quantity calculation at pump startup
The Formula to Calculate the Static Head of Water in a WellTo find the amount of water in the static head of a well we find (h), the depth of the column of water in the well when the well is at rest, and then based on the well diameter we calculate the volume of (h) in cubic meters, feet, or inches. Last we convert that volume into common liquid measures such as liters or gallons. Using the symbols and definitions given just above, the formula to express the size of the static head of water in a well first in feet of height is simply: (h) = (d)  [(a) + (c)]  we subtract the well top air air space and pump to bottom clearance distances from total well depth The actual water quantity in (h) is calculated based on the volume of the well cylinder interior. In a standard 6" steel casing well, the water volume is about 1.5 gallons per foot of height of the static headBut remember that's just for the portion of the casing that actually contains water when the well is at rest  don't count the air. The formulas for volume of a cylinder and thus of water in a well casing are shown and an example are calculated just below. The formula to calculate the volume of water in a cylinder isVcyl = pi x r^{2} x h where pi = 3.1416, Watch out! be sure to write the radius and height in the same units of measure  here we're going to use inches. Vcyl_{inches} = 3.1416 x r^{2}_{inches} x h_{inches} So for a 12inch (one foot) height of 6" diameter steel well casing, Now we can calculate the static head water volume in cubic inches: Vcyl_{inches}= 3.1416 x 3^{2}_{inches} x 12_{inches} Vcyl_{inches} = 339 cubic inches (in this example, for a one foot high, 6" diameter cylinder of water in a well casing) How to convert cubic inches to cubic feetSince there are 1728 cubic inches in a cubic foot (12 x 12 x 12) we divide: Vc_{feet} = 339 / 1728 Vc_{feet} = 0.196 cubic feet How to Convert Cubic Feet to Gallonssince 1 ftÂ³ = 7.48051 gal(US Liq), Vc_{gallons} = 0.196 x 7.4 = 1.46 gallons That's why we use an easy to remember "rule of thumb" of 1.5 gallons per foot of static head of water found inside of a 6" drilled well casing. Formula for Static Head in Gallons of Water in a Typical 6" Steel Well CasingStatic Head (h)_{gallons} = (1.5 gallons per foot) x (h) measured in feet Here's a simple example to calculate the volume of water in the static head of a particular 100 foot deep well. Remember that for your well you'll need to plug in the actual measurements. (d) = total well depth = 100 ft. We want to calculate (h), the static head, in gallons of water  we just need to calculate the height of the column of water (in feet) inside the 6" diameter well casing and multiply it by 1.5 (gallons per foot) Static head water quantity (h)_{gallons} = (Total well depth (d)  Air (a)  Clearance at bottom (c) ) x 1.5 Or if you prefer (h)_{gallons} = (h)_{feet} x 1.5 For this example, using the (d), (a), and (c) measurements from above, we calculate (h)_{feet} and multiply it by 1.5 to find the static head in gallons  (h)_{gallons} (h)_{gallons} = [(100  45  5) feet of height of static head ] x [1.5 gallons per foot] (h)_{gallons} = (50) x 1.5 (h)_{gallons} = 75 gallons of water  that's how much water is in the static head of the example well.
Static Head Measurements for Other Well TypesNote that the static head description and calculations given in this article apply to round drilled wells and round dug wells. If your dug well is a different shape, say a rectangle, the principles are the same but you'll need to use the formula for volume of a rectangular shape V= length x width x height rather than a cylindrical shape given above and again just below. The static head of a driven point well is practically zero  just the volume of water inside the lower section of the driven well point (a pipe) below ground. For a driven point well, if you still want to know its static head, you might try the calculation of volume of water stored in water piping, just below. Calculating the volume of water or gallons of water stored in water pipingIn some circumstances such as deciding how much water to flush out of a pipe for certain water tests, it is useful to know the volume of water required to fill well piping or water piping. But let's be clear  the volume of water resting in well piping does not increase the volume of water available at a property. That is, the water stored in well piping does not increase (nor decrease) the well's static head as we defined it above. For long runs of well piping there may be a significant volume of water in the piping itself. Using 600' of plastic well piping as an example, we need simply to calculate the volume of a cylinder (the inside of a water pipe) into cubic inches per foot. The volume of a cylinder V = pi x r^{2} x h where pi = 3.1416, r = cylinder radius (1/2 the diameter) and h = the cylinder height or length of pipe in our case and G = the volume of water in gallons = 0.004329 gallons per cubic inch There is more water in long piping runs than one would have guessed. To translate cubic inches of water inside of a pipe, 1 cu. in. is about 0.004329 gallons
Does the Static Head Quantity in a Well Change?Absolutely. The static head, the amount of water in a well when the well is "at rest"  that is, no one has pumped water out of the well for some time and the well has filled back up as much as it's going to  changes:
Continue reading at WELL QUANTITY TOTAL or select a topic from the More Reading links shown below. Suggested citation for this web pageSTATIC HEAD, WELL DEFINITION at InspectApedia.com  online encyclopedia of building & environmental inspection, testing, diagnosis, repair, & problem prevention advice. More ReadingGreen link shows where you are in this article series.
...
Frequently Asked Questions (FAQs)No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia. Ask a Question or Search InspectApediaQuestions & answers or comments about water well flow rate, well recovery rate, and well water quantity  does your well run out of water?. Use the "Click to Show or Hide FAQs" link just above to see recentlyposted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly. Search the InspectApedia website HTML Comment Box is loading comments...
Technical Reviewers & ReferencesPublisher's Google+ Page by Daniel Friedman Click to Show or Hide Citations & References
Books & Articles on Building & Environmental Inspection, Testing, Diagnosis, & Repair
