Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
OIL STORAGE TANKS
ABANDONING OIL TANKS
OIL TANK INDOOR INSPECTION
AFUE DEFINITION, RATINGS
AGE of OIL TANK
ANODES & DIP TUBES on WATER HEATERS
BIOGAS PRODUCTION & USE
BURIED OIL TANK ADVICE
BURIED OIL TANKS, FINDING
COMBUSTION PRODUCTS & IAQ
DEFINITION of Heating & Cooling Terms
DIAGNOSE & FIX HEATING PROBLEMS-BOILER
DIAGNOSE & FIX HEATING PROBLEMS-FURNACE
DIRECT VENTS / SIDE WALL VENTS
DIRECTORY of OIL TANK EXPERTS
FILTERS, OIL on HEATING EQUIPMENT
FIRE SAFETY CONTROLS
FLAME COLOR, BLUE vs YELLOW COMBUSTION
FLOATING UP OIL STORAGE or SEPTIC TANKS
FLOODED HEATING EQUIPMENT REPAIR
FLOODED WATER HEATER REPAIR
FUEL OIL TYPES & CHARACTERISTICS
FUEL UNIT, HEATING OIL PUMPS
GALVANIC SCALE & METAL CORROSION
GAUGES ON HEATING EQUIPMENT
HEAT LOSS in BUILDINGS
HEAT TAPES, Heat, Insulation prevent Freeze-Up
HEATING COST FUEL & BTU Cost Table
HEATING COST SAVINGS METHODS
HEATING OIL CLOUD WAX GEL POINT
HEATING OIL EXPOSURE HAZARDS, LIMITS
HEATING OIL - OLD, USEABLE?
HEATING OIL PIPING TROUBLES
HEATING OIL SLUDGE
HEATING OIL TANKS
HEATING OIL TYPES & PROPERTIES
HEATING OIL USAGE RATE
HEATING SYSTEM NOISES
HOME BUYERS GUIDE TO OIL TANKS
HOT WATER HEATERS
NO HEAT - BOILER
NO HEAT - FURNACE
NOISE CONTROL for HEATING SYSTEMS
NOISES COMING FROM WATER HEATER
ODORS & SMELLS DIAGNOSIS & CURE
ODORS FROM HEATING SYSTEMS
OIL BURNER FUEL UNIT
OIL BURNER INSPECTION & REPAIR
OIL BURNER NOISE SMOKE ODORS
OIL BURNER NOZZLE & ELECTRODES
OIL BURNERS, RETENTION HEAD
OIL BURNER SOOT & PUFFBACKS
OIL FILTERS on HEATING EQUIPMENT
OIL FILTER MISSING
OIL FUEL TYPES & CHARACTERISTICS
OIL LINE CLOGGING FIX
OIL LINE QUICK STOP VALVES
OIL LINE SAFETY VALVES
OIL ODORS, LEAKY OIL TANK PIPING
OIL PUMP FUEL UNIT
OIL SPILL CLEANUP / PREVENTION
OIL TANK ABANDONING PROCEDURE
OIL TANK AGE
OIL TANK, BURIED, ADVICE
OIL TANK, BURIED, FINDING
OIL TANK FAILURE CAUSES
OIL TANK FAILURE RATES
OIL TANK FLOATING UP
OIL TANK GAUGES
OIL TANK INSPECTION, ABOVE GROUND
OIL TANK INSPECTION REPORTS
OIL TANK LEAKS & SMELLS
OIL TANK LEGAL ISSUES
OIL TANK LIFE
OIL TANK PIPING & PIPING DEFECTS
OIL TANK PRESSURE
OIL TANK REGULATIONS
OIL TANK REMOVAL COs
OIL TANK REMOVAL FINANCIAL AID
OIL TANK REPORT LANGUAGE
OIL TANK SAFETY
OIL TANK SLUDGE
OIL TANK STANDARDS
OIL TANK STANDARDS - Detailed List
OIL TANK SPILL CLEANUP / PREVENTION
OIL TANK SUPPORT
OIL TANK TESTING
Mesa 2-D TEST for OIL TANK LEAKS
PRESSURE TESTING OIL TANKS
SOIL TESTING FOR OIL TANK LEAKS
STANDARDS FOR TANK TESTING
ULTRASOUND TEST for AST OIL TANKS
WATER in OIL TANKS, TEST FOR
OIL TANK TESTING COs
OIL TANK WATER CONTAMINATION
OIL TANK WATER REMOVAL
SOOT on OIL FIRED HEATING EQUIPMENT
STAIN DIAGNOSIS on BUILDING INTERIORS
Here we explain the typical oil tank test pressure at the factory, the pressures that an oil tank is subjected to during oil tank fill-up, and the cause and prevention of excessive pressures that can cause leaks at oil tanks. We also answer the question of the amount of pressure to which an oil tank is subjected during an oil delivery, providing pressure limits, calculation of oil tank pressure changes, and listing both causes and steps to prevent over pressurizing a home heating oil tank. This series of articles discusses the causes of leaks at oil tank fill or vent piping, what the leak and other hazards are, and what to do about oil tank piping leaks.
Green links show where you are. © Copyright 2013 InspectAPedia.com, All Rights Reserved. Author Daniel Friedman.
Thanks to David Hollen, Applications & Technical Support, at pump manufacturer and distributor Yamada America for help with this data. We discuss pressure testing of oil tanks at OIL TANK TESTING. Readers should also see LEAKY OIL TANK FILL PIPES as well as LEAKY OIL TANK FILL PIPES and as OIL TANK LEAK CAUSES.
Residential above ground steel heating oil tanks are typically factory tested to 5 psi to 7 psi by the manufacturer, as our two photographs of oil tank labels show (above).
In fact, as the labels show on oil tanks we photographed early in 2009 (at left and at the top of this page), some steel oil tank manufacturers specifically advise against further pressure testing of their oil tanks.
If you need to know the condition of an above-ground home heating oil tank after it has been installed, ask your heating oil company to perform a metal thickness scan of the oil tank. The technician will use a sonic test instrument to measure the thickness of the steel at a number of locations on the lower portion of the tank.
The reason the technician tests the lower tank areas is that it is there that corrosion and thus thinning of the tank steel most often occurs. This inspection procedure will not, however, detect a faulty tank weld nor piping errors in the heating oil handling system.
If you are concerned about the chances that a buried oil tank has leaked, you'll need to locate the tank and have appropriate soil tests performed. We discuss pressure testing of oil tanks at OIL TANK TESTING. Also see OIL TANK LEAK ADVICE and TANK TESTING COs.
How Much Pressure is There on a Home Heating Oil Tank During an Oil Delivery?
But what is the pressure to which a heating oil tank is subjected during an oil delivery? The pressure experienced by the oil tank during fill from the home heating oil delivery truck is expected to be less than the oil tank manufacturer's tank test pressure (5-7 psi) if the oil tank is adequately vented.
A more detailed answer to the question of oil tank pressures is that it depends on several factors including the two main oil tank pressure factors listed below.
So What is the PSI Pressure the Oil Tank is Exposed To During Fill-Up?
Home heating oil is delivered under pressure at many buildings: the oil delivery truck's hose nozzle latches onto a special fitting at the top of the oil tank fill-valve. When this type of connection is made, the driver can fill the oil tank more rapidly than otherwise, and also can avoid spillage around the oil tank fill pipe.
Just how much pressure an oil tank is subjected to during filling varies as follows:
Normal oil tank fill tank pressure: less than 5 psi on a properly vented heating oil tank (the presumed tank pressurization must be less than the manufacturer's factory tested tank pressure)
Totally-blocked or missing oil tank venting: pressures up to 280 psi - this would be an unusual condition such as an oil tank vent that has not only become totally blocked, but the vent blockage is not "blown out" by pressures created during the tank filling operation.
Anticipated partially-blocked oil tank venting: as oil tank pressure increases due to compressed air in the tank pressing against an obstruction in the oil tank vent pipe (such as an oil slug blocking the vent line or a cap blockage by an insect nest or a painted-over vent cap screen) the pressure may be sufficient to "blow out" a transient blockage of that type.
The pressure required depends on the solidity and adhesion of the blocking oil tank vent line debris. Our opinion is that considering the range of possible oil tank pressures, between 0 psi and over 200 psi (with a totally obstructed vent), it should be quite easy for an oil tank pressure to exceed the manufacturer's factory-test pressure of 5 to 7 psi.
Calculation of Increase in Oil Tank Pressure During Fill-up
If an oil tank is NOT vented, depending on how empty the tank was (how much air it contained), when the tank is filled it could be subjected to quite high pressure. Using Boyle's Law (P1V1 = P2V2),
then the pressure would increase from atmospheric (14.7 psi) to 294 psi. If we subtract out our starting 14.7 psi that means we've pressurized the tank to about 280 psi.
Examples of Causes of Excessive Pressures in a Heating Oil Tank
Protection from Oil Tank Overfill - Methods
Because overfilling an oil tank might contribute to high oil tank pressures, we list some methods and products used to avoid over-filling a home heating oil tank:
Frequently Asked Questions (FAQs) About Residential Oil Tank Pressures & Pressure Problems or Leaks
What is the drawing symbol for a vent whistle? - Anon. 11/7/11
The schematic uses a simple representational shape at the oil tank vent pipe base connection to the oil tank and labels it as "vent alarm".
Anon, we took a look at the FDNY's training materials for the certification for supervising fuel oil piping & storage in buildings (above-left). Plumbing layout schematics for oil tank vent alarms or vent whistles may vary - we'll continue to look and post details here.
Four overfill protection devices used on USTs and in some cases ASTs include
Vent alarms are one of four common heating oil tank overfill protection device, but you should not rely on the alarm alone. Make sure that the fill and vent piping is properly sized, routed, and installed too.
Frequently Asked Questions (FAQs)
Questions & answers or comments about the pressures encountered in and on oil storage tanks under various conditions
Ask a Question or Enter Search Terms in the InspectApedia search box just below.
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.