Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
ELECTRICAL INSPECTION, DIAGNOSIS, REPAIR
AFCIs ARC FAULT CIRCUIT INTERRUPTERS
ALUMINUM WIRING HAZARDS & REPAIRS
AMPS VOLTS DETERMINATION
AMPERAGE MEASUREMENT METHODS
APPLIANCE EFFICIENCY RATINGS
BACKUP ELECTRICAL GENERATORS
BACK-WIRED ELECTRICAL DEVICES
BOOKSTORE - ELECTRICAL
CIRCUIT BREAKER SIZE for A/C or HEAT PUMP
DEFINITIONS of ELECTRICAL TERMS
DIRECTORY OF ELECTRICIANS
ELECTRIC METERS & METER BASES
ELECTRIC MOTOR DIAGNOSTIC GUIDE
ELECTRIC PANEL INSPECTION
ELECTRICAL GROUND SYSTEM INSPECTION
ELECTRICAL SERVICE DROP
ELECTRICAL SERVICE ENTRY WIRING
ELECTRICAL SPLICES, HOW TO MAKE
ELECTRICAL WIRING COLOR CODES
FIRE SAFETY Checklist, CPSC
GFCI PROTECTION,Testing GFCIs AFCIs
HEAT TAPE USAGE GUIDE
KNOB & TUBE WIRING
LIGHTING, EXTERIOR GUIDE
LIGHTING, INTERIOR GUIDE
LIGHTNING PROTECTION SYSTEMS
LOW VOLTAGE BUILDING WIRING
MAIN ELECTRICAL DISCONNECT
PHOTOVOLTAIC POWER SYSTEMS
RUST in ELECTRICAL PANELS
SAFETY for ELECTRICAL INSPECTORS
SE CABLE SIZES vs AMPS
VOLTS / AMPS MEASUREMENT EQUIP
VOLTAGE MEASUREMENT METHODS
Types of electrical receptacles: how to select the right type of electrical receptacle (outlet):
It's important to use 20-A rated receptacles if the electrical circuit is a 20-amp circuit. Don't install a grounded electrical receptacle plug on a circuit that has no electrical ground. Remember to install AFCI or GFCI devices where they are required.
This article explains how to match the receptacle type to the circuit type and use. This article series describes how to choose, locate, and wire an electrical receptacle in a home. Electrical receptacles (also called electrical outlets or "plugs" or "sockets") are simple devices that are easy to install, but there are details to get right if you want to be safe.
Green links show where you are. © Copyright 2015 InspectApedia.com, All Rights Reserved.
The proper type of electrical receptacle must be selected: some receptacles are rated only for 15-Amp circuits and must not be installed on a 20-Amp circuit.
It's generally ok to plug a 15-A appliance into a 20-A circuit since that appliance is not going to overload the circuit in normal use. But the opposite is not true. If you plug a 20-Amp appliance into a 15-Amp circuit you are risking overloading the circuit and tripping the circuit breaker, blowing the fuse, or worse, overheating the circuit and risking a fire.
Below our photographs illustrate a 15-Amp grounded electrical (below left) and a 20-Amp grounded electrical receptacle (below right). You'll notice that the heavier-duty 20-Amp electrical receptacle has that T-slot at it's wider connection opening - an easy way to identify a wall receptacle rated for 20-Amps - provided that the receptacle was properly matched to the wire size and the circuit breaker or fuse size.
Details about how to wire up an electrical receptacle are at CONNECTION DETAILS - where to connect black, white, red, green, ground wires .
Older two-wire electrical circuits, such as the two circuits depicted at the right of our sketch above may provide only the hot and neutral wires and no ground wire.
If no ground wire or ground path is provided, it is improper and unsafe to install a grounding (3-prong) electrical receptacle on that circuit.
Our photo (left) shows a conventional grounded three-prong electrical receptacle - the round hole is the ground connection - at the left end of the picture closest to my thumb.
At right in the photo is an ungrounded electrical receptacle. This is the right device to install if no ground is present on the electrical circuit. You don't want to "fool" a building occupant into thinking that a ground is present when there is not one, so you don't install a receptacle that has that third ground opening in its face. Some older two-wire circuits which are covered with a flexible metal jacket ("BX" or "armored cable" wire) may provide a ground path by means of the cable jacket itself.
We don't rely on it, and in event of certain short circuits it's unsafe: the exposed metal sheathing of the wire becomes live, risking a shock.
Details about how to wire up an un-grounded receptacle are at CONNECTION for 2-WIRE RECEPTACLE CIRCUITS - no ground
The illustration at left shows the typical wiring of an electrical outlet or "receptacle", courtesy of Carson Dunlop Associates.
Click any image to see an enlarged, detailed view of electrical wiring details for "plugs" or electrical receptacles.
Ground fault protection - GFCI's: The NEC also requires that only special ground fault circuit interrupter (GFCI) protected outlets can be installed in certain hazardous locations like kitchens, baths, garages, outdoors. A GFCI-protected electrical receptacle includes circuitry that turns the electric power off at the outlet quickly should a ground-fault (electricity flowing to earth, such as through your hand and down a water pipe) be detected. 
Arc fault protection - AFCI's: Beginning in 2002 the NEC also required arc fault protection for electrical outlets for bedrooms. 
AFCI's are similar to GFCI's discussed above, but they include an additional level of protection against fire by detecting small electrical arcing at a connection - a condition that can lead to overheating and fire.
As you can see from this US CPSC photo, you can add Arc fault protection to a home circuit by installing a special circuit breaker in the electrical panel.
By this means you can provide arc fault protection and thus improved fire safety for all electrical outlets on the circuit - for example in the building's bedrooms
In the FAQs (below) we discuss the importance of wiring the Line and Load terminals of GFCIs and AFCIs correctly.
and AFCIs ARC FAULT CIRCUIT INTERRUPTERS for details about these devices.
Readers of this article should also see SAFETY for ELECTRICAL INSPECTORS.
This website provides information about a variety of electrical hazards in buildings, with articles focused on the inspection, detection, and reporting of electrical hazards and on proper electrical repair methods for unsafe electrical conditions. Critique and content suggestions are invited. Credit is given to content editors and contributors.
Question: Is it safe to plug a 10-Amp A/C into an outlet that is back wired?
is it safe to plug in an ac unit that runs 10 amps , into outlet that is backed wired, i had read that you don't like this method, the outlet is on third floor and is on a 15 amp breaker - Johnny B 5/2/12
Reply: Comparing Three Types of Backwired Receptacles: 20-A Clamp Type & 15-ASpring Type & Clamp Type Backwiring Devices
Details about back-wired electrical devices (receptacles & switches) are at BACK-WIRED ELECTRICAL DEVICES.
Here we will illustrate three different types of electrical receptacles that can be wired from their back-side.
Our photo (left) illustrates a spec-grade 20-Amp, 125V rated electrical receptacle that looks as if it is "back-wired" - in fact while a wire can be wrapped around the terminal screws on this device, the screw is intended to be used to tighten a rectangular brass plate against a square metal nut (silver in color) that makes a very strong and positive connection over a good area of wire surface. This receptacle is marked on its back surface as CU Wire Only - copper only. [Click images to see enlarged details.]
Contractor-grade 15-A spring-type-connector back-wired electrical receptacles (below left) provide a single opening at each of the four terminals (two neutral wires, two hot wires) on the back of the receptacle (red arrow). The yellow arrow points to a release spring that will allow removal of the wire, but we prefer not to re-use this type of back-wired receptacle. Tightening the screw at the main wire terminal (blue arrow) has nothing to do with the spring-clamp that is securing the back-wired terminal wire.
Some newer heavy-duty 15-A back-wired electrical receptacles (above right) o not rely on a simple spring-edge to contact the electrical wire, as we illustrate in our second photo (above right). Rather, when the wire is inserted into a receiving hole on the back of the receptacle (either of the two red arrows). When the terminal screw is tightened (blue arrow) that actually snugs up a clamp that contacts a much larger surface area of the back-wired wire. That's a more secure connection mechanically. On this receptacle, instead on a single back terminal accepting a single wire, there are a pair of back terminal openings at each of the four terminal screws.
Thank you for responding, my town home was built in 1999, not sure if that is considered newer or older, lights do dim though when i use 10 amp vacuum . - Johnny B.
Backwiring electrical receptacles is a permitted installation and might be found in a 1999 home - but as we show above, there are two different approaches, the second of which is a better quality installation and is in our opinion more reliable.
Continue reading at BACK-WIRED ELECTRICAL DEVICES or select a topic from the More Reading links shown below.
Or see HOW TO ADD an ELECTRICAL OUTLET - home
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References