Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
ELECTRICAL INSPECTION, DIAGNOSIS, REPAIR
AFCIs ARC FAULT CIRCUIT INTERRUPTERS
ALUMINUM WIRING HAZARDS & REPAIRS
AMPS VOLTS DETERMINATION
AMPERAGE MEASUREMENT METHODS
APPLIANCE EFFICIENCY RATINGS
BACKUP ELECTRICAL GENERATORS
BACK-WIRED ELECTRICAL DEVICES
BOOKSTORE - ELECTRICAL
CADET & ENCORE HEATER RECALL
CHALLENGER ELECTRIC PANELS
CIRCUIT BREAKER SIZE for A/C or HEAT PUMP
Classified CIRCUIT BREAKER WARNING
CUTLER HAMMER PANEL FIRE
CORROSION in ELECTRICAL PANELS
DEFINITIONS of ELECTRICAL TERMS
DIRECTORY OF ELECTRICIANS
DMM Digital Multimeter HOW TO USE
ELECTRIC METERS & METER BASES
ELECTRIC MOTOR DIAGNOSTIC GUIDE
ELECTRIC MOTOR OVERLOAD RESET SWITCH
ELECTRIC PANEL AMPACITY
ELECTRIC PANEL INSPECTION
ELECTRIC PANEL MOISTURE
Electric Power Frequency Table
EMF RF FIELD & FREQUENCY DEFINITIONS
ELECTRICAL GROUND SYSTEM INSPECTION
ELECTRICAL SERVICE DROP
ELECTRICAL SERVICE ENTRY WIRING
EMF RF FIELD & FREQUENCY DEFINITIONS
FIRE SAFETY Checklist, CPSC
GFCI PROTECTION,Testing GFCIs AFCIs
HEATING COST FUEL & BTU COST TABLES
HEAT TAPE USAGE GUIDE
Hertz - Definitions of KHz MHz GHz THz
KNOB & TUBE WIRING
LIGHTING, EXTERIOR GUIDE
LIGHTING, INTERIOR GUIDE
LIGHTNING PROTECTION SYSTEMS
LOW VOLTAGE BUILDING WIRING
LOW VOLTAGE TRANSFORMER TEST
MAIN ELECTRICAL DISCONNECT
MAIN DISCONNECT AMPACITY
MOISTURE SOURCES in PANELS
MURRAY SIEMENS Recall
PHOTOVOLTAIC POWER SYSTEMS
PUSHMATIC - BULLDOG PANELS
REMOTE ELECTRIC POWER, PHOTOVOLTAIC
RUST in ELECTRICAL PANELS
SAFETY for ELECTRICAL INSPECTORS
SE CABLE SIZES vs AMPS
SIEMENS MURRAY Recall
THERMAL EXPANSION of HOT WATER
THERMAL EXPANSION of MATERIALS
UNDERGROUND SERVICE LATERALS
VOLTS / AMPS MEASUREMENT EQUIP
VOLTAGE MEASUREMENT METHODS
WIND TURBINES & LIGHTNING
ZINSCO SYLVANIA ELECTRICAL PANELS
Definitions of electrical ground, grounding, grounding system components & terms: this article defines the terms used to describe the building electrical grounding system & its components, including grounding & grounded conductors, grounding electrode, bonding, ufer and related terms.
Green links show where you are. © Copyright 2015 InspectApedia.com, All Rights Reserved.
[Click to enlarge any image]
Page top sketch and other electrical ground system sketches used in this article are used with permission and were provided courtesy of Carson Dunlop Associates, a Toronto home inspection education firm and inspection firm.
Ground: means the physical earth, the soil or ground. In some countries the term earth is used and is synonymous with ground. In the electrical code, ground means an electrically conducting connection, intentional or accidental, between an electrical circuit and the earth.
Grounded means that something has been electrically connected to the earth. Watch out: even among inspectors and electricians, people may use the term "ground" more loosely to refer to the equipment grounding conductor or other components. Also see Grounded Conductor (below).
What is a Grounding Electrode?
Grounding electrode or ground electrode: a metal conductor, usually a solid copper-alloy rod of specified length, driven into the ground in order to provide a point for electrical connection between the building grounding system and ground or earth.
In the electrical code, the grounding electrode conductor is the conductor (a wire) used to connect the grounding rod(s) to the equipment grounding conductor (the ground bus and ground wires in the electrical panel) OR to the grounded conductor (the neutral bus and neutral wires) OR to connect both of these to the grounding electrode (which is usually the case in residential electrical systems).
What's the difference between "Grounded electrical conductor" and "Grounding Conductor"?
Grounded Conductor (the neutral wire): by convention the grounded conductor or neutral wire is white or gray. In an electrical circuit the grounded conductor (white or neutral wire) normally carries electrical current between the un-grounded (hot) electrical wire and (back through the main electrical panel and grounding system) earth.
In the electrical code, a grounded conductor is one which has been intentionally grounded - connected to the earth.
The amount of current carried by the neutral wire is called the un-balanced load and depends on the characteristics of the electrical device being operated by the circuit. The neutral conductor is grounded in the main electrical panel. Be careful, inspectors and electricians, speaking loosely, may simply call this the "neutral wire".
Equipment Grounding Conductor (the ground wire): By convention the equipment grounding conductor (ground wire) is bare copper or carries green insulation. the individual wire in a (grounded) electrical circuit that is connected through the ground bus in the electrical panels and ultimately in the main electrical panel is connected to ground or earth.
In the U.S. National Electrical Code and most other model electrical codes, a grounding conductor is a conductor (metal wire, metal bar, etc) which is used to connect electrical equipment (like an electrical panel enclosure) or the grounded circuit (the neutral wires) of a wiring system to a grounding electrode (and thus to earth).
The ground wire in an electrical circuit does not normally carry any electrical current, but it remains available as an emergency path to allow current to flow to earth should an electrical fault such as a short circuit occur (a connection between a hot wire and some metal (conductive) material that could cause an electrical shock to someone), thus assuring that a fuse or circuit breaker in the main panel can sense the current flow and switch off the circuit.
Watch out: In an older two-wire armored cable (BX) electrical circuit, the metallic cable of the circuit may be serving as the only grounding conductor. This is not a safe installation: should the metallic cable sheath carry live current (say due to a fault or faulty electrial wiring) someone touching the BX cable can be shocked - an event witnessed by the author.
It helps to keep these terms straight if we remember that we use the ing form of the word grounding to mean that this conductor causes an electrical connection between earth and whatever the grounding conductor is connected to.
Electrical Bonding Definitions (consistent with NEC article 100)
Bonding or Bonded: means that metallic parts are permanently joined so as to assure that they form a reliably continuous electrical path and that the parts are capable of conducting any electrical current that may be imposed on them.
A bonding jumper is a reliable electrical conductor used to connect metal parts together and a main bonding jumper is the connection between the grounded circuit conductor and the equipment grounding conductor at the electrical service (panel).
Ground bond: refers to a physical electrical connection between any metal component (like metal water pipes, metal gas piping, a metal electrical panel enclosure, or a neutral or ground bus in the main electrical panel) and the building electrical ground system.
In the main electrical panel the neutral wires are physically bonded to the ground wires (by a larger diameter wire or by a metal bar inside the panel) and the ground wire bus (a metal bar) is further connected to a grounding conductor that connects those components to the building ground system: one or more grounding electrodes and possibly a connection to an incoming metal water pipe that is buried outside. An electrician would say that the building's ground and neutral wires are bonded to earth
Bonding electrical components together makes certain that all of the joined items are at the same electrical potential (that is, that current will not flow from one to the other). Examples of electrical bonds in buildings include:
What is a Ufer ground?
A UFER is an electrical ground connection to earth provided by a concrete encased grounding electrode. This approach to electrical grounding improves the ground connection to earth in areas where soils are so dry that otherwise grounding may be ineffective. UFER grounding has been included in the U.S. National Electrical Code (NEC) since 1968.
UFER electrical grounding was developed in 1942 by Herbert G. Ufer who worked as a consultant to the U.S. Army to improve electrical grounding for bomb storage vaults in Arizona where dry soils limited the efficacy of electrical grounding using a driven copper electrode hammered into the soil.
Below we include additional research citations on the efficacy of Ufer grounding for electrical systems & buildings where you'll see H.G. Ufer's seminal paper on Ufer ground in in bold font. Wikipedia's entry for Ufer ground points out that Ufer observed that concrete was more conductive than most types of soil, permitting grounding by concrete-encased electrodes.
In modern construction a UFER connection may refer to a continuously bonded steel re-bar (or other grounding electrode) used in construction of a concrete footing or slab that is in turn bonded to the electrical ground system for the building.
We presume that the increased area and conductivity of the larger area of concrete in contact with the soil combined with conductivity of the concrete itself is what gives an improved local electrical ground-to-earth connection for the building. - "Ufer ground", Wikipedia, retrieved 4/27/14, original source: http://en.wikipedia.org/wiki/Ufer_ground
Useful References & Citations on Ufer Grounding
Continue reading at ELECTRICAL GROUND INSPECTION SAFETY or select a topic from the More Reading links shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References