Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
ELECTRICAL INSPECTION, DIAGNOSIS, REPAIR
AFCIs ARC FAULT CIRCUIT INTERRUPTERS
ALUMINUM WIRING HAZARDS & REPAIRS
AMPS VOLTS DETERMINATION
AMPERAGE MEASUREMENT METHODS
APPLIANCE EFFICIENCY RATINGS
BOOKSTORE - ELECTRICAL
Cadet & Encore Heater Recall
CIRCUIT BREAKER SIZE for A/C or HEAT PUMP
Classified CIRCUIT BREAKER WARNING
CUTLER HAMMER PANEL FIRE
CORROSION in ELECTRICAL PANELS
DEFINITIONS of ELECTRICAL TERMS
DIRECTORY OF ELECTRICIANS
DMM Digital Multimeter HOW TO USE
ELECTRIC METERS & METER BASES
ELECTRIC MOTOR DIAGNOSTIC GUIDE
ELECTRIC MOTOR OVERLOAD RESET SWITCH
ELECTRIC PANEL AMPACITY
ELECTRIC PANEL INSPECTION
ELECTRIC PANEL MOISTURE
Electric Power Frequency Table
EMF RF FIELD & FREQUENCY DEFINITIONS
ELECTRICAL GROUND SYSTEM INSPECTION
ELECTRICAL SERVICE DROP
ELECTRICAL SERVICE ENTRY WIRING
EMF RF FIELD & FREQUENCY DEFINITIONS
FIRE SAFETY Checklist, CPSC
GFCI PROTECTION,Testing GFCIs AFCIs
HEATING COST FUEL & BTU Cost Table
HEAT TAPE USAGE GUIDE
Hertz - Definitions of KHz MHz GHz THz
KNOB & TUBE WIRING
LIGHTING, EXTERIOR GUIDE
LIGHTING, INTERIOR GUIDE
LIGHTNING PROTECTION SYSTEMS
LOW VOLTAGE BUILDING WIRING
LOW VOLTAGE TRANSFORMER TEST
MAIN ELECTRICAL DISCONNECT
MAIN DISCONNECT AMPACITY
MOISTURE SOURCES in PANELS
MURRAY SIEMENS Recall
PHOTOVOLTAIC POWER SYSTEMS
PUSHMATIC - BULLDOG PANELS
REMOTE ELECTRIC POWER, PHOTOVOLTAIC
RUST in ELECTRICAL PANELS
SAFETY for ELECTRICAL INSPECTORS
SE CABLE SIZES vs AMPS
SIEMENS MURRAY Recall
THERMAL EXPANSION of HOT WATER
THERMAL EXPANSION of MATERIALS
UNDERGROUND SERVICE LATERALS
VOLTS / AMPS MEASUREMENT EQUIP
VOLTAGE MEASUREMENT METHODS
WIND TURBINES & LIGHTNING
ZINSCO SYLVANIA ELECTRICAL PANELS
Electrical ground lost: what happens. This document describes the loss of both neutral (utility company) and local building ground connections at a building leading to loss of electrical power and dangerous risk of electrocution.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Case History of an Lost Electric Company Neutral AND a Local Electrical Ground Failure: a Double Fault Leads to Loss of Electrical Power in San Miguel de Allende, Mexico
Readers of this article should also be sure to review SAFETY HAZARDS & SAFE ELECTRICAL INSPECTION PROCEDURES for Inspectors examining Residential Electrical Systems and Local Electrical Grounding for safety procedures during inspection of the grounding system.
“Grounding”, article 250 in the NEC, is probably one of the most difficult of the often used articles. In 2005 article 250 became “Grounding and bonding”. In the 2008 NEC there has been a major revision in language, and phrases like “shall be grounded” have changed to “shall be connected to an equipment grounding conductor.” The example discussed in this article helps explain what happens when the neutral connection to the utility company, or the ground connection at a building or both are lost.
Never assume anything during a building inspection. For example, never assume that because you see that ground wires are present, that the building and its electrical system are safely grounded.
First of all, there are usually at least two possible return-current connections at a building:
One is the incoming neutral wire from the electrical service - grounded somewhere by the utility company - don't' assume that it's connected.
The second is the local electrical ground (connection to earth, typically through a ground rod or grounding electrode (sometimes water piping) at a building. This is the building's own local connection to earth through one or more grounding electrodes, or in older buildings, possibly by a connection between the electrical panel's ground bus and a metal water pipe entering the building from outdoors. Also see Why Grounding is Needed.
Dim lights and no refrigerator after a storm: In a home in San Miguel de Allende, Guanajuato, Mexico after a severe rain storm the building's lights were severely dimmed. If the occupants turned on any high-amperage device such as a toaster or refrigerator, the lights began to flicker. The home's refrigerator motor would not even start. We assumed (that was the first mistake) that the building's connection to the electrical utility company's overhead service wire had been lost because we saw that wet tree branches had leaned over, pulling on the service drop wire.
Measuring electrical voltage showed that 120V was available at the wiring lugs in the electric meter base (photo below), but when any electrical load was placed on the building electrical system voltage plummeted.
After more than a week of haggling with CFE, the electric utility company, and after watching their service tech climb poles, cut and re-make electrical connections to the building's service entry cables, nothing was changed,and the building still did not have functional electrical power.
Here is a common dual electric meter setup at a single family home in Mexico. The blue wire entering at upper right is the 120V "hot" wire bringing in 120Volts to this pair of electric meter bases which are wired in parallel. We pulled the electric meters to give an easy view of the wiring itself. This setup simply splits the electric bill into two parts.
Each electric meter feeds one side of the electrical panel indoors. Circuits in the building are thus fed from one or the other electric meter. Why people do this bears explaining: all that this dual meter setup is doing is splitting the electric bill into two bills.
People do this when they want to create an apartment whose tenant pays their own utilities, or in some cases because the size of a utility bill can affect the electricity rates. In this home there is no apartment.
The second meter was installed by prior owners who thought they were obtaining doubling the electrical power at their home. They were completely mistaken.
Above the incoming blue "hot" wire (the service drop wire) you can see the aluminum ground wire coming from the utility pole and being fed into the meter enclosure from the overhead electrical service drop. Everyone was focused on testing the "hot" blue wire back to the pole and we forgot to also test the ground wire back to the same pole.
Before the replacement service entry cable could be installed, we asked for some additional diagnostic help from a local electrician familiar with electrical wiring problems in Mexico.
Figuring out what was wrong - a bad service drop ground wire: The electrician too thought at first that the problem was a shorting service drop cable. But we also discussed the alternative possibility that the problem could be not the loss of the building's incoming or "hot" service entry wire, but rather the loss of the building's ground connections.
No ground-connection means no current flows in a building's electrical circuit. A very weak connection between a building's electrical system and earth could result in power loss when the electrical system was under load - not enough electrons could flow to earth.
The loss of the building ground connection seemed unlikely. After all, we could see a grounding electrode driven into the soil (for some unknown depth) and surely, all that rain had wet the soil, improving the ground connection. The left-hand photo below shows the original building local ground wire (red) connected to the original building grounding electrode. (The green wire was added as we explain below).
A simple electrical system grounding experiment told the story of a double fault in both the utility company's ground and the building's local ground connection: the electrician made a temporary grounding connection between our electrical panel and an incoming metal municipal water supply pipe.
Suddenly all of our lights went on and everything worked.
Our photo above of the electric meter enclosure shows the temporary green ground wire that the electrician connected between the meter-ground (which also connected to our electrical panel ground and neutral buses).
Our photo at left shows the ground wire wrapped around the building's incoming water pipe. (A clamp would be added later.)
In the photos we show here we had not yet found and installed a proper grounding clamp to secure the ground wire to the water pipe.
A ground wire that is just wrapped around a water pipe is certainly not a reliable connection, but it was sufficient to demonstrate that providing a good local ground at the building turned the lights back on.
We determined that the building had experienced a "double fault" in its grounding system: the local building ground had always been inadequate. But when the storm damaged and pulled loose our overhead connection to the utility company's ground system, we had lost our second connection to earth.
While waiting for the electrical utility company, CFE (Comision Federal de Electricidad) in San Miguel to get around to fixing their own ground ("cable de tierra") back at their pole, the electrician installed a new and longer grounding electrode at the building's electrical service.
Loss of all building ground connections was extremely dangerous: Assuring that the building had at least one working ground was very smart. The near total loss of electrical grounding at this building could certainly have killed someone.
Keeping the building well grounded: At this building the electrician kept the additional bond between the local ground system and the local municipal water pipe as well as installing a new grounding electrode.
Additional comments from Bud, a master electrician in Minnesota:
Other risks remain when the utility company ground is not effective: After this temporary fix we were still very nervous about the missing utility company ground. Why? Because we don't know how many other homes may be affected by the failure in the utility company's ground system. The fact that only our building lost power does not mean that we were the only one connected to this "bad ground" back at the pole - it could simply be the case that the other houses on the street each had their own good local ground connection.
But should someone else's ground connection fail, and should the utility company's ground connection remain un-repaired, then our neighbors could be depending on our local ground wire (which is pretty small) for their own safety - a dangerous dependence.
The utility company ground was finally restored when CFE, the electric utility company, routed a new neutral wire between the building's electrical meters and their overhead neutral wire.
Our case study of a shock and fire hazard in a garage shows what happens when a local ground is the only connection to earth at a property and when that condition combines with other wiring defects.
Continue reading at LOST NEUTRAL Shocks Homeowner or select a topic from the More Reading links shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs) about the effects of lost elecrical ground at a building: detection, tests, risks, repairs
Questions & answers or comments about what happens when the electrical ground connections are lost at a building.
Check the FAQs just above, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.