Electric motor horsepower: this article explains how to calculate the horsepower of an electric motor if we know its wattage or current draw in amps. The article gives a simple formulat to convert electrical amps to horsepower and explains what data are actually needed to make an accurate horsepower calculation or rating.
We explain the relationship between rated load amps (RLA), and full load amps (FLA) and lock rotor amps (LRA) ratings on electric motors. These electric motor horsepower formulas, definitions, and ratings are suitable for determining the horsepower of an air conditioner compressor motor, a fan motor, a well pump motor and similar equipment.
Green links show where you are. © Copyright 2017 InspectApedia.com, All Rights Reserved.
(Aug 2, 2014) Eng.M.Mossad2010@gmail.com said:
From the part of " FROM EQUIPMENT RLA # - Air Conditioning Equipment Capacity from Equipment RLA Numbers " in the article above can we find a relation between the equipment's RLA and the HP "horse power " for the Compressor motor?
This question was originally posted at COOLING CAPACITY, RATED
Mossad: for a specific air conditioner or heat pump motor I'd obtain the horsepower rating first by looking at the BTUh rating on the data tag or encoded in the model number. For example, 18,000 BTUh is equivalent to 2 HP (horsepower) or 24,000 = 2.5 HP. You can find the basic rating data for an air conditioner compressor motor (or for other HVACR motors) by noting information on the data plates we describe in detail at DATA TAGS on AIR CONDITIONERS
Let's also note for other readers that RLA = running load amps - the current drawn normally during the operation of an electric motor.
RLA will always be a smaller number than LRA which is lock rotor amps - the start-up current draw. FLA = full load amps, a fixed number that will also always be higher than RLA. Refrigeration engineers generally state that if we know LRA we can estimate RLA as follows:
RLA = LRA / 5.56
(for most electric motors LRA is about 5 times greater than its RLA/FLA and some may be 7 times greater.
An accurate answer to the question of translating RLA into horsepower requires more data: the voltage leel and the number of phases of electrical current. And comparing HVAC compressor motors by amperage ratings alone may be misleading. Compressors need to be compared for the same rated conditions and same area of application, as motor designs and uses vary.
But for typical residential air conditioner systems and heat pump systems we can assume we're talking about 240V and 2-phases of power.
Since the maximum rotating power or force exerted by an electrical motor is that needed to get the motor spinning we should look at the motor's LRA or FLA rating. The RLA or running load current draw in amps will always be a smaller number than the motor's maximum. We'll give the motor horsepower as its maximum in our examples below but you can choose any amperage rating to calculate an equivalent horsepower number.
Details about locked rotor amp ratings and LRA FLA data tables are given at TIGHT or SEIZED AC COMPRESSORS
1 HP (horsepower) = 745.7 Watts (round to 746 W)
To express watts in amps or current is not reasonable since these are two different measurement scales (Watts in power and amps in coulombs per second). But if we know any two of the three basic electrical measures (amps, watts, and volts) we can calculate the third value. We can write the famous (and simplified) equation in any of the three ways using simple algebra:
AMPS = Watts / Volts OR Watts = Amps x Volts OR Volts = Watts / Amps
E.G. 120 Watts / 120 Volts = 1 Amp of current.
For complete details about these basic electrical formulae see DEFINITIONS of ELECTRICAL TERMS
We can easily express Amps in a formula to obtain horsepower as follows:
AMPS = ( Horsepower x 746 ) / Voltage
Example: For a 220V electric motor with a 40-Amp LRA or FLA rating
40A = (Horsepower x 746) / V
40 = (HP x 746) / 220
(40 x 220 ) = HP x 746
(40 x 220) / 746 = Horsepower
11.8 = Horsepower
So this is a 12 horsepower motor based on its LRA or FLA rating.
Here is a different example:
At 220V a 240kBTUh A/C unit will draw around 8 amps when running. Using the same calculation as above but finding the horsepower exerted when the air conditioner motor is running at normal load (that is not at start-up and not with abnormal head pressure),
8 A = (HP x 746) / 220 which calculates out as 2.4 HP
So the horesepower being delivered by our air conditioner when running at normal load is around 2.4 HP
On 2017-03-13 15:48:10.136370 by (mod)Excellent points, Steve, thank you. We'll keep your comments in the article.
On 2017-03-13 15:18:23.510985 by Steve - Horsepower is OUTPUT POWER. The electrical requirements is INPUT POWER.
Horsepower is OUTPUT POWER. The electrical requirements is INPUT POWER. To make those two things comparable you need to consider motor efficiency in the equation.
If you assume the efficiency is about 80% (pretty safe), then the Input power would be 1 / 0.8 or 1.25x the output horsepower, in order to deliver that much power. Also if the motor is three phase you can reduce the amps by 1.73 when converting from watts to FLA. There is more but this is the basics.
On 2016-02-25 16:54:04.174511 by Anonymous - RLA = Rated Load Amps, not Running Load Amps.
RLA = Rated Load Amps, not Running Load Amp. If motor is driving the max load it is allowed, it will run at RLA. Most compressor motors will run less than RLA because they are not typically fully loaded.
Continue reading at ELECTRIC MOTOR DIAGNOSTIC GUIDE or select a topic from closely-related articles below, or see our complete INDEX to RELATED ARTICLES below.
Or see these other articles discussing electric motor horsepower
Or see ELECTRIC MOTOR DIAGNOSTIC FAQs-2 - more questions & answers about fixing electric motors
Or see ELECTRIC MOTOR RUN DIRECTION
Or use the SEARCH BOX found below to Ask a Question or Search InspectApedia
Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website