Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
ELECTRICAL INSPECTION, DIAGNOSIS, REPAIR
AFCIs ARC FAULT CIRCUIT INTERRUPTERS
ALUMINUM WIRING HAZARDS & REPAIRS
AMPS VOLTS DETERMINATION
AMPERAGE MEASUREMENT METHODS
APPLIANCE EFFICIENCY RATINGS
BACKUP ELECTRICAL GENERATORS
BACK-WIRED ELECTRICAL DEVICES
BOOKSTORE - ELECTRICAL
CADET & ENCORE HEATER RECALL
CHALLENGER ELECTRIC PANELS
CIRCUIT BREAKER SIZE for A/C or HEAT PUMP
Classified CIRCUIT BREAKER WARNING
CUTLER HAMMER PANEL FIRE
CORROSION in ELECTRICAL PANELS
DEFINITIONS of ELECTRICAL TERMS
DIRECTORY OF ELECTRICIANS
DMM Digital Multimeter HOW TO USE
ELECTRIC METERS & METER BASES
ELECTRIC MOTOR DIAGNOSTIC GUIDE
ELECTRIC MOTOR OVERLOAD RESET SWITCH
ELECTRIC PANEL AMPACITY
ELECTRIC PANEL INSPECTION
ELECTRIC PANEL MOISTURE
Electric Power Frequency Table
EMF RF FIELD & FREQUENCY DEFINITIONS
ELECTRICAL GROUND SYSTEM INSPECTION
ELECTRICAL SERVICE DROP
ELECTRICAL SERVICE ENTRY WIRING
EMF RF FIELD & FREQUENCY DEFINITIONS
FIRE SAFETY Checklist, CPSC
GFCI PROTECTION,Testing GFCIs AFCIs
HEATING COST FUEL & BTU COST TABLES
HEAT TAPE USAGE GUIDE
Hertz - Definitions of KHz MHz GHz THz
KNOB & TUBE WIRING
LIGHTING, EXTERIOR GUIDE
LIGHTING, INTERIOR GUIDE
LIGHTNING PROTECTION SYSTEMS
LOW VOLTAGE BUILDING WIRING
LOW VOLTAGE TRANSFORMER TEST
MAIN ELECTRICAL DISCONNECT
MAIN DISCONNECT AMPACITY
MOISTURE SOURCES in PANELS
MURRAY SIEMENS Recall
PHOTOVOLTAIC POWER SYSTEMS
PUSHMATIC - BULLDOG PANELS
REMOTE ELECTRIC POWER, PHOTOVOLTAIC
RUST in ELECTRICAL PANELS
SAFETY for ELECTRICAL INSPECTORS
SE CABLE SIZES vs AMPS
SIEMENS MURRAY Recall
THERMAL EXPANSION of HOT WATER
THERMAL EXPANSION of MATERIALS
UNDERGROUND SERVICE LATERALS
VOLTS / AMPS MEASUREMENT EQUIP
VOLTAGE MEASUREMENT METHODS
WIND TURBINES & LIGHTNING
ZINSCO SYLVANIA ELECTRICAL PANELS
Electric meter inspection: this article discusses the visual inspection of electrical meters & meter bases & explains how to estimate the electrical service size, (or "electrical power" or "service amps") at a building by visual examination of the service entry cables, electric meter and meter base, electrical service panel, main switch, & other details. We also discuss electrical arc burns at the meter base.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
ELECTRIC METERS & METER BASES - Inspecting Electric Meters & Meter Bases - Another Consideration When Determining Service Ampacity
Visual inspection of the electric meter and use of digital multimeters(DMMs), Volt-ohm meters (VOMs), neon testers, and electrical inspection safety are discussed. Photographs and sketches illustrate electrical panels, meter bases, and electric meters. One of the most frequently asked questions at home inspection conferences and education seminars is "How do I determine the service amperage?"
This question is no surprise, as even a casual inspection of the components of a building electrical service can turn up inconsistencies among service entry cable size, electrical meter rating, electrical panel rating and the main power disonnect ampacity.
Watch out: building inspectors learn quickly enough that just reading off the amperage number on the main power disconnect or5 "main breaker" is not an assurance that we have correctly named the building electrical service ampacity.
And discussion among various experts and one of the original reviewers (Douglas Hansen) quite aptly raised questions about the accuracy of estimating service size in volts or amps by inspecting modern electrical meters. While some of the cases illustrated here remain accurate, these methods may be unreliable when examining modern electrical meters and meter bases.
It's not as difficult as one may think to get a reasonable handle on the electrical service capacity at a building without sophisticated analysis. But there are some pitfalls, and the process itself is dangerous.
The photos and text below will assist in identifying a variety of electrical meters and service panels of various ages and capacities.
An article in the Winter, in 1992 an ASHI Technical Journal produce & edited b DF discussed the procedure and considerations for inspectors to determine the service ampacity of an electrical system. That article indicated that the safe and proper service amperage available at a property is set by the smallest of the service entrance conductor, the main disconnect fuse or circuit breaker, and the rated capacity of the panel itself. These are also issues of concern for the electrical contractor installing the service. ASHI Technical Journal, Vol. 3. No. 1, Spring, 1993, "Determining Service Ampacity - Another Consideration," Robert L. Klewitz, P.E. Here information has been updated through March 2014. .
The concerns of inspectors must be broad in scope. Inspectors must look at the entire system, some of which may be dictated by the electric utility, and may not be a concern of the wiring installer or National Electrical Code. [National Electrical Code, article 90-2(b)(5)]
Because of this, there is one additional item that must be considered when determining service ampacity. This item is the rating of the electrical meter base and the meter itself. Many times there will be no sure way of determining this rating on a visual inspection, since the rating sticker would typically be inside the meter base and would require pulling the meter off to see it. However, there are some guidelines and "rules of thumb" that can be used.
Warning: Looking at meter bases and meters to guess at ampacity is questioned by some experts as too unreliable.Systems that have been installed for the last 20 years or so will typically have a rectangular meter base of various sizes as shown in the rectangular-base meter at left. These are usually compatible with 200 Amp services, although undoubtedly there are exceptions to this.
NOTE: Did you notice the measuring tape marking the 3" gap between the siding "J" channel and the top of the meter? This electric meter had been pulled downwards by backfill settlement which pushed down the horizontal portion of the buried conduit bringing the service laterals to the building.
We [DF] considered this a reportable defect as it was possible that the buried conduit was broken and subject to water entry from this condition and since the wires entering the building panel from the meter box have were disturbed. However M. Cramer points out that most conduit is not continuous, so breaking it is not really an issue aside from damage to conductors underground.
In 1976, an Underwriters Laboratory (UL) ruling required that all new meter bases be "continuous rated for 200 Amps," otherwise only 70% of the actual rating would be considered usable, (i.e., a 200 Amp meter base that was not "continuous rated" could only be used on a 160 Amp or smaller service). Inspectors can probably assume that a rectangular meter base is compatible with the system it is serving, unless a major change or a new panel has been installed.
The meter in our photo at left is obsolete.
Square meter bases such as the unit being pointed to with great caution by an ASHI Headquarters staff member on a field trip in the photo at below-left were normally rated at 100 Amps. Later generations of them were sometimes rated at 125 Amps.
Older electrical systems that were installed 30 or more years ago may be served by a square meter base with a round meter mounted on top of the square base as seen in the next photo at below-center - often called an "A-base" meter.
Still older electrical metering systems used the round meter base shown at below right. Round meter bases originally were rated for 60 Amps when installed 50 or more years ago. (Later generations of round meter bases were rated at 100 Amps.)
These meters can have a NMC main service wire running to and from them, or the wire may be installed in conduit.
[Click any image for a larger, more detailed view.]
The photo just above is an exciting collection of main switch, meter base, round meter above the square base, and a four-fuse "main" panel.
What do you think the ampacity was of this electrical meter, main switch, and fuse panel system?
Most modern electrical meters for single family homes have the designation "CL200" somewhere on their face, which indicates they are rated for up to a 200 Amp service. The CL200 rating may not limit these to 200 amps. Cramer reports finding larger services with CL200 meter bases.
Inspectors will also occasionally find a "CL10" meter which is a transformer-rated meter for large houses with larger electrical systems or two separate main panels.
Some older meters have other designations such as "15 Amps" on their face. This was their test rating. These meters are only usable on systems up to 100 Amps.
Some older meters were also designated as "30 Amps" on their face and these are compatible with 200 Amp services.
For example, one may occasionally find an older house with an upgraded 200 Amp service that still has an old 15 Amp meter plugged into a new meter base.
This meter is not really compatible with the system and should be replaced. Since the responsibility for the meter varies throughout the country, inspectors should contact the local electric utility for their policies and procedures concerning meters.
INSPECTING Electrical METERS & Electric Meter BASES - Inspecting Electric Meters and Electric Meter Bases
Electrical inspectors need to examine the meter and meter base and should take them into account when determining service ampacity. The elements to consider are:
The weakest or smallest of these five items will determine the service ampacity of the system. This inspection will also determine whether or not all parts of the system are compatible with each other and proper for the installation. There are other good reasons to look at the meter base and meter during your inspection. Occasionally one may discover other meter defects or concerns:
The building inspector's responsibility goes beyond that of the electrical contractor and the local electric utility. Because of this, the inspection of the meter and meter base is an important part of your electrical system inspection, and must be done carefully. This will help to protect your client's interests and will help fully inform them about electrical system defects and the proper service ampacity of the house they are considering to buy.
Experienced Electrical Worker Warns of Electric Meter Base Arcing & Burns
Our photos (below) show a simple electrical meter base and meter connection mounts where arcing was not present. Field photos of electric meter damage or arcing are wanted. CONTACT us.
There's one important point about electrical meter sockets I'd like to make. I've been in the electrical trade since 1976, and have seen a lot of interesting situations over the years. One that I feel needs to be addressed is on existing installations, involving arcing at the meter stabs.
I live in California, and So. Cal. Edison loves their "vandal proof" meter locking rings, so in order to do a "proper" service entrance inspection, we have to call a service tech out to unlock the meter ring, they always pitch a "bad time", about coming all the way out to unlock a ring, but it's my reputation and the customer's safety that are both on the line.
More than once, but not really-often I've discovered electrical arcing damage to the electrical meter mounting stabs. Arcing and burning in this location can only be seen by removing the meter. When I find one of these electrical meter mount arc-burn cases, the Edison guy is always amazed.
Not too many sparky's pull the electrical meters to inspect the meter connections, but I recommend it.
And pulling all the breakers off the bus and checking for discoloration or arcing on the bus bars, and breaker clips is a good practice to live by, Especially Zinsco panels (see ZINSCO / SYLVANIA HAZARDS), and especially 30 and 40 amp breakers. - Kirk Schwoebel
Photographs of Arcing Damage & Heat Damage at Connectors in Electric Meter Bases
The electrical meter arcing damage photographs below were provided courtesy of Robert McBride.
At below left the photograph of an electrical meter base shows severe arcing burns at the connecting jaws. At below right you will note (arrow) arc burns at the upper left connector in the photograph. The contributor indicated that this arcing burn occurred because the meter was inserted into the meter base while the system was under load.
Below the McBride photo of a burned electrical meter base connection shows heat damage at the electric meter mounting base due to loose connections.
Keep in mind that even minor electrical arcing such as shown in the photograph at right can be the beginning of a more serious problem, failure, or electrical fire.
The articles from which some of this online material originated appeared first in the ASHI Technical Journal, Vol. 2. No. 1, January 1992, "Determining Service Ampacity," Dan Friedman and Alan Carson, and the ASHI Technical Journal, Vol. 3. No. 1, Spring, 1993, "Determining Service Ampacity - Another Consideration," Robert L. Klewitz, P.E., with subsequent updates and additions to the original text ongoing to 2/19/2006. Reprints of the originals and reprints of the Journal are available from ASHI, the American Society of Home Inspectors www.ashi.com
Readers of this article should also be sure to review SAFETY HAZARDS & SAFE ELECTRICAL INSPECTION PROCEDURES for examining Residential Electrical Panels.
Also see the US DOE publication "How to Read Residential Electric and Natural Gas Meters".
Electric Meters that Run Backwards
Reader Question: Duncan and General Electric 3 phase meters running sometimes forward and sometimes backwards
8/21/14 Anonymous said:
I have a Duncan and General Electric 3 phase meters running sometimes forward and sometimes backwards. These are not smart meters. I've checked voltages, neutrals and connections. Can anyone help answer or have a remedy for these two meters. The other meters fed from the same source are running fine.
Reply: USDoI document on electric meter testing gives details about meter creep and backwards-running electric meters
If you are not sending electrical power backwards into the grid - say from a local energy source - then I suspect the meter is defective OR more likely your meter is experiencing what I quote below:
The document we cite lists eight reasons for this "backwards creep" in some electrical meters
Continue reading at MAIN ELECTRICAL DISCONNECT or select a topic from the More Reading links shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
Question: squatters stealing electrical power, meter removed
(June 30, 2014) Lateefa said:
I live next door to swatters who was stealing electric service but has since had their outside meter removed by the local utility company. These idiots have decided to go outside and re-open the seal that was put in place by the electric company and now were the meter was is all exposed, does this pose any danger to my home in any way? Thanks for reading.. Lateefa in Philly.
The squatters are exposing anyone who might touch their electrical meter or system to death by electrocution and of course are violating the law by theft of services.
The risk to your home might be an indirect one: the same carelessness that leads someone to hot-wire an electric meter to steal power may show up in other electrical system modifications that in turn risk both shock and fire. If the building catches fire neighbors are also at risk.
While no one likes to be a squealer, we certainly cannot condone stealing nor the risk of harm to neighbors. A call to the electric utility should lead that company to come to inspect the site for safety and if appropriate, drop electrical power at the pole or take other means to assure the system is safe.
Question: meter mounting box blamed for dimming lights
(July 23, 2014) brian korba said:
I called hydro because my lights were dimming in my house. They said I had to change the meter box because one of the meter receptor slots were too wide and was causing arcing. The electrician who changed the box said the cause of the arcing was a loose incoming hydro wire in the box. Which is more likely? I would like to put a claim in for this but am unsure how best to present the cause.
It's a perfectly fair question but not one we can answer by e-Text.
If the incoming wire was indeed loose it would have been helpful to document that thoroughly so as to establish responsibility. Even then, if the meter connection was made by your own or the original installing electrician, that is not by Hydro, then the responsibility falls back to the homeowner. In most areas the utility company's responsibility stops at the connection of their overhead or underground supply to the service entry cable that in turn connects to the meter.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References