Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
CHIMNEY INSPECTION DIAGNOSIS REPAIR
BACKDRAFTING HEATING EQUIPMENT
CARBON MONOXIDE - CO
CHIMNEY COMPONENT DEFINITIONS
CHIMNEY FIRE ACTION / PREVENTION
COMBUSTION GASES & PARTICLE HAZARDS
COMBUSTION PRODUCTS & IAQ
FLAME COLOR, BLUE vs YELLOW COMBUSTION
HEATING SYSTEM INSPECTION
HOME HEATING SAFETY
ODORS GASES SMELLS, DIAGNOSIS & CURE
SAFETY RECALLS CHIMNEYS VENTS HEATERS
STAIN DIAGNOSIS on BUILDING EXTERIORS
WOOD, COAL STOVES & FIREPLACES
WOOD STOVE SAFETY
This article explains what a bracket chimney is, why they are found (usually in older homes), why they are unsafe, and what to do about abandoning, removing or supporting a bracket chimney. We include photographs of bracket chimneys as well as sketches to help you recognize when this unsafe type of chimney is found in a building.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
[Click to enlarge any image]
What is a Bracket Chimney - see sketch below
Our photos above show two bracket chimneys in a pre-1900 home in New York.
[Click to enlarge any image]
A wooden framed "bracket" supports a masonry chimney on and in a building. Current building codes which require that a masonry chimney be self supporting expect that a masonry chimney will rest on a footing below ground level where it is sound and protected from frost, settlement, tipping, movement.
Wood bracket supports for masonry chimneys such as shown in our sketch (left) are often under-designed and lack sufficient strength to carry the weight of the chimney over time. Further, wood chimney supports may decay from leaks, rot, and insects.
As Carson Dunlop point out in this sketch, these chimneys are often inadequately supported and are a collapse hazard.
If the bracket-supported chimney is in use there are very often fire hazards as well.
Inspectors of older homes may find a bracket chimney in the building attic, with no masonry extending to the floors below. Instead, a wood stove or coal stove on lower floors used a metal chimney which passed up through the ceiling above and into the bracket chimney supported on a wood shelf in the attic. From outside the building it may appear that a normal masonry chimney is installed - possibly a false and unsafe assumption.
Repair alternatives for bracket chimneys and similar chimneys supported by wood framing include
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Questions & answers or comments about bracket chimneys: detection, inspection, hazards, removal or repair recommendations
Try the search box just below or if you prefer, post a question or a comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.