Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
ELECTRICAL INSPECTION, DIAGNOSIS, REPAIR
ALUMINUM WIRING HAZARDS & REPAIRS
Aluminum Wiring Summary Page for Public Use
BUILDING SAFETY HAZARDS GUIDE
BOOKSTORE - ELECTRICAL
Cadet & Encore Heater Recall
CIRCUIT BREAKER FAILURES
Classified CIRCUIT BREAKER WARNING
CUTLER HAMMER PANEL FIRE
DEFINITIONS of ELECTRICAL TERMS
DMM Digital Multimeter HOW TO USE
ELECTRIC PANEL INSPECTION
ELECTRICAL GROUND SYSTEM INSPECTION
FIRE SAFETY Checklist, CPSC
GFCI PROTECTION,Testing GFCIs AFCIs
KNOB & TUBE WIRING
LIGHTNING PROTECTION SYSTEMS
LOW VOLTAGE BUILDING WIRING
MURRAY SIEMENS Recall
PUSHMATIC - BULLDOG PANELS
RUST in ELECTRICAL PANELS
SAFETY for ELECTRICAL INSPECTORS
SIEMENS MURRAY Recall
VOLTS / AMPS MEASUREMENT EQUIP
VOLTAGE MEASUREMENT METHODS
ZINSCO / SYLVANIA HAZARDS
Field reports & photos of aluminum electrical wiring failures, overheats, fires: this article contains photo-documented reports of actual in-service aluminum wiring failures in homes.
We have been receiving reports from home owners, builders, and building professionals since 1990. However this page was created in July 2004, so it will not contain all of the historical data. Recent reports, photographs, anecdotes are be displayed here. When I complete statistical analysis of prior reports I'll add that data at this page.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
"I was replacing the heat pump unit on our home and went under the house to wire in the new unit to an existing junction
box. Upon opening the box I let out an expletive and then went right to our local home center to purchase some new copper
wire to run from the service panel to the new unit.
Whoever wired the previous unit must have had some Al wire around but
not quite enough to reach the unit, so they used a junction box to connect Al and Cu wire. Fortunately, the so-called
technicians used a steel box otherwise the house could have burned down.
Additional details about this failure are at Mr. Costantino's Web Page about this case.
Contributor - Gordon Cohen: These thermal imaging photos of overheating aluminum splices and circuit breakers with aluminum wiring are courtesy of Gordon Cohen, June 2006. Mr. Gordon offers home inspections and thermal imaging services in Florida and is also employed by ServiceMaster as a project manager. Email: Infraredinspections@cfl.rr.com
Aronstein reports and provides these additional examples of aluminum wiring field failures.
Continue reading at ALUMINUM WIRING REPAIRS NOT-RECOMMENDED or select a topic from the More Reading links shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
The link just above provides access to Reducing the Fire Hazards in Aluminum-Wired Homes, by Dr. Jess Aronstein, Ph.D., This document answers most technical questions about the hazards and remedies of aluminum electrical wiring. An easy to print form of this guide in PDF form is also provided free at ALUMINUM-WIRED HOMES, REDUCE THE HAZARD [PDF].
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Questions & answers or comments about aluminum electrical wiring field failure reports.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References