Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
AIR CONDITIONING & HEAT PUMP SYSTEMS
A/C - HEAT PUMP CONTROLS & SWITCHES
AIR CONDITIONER COMPONENT PARTS
AIR CONDITIONER TYPES, ENERGY SOURCES
AIR FILTER EFFICIENCY
AIR FILTERS, FIBERGLASS PARTICLES
AIR FLOW MEASUREMENT CFM
APPLIANCE DIAGNOSIS & REPAIR
APPLIANCE EFFICIENCY RATINGS
BLOWER DOORS & AIR INFILTRATION
BLOWER FAN CONTINUOUS OPERATION
BLOWER FAN OPERATION & TESTING
BOOKSTORE - Air Conditioning "How To" Books
CAPACITORS for HARD STARTING MOTORS
CLEANING & Legionella BACTERIA
CHINESE DRYWALL HAZARDS
CONDENSATION or SWEATING PIPES, TANKS
DEFINITION of HEATING & COOLING TERMS
DEW POINT CALCULATION for WALLS
DEW POINT TABLE - CONDENSATION POINT GUIDE
DIAGNOSTIC GUIDES A/C / HEAT PUMP
DIAGNOSE & FIX HEATING PROBLEMS-BOILER
DIAGNOSE & FIX HEATING PROBLEMS-FURNACE
DUCTS - Asbestos
DUCT INSULATION, Asbestos Paper
DUCT INSULATION for SOUNDPROOFING
DUCT SYSTEM & DUCT DEFECTS
DUCT SYSTEM NOISES
DUCTS, Asbestos Transite Pipe
DUST, HVAC CONTAMINATION STUDY
ELECTRIC MOTOR OVERLOAD RESET SWITCH
EVAPORATIVE COOLING SYSTEMS
FAN LIMIT SWITCH
FAN NOISES, HVAC
GAS EXPOSURE EFFECTS, TOXIC
GAS DETECTION INSTRUMENTS
HEAT LOSS (or GAIN) in buildings
HEAT LOSS (or GAIN) INDICATORS
HEAT LOSS R U & K VALUE CALCULATION
HEATING SMALL LOADS
INSPECTION CHECKLIST - OUTDOOR UNIT
INSPECTION LIMITATIONS, A/C SYSTEMS
LEED GREEN BUILDING CERTIFICATION
LOST COOLING CAPACITY
LOW VOLTAGE TRANSFORMER TEST
MOTOR OVERLOAD RESET SWITCH
MOLD in AIR HANDLERS & DUCT WORK
OPERATING COST, AIR CONDITIONER
OPERATING DEFECTS, AIR CONDITIONING
REPAIR GUIDES A/C / HEAT PUMP
REPAIR & DIAGNOSTIC FAQs for A/C
THERMOSTATS, HEATING / COOLING
THERMOSTATIC EXPANSION VALVES
WATER COOLED AIR CONDITIONERS
WINDOW / WALL AIR CONDITIONERS
WINDOW / WALL A/C SUPPORTS
This article describes the proper location and placement of air supply and air return registers in HVAC systems and addresses problems such as misplaced or missing air conditioning cool air supply or return air registers, improper cooling duct routing, cooling (or heating) air duct corrosion, and defective heating or cooling duct work. This article is part of our series How to Inspect, Diagnose, & Repair the Air Conditioners or Heat Pumps.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Supply and return too close together
Location of Heating or Cooling Return Registers in Basements
Placement of Heating or Cooling Air Returns at Outside Walls
Other Bad Locations for Air Registers
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Questions & answers or comments about the proper location for heating or cooling air registers.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.