DOWNSPOUT / LEADER DEFECTS - home - CONTENTS: Downspout or gutter leader defects, clogging, overflowing, holes corrosion, leaks that cause wet basements or crawl areas. Proper installation of buried downspout extensions. Proper installation of French drains & seepage pits at flat sites. Gutter & downspout defects cause wet basements & crawl areas. Roof gutters downspouts & roof drainage control systems
POST a QUESTION or READ FAQs about roof drainage systems: downspouts & leaders: installation, maintenance, repairs, leaks, screens, routing, clogs, and just about anything else.
InspectAPedia tolerates no conflicts of interest. We have no relationship with advertisers, products, or services discussed at this website.
Gutter roof drains, downspouts & leaders:
These articles, sketches and photographs decribe the types of defects or leaks in the downspouts or leaders for roof drainage systems: leaks or other defects that cause basement or crawl space water entry.
Downspouts collect water from the gutters and discharge it into drains or onto the ground. Underground drains (usually made of clay tile, cast iron or plastic) become clogged or break below grade. If an underground downspout malfunctions, water problems will likely develop in that part of the basement. There are two options.
Exterior digging and repairs can be
undertaken; however, it is faster and cheaper to simply disconnect the downspout and redirect it to discharge away from the house. It’s also easier to monitor the performance, and problems are corrected easily. Downspouts should discharge above grade onto the ground at least six feet from the home. The slope of the ground in this area should be away from the house, to direct water away from the basement.
Common Downspout Defects Causing Building Water Entry or Leaks
[Click to enlarge any image]
The small diameter gutter pipes (downspouts or leaders) on the roof drainage system shown above are on flats located in Oxford in the U.K. In an area of significant rainfall we speculate that this system may not be providing adequate drainage. The roof drain pipes shown below, installed on a London building have been adequately sized and in-service since 1953.
Our list of common downspout or leader defects shown just below is followed by illustrations or photographs of many of these conditions.
Downspout empties too close to the building, concentrating water against the foundation, a very likely source of basement or crawl space water entry.
Downspouts connected to footing drains, building interior drains, floor drains, or sewer system (storm drain connections are ok). This is a common but serious mistake made by uninformed builders. Adding the load of roof runoff to building foundation drains overloads that drain system and invites basement or crawl space water entry and even flooding.
A basement flood from this mistake can happen very suddenly, often less than 10 years after new construction, when a hand full of leaves or other debris enters and clogs the footing drain system through the gutter and downspout system.
Insufficient size or number of downspouts to handle roof drainage water volume. In general, provide a downspout for every 35-40' of gutter length. More downspouts may be needed around complex roof structures.
Downspout Extension Spills Too Close to the Building
The sketch at left illustrates a major cause of wet basements and crawl spaces: the downspout ends too close to the building, backfill at the building has settled, and in addition, the original grade left from the excavation to build the foundation remains as hard-packed soil that directs spillage back towards the structure.
Our photos below illustrate downspouts emptying too close to the building.
At below left you can see erosion that is sending most of the roof runoff out of the downspout and right down the foundation wall.
At below right a downspout is terminated on the deck surface. That detail can lead to slip/fall hazards (slippery algae-covered deck boards) and basement water entry (due to in-slope grade towards the building, hidden below the deck surface.)
Downspout Empties onto Settled Backfill
Here we show the most common roof drainage system error that leads to basement or crawl space water entry: the downspout empties too close to the building foundation wall.
This mistake, combined with settled backfill that slopes back towards the building sends this concentration of water from the roof right into the building.
While there are rules of thumb for the length of downspout extensions (minimum of six feet, or more from the building), the common sense downspout rule is:
When the water leaves the end of the downspout, it should keep going away from the building, not back towards it.
Downspout Empties onto Sloped backfill over compacted in-slope virgin soils or clay
A more subtle version of the "downspout too close to the building" problem we described above is illustrated in the sketch at left.
After a building foundation and structure have been completed, backfill may have been spread around the building and may appear to slope nicely away from the structure.
But because the new backfill is less compacted than virgin soil, even though it slopes away from the building, water soaking through the backfill may encounter below-ground hard-packed original soils that slope towards the structure.
The result is a hidden in-slope grade problem sending roof spillage or downspout spillage right back into the building.
Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Ask a Question or Search InspectApedia
Questions & answers or comments about roof drainage systems: downspouts & leaders: installation, maintenance, repairs, leaks, screens, routing, clogs, and just about anything else.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Mark Cramer Inspection Services Mark Cramer, Tampa Florida, Mr. Cramer is a past president of ASHI, the American Society of Home Inspectors and is a Florida home inspector and home inspection educator. Mr. Cramer serves on the ASHI Home Inspection Standards. Contact Mark Cramer at: 727-595-4211 mark@BestTampaInspector.com
John Cranor is an ASHI member and a home inspector (The House Whisperer) is located in Glen Allen, VA 23060. He is also a contributor to InspectApedia.com in several technical areas such as plumbing and appliances (dryer vents). Contact Mr. Cranor at 804-747-7747 or by Email: email@example.com
Books & Articles on Building & Environmental Inspection, Testing, Diagnosis, & Repair
Certainteed Weatherboard fiber cement siding and trim products - see certainteed.com/ or see certainteed.com/resources/sidingandtrimspecsheet.pdf
"Flashing: the plain solution to leaky walls", Thomas E. Remmele, Manager, Technical Services, Sto Corporation, Building Standards, November/December 1999 p. 21-25.
"Weather-Resistive Barriers [copy on file as /interiors/Weather_Resistant_Barriers_DOE.pdf ] - ", how to select and install housewrap and other types of weather resistive barriers, U.S. DOE
Carson, Dunlop & Associates Ltd., 120 Carlton Street Suite 407, Toronto ON M5A 4K2. Tel: (416) 964-9415 1-800-268-7070 Email: firstname.lastname@example.org. The firm provides professional home inspection services & home inspection education & publications. Alan Carson is a past president of ASHI, the American Society of Home Inspectors. Thanks to Alan Carson and Bob Dunlop, for permission for InspectAPedia to use text excerpts from The Home Reference Book & illustrations from The Illustrated Home. Carson Dunlop Associates' provides extensive home inspection education and report writing material.
The Illustrated Home illustrates construction details and building components, a reference for owners & inspectors. Special Offer: For a 5% discount on any number of copies of the Illustrated Home purchased as a single order Enter INSPECTAILL in the order payment page "Promo/Redemption" space.
TECHNICAL REFERENCE GUIDE to manufacturer's model and serial number information for heating and cooling equipment, useful for determining the age of heating boilers, furnaces, water heaters is provided by Carson Dunlop, Associates, Toronto - Carson Dunlop Weldon & Associates Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on any number of copies of the Technical Reference Guide purchased as a single order. Just enter INSPECTATRG in the order payment page "Promo/Redemption" space.
The Home Reference Book - the Encyclopedia of Homes, Carson Dunlop & Associates, Toronto, Ontario, 25th Ed., 2012, is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. Field inspection worksheets are included at the back of the volume.
Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on these courses: Enter INSPECTAHITP in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Horizon Software System manages business operations,scheduling, & inspection report writing using Carson Dunlop's knowledge base & color images. The Horizon system runs on always-available cloud-based software for office computers, laptops, tablets, iPad, Android, & other smartphones