InspectAPedia®

Electrical Service Entry Cable Visual Inspection Can Determine Voltage Range

• VOLTAGE at the SEC - CONTENTS: How to inspect the electrical service entry cables at a building - How to determine the size, capacity, or ampacity of electrical service at a building
• POST a QUESTION or READ FAQs about how to determine the building electrical voltage or service capacity by visual inspection of the service entry cables or wires
• REFERENCES
InspectAPedia tolerates no conflicts of interest. We have no relationship with advertisers, products, or services discussed at this website.

This article explains how to estimate the electrical service size, (or "electrical power" or "service amps") at a building by visual examination of the service entry cables, electric meter and meter base, electrical service panel, main switch, and other details.

Visual inspection and use of digital multimeters(DMMs), Volt-ohm meters (VOMs), neon testers, and electrical inspection safety are discussed. Photographs and sketches illustrate electrical panels, meter bases, and electric meters.

One of the most frequently asked questions at ASHI Education Seminars and Conferences is "How do I determine the service amperage?" Our page top sketch of a 240V service entrance is provided courtesy of Carson Dunlop Associates.

VOLTAGE at the SEC - How to figure out Electrical Service Voltage by visual examination at the service entry

 It's not as difficult as one may think to get a reasonable handle on the electrical service capacity at a building without sophisticated analysis. This article explains the visual examination of overhead electrical wires at the service entry. This procedure pertains to overhead wires, not underground conduit. Examination is made at the point of connection of the ELECTRICAL SERVICE DROP to the service conductors. In lay terms, the service conductors are also called the service entry cable or SEC. Underground wiring up to the building is called a service lateral. A 240V electrical service [three-wire figure at left] will include three wires connected to the building - the two 120V "hot" legs which together provide 240V, and a third grounded conductor. Readers of this article should also be sure to review SAFETY HAZARDS & SAFE ELECTRICAL INSPECTION PROCEDURES for examining Residential Electrical Panels.

 A 120V service [second, two wire figure at left] will have only two wires, a 120V power line and a grounded line or neutral. However simple visual examination from the ground is not a certain proof of voltage available in the building. In a few unusual circumstances, all three wires may be present but one of them may be disconnected at the utility pole or masthead. Such "mistakes" occur during temporary hookups in new construction or renovation. Could there be 240V service to a building with only two wires? Yes but not normally in the U.S. Some Canadian rural properties served by long private wires may have only two overhead conductors on a 240 volt service. For these systems ground connections are made only at the building, not back to the utility company's lines. In the U.S. this would be unusual but be alert for it, especially at rural properties.

 Table 1. Service Voltage Configurations Number of Visible Wires at Masthead Probable Voltage Insulated Uninsulated-Ground 1 1 120 2 0 120/240 2 1 120/240 3 0 or 1 120/240, 120/208 3-phase [1] 4 . 3 phase, need to measure volts [2]

Notes to Table:
1. This could also be a delta 3-phase with 3 120V legs; 3 phase power not common at residential properties.
2. 208 Volt service may be present on 3rd red wire.

The articles from which much of this online material originated appeared first in the ASHI Technical Journal, Vol. 2. No. 1, January 1992, "Determining Service Ampacity," Dan Friedman and Alan Carson, and the ASHI Technical Journal, Vol. 3. No. 1, Spring, 1993, "Determining Service Ampacity - Another Consideration," Robert L. Klewitz, P.E., with subsequent updates and additions to the original text ongoing to 2/19/2006. Reprints of the originals and reprints of the Journal are available from ASHI, the American Society of Home Inspectors www.ashi.com

Articles on Building Electrical Service Wiring - SEC Cabling

...

Continue reading at UNDERGROUND SERVICE LATERALS or select a topic from closely-related articles below, or see our complete INDEX to RELATED ARTICLES below.

Or see ELECTRICAL INSPECTOR SAFETY PROCEDURES important basic safety procedures, clothing, and equipment for home inspectors and electrical inspectors.

Suggested citation for this web page

VOLTAGE at the SEC at InspectApedia.com - online encyclopedia of building & environmental inspection, testing, diagnosis, repair, & problem prevention advice.

INDEX to RELATED ARTICLES: ARTICLE INDEX to ELECTRICAL INSPECTION & TESTING

Or use the SEARCH BOX found below to Ask a Question or Search InspectApedia

...

Frequently Asked Questions (FAQs)

Click to Show or Hide FAQs

Ask a Question or Search InspectApedia

Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.

Search the InspectApedia website